# python version 1.0						DO NOT EDIT
#
# Generated by smidump version 0.4.8:
#
#   smidump -f python CPQPOWER-MIB

FILENAME = "./CPQPOWER-MIB"

MIB = {
    "moduleName" : "CPQPOWER-MIB",

    "CPQPOWER-MIB" : {
        "nodetype" : "module",
        "language" : "SMIv1",
    },

    "imports" : (
        {"module" : "CPQHOST-MIB", "name" : "compaq"},
        {"module" : "RFC1155-SMI", "name" : "Counter"},
        {"module" : "RFC1213-MIB", "name" : "DisplayString"},
        {"module" : "RFC1213-MIB", "name" : "ifIndex"},
        {"module" : "RFC1213-MIB", "name" : "ifDescr"},
        {"module" : "RFC1213-MIB", "name" : "sysName"},
        {"module" : "RFC1213-MIB", "name" : "sysDescr"},
        {"module" : "RFC1213-MIB", "name" : "sysContact"},
        {"module" : "RFC1213-MIB", "name" : "sysLocation"},
        {"module" : "RFC-1212", "name" : "OBJECT-TYPE"},
        {"module" : "RFC-1215", "name" : "TRAP-TYPE"},
    ),

    "nodes" : {
        "cpqPower" : {
            "nodetype" : "node",
            "moduleName" : "CPQPOWER-MIB",
            "oid" : "1.3.6.1.4.1.232.165",
        }, # node
        "powerDevice" : {
            "nodetype" : "node",
            "moduleName" : "CPQPOWER-MIB",
            "oid" : "1.3.6.1.4.1.232.165.1",
        }, # node
        "trapInfo" : {
            "nodetype" : "node",
            "moduleName" : "CPQPOWER-MIB",
            "oid" : "1.3.6.1.4.1.232.165.1.1",
        }, # node
        "trapCode" : {
            "nodetype" : "scalar",
            "moduleName" : "CPQPOWER-MIB",
            "oid" : "1.3.6.1.4.1.232.165.1.1.1",
            "status" : "current",
            "syntax" : {
                "type" : { "module" :"", "name" : "Integer32"},
            },
            "access" : "readonly",
            "description" :
                """A number identifying the event for the trap that was sent.
Mapped unique trap code per unique event to be used by ISEE's
decoder ring.""",
        }, # scalar
        "trapDescription" : {
            "nodetype" : "scalar",
            "moduleName" : "CPQPOWER-MIB",
            "oid" : "1.3.6.1.4.1.232.165.1.1.2",
            "status" : "current",
            "syntax" : {
                "type" :                 {
                    "basetype" : "OctetString",
                    "parent module" : {
                        "name" : "RFC1213-MIB",
                        "type" : "DisplayString",
                    },
                    "ranges" : [
                    {
                        "min" : "0",
                        "max" : "255"
                    },
                    ],
                    "range" : {
                        "min" : "0",
                        "max" : "255"
                    },
                },
            },
            "access" : "readonly",
            "description" :
                """A string identifying the event for that last trap that was sent.""",
        }, # scalar
        "trapDeviceMgmtUrl" : {
            "nodetype" : "scalar",
            "moduleName" : "CPQPOWER-MIB",
            "oid" : "1.3.6.1.4.1.232.165.1.1.3",
            "status" : "current",
            "syntax" : {
                "type" :                 {
                    "basetype" : "OctetString",
                    "parent module" : {
                        "name" : "RFC1213-MIB",
                        "type" : "DisplayString",
                    },
                    "ranges" : [
                    {
                        "min" : "0",
                        "max" : "255"
                    },
                    ],
                    "range" : {
                        "min" : "0",
                        "max" : "255"
                    },
                },
            },
            "access" : "readonly",
            "description" :
                """A string contains the URL for the management software.""",
        }, # scalar
        "trapDeviceDetails" : {
            "nodetype" : "scalar",
            "moduleName" : "CPQPOWER-MIB",
            "oid" : "1.3.6.1.4.1.232.165.1.1.4",
            "status" : "current",
            "syntax" : {
                "type" :                 {
                    "basetype" : "OctetString",
                    "parent module" : {
                        "name" : "RFC1213-MIB",
                        "type" : "DisplayString",
                    },
                    "ranges" : [
                    {
                        "min" : "0",
                        "max" : "255"
                    },
                    ],
                    "range" : {
                        "min" : "0",
                        "max" : "255"
                    },
                },
            },
            "access" : "readonly",
            "description" :
                """A string details information about the UPS such as SN (serial number), 
PN (part number), and MN (Model Name).""",
        }, # scalar
        "trapDeviceName" : {
            "nodetype" : "scalar",
            "moduleName" : "CPQPOWER-MIB",
            "oid" : "1.3.6.1.4.1.232.165.1.1.5",
            "status" : "current",
            "syntax" : {
                "type" :                 {
                    "basetype" : "OctetString",
                    "parent module" : {
                        "name" : "RFC1213-MIB",
                        "type" : "DisplayString",
                    },
                    "ranges" : [
                    {
                        "min" : "0",
                        "max" : "255"
                    },
                    ],
                    "range" : {
                        "min" : "0",
                        "max" : "255"
                    },
                },
            },
            "access" : "readonly",
            "description" :
                """A string contains the name of the HP Management Module.""",
        }, # scalar
        "managementModuleIdent" : {
            "nodetype" : "node",
            "moduleName" : "CPQPOWER-MIB",
            "oid" : "1.3.6.1.4.1.232.165.1.2",
        }, # node
        "deviceManufacturer" : {
            "nodetype" : "scalar",
            "moduleName" : "CPQPOWER-MIB",
            "oid" : "1.3.6.1.4.1.232.165.1.2.1",
            "status" : "current",
            "syntax" : {
                "type" : { "module" :"RFC1213-MIB", "name" : "DisplayString"},
            },
            "access" : "readonly",
            "description" :
                """The device's manufacturer.""",
        }, # scalar
        "deviceModel" : {
            "nodetype" : "scalar",
            "moduleName" : "CPQPOWER-MIB",
            "oid" : "1.3.6.1.4.1.232.165.1.2.2",
            "status" : "current",
            "syntax" : {
                "type" : { "module" :"RFC1213-MIB", "name" : "DisplayString"},
            },
            "access" : "readonly",
            "description" :
                """The device's model.""",
        }, # scalar
        "deviceFirmwareVersion" : {
            "nodetype" : "scalar",
            "moduleName" : "CPQPOWER-MIB",
            "oid" : "1.3.6.1.4.1.232.165.1.2.3",
            "status" : "current",
            "syntax" : {
                "type" : { "module" :"RFC1213-MIB", "name" : "DisplayString"},
            },
            "access" : "readonly",
            "description" :
                """The device's firmware version(s).""",
        }, # scalar
        "deviceHardwareVersion" : {
            "nodetype" : "scalar",
            "moduleName" : "CPQPOWER-MIB",
            "oid" : "1.3.6.1.4.1.232.165.1.2.4",
            "status" : "current",
            "syntax" : {
                "type" : { "module" :"RFC1213-MIB", "name" : "DisplayString"},
            },
            "access" : "readonly",
            "description" :
                """The device's hardware version.""",
        }, # scalar
        "deviceIdentName" : {
            "nodetype" : "scalar",
            "moduleName" : "CPQPOWER-MIB",
            "oid" : "1.3.6.1.4.1.232.165.1.2.5",
            "status" : "current",
            "syntax" : {
                "type" : { "module" :"RFC1213-MIB", "name" : "DisplayString"},
            },
            "access" : "readwrite",
            "description" :
                """A string identifying the device. it came from sysName entered by user""",
        }, # scalar
        "devicePartNumber" : {
            "nodetype" : "scalar",
            "moduleName" : "CPQPOWER-MIB",
            "oid" : "1.3.6.1.4.1.232.165.1.2.6",
            "status" : "current",
            "syntax" : {
                "type" : { "module" :"RFC1213-MIB", "name" : "DisplayString"},
            },
            "access" : "readonly",
            "description" :
                """The device's part number.""",
        }, # scalar
        "deviceSerialNumber" : {
            "nodetype" : "scalar",
            "moduleName" : "CPQPOWER-MIB",
            "oid" : "1.3.6.1.4.1.232.165.1.2.7",
            "status" : "current",
            "syntax" : {
                "type" : { "module" :"RFC1213-MIB", "name" : "DisplayString"},
            },
            "access" : "readonly",
            "description" :
                """The device's serial number.""",
        }, # scalar
        "deviceMACAddress" : {
            "nodetype" : "scalar",
            "moduleName" : "CPQPOWER-MIB",
            "oid" : "1.3.6.1.4.1.232.165.1.2.8",
            "status" : "current",
            "syntax" : {
                "type" : { "module" :"RFC1213-MIB", "name" : "DisplayString"},
            },
            "access" : "readonly",
            "description" :
                """The device's MAC address.""",
        }, # scalar
        "pdu" : {
            "nodetype" : "node",
            "moduleName" : "CPQPOWER-MIB",
            "oid" : "1.3.6.1.4.1.232.165.2",
        }, # node
        "pduIdent" : {
            "nodetype" : "node",
            "moduleName" : "CPQPOWER-MIB",
            "oid" : "1.3.6.1.4.1.232.165.2.1",
        }, # node
        "numOfPdu" : {
            "nodetype" : "scalar",
            "moduleName" : "CPQPOWER-MIB",
            "oid" : "1.3.6.1.4.1.232.165.2.1.1",
            "status" : "current",
            "syntax" : {
                "type" :                 {
                    "basetype" : "Integer32",
                    "ranges" : [
                    {
                        "min" : "0",
                        "max" : "63"
                    },
                    ],
                    "range" : {
                        "min" : "0",
                        "max" : "63"
                    },
                },
            },
            "access" : "readonly",
            "description" :
                """The number of PDUs.""",
        }, # scalar
        "pduIdentTable" : {
            "nodetype" : "table",
            "moduleName" : "CPQPOWER-MIB",
            "oid" : "1.3.6.1.4.1.232.165.2.1.2",
            "status" : "current",
            "description" :
                """The Aggregate Object with number of entries equal to
NumOfPdu and including the PduIdent group.""",
        }, # table
        "pduIdentEntry" : {
            "nodetype" : "row",
            "moduleName" : "CPQPOWER-MIB",
            "oid" : "1.3.6.1.4.1.232.165.2.1.2.1",
            "status" : "current",
            "linkage" : [
                "pduIdentIndex",
            ],
            "description" :
                """The ident table entry containing the name,
model, manufacturer, firmware version, part number, etc.""",
        }, # row
        "pduIdentIndex" : {
            "nodetype" : "column",
            "moduleName" : "CPQPOWER-MIB",
            "oid" : "1.3.6.1.4.1.232.165.2.1.2.1.1",
            "status" : "current",
            "syntax" : {
                "type" :                 {
                    "basetype" : "Integer32",
                    "ranges" : [
                    {
                        "min" : "0",
                        "max" : "100"
                    },
                    ],
                    "range" : {
                        "min" : "0",
                        "max" : "100"
                    },
                },
            },
            "access" : "readonly",
            "description" :
                """Index for the PduIdentEntry table.""",
        }, # column
        "pduName" : {
            "nodetype" : "column",
            "moduleName" : "CPQPOWER-MIB",
            "oid" : "1.3.6.1.4.1.232.165.2.1.2.1.2",
            "status" : "current",
            "syntax" : {
                "type" :                 {
                    "basetype" : "OctetString",
                    "parent module" : {
                        "name" : "RFC1213-MIB",
                        "type" : "DisplayString",
                    },
                    "ranges" : [
                    {
                        "min" : "0",
                        "max" : "63"
                    },
                    ],
                    "range" : {
                        "min" : "0",
                        "max" : "63"
                    },
                },
            },
            "access" : "readwrite",
            "description" :
                """The string identify the device.""",
        }, # column
        "pduModel" : {
            "nodetype" : "column",
            "moduleName" : "CPQPOWER-MIB",
            "oid" : "1.3.6.1.4.1.232.165.2.1.2.1.3",
            "status" : "current",
            "syntax" : {
                "type" :                 {
                    "basetype" : "OctetString",
                    "parent module" : {
                        "name" : "RFC1213-MIB",
                        "type" : "DisplayString",
                    },
                    "ranges" : [
                    {
                        "min" : "0",
                        "max" : "63"
                    },
                    ],
                    "range" : {
                        "min" : "0",
                        "max" : "63"
                    },
                },
            },
            "access" : "readonly",
            "description" :
                """The Device Model.""",
        }, # column
        "pduManufacturer" : {
            "nodetype" : "column",
            "moduleName" : "CPQPOWER-MIB",
            "oid" : "1.3.6.1.4.1.232.165.2.1.2.1.4",
            "status" : "current",
            "syntax" : {
                "type" :                 {
                    "basetype" : "OctetString",
                    "parent module" : {
                        "name" : "RFC1213-MIB",
                        "type" : "DisplayString",
                    },
                    "ranges" : [
                    {
                        "min" : "0",
                        "max" : "63"
                    },
                    ],
                    "range" : {
                        "min" : "0",
                        "max" : "63"
                    },
                },
            },
            "access" : "readonly",
            "description" :
                """The Device Manufacturer Name (e.g. Hewlett-Packard).""",
        }, # column
        "pduFirmwareVersion" : {
            "nodetype" : "column",
            "moduleName" : "CPQPOWER-MIB",
            "oid" : "1.3.6.1.4.1.232.165.2.1.2.1.5",
            "status" : "current",
            "syntax" : {
                "type" :                 {
                    "basetype" : "OctetString",
                    "parent module" : {
                        "name" : "RFC1213-MIB",
                        "type" : "DisplayString",
                    },
                    "ranges" : [
                    {
                        "min" : "0",
                        "max" : "63"
                    },
                    ],
                    "range" : {
                        "min" : "0",
                        "max" : "63"
                    },
                },
            },
            "access" : "readonly",
            "description" :
                """The firmware revision level of the device.""",
        }, # column
        "pduPartNumber" : {
            "nodetype" : "column",
            "moduleName" : "CPQPOWER-MIB",
            "oid" : "1.3.6.1.4.1.232.165.2.1.2.1.6",
            "status" : "current",
            "syntax" : {
                "type" :                 {
                    "basetype" : "OctetString",
                    "parent module" : {
                        "name" : "RFC1213-MIB",
                        "type" : "DisplayString",
                    },
                    "ranges" : [
                    {
                        "min" : "0",
                        "max" : "63"
                    },
                    ],
                    "range" : {
                        "min" : "0",
                        "max" : "63"
                    },
                },
            },
            "access" : "readonly",
            "description" :
                """The device part number.""",
        }, # column
        "pduSerialNumber" : {
            "nodetype" : "column",
            "moduleName" : "CPQPOWER-MIB",
            "oid" : "1.3.6.1.4.1.232.165.2.1.2.1.7",
            "status" : "current",
            "syntax" : {
                "type" :                 {
                    "basetype" : "OctetString",
                    "parent module" : {
                        "name" : "RFC1213-MIB",
                        "type" : "DisplayString",
                    },
                    "ranges" : [
                    {
                        "min" : "0",
                        "max" : "63"
                    },
                    ],
                    "range" : {
                        "min" : "0",
                        "max" : "63"
                    },
                },
            },
            "access" : "readonly",
            "description" :
                """The device serial number.""",
        }, # column
        "pduStatus" : {
            "nodetype" : "column",
            "moduleName" : "CPQPOWER-MIB",
            "oid" : "1.3.6.1.4.1.232.165.2.1.2.1.8",
            "status" : "current",
            "syntax" : {
                "type" :                 {
                    "basetype" : "Enumeration",
                    "other" : {
                        "nodetype" : "namednumber",
                        "number" : "1"
                    },
                    "ok" : {
                        "nodetype" : "namednumber",
                        "number" : "2"
                    },
                    "degraded" : {
                        "nodetype" : "namednumber",
                        "number" : "3"
                    },
                    "failed" : {
                        "nodetype" : "namednumber",
                        "number" : "4"
                    },
                },
            },
            "access" : "readonly",
            "description" :
                """The overall status of the device.  A value of OK(2) indicates the device is operating normally.
A value of degraded(3) indicates the device is operating with warning indicators.  A value of
failed(4) indicates the device is operating with critical indicators.""",
        }, # column
        "pduControllable" : {
            "nodetype" : "column",
            "moduleName" : "CPQPOWER-MIB",
            "oid" : "1.3.6.1.4.1.232.165.2.1.2.1.9",
            "status" : "current",
            "syntax" : {
                "type" :                 {
                    "basetype" : "Enumeration",
                    "yes" : {
                        "nodetype" : "namednumber",
                        "number" : "1"
                    },
                    "no" : {
                        "nodetype" : "namednumber",
                        "number" : "2"
                    },
                },
            },
            "access" : "readonly",
            "description" :
                """This object indicates whether or not the device is controllable.""",
        }, # column
        "pduInput" : {
            "nodetype" : "node",
            "moduleName" : "CPQPOWER-MIB",
            "oid" : "1.3.6.1.4.1.232.165.2.2",
        }, # node
        "pduInputTable" : {
            "nodetype" : "table",
            "moduleName" : "CPQPOWER-MIB",
            "oid" : "1.3.6.1.4.1.232.165.2.2.1",
            "status" : "current",
            "description" :
                """The Aggregate Object with number of entries equal to
NumOfPdu and including the PduInput group.""",
        }, # table
        "pduInputEntry" : {
            "nodetype" : "row",
            "moduleName" : "CPQPOWER-MIB",
            "oid" : "1.3.6.1.4.1.232.165.2.2.1.1",
            "status" : "current",
            "linkage" : [
                "pduInputIndex",
            ],
            "description" :
                """The input table entry containing the voltage and 
current for the PDU""",
        }, # row
        "pduInputIndex" : {
            "nodetype" : "column",
            "moduleName" : "CPQPOWER-MIB",
            "oid" : "1.3.6.1.4.1.232.165.2.2.1.1.1",
            "status" : "current",
            "syntax" : {
                "type" :                 {
                    "basetype" : "Integer32",
                    "ranges" : [
                    {
                        "min" : "0",
                        "max" : "100"
                    },
                    ],
                    "range" : {
                        "min" : "0",
                        "max" : "100"
                    },
                },
            },
            "access" : "readonly",
            "description" :
                """Index for the PduInputEntry table.""",
        }, # column
        "inputVoltage" : {
            "nodetype" : "column",
            "moduleName" : "CPQPOWER-MIB",
            "oid" : "1.3.6.1.4.1.232.165.2.2.1.1.2",
            "status" : "current",
            "syntax" : {
                "type" :                 {
                    "basetype" : "Integer32",
                    "ranges" : [
                    {
                        "min" : "0",
                        "max" : "2147483647"
                    },
                    ],
                    "range" : {
                        "min" : "0",
                        "max" : "2147483647"
                    },
                },
            },
            "access" : "readonly",
            "description" :
                """The measured input voltage from the PDU meters in volts.""",
        }, # column
        "inputCurrent" : {
            "nodetype" : "column",
            "moduleName" : "CPQPOWER-MIB",
            "oid" : "1.3.6.1.4.1.232.165.2.2.1.1.3",
            "status" : "current",
            "syntax" : {
                "type" :                 {
                    "basetype" : "Integer32",
                    "ranges" : [
                    {
                        "min" : "0",
                        "max" : "2147483647"
                    },
                    ],
                    "range" : {
                        "min" : "0",
                        "max" : "2147483647"
                    },
                },
            },
            "access" : "readonly",
            "description" :
                """The measured input current from the PDU meters in hundredths of Amp.""",
        }, # column
        "pduOutput" : {
            "nodetype" : "node",
            "moduleName" : "CPQPOWER-MIB",
            "oid" : "1.3.6.1.4.1.232.165.2.3",
        }, # node
        "pduOutputTable" : {
            "nodetype" : "table",
            "moduleName" : "CPQPOWER-MIB",
            "oid" : "1.3.6.1.4.1.232.165.2.3.1",
            "status" : "current",
            "description" :
                """The Aggregate Object with number of entries equal to
NumOfPdu and including the PduInput group.""",
        }, # table
        "pduOutputEntry" : {
            "nodetype" : "row",
            "moduleName" : "CPQPOWER-MIB",
            "oid" : "1.3.6.1.4.1.232.165.2.3.1.1",
            "status" : "current",
            "linkage" : [
                "pduOutputIndex",
            ],
            "description" :
                """The input table entry containing the name,
heat load, current load, power load, firmware, etc.""",
        }, # row
        "pduOutputIndex" : {
            "nodetype" : "column",
            "moduleName" : "CPQPOWER-MIB",
            "oid" : "1.3.6.1.4.1.232.165.2.3.1.1.1",
            "status" : "current",
            "syntax" : {
                "type" :                 {
                    "basetype" : "Integer32",
                    "ranges" : [
                    {
                        "min" : "0",
                        "max" : "100"
                    },
                    ],
                    "range" : {
                        "min" : "0",
                        "max" : "100"
                    },
                },
            },
            "access" : "readonly",
            "description" :
                """Index for the PduOutputEntry table.""",
        }, # column
        "pduOutputLoad" : {
            "nodetype" : "column",
            "moduleName" : "CPQPOWER-MIB",
            "oid" : "1.3.6.1.4.1.232.165.2.3.1.1.2",
            "status" : "current",
            "syntax" : {
                "type" :                 {
                    "basetype" : "Integer32",
                    "ranges" : [
                    {
                        "min" : "0",
                        "max" : "200"
                    },
                    ],
                    "range" : {
                        "min" : "0",
                        "max" : "200"
                    },
                },
            },
            "access" : "readonly",
            "description" :
                """The device output load in percent of rated capacity.  A value of -1 will be
returned if the heat load is unable to be measured.""",
        }, # column
        "pduOutputHeat" : {
            "nodetype" : "column",
            "moduleName" : "CPQPOWER-MIB",
            "oid" : "1.3.6.1.4.1.232.165.2.3.1.1.3",
            "status" : "current",
            "syntax" : {
                "type" : { "module" :"", "name" : "Integer32"},
            },
            "access" : "readonly",
            "description" :
                """The total heat load measured on the PDU in BTUs.  A value of -1 will be
returned if the heat load is unable to be measured.""",
        }, # column
        "pduOutputPower" : {
            "nodetype" : "column",
            "moduleName" : "CPQPOWER-MIB",
            "oid" : "1.3.6.1.4.1.232.165.2.3.1.1.4",
            "status" : "current",
            "syntax" : {
                "type" : { "module" :"", "name" : "Integer32"},
            },
            "access" : "readonly",
            "description" :
                """The total power load measured on the PDU in watts.  A value of -1 will be
returned if the power load is unable to be measured.""",
        }, # column
        "pduOutputNumBreakers" : {
            "nodetype" : "column",
            "moduleName" : "CPQPOWER-MIB",
            "oid" : "1.3.6.1.4.1.232.165.2.3.1.1.5",
            "status" : "current",
            "syntax" : {
                "type" : { "module" :"", "name" : "Integer32"},
            },
            "access" : "readonly",
            "description" :
                """The number of breakers for the device.  This variable indicates the number 
of rows in the breakers table.""",
        }, # column
        "pduOutputBreakerTable" : {
            "nodetype" : "table",
            "moduleName" : "CPQPOWER-MIB",
            "oid" : "1.3.6.1.4.1.232.165.2.3.2",
            "status" : "current",
            "description" :
                """List of breaker table entries.  The number of entries is given by pduOutputNumBreakers .""",
        }, # table
        "pduOutputBreakerEntry" : {
            "nodetype" : "row",
            "moduleName" : "CPQPOWER-MIB",
            "oid" : "1.3.6.1.4.1.232.165.2.3.2.1",
            "status" : "current",
            "linkage" : [
                "pduOutputIndex",
                "breakerIndex",
            ],
            "description" :
                """An entry containing information applicable to an breaker.""",
        }, # row
        "breakerIndex" : {
            "nodetype" : "column",
            "moduleName" : "CPQPOWER-MIB",
            "oid" : "1.3.6.1.4.1.232.165.2.3.2.1.1",
            "status" : "current",
            "syntax" : {
                "type" :                 {
                    "basetype" : "Integer32",
                    "ranges" : [
                    {
                        "min" : "0",
                        "max" : "100"
                    },
                    ],
                    "range" : {
                        "min" : "0",
                        "max" : "100"
                    },
                },
            },
            "access" : "readonly",
            "description" :
                """The breaker identifier.""",
        }, # column
        "breakerVoltage" : {
            "nodetype" : "column",
            "moduleName" : "CPQPOWER-MIB",
            "oid" : "1.3.6.1.4.1.232.165.2.3.2.1.2",
            "status" : "current",
            "syntax" : {
                "type" : { "module" :"", "name" : "Integer32"},
            },
            "access" : "readonly",
            "description" :
                """The breaker voltage in volts.""",
        }, # column
        "breakerCurrent" : {
            "nodetype" : "column",
            "moduleName" : "CPQPOWER-MIB",
            "oid" : "1.3.6.1.4.1.232.165.2.3.2.1.3",
            "status" : "current",
            "syntax" : {
                "type" : { "module" :"", "name" : "Integer32"},
            },
            "access" : "readonly",
            "description" :
                """The breaker current draw in hundredths of Amp.""",
        }, # column
        "breakerPercentLoad" : {
            "nodetype" : "column",
            "moduleName" : "CPQPOWER-MIB",
            "oid" : "1.3.6.1.4.1.232.165.2.3.2.1.4",
            "status" : "current",
            "syntax" : {
                "type" : { "module" :"", "name" : "Integer32"},
            },
            "access" : "readonly",
            "description" :
                """The breaker load in percent.""",
        }, # column
        "breakerStatus" : {
            "nodetype" : "column",
            "moduleName" : "CPQPOWER-MIB",
            "oid" : "1.3.6.1.4.1.232.165.2.3.2.1.5",
            "status" : "current",
            "syntax" : {
                "type" :                 {
                    "basetype" : "Enumeration",
                    "normal" : {
                        "nodetype" : "namednumber",
                        "number" : "1"
                    },
                    "overloadWarning" : {
                        "nodetype" : "namednumber",
                        "number" : "2"
                    },
                    "overloadCritical" : {
                        "nodetype" : "namednumber",
                        "number" : "3"
                    },
                    "voltageRangeWarning" : {
                        "nodetype" : "namednumber",
                        "number" : "4"
                    },
                    "voltageRangeCritical" : {
                        "nodetype" : "namednumber",
                        "number" : "5"
                    },
                },
            },
            "access" : "readonly",
            "description" :
                """This object indicates the status of the breaker.  A value of normal(1)
indicates the breaker is operating normally.  A value of overloadWarning(2)
indicates the breaker has an overload warning.  A value of overloadCritical(3)
indicates the breaker is overloaded.  A value of voltageRangeWarning(4)
indicates the breaker voltage is out of tolerance by 10-20%.  A value of
voltageRangeCritical(5) indicates the breaker voltage is out of tolerance
by more than 20%.  Note: Overload status has priority over voltage tolerance
status.""",
        }, # column
        "ups" : {
            "nodetype" : "node",
            "moduleName" : "CPQPOWER-MIB",
            "oid" : "1.3.6.1.4.1.232.165.3",
        }, # node
        "upsIdent" : {
            "nodetype" : "node",
            "moduleName" : "CPQPOWER-MIB",
            "oid" : "1.3.6.1.4.1.232.165.3.1",
        }, # node
        "upsIdentManufacturer" : {
            "nodetype" : "scalar",
            "moduleName" : "CPQPOWER-MIB",
            "oid" : "1.3.6.1.4.1.232.165.3.1.1",
            "status" : "current",
            "syntax" : {
                "type" :                 {
                    "basetype" : "OctetString",
                    "parent module" : {
                        "name" : "RFC1213-MIB",
                        "type" : "DisplayString",
                    },
                    "ranges" : [
                    {
                        "min" : "0",
                        "max" : "31"
                    },
                    ],
                    "range" : {
                        "min" : "0",
                        "max" : "31"
                    },
                },
            },
            "access" : "readonly",
            "description" :
                """The UPS Manufacturer Name (e.g. Hewlett-Packard).""",
        }, # scalar
        "upsIdentModel" : {
            "nodetype" : "scalar",
            "moduleName" : "CPQPOWER-MIB",
            "oid" : "1.3.6.1.4.1.232.165.3.1.2",
            "status" : "current",
            "syntax" : {
                "type" :                 {
                    "basetype" : "OctetString",
                    "parent module" : {
                        "name" : "RFC1213-MIB",
                        "type" : "DisplayString",
                    },
                    "ranges" : [
                    {
                        "min" : "0",
                        "max" : "63"
                    },
                    ],
                    "range" : {
                        "min" : "0",
                        "max" : "63"
                    },
                },
            },
            "access" : "readonly",
            "description" :
                """The UPS Model;Part number;Serial number (e.g. HP R5500 XR;204451-B21;B00123456W).""",
        }, # scalar
        "upsIdentSoftwareVersions" : {
            "nodetype" : "scalar",
            "moduleName" : "CPQPOWER-MIB",
            "oid" : "1.3.6.1.4.1.232.165.3.1.3",
            "status" : "current",
            "syntax" : {
                "type" :                 {
                    "basetype" : "OctetString",
                    "parent module" : {
                        "name" : "RFC1213-MIB",
                        "type" : "DisplayString",
                    },
                    "ranges" : [
                    {
                        "min" : "0",
                        "max" : "63"
                    },
                    ],
                    "range" : {
                        "min" : "0",
                        "max" : "63"
                    },
                },
            },
            "access" : "readonly",
            "description" :
                """The firmware revision level(s) of the UPS microcontroller(s).""",
        }, # scalar
        "upsIdentOemCode" : {
            "nodetype" : "scalar",
            "moduleName" : "CPQPOWER-MIB",
            "oid" : "1.3.6.1.4.1.232.165.3.1.4",
            "status" : "current",
            "syntax" : {
                "type" :                 {
                    "basetype" : "Integer32",
                    "ranges" : [
                    {
                        "min" : "0",
                        "max" : "255"
                    },
                    ],
                    "range" : {
                        "min" : "0",
                        "max" : "255"
                    },
                },
            },
            "access" : "readonly",
            "description" :
                """A binary code indicating vendor. This should be a ?0x0c? for HP""",
        }, # scalar
        "upsBattery" : {
            "nodetype" : "node",
            "moduleName" : "CPQPOWER-MIB",
            "oid" : "1.3.6.1.4.1.232.165.3.2",
        }, # node
        "upsBatTimeRemaining" : {
            "nodetype" : "scalar",
            "moduleName" : "CPQPOWER-MIB",
            "oid" : "1.3.6.1.4.1.232.165.3.2.1",
            "status" : "current",
            "syntax" : {
                "type" :                 {
                    "basetype" : "Integer32",
                    "ranges" : [
                    {
                        "min" : "0",
                        "max" : "2147483647"
                    },
                    ],
                    "range" : {
                        "min" : "0",
                        "max" : "2147483647"
                    },
                },
            },
            "access" : "readonly",
            "description" :
                """Battery run time in seconds before UPS turns off due
to low battery.""",
        }, # scalar
        "upsBatVoltage" : {
            "nodetype" : "scalar",
            "moduleName" : "CPQPOWER-MIB",
            "oid" : "1.3.6.1.4.1.232.165.3.2.2",
            "status" : "current",
            "syntax" : {
                "type" :                 {
                    "basetype" : "Integer32",
                    "ranges" : [
                    {
                        "min" : "0",
                        "max" : "2147483647"
                    },
                    ],
                    "range" : {
                        "min" : "0",
                        "max" : "2147483647"
                    },
                },
            },
            "access" : "readonly",
            "description" :
                """Battery voltage as reported by the UPS meters.""",
        }, # scalar
        "upsBatCurrent" : {
            "nodetype" : "scalar",
            "moduleName" : "CPQPOWER-MIB",
            "oid" : "1.3.6.1.4.1.232.165.3.2.3",
            "status" : "current",
            "syntax" : {
                "type" :                 {
                    "basetype" : "Integer32",
                    "ranges" : [
                    {
                        "min" : "-2147483648",
                        "max" : "2147483647"
                    },
                    ],
                    "range" : {
                        "min" : "-2147483648",
                        "max" : "2147483647"
                    },
                },
            },
            "access" : "readonly",
            "description" :
                """Battery Current as reported by the UPS metering.
Current is positive when discharging, negative
when recharging the battery.""",
        }, # scalar
        "upsBatCapacity" : {
            "nodetype" : "scalar",
            "moduleName" : "CPQPOWER-MIB",
            "oid" : "1.3.6.1.4.1.232.165.3.2.4",
            "status" : "current",
            "syntax" : {
                "type" :                 {
                    "basetype" : "Integer32",
                    "ranges" : [
                    {
                        "min" : "0",
                        "max" : "100"
                    },
                    ],
                    "range" : {
                        "min" : "0",
                        "max" : "100"
                    },
                },
            },
            "access" : "readonly",
            "description" :
                """Battery percent charge.""",
        }, # scalar
        "upsBatteryAbmStatus" : {
            "nodetype" : "scalar",
            "moduleName" : "CPQPOWER-MIB",
            "oid" : "1.3.6.1.4.1.232.165.3.2.5",
            "status" : "current",
            "syntax" : {
                "type" :                 {
                    "basetype" : "Enumeration",
                    "batteryCharging" : {
                        "nodetype" : "namednumber",
                        "number" : "1"
                    },
                    "batteryDischarging" : {
                        "nodetype" : "namednumber",
                        "number" : "2"
                    },
                    "batteryFloating" : {
                        "nodetype" : "namednumber",
                        "number" : "3"
                    },
                    "batteryResting" : {
                        "nodetype" : "namednumber",
                        "number" : "4"
                    },
                    "unknown" : {
                        "nodetype" : "namednumber",
                        "number" : "5"
                    },
                },
            },
            "access" : "readonly",
            "description" :
                """Gives the status of the Advanced Battery Management;
batteryFloating(3) status means that the charger is temporarily 
charging the battery to its float voltage; batteryResting(4) is the 
state when the battery is fully charged and none of the other actions 
(charging/discharging/floating) is being done.""",
        }, # scalar
        "upsInput" : {
            "nodetype" : "node",
            "moduleName" : "CPQPOWER-MIB",
            "oid" : "1.3.6.1.4.1.232.165.3.3",
        }, # node
        "upsInputFrequency" : {
            "nodetype" : "scalar",
            "moduleName" : "CPQPOWER-MIB",
            "oid" : "1.3.6.1.4.1.232.165.3.3.1",
            "status" : "current",
            "syntax" : {
                "type" :                 {
                    "basetype" : "Integer32",
                    "ranges" : [
                    {
                        "min" : "0",
                        "max" : "2147483647"
                    },
                    ],
                    "range" : {
                        "min" : "0",
                        "max" : "2147483647"
                    },
                },
            },
            "access" : "readonly",
            "description" :
                """The utility line frequency in tenths of Hz.""",
        }, # scalar
        "upsInputLineBads" : {
            "nodetype" : "scalar",
            "moduleName" : "CPQPOWER-MIB",
            "oid" : "1.3.6.1.4.1.232.165.3.3.2",
            "status" : "current",
            "syntax" : {
                "type" : { "module" :"RFC1155-SMI", "name" : "Counter"},
            },
            "access" : "readonly",
            "description" :
                """The number of times the Input was out of tolerance
in voltage or frequency.""",
        }, # scalar
        "upsInputNumPhases" : {
            "nodetype" : "scalar",
            "moduleName" : "CPQPOWER-MIB",
            "oid" : "1.3.6.1.4.1.232.165.3.3.3",
            "status" : "current",
            "syntax" : {
                "type" :                 {
                    "basetype" : "Integer32",
                    "ranges" : [
                    {
                        "min" : "0",
                        "max" : "6"
                    },
                    ],
                    "range" : {
                        "min" : "0",
                        "max" : "6"
                    },
                },
            },
            "access" : "readonly",
        }, # scalar
        "upsInputTable" : {
            "nodetype" : "table",
            "moduleName" : "CPQPOWER-MIB",
            "oid" : "1.3.6.1.4.1.232.165.3.3.4",
            "status" : "current",
            "description" :
                """The Aggregate Object with number of entries equal to
NumPhases and including the UpsInput group.""",
        }, # table
        "upsInputEntry" : {
            "nodetype" : "row",
            "moduleName" : "CPQPOWER-MIB",
            "oid" : "1.3.6.1.4.1.232.165.3.3.4.1",
            "status" : "current",
            "linkage" : [
                "upsInputPhase",
            ],
            "description" :
                """The input table entry containing the current, voltage, etc.""",
        }, # row
        "upsInputPhase" : {
            "nodetype" : "column",
            "moduleName" : "CPQPOWER-MIB",
            "oid" : "1.3.6.1.4.1.232.165.3.3.4.1.1",
            "status" : "current",
            "syntax" : {
                "type" :                 {
                    "basetype" : "Integer32",
                    "ranges" : [
                    {
                        "min" : "0",
                        "max" : "6"
                    },
                    ],
                    "range" : {
                        "min" : "0",
                        "max" : "6"
                    },
                },
            },
            "access" : "readonly",
            "description" :
                """The number of the phase.  Serves as index for input table.""",
        }, # column
        "upsInputVoltage" : {
            "nodetype" : "column",
            "moduleName" : "CPQPOWER-MIB",
            "oid" : "1.3.6.1.4.1.232.165.3.3.4.1.2",
            "status" : "current",
            "syntax" : {
                "type" :                 {
                    "basetype" : "Integer32",
                    "ranges" : [
                    {
                        "min" : "0",
                        "max" : "2147483647"
                    },
                    ],
                    "range" : {
                        "min" : "0",
                        "max" : "2147483647"
                    },
                },
            },
            "access" : "readonly",
            "description" :
                """The measured input voltage from the UPS meters in volts.""",
        }, # column
        "upsInputCurrent" : {
            "nodetype" : "column",
            "moduleName" : "CPQPOWER-MIB",
            "oid" : "1.3.6.1.4.1.232.165.3.3.4.1.3",
            "status" : "current",
            "syntax" : {
                "type" :                 {
                    "basetype" : "Integer32",
                    "ranges" : [
                    {
                        "min" : "0",
                        "max" : "2147483647"
                    },
                    ],
                    "range" : {
                        "min" : "0",
                        "max" : "2147483647"
                    },
                },
            },
            "access" : "readonly",
            "description" :
                """The measured input current from the UPS meters in amps.""",
        }, # column
        "upsInputWatts" : {
            "nodetype" : "column",
            "moduleName" : "CPQPOWER-MIB",
            "oid" : "1.3.6.1.4.1.232.165.3.3.4.1.4",
            "status" : "current",
            "syntax" : {
                "type" :                 {
                    "basetype" : "Integer32",
                    "ranges" : [
                    {
                        "min" : "0",
                        "max" : "2147483647"
                    },
                    ],
                    "range" : {
                        "min" : "0",
                        "max" : "2147483647"
                    },
                },
            },
            "access" : "readonly",
            "description" :
                """The measured input real power in watts. Most UPSs do not report
this XCP data""",
        }, # column
        "upsInputSource" : {
            "nodetype" : "scalar",
            "moduleName" : "CPQPOWER-MIB",
            "oid" : "1.3.6.1.4.1.232.165.3.3.5",
            "status" : "current",
            "syntax" : {
                "type" :                 {
                    "basetype" : "Enumeration",
                    "other" : {
                        "nodetype" : "namednumber",
                        "number" : "1"
                    },
                    "none" : {
                        "nodetype" : "namednumber",
                        "number" : "2"
                    },
                    "primaryUtility" : {
                        "nodetype" : "namednumber",
                        "number" : "3"
                    },
                    "bypassFeed" : {
                        "nodetype" : "namednumber",
                        "number" : "4"
                    },
                    "secondaryUtility" : {
                        "nodetype" : "namednumber",
                        "number" : "5"
                    },
                    "generator" : {
                        "nodetype" : "namednumber",
                        "number" : "6"
                    },
                    "flywheel" : {
                        "nodetype" : "namednumber",
                        "number" : "7"
                    },
                    "fuelcell" : {
                        "nodetype" : "namednumber",
                        "number" : "8"
                    },
                },
            },
            "access" : "readonly",
            "description" :
                """The present external source of input power.  The enumeration
none(2) indicates that there is no external source of 
power, for example, the UPS is On Battery (an internal source).
The bypassFeed(4) can only be used when the Bypass source is known
to be a separate utility feed than the primaryUtility(3).""",
        }, # scalar
        "upsOutput" : {
            "nodetype" : "node",
            "moduleName" : "CPQPOWER-MIB",
            "oid" : "1.3.6.1.4.1.232.165.3.4",
        }, # node
        "upsOutputLoad" : {
            "nodetype" : "scalar",
            "moduleName" : "CPQPOWER-MIB",
            "oid" : "1.3.6.1.4.1.232.165.3.4.1",
            "status" : "current",
            "syntax" : {
                "type" :                 {
                    "basetype" : "Integer32",
                    "ranges" : [
                    {
                        "min" : "0",
                        "max" : "200"
                    },
                    ],
                    "range" : {
                        "min" : "0",
                        "max" : "200"
                    },
                },
            },
            "access" : "readonly",
            "description" :
                """The UPS output load in percent of rated capacity.""",
        }, # scalar
        "upsOutputFrequency" : {
            "nodetype" : "scalar",
            "moduleName" : "CPQPOWER-MIB",
            "oid" : "1.3.6.1.4.1.232.165.3.4.2",
            "status" : "current",
            "syntax" : {
                "type" :                 {
                    "basetype" : "Integer32",
                    "ranges" : [
                    {
                        "min" : "0",
                        "max" : "2147483647"
                    },
                    ],
                    "range" : {
                        "min" : "0",
                        "max" : "2147483647"
                    },
                },
            },
            "access" : "readonly",
            "description" :
                """The measured UPS output frequency in tenths of Hz.""",
        }, # scalar
        "upsOutputNumPhases" : {
            "nodetype" : "scalar",
            "moduleName" : "CPQPOWER-MIB",
            "oid" : "1.3.6.1.4.1.232.165.3.4.3",
            "status" : "current",
            "syntax" : {
                "type" :                 {
                    "basetype" : "Integer32",
                    "ranges" : [
                    {
                        "min" : "0",
                        "max" : "6"
                    },
                    ],
                    "range" : {
                        "min" : "0",
                        "max" : "6"
                    },
                },
            },
            "access" : "readonly",
            "description" :
                """The number of metered output phases, serves as the table
index.""",
        }, # scalar
        "upsOutputTable" : {
            "nodetype" : "table",
            "moduleName" : "CPQPOWER-MIB",
            "oid" : "1.3.6.1.4.1.232.165.3.4.4",
            "status" : "current",
            "description" :
                """The Aggregate Object with number of entries equal to NumPhases
and including the UpsOutput group.""",
        }, # table
        "upsOutputEntry" : {
            "nodetype" : "row",
            "moduleName" : "CPQPOWER-MIB",
            "oid" : "1.3.6.1.4.1.232.165.3.4.4.1",
            "status" : "current",
            "linkage" : [
                "upsOutputPhase",
            ],
            "description" :
                """Output Table Entry containing voltage, current, etc.""",
        }, # row
        "upsOutputPhase" : {
            "nodetype" : "column",
            "moduleName" : "CPQPOWER-MIB",
            "oid" : "1.3.6.1.4.1.232.165.3.4.4.1.1",
            "status" : "current",
            "syntax" : {
                "type" :                 {
                    "basetype" : "Integer32",
                    "ranges" : [
                    {
                        "min" : "0",
                        "max" : "6"
                    },
                    ],
                    "range" : {
                        "min" : "0",
                        "max" : "6"
                    },
                },
            },
            "access" : "readonly",
            "description" :
                """The number {1..3} of the output phase.""",
        }, # column
        "upsOutputVoltage" : {
            "nodetype" : "column",
            "moduleName" : "CPQPOWER-MIB",
            "oid" : "1.3.6.1.4.1.232.165.3.4.4.1.2",
            "status" : "current",
            "syntax" : {
                "type" :                 {
                    "basetype" : "Integer32",
                    "ranges" : [
                    {
                        "min" : "0",
                        "max" : "2147483647"
                    },
                    ],
                    "range" : {
                        "min" : "0",
                        "max" : "2147483647"
                    },
                },
            },
            "access" : "readonly",
            "description" :
                """The measured output voltage from the UPS metering in volts.""",
        }, # column
        "upsOutputCurrent" : {
            "nodetype" : "column",
            "moduleName" : "CPQPOWER-MIB",
            "oid" : "1.3.6.1.4.1.232.165.3.4.4.1.3",
            "status" : "current",
            "syntax" : {
                "type" :                 {
                    "basetype" : "Integer32",
                    "ranges" : [
                    {
                        "min" : "0",
                        "max" : "2147483647"
                    },
                    ],
                    "range" : {
                        "min" : "0",
                        "max" : "2147483647"
                    },
                },
            },
            "access" : "readonly",
            "description" :
                """The measured UPS output current in amps.""",
        }, # column
        "upsOutputWatts" : {
            "nodetype" : "column",
            "moduleName" : "CPQPOWER-MIB",
            "oid" : "1.3.6.1.4.1.232.165.3.4.4.1.4",
            "status" : "current",
            "syntax" : {
                "type" :                 {
                    "basetype" : "Integer32",
                    "ranges" : [
                    {
                        "min" : "0",
                        "max" : "2147483647"
                    },
                    ],
                    "range" : {
                        "min" : "0",
                        "max" : "2147483647"
                    },
                },
            },
            "access" : "readonly",
            "description" :
                """The measured real output power in watts.""",
        }, # column
        "upsOutputSource" : {
            "nodetype" : "scalar",
            "moduleName" : "CPQPOWER-MIB",
            "oid" : "1.3.6.1.4.1.232.165.3.4.5",
            "status" : "current",
            "syntax" : {
                "type" :                 {
                    "basetype" : "Enumeration",
                    "other" : {
                        "nodetype" : "namednumber",
                        "number" : "1"
                    },
                    "none" : {
                        "nodetype" : "namednumber",
                        "number" : "2"
                    },
                    "normal" : {
                        "nodetype" : "namednumber",
                        "number" : "3"
                    },
                    "bypass" : {
                        "nodetype" : "namednumber",
                        "number" : "4"
                    },
                    "battery" : {
                        "nodetype" : "namednumber",
                        "number" : "5"
                    },
                    "booster" : {
                        "nodetype" : "namednumber",
                        "number" : "6"
                    },
                    "reducer" : {
                        "nodetype" : "namednumber",
                        "number" : "7"
                    },
                    "parallelCapacity" : {
                        "nodetype" : "namednumber",
                        "number" : "8"
                    },
                    "parallelRedundant" : {
                        "nodetype" : "namednumber",
                        "number" : "9"
                    },
                    "highEfficiencyMode" : {
                        "nodetype" : "namednumber",
                        "number" : "10"
                    },
                },
            },
            "access" : "readonly",
            "description" :
                """The present source of output power.  The enumeration
none(2) indicates that there is no source of output
power (and therefore no output power), for example,
the system has opened the output breaker.""",
        }, # scalar
        "upsBypass" : {
            "nodetype" : "node",
            "moduleName" : "CPQPOWER-MIB",
            "oid" : "1.3.6.1.4.1.232.165.3.5",
        }, # node
        "upsBypassFrequency" : {
            "nodetype" : "scalar",
            "moduleName" : "CPQPOWER-MIB",
            "oid" : "1.3.6.1.4.1.232.165.3.5.1",
            "status" : "current",
            "syntax" : {
                "type" :                 {
                    "basetype" : "Integer32",
                    "ranges" : [
                    {
                        "min" : "0",
                        "max" : "2147483647"
                    },
                    ],
                    "range" : {
                        "min" : "0",
                        "max" : "2147483647"
                    },
                },
            },
            "access" : "readonly",
            "description" :
                """The bypass frequency in tenths of Hz.""",
        }, # scalar
        "upsBypassNumPhases" : {
            "nodetype" : "scalar",
            "moduleName" : "CPQPOWER-MIB",
            "oid" : "1.3.6.1.4.1.232.165.3.5.2",
            "status" : "current",
            "syntax" : {
                "type" :                 {
                    "basetype" : "Integer32",
                    "ranges" : [
                    {
                        "min" : "0",
                        "max" : "6"
                    },
                    ],
                    "range" : {
                        "min" : "0",
                        "max" : "6"
                    },
                },
            },
            "access" : "readonly",
            "description" :
                """The number of lines in the UPS bypass table.""",
        }, # scalar
        "upsBypassTable" : {
            "nodetype" : "table",
            "moduleName" : "CPQPOWER-MIB",
            "oid" : "1.3.6.1.4.1.232.165.3.5.3",
            "status" : "current",
        }, # table
        "upsBypassEntry" : {
            "nodetype" : "row",
            "moduleName" : "CPQPOWER-MIB",
            "oid" : "1.3.6.1.4.1.232.165.3.5.3.1",
            "status" : "current",
            "linkage" : [
                "upsBypassPhase",
            ],
            "description" :
                """Entry in the UpsBypassTable.""",
        }, # row
        "upsBypassPhase" : {
            "nodetype" : "column",
            "moduleName" : "CPQPOWER-MIB",
            "oid" : "1.3.6.1.4.1.232.165.3.5.3.1.1",
            "status" : "current",
            "syntax" : {
                "type" :                 {
                    "basetype" : "Integer32",
                    "ranges" : [
                    {
                        "min" : "0",
                        "max" : "6"
                    },
                    ],
                    "range" : {
                        "min" : "0",
                        "max" : "6"
                    },
                },
            },
            "access" : "readonly",
            "description" :
                """The Bypass Phase, index for the table.""",
        }, # column
        "upsBypassVoltage" : {
            "nodetype" : "column",
            "moduleName" : "CPQPOWER-MIB",
            "oid" : "1.3.6.1.4.1.232.165.3.5.3.1.2",
            "status" : "current",
            "syntax" : {
                "type" :                 {
                    "basetype" : "Integer32",
                    "ranges" : [
                    {
                        "min" : "0",
                        "max" : "2147483647"
                    },
                    ],
                    "range" : {
                        "min" : "0",
                        "max" : "2147483647"
                    },
                },
            },
            "access" : "readonly",
            "description" :
                """The measured UPS bypass voltage in volts.""",
        }, # column
        "upsEnvironment" : {
            "nodetype" : "node",
            "moduleName" : "CPQPOWER-MIB",
            "oid" : "1.3.6.1.4.1.232.165.3.6",
        }, # node
        "upsEnvAmbientTemp" : {
            "nodetype" : "scalar",
            "moduleName" : "CPQPOWER-MIB",
            "oid" : "1.3.6.1.4.1.232.165.3.6.1",
            "status" : "current",
            "syntax" : {
                "type" :                 {
                    "basetype" : "Integer32",
                    "ranges" : [
                    {
                        "min" : "-100",
                        "max" : "200"
                    },
                    ],
                    "range" : {
                        "min" : "-100",
                        "max" : "200"
                    },
                },
            },
            "access" : "readonly",
            "description" :
                """The reading of the ambient temperature in the vicinity of the 
UPS or SNMP agent.""",
        }, # scalar
        "upsEnvAmbientLowerLimit" : {
            "nodetype" : "scalar",
            "moduleName" : "CPQPOWER-MIB",
            "oid" : "1.3.6.1.4.1.232.165.3.6.2",
            "status" : "current",
            "syntax" : {
                "type" :                 {
                    "basetype" : "Integer32",
                    "ranges" : [
                    {
                        "min" : "-100",
                        "max" : "200"
                    },
                    ],
                    "range" : {
                        "min" : "-100",
                        "max" : "200"
                    },
                },
            },
            "access" : "readwrite",
            "description" :
                """The Lower Limit of the ambient temperature; if UpsEnvAmbientTemp 
falls below this value, the UpsAmbientTempBad alarm will occur.""",
        }, # scalar
        "upsEnvAmbientUpperLimit" : {
            "nodetype" : "scalar",
            "moduleName" : "CPQPOWER-MIB",
            "oid" : "1.3.6.1.4.1.232.165.3.6.3",
            "status" : "current",
            "syntax" : {
                "type" :                 {
                    "basetype" : "Integer32",
                    "ranges" : [
                    {
                        "min" : "-100",
                        "max" : "200"
                    },
                    ],
                    "range" : {
                        "min" : "-100",
                        "max" : "200"
                    },
                },
            },
            "access" : "readwrite",
            "description" :
                """The Upper Limit of the ambient temperature; if UpsEnvAmbientTemp 
rises above this value, the UpsAmbientTempBad alarm will occur.
This value should be greater than UpsEnvAmbientLowerLimit.""",
        }, # scalar
        "upsEnvAmbientHumidity" : {
            "nodetype" : "scalar",
            "moduleName" : "CPQPOWER-MIB",
            "oid" : "1.3.6.1.4.1.232.165.3.6.4",
            "status" : "current",
            "syntax" : {
                "type" :                 {
                    "basetype" : "Integer32",
                    "ranges" : [
                    {
                        "min" : "0",
                        "max" : "100"
                    },
                    ],
                    "range" : {
                        "min" : "0",
                        "max" : "100"
                    },
                },
            },
            "access" : "readonly",
            "description" :
                """The reading of the ambient humidity in the vicinity of the 
UPS or SNMP agent.""",
        }, # scalar
        "upsEnvRemoteTemp" : {
            "nodetype" : "scalar",
            "moduleName" : "CPQPOWER-MIB",
            "oid" : "1.3.6.1.4.1.232.165.3.6.5",
            "status" : "current",
            "syntax" : {
                "type" :                 {
                    "basetype" : "Integer32",
                    "ranges" : [
                    {
                        "min" : "-100",
                        "max" : "200"
                    },
                    ],
                    "range" : {
                        "min" : "-100",
                        "max" : "200"
                    },
                },
            },
            "access" : "readonly",
            "description" :
                """The reading of a remote temperature sensor connected to the  
UPS or SNMP agent.""",
        }, # scalar
        "upsEnvRemoteHumidity" : {
            "nodetype" : "scalar",
            "moduleName" : "CPQPOWER-MIB",
            "oid" : "1.3.6.1.4.1.232.165.3.6.6",
            "status" : "current",
            "syntax" : {
                "type" :                 {
                    "basetype" : "Integer32",
                    "ranges" : [
                    {
                        "min" : "0",
                        "max" : "100"
                    },
                    ],
                    "range" : {
                        "min" : "0",
                        "max" : "100"
                    },
                },
            },
            "access" : "readonly",
            "description" :
                """The reading of a remote humidity sensor connected to the 
UPS or SNMP agent.""",
        }, # scalar
        "upsEnvNumContacts" : {
            "nodetype" : "scalar",
            "moduleName" : "CPQPOWER-MIB",
            "oid" : "1.3.6.1.4.1.232.165.3.6.7",
            "status" : "current",
            "syntax" : {
                "type" :                 {
                    "basetype" : "Integer32",
                    "ranges" : [
                    {
                        "min" : "1",
                        "max" : "1024"
                    },
                    ],
                    "range" : {
                        "min" : "1",
                        "max" : "1024"
                    },
                },
            },
            "access" : "readonly",
            "description" :
                """The number of Contacts in the UpsContactsTable.
This object indicates the number of rows in the 
UpsContactsTable.""",
        }, # scalar
        "upsContactsTable" : {
            "nodetype" : "table",
            "moduleName" : "CPQPOWER-MIB",
            "oid" : "1.3.6.1.4.1.232.165.3.6.8",
            "status" : "current",
            "description" :
                """A list of Contact Sensing table entries.  
The number of entries is given by the value of 
UpsEnvNumContacts.""",
        }, # table
        "upsContactsTableEntry" : {
            "nodetype" : "row",
            "moduleName" : "CPQPOWER-MIB",
            "oid" : "1.3.6.1.4.1.232.165.3.6.8.1",
            "status" : "current",
            "linkage" : [
                "upsContactIndex",
            ],
            "description" :
                """An entry containing information applicable 
to a particular Contact input.""",
        }, # row
        "upsContactIndex" : {
            "nodetype" : "column",
            "moduleName" : "CPQPOWER-MIB",
            "oid" : "1.3.6.1.4.1.232.165.3.6.8.1.1",
            "status" : "current",
            "syntax" : {
                "type" :                 {
                    "basetype" : "Integer32",
                    "ranges" : [
                    {
                        "min" : "1",
                        "max" : "1024"
                    },
                    ],
                    "range" : {
                        "min" : "1",
                        "max" : "1024"
                    },
                },
            },
            "access" : "readonly",
            "description" :
                """The Contact identifier; identical to the Contact Number.""",
        }, # column
        "upsContactType" : {
            "nodetype" : "column",
            "moduleName" : "CPQPOWER-MIB",
            "oid" : "1.3.6.1.4.1.232.165.3.6.8.1.2",
            "status" : "current",
            "syntax" : {
                "type" :                 {
                    "basetype" : "Enumeration",
                    "normallyOpen" : {
                        "nodetype" : "namednumber",
                        "number" : "1"
                    },
                    "normallyClosed" : {
                        "nodetype" : "namednumber",
                        "number" : "2"
                    },
                    "anyChange" : {
                        "nodetype" : "namednumber",
                        "number" : "3"
                    },
                    "notUsed" : {
                        "nodetype" : "namednumber",
                        "number" : "4"
                    },
                },
            },
            "access" : "readwrite",
            "description" :
                """The normal state for this contact.  The 'other'
state is the Active state for generating the UpstdContactActiveNotice
trap.  If anyChange(3) is selected, then this trap is sent
any time the contact changes to either Open or Closed.
No traps are sent if the Contact is set to notUsed(4).
In many cases, the configuration for Contacts may be done by other 
means, so this object may be read-only.""",
        }, # column
        "upsContactState" : {
            "nodetype" : "column",
            "moduleName" : "CPQPOWER-MIB",
            "oid" : "1.3.6.1.4.1.232.165.3.6.8.1.3",
            "status" : "current",
            "syntax" : {
                "type" :                 {
                    "basetype" : "Enumeration",
                    "open" : {
                        "nodetype" : "namednumber",
                        "number" : "1"
                    },
                    "closed" : {
                        "nodetype" : "namednumber",
                        "number" : "2"
                    },
                    "openWithNotice" : {
                        "nodetype" : "namednumber",
                        "number" : "3"
                    },
                    "closedWithNotice" : {
                        "nodetype" : "namednumber",
                        "number" : "4"
                    },
                },
            },
            "access" : "readonly",
            "description" :
                """The current state of the Contact input;
the value is based on the open/closed input state 
and the setting for UpsContactType.
When entering the openWithNotice(3) and closedWithNotice(4) 
states, no entries added to the UpsAlarmTable, but
the UpstdContactActiveNotice trap is sent.""",
        }, # column
        "upsContactDescr" : {
            "nodetype" : "column",
            "moduleName" : "CPQPOWER-MIB",
            "oid" : "1.3.6.1.4.1.232.165.3.6.8.1.4",
            "status" : "current",
            "syntax" : {
                "type" :                 {
                    "basetype" : "OctetString",
                    "parent module" : {
                        "name" : "RFC1213-MIB",
                        "type" : "DisplayString",
                    },
                    "ranges" : [
                    {
                        "min" : "0",
                        "max" : "63"
                    },
                    ],
                    "range" : {
                        "min" : "0",
                        "max" : "63"
                    },
                },
            },
            "access" : "readwrite",
            "description" :
                """A label identifying the Contact.  This object should be
set by the administrator.""",
        }, # column
        "upsEnvRemoteTempLowerLimit" : {
            "nodetype" : "scalar",
            "moduleName" : "CPQPOWER-MIB",
            "oid" : "1.3.6.1.4.1.232.165.3.6.9",
            "status" : "current",
            "syntax" : {
                "type" :                 {
                    "basetype" : "Integer32",
                    "ranges" : [
                    {
                        "min" : "-100",
                        "max" : "200"
                    },
                    ],
                    "range" : {
                        "min" : "-100",
                        "max" : "200"
                    },
                },
            },
            "access" : "readwrite",
            "description" :
                """The Lower Limit of the remote temperature; if UpsEnvRemoteTemp 
falls below this value, the UpsRemoteTempBad alarm will occur.""",
        }, # scalar
        "upsEnvRemoteTempUpperLimit" : {
            "nodetype" : "scalar",
            "moduleName" : "CPQPOWER-MIB",
            "oid" : "1.3.6.1.4.1.232.165.3.6.10",
            "status" : "current",
            "syntax" : {
                "type" :                 {
                    "basetype" : "Integer32",
                    "ranges" : [
                    {
                        "min" : "-100",
                        "max" : "200"
                    },
                    ],
                    "range" : {
                        "min" : "-100",
                        "max" : "200"
                    },
                },
            },
            "access" : "readwrite",
            "description" :
                """The Upper Limit of the remote temperature; if UpsEnvRemoteTemp 
rises above this value, the UpsRemoteTempBad alarm will occur.
This value should be greater than UpsEnvRemoteTempLowerLimit.""",
        }, # scalar
        "upsEnvRemoteHumidityLowerLimit" : {
            "nodetype" : "scalar",
            "moduleName" : "CPQPOWER-MIB",
            "oid" : "1.3.6.1.4.1.232.165.3.6.11",
            "status" : "current",
            "syntax" : {
                "type" :                 {
                    "basetype" : "Integer32",
                    "ranges" : [
                    {
                        "min" : "0",
                        "max" : "100"
                    },
                    ],
                    "range" : {
                        "min" : "0",
                        "max" : "100"
                    },
                },
            },
            "access" : "readwrite",
            "description" :
                """The Lower Limit of the remote humidity reading; if UpsEnvRemoteHumidity
falls below this value, the UpsRemoteHumidityBad alarm will occur.""",
        }, # scalar
        "upsEnvRemoteHumidityUpperLimit" : {
            "nodetype" : "scalar",
            "moduleName" : "CPQPOWER-MIB",
            "oid" : "1.3.6.1.4.1.232.165.3.6.12",
            "status" : "current",
            "syntax" : {
                "type" :                 {
                    "basetype" : "Integer32",
                    "ranges" : [
                    {
                        "min" : "0",
                        "max" : "100"
                    },
                    ],
                    "range" : {
                        "min" : "0",
                        "max" : "100"
                    },
                },
            },
            "access" : "readwrite",
            "description" :
                """The Upper Limit of the remote humidity reading; if UpsEnvRemoteHumidity 
rises above this value, the UpsRemoteHumidityBad alarm will occur.
This value should be greater than UpsEnvRemoteHumidityLowerLimit.""",
        }, # scalar
        "upsTest" : {
            "nodetype" : "node",
            "moduleName" : "CPQPOWER-MIB",
            "oid" : "1.3.6.1.4.1.232.165.3.7",
        }, # node
        "upsTestBattery" : {
            "nodetype" : "scalar",
            "moduleName" : "CPQPOWER-MIB",
            "oid" : "1.3.6.1.4.1.232.165.3.7.1",
            "status" : "current",
            "syntax" : {
                "type" :                 {
                    "basetype" : "Enumeration",
                    "startTest" : {
                        "nodetype" : "namednumber",
                        "number" : "1"
                    },
                },
            },
            "access" : "readwrite",
            "description" :
                """Setting this variable to startTest initiates the
battery test.  All other set values are invalid.""",
        }, # scalar
        "upsTestBatteryStatus" : {
            "nodetype" : "scalar",
            "moduleName" : "CPQPOWER-MIB",
            "oid" : "1.3.6.1.4.1.232.165.3.7.2",
            "status" : "current",
            "syntax" : {
                "type" :                 {
                    "basetype" : "Enumeration",
                    "unknown" : {
                        "nodetype" : "namednumber",
                        "number" : "1"
                    },
                    "passed" : {
                        "nodetype" : "namednumber",
                        "number" : "2"
                    },
                    "failed" : {
                        "nodetype" : "namednumber",
                        "number" : "3"
                    },
                    "inProgress" : {
                        "nodetype" : "namednumber",
                        "number" : "4"
                    },
                    "notSupported" : {
                        "nodetype" : "namednumber",
                        "number" : "5"
                    },
                    "inhibited" : {
                        "nodetype" : "namednumber",
                        "number" : "6"
                    },
                    "scheduled" : {
                        "nodetype" : "namednumber",
                        "number" : "7"
                    },
                },
            },
            "access" : "readonly",
            "description" :
                """Reading this enumerated value gives an indication of the
UPS Battery test status.""",
        }, # scalar
        "upsTestTrap" : {
            "nodetype" : "scalar",
            "moduleName" : "CPQPOWER-MIB",
            "oid" : "1.3.6.1.4.1.232.165.3.7.3",
            "status" : "current",
            "syntax" : {
                "type" :                 {
                    "basetype" : "Enumeration",
                    "startTestTrap" : {
                        "nodetype" : "namednumber",
                        "number" : "1"
                    },
                },
            },
            "access" : "readwrite",
            "description" :
                """Setting startTestTrap to 1 will initiate a TrapTest
is sent out from HPMM.  All other set values are invalid.""",
        }, # scalar
        "upsControl" : {
            "nodetype" : "node",
            "moduleName" : "CPQPOWER-MIB",
            "oid" : "1.3.6.1.4.1.232.165.3.8",
        }, # node
        "upsControlOutputOffDelay" : {
            "nodetype" : "scalar",
            "moduleName" : "CPQPOWER-MIB",
            "oid" : "1.3.6.1.4.1.232.165.3.8.1",
            "status" : "current",
            "syntax" : {
                "type" :                 {
                    "basetype" : "Integer32",
                    "ranges" : [
                    {
                        "min" : "0",
                        "max" : "2147483647"
                    },
                    ],
                    "range" : {
                        "min" : "0",
                        "max" : "2147483647"
                    },
                },
            },
            "access" : "readwrite",
            "description" :
                """Setting this value to other than zero will cause the UPS
output to turn off after the number of seconds.
Setting it to 0 will cause an attempt to abort a pending
shutdown.""",
        }, # scalar
        "upsControlOutputOnDelay" : {
            "nodetype" : "scalar",
            "moduleName" : "CPQPOWER-MIB",
            "oid" : "1.3.6.1.4.1.232.165.3.8.2",
            "status" : "current",
            "syntax" : {
                "type" :                 {
                    "basetype" : "Integer32",
                    "ranges" : [
                    {
                        "min" : "0",
                        "max" : "2147483647"
                    },
                    ],
                    "range" : {
                        "min" : "0",
                        "max" : "2147483647"
                    },
                },
            },
            "access" : "readwrite",
            "description" :
                """Setting this value to other than zero will cause the UPS
output to turn on after the number of seconds.
Setting it to 0 will cause an attempt to abort a pending
startup.""",
        }, # scalar
        "upsControlOutputOffTrapDelay" : {
            "nodetype" : "scalar",
            "moduleName" : "CPQPOWER-MIB",
            "oid" : "1.3.6.1.4.1.232.165.3.8.3",
            "status" : "current",
            "syntax" : {
                "type" :                 {
                    "basetype" : "Integer32",
                    "ranges" : [
                    {
                        "min" : "0",
                        "max" : "2147483647"
                    },
                    ],
                    "range" : {
                        "min" : "0",
                        "max" : "2147483647"
                    },
                },
            },
            "access" : "readwrite",
            "description" :
                """When UpsControlOutputOffDelay reaches this value, a trap will
be sent.""",
        }, # scalar
        "upsControlOutputOnTrapDelay" : {
            "nodetype" : "scalar",
            "moduleName" : "CPQPOWER-MIB",
            "oid" : "1.3.6.1.4.1.232.165.3.8.4",
            "status" : "obsolete",
            "syntax" : {
                "type" :                 {
                    "basetype" : "Integer32",
                    "ranges" : [
                    {
                        "min" : "0",
                        "max" : "2147483647"
                    },
                    ],
                    "range" : {
                        "min" : "0",
                        "max" : "2147483647"
                    },
                },
            },
            "access" : "readwrite",
            "description" :
                """When UpsControlOutputOnDelay reaches this value, a
UpsOutputOff trap will be sent.""",
        }, # scalar
        "upsControlToBypassDelay" : {
            "nodetype" : "scalar",
            "moduleName" : "CPQPOWER-MIB",
            "oid" : "1.3.6.1.4.1.232.165.3.8.5",
            "status" : "current",
            "syntax" : {
                "type" :                 {
                    "basetype" : "Integer32",
                    "ranges" : [
                    {
                        "min" : "0",
                        "max" : "2147483647"
                    },
                    ],
                    "range" : {
                        "min" : "0",
                        "max" : "2147483647"
                    },
                },
            },
            "access" : "readwrite",
            "description" :
                """Setting this value to other than zero will cause the UPS
output to go to Bypass after the number of seconds.
	 If the Bypass is unavailable, this may cause the UPS
	 to not supply power to the load.
Setting it to 0 will cause an attempt to abort a pending
shutdown.""",
        }, # scalar
        "upsLoadShedSecsWithRestart" : {
            "nodetype" : "scalar",
            "moduleName" : "CPQPOWER-MIB",
            "oid" : "1.3.6.1.4.1.232.165.3.8.6",
            "status" : "current",
            "syntax" : {
                "type" :                 {
                    "basetype" : "Integer32",
                    "ranges" : [
                    {
                        "min" : "0",
                        "max" : "2147483647"
                    },
                    ],
                    "range" : {
                        "min" : "0",
                        "max" : "2147483647"
                    },
                },
            },
            "access" : "readwrite",
            "description" :
                """Setting this value will cause the UPS output to turn off 
after the set number of seconds, then restart (after a UPS-defined
'down time') when the utility is again available.  
Unlike UpsControlOutputOffDelay, which might or might not,
this object always maps to the XCP 0x8A Load Dump & Restart command,
so the desired shutdown and restart behavior is guaranteed to happen.
Once set, this command cannot be aborted.
This is the preferred Control object to use when performing an On
Battery OS Shutdown.""",
        }, # scalar
        "upsConfig" : {
            "nodetype" : "node",
            "moduleName" : "CPQPOWER-MIB",
            "oid" : "1.3.6.1.4.1.232.165.3.9",
        }, # node
        "upsConfigOutputVoltage" : {
            "nodetype" : "scalar",
            "moduleName" : "CPQPOWER-MIB",
            "oid" : "1.3.6.1.4.1.232.165.3.9.1",
            "status" : "current",
            "syntax" : {
                "type" :                 {
                    "basetype" : "Integer32",
                    "ranges" : [
                    {
                        "min" : "0",
                        "max" : "2147483647"
                    },
                    ],
                    "range" : {
                        "min" : "0",
                        "max" : "2147483647"
                    },
                },
            },
            "access" : "readonly",
            "description" :
                """The nominal UPS Output voltage per phase in volts.""",
        }, # scalar
        "upsConfigInputVoltage" : {
            "nodetype" : "scalar",
            "moduleName" : "CPQPOWER-MIB",
            "oid" : "1.3.6.1.4.1.232.165.3.9.2",
            "status" : "current",
            "syntax" : {
                "type" :                 {
                    "basetype" : "Integer32",
                    "ranges" : [
                    {
                        "min" : "0",
                        "max" : "2147483647"
                    },
                    ],
                    "range" : {
                        "min" : "0",
                        "max" : "2147483647"
                    },
                },
            },
            "access" : "readonly",
            "description" :
                """The nominal UPS Input voltage per phase in volts.""",
        }, # scalar
        "upsConfigOutputWatts" : {
            "nodetype" : "scalar",
            "moduleName" : "CPQPOWER-MIB",
            "oid" : "1.3.6.1.4.1.232.165.3.9.3",
            "status" : "current",
            "syntax" : {
                "type" :                 {
                    "basetype" : "Integer32",
                    "ranges" : [
                    {
                        "min" : "0",
                        "max" : "2147483647"
                    },
                    ],
                    "range" : {
                        "min" : "0",
                        "max" : "2147483647"
                    },
                },
            },
            "access" : "readonly",
            "description" :
                """The nominal UPS available real power output in watts.""",
        }, # scalar
        "upsConfigOutputFreq" : {
            "nodetype" : "scalar",
            "moduleName" : "CPQPOWER-MIB",
            "oid" : "1.3.6.1.4.1.232.165.3.9.4",
            "status" : "current",
            "syntax" : {
                "type" :                 {
                    "basetype" : "Integer32",
                    "ranges" : [
                    {
                        "min" : "0",
                        "max" : "2147483647"
                    },
                    ],
                    "range" : {
                        "min" : "0",
                        "max" : "2147483647"
                    },
                },
            },
            "access" : "readonly",
            "description" :
                """The nominal output frequency in tenths of Hz.""",
        }, # scalar
        "upsConfigDateAndTime" : {
            "nodetype" : "scalar",
            "moduleName" : "CPQPOWER-MIB",
            "oid" : "1.3.6.1.4.1.232.165.3.9.5",
            "status" : "current",
            "syntax" : {
                "type" :                 {
                    "basetype" : "OctetString",
                    "parent module" : {
                        "name" : "RFC1213-MIB",
                        "type" : "DisplayString",
                    },
                    "ranges" : [
                    {
                        "min" : "0",
                        "max" : "22"
                    },
                    ],
                    "range" : {
                        "min" : "0",
                        "max" : "22"
                    },
                },
            },
            "access" : "readwrite",
            "description" :
                """Date and time information for the UPS.  Setting this variable
will initiate a set UPS date and time to this value.  Reading
this variable will return the UPS time and date.  This value
is not referenced to sysUpTime.  It is simply the clock value
from the UPS real time clock.
Format is as follows: MM/DD/YYYY:HH:MM:SS.""",
        }, # scalar
        "upsConfigLowOutputVoltageLimit" : {
            "nodetype" : "scalar",
            "moduleName" : "CPQPOWER-MIB",
            "oid" : "1.3.6.1.4.1.232.165.3.9.6",
            "status" : "current",
            "syntax" : {
                "type" :                 {
                    "basetype" : "Integer32",
                    "ranges" : [
                    {
                        "min" : "0",
                        "max" : "2147483647"
                    },
                    ],
                    "range" : {
                        "min" : "0",
                        "max" : "2147483647"
                    },
                },
            },
            "access" : "readonly",
            "description" :
                """The Lower limit for acceptable Output Voltage, per the UPS
specifications.""",
        }, # scalar
        "upsConfigHighOutputVoltageLimit" : {
            "nodetype" : "scalar",
            "moduleName" : "CPQPOWER-MIB",
            "oid" : "1.3.6.1.4.1.232.165.3.9.7",
            "status" : "current",
            "syntax" : {
                "type" :                 {
                    "basetype" : "Integer32",
                    "ranges" : [
                    {
                        "min" : "0",
                        "max" : "2147483647"
                    },
                    ],
                    "range" : {
                        "min" : "0",
                        "max" : "2147483647"
                    },
                },
            },
            "access" : "readonly",
            "description" :
                """The Upper limit for acceptable Output Voltage, per the UPS
specifications.""",
        }, # scalar
        "upsRecep" : {
            "nodetype" : "node",
            "moduleName" : "CPQPOWER-MIB",
            "oid" : "1.3.6.1.4.1.232.165.3.10",
        }, # node
        "upsNumReceptacles" : {
            "nodetype" : "scalar",
            "moduleName" : "CPQPOWER-MIB",
            "oid" : "1.3.6.1.4.1.232.165.3.10.1",
            "status" : "current",
            "syntax" : {
                "type" :                 {
                    "basetype" : "Integer32",
                    "ranges" : [
                    {
                        "min" : "0",
                        "max" : "64"
                    },
                    ],
                    "range" : {
                        "min" : "0",
                        "max" : "64"
                    },
                },
            },
            "access" : "readonly",
            "description" :
                """The number of independently controllable Receptacles, as described in the 
UpsRecepTable.""",
        }, # scalar
        "upsRecepTable" : {
            "nodetype" : "table",
            "moduleName" : "CPQPOWER-MIB",
            "oid" : "1.3.6.1.4.1.232.165.3.10.2",
            "status" : "current",
            "description" :
                """The Aggregate Object with number of entries equal to
NumReceptacles and including the UpsRecep group.""",
        }, # table
        "upsRecepEntry" : {
            "nodetype" : "row",
            "moduleName" : "CPQPOWER-MIB",
            "oid" : "1.3.6.1.4.1.232.165.3.10.2.1",
            "status" : "current",
            "linkage" : [
                "upsRecepIndex",
            ],
            "description" :
                """The Recep table entry, etc.""",
        }, # row
        "upsRecepIndex" : {
            "nodetype" : "column",
            "moduleName" : "CPQPOWER-MIB",
            "oid" : "1.3.6.1.4.1.232.165.3.10.2.1.1",
            "status" : "current",
            "syntax" : {
                "type" :                 {
                    "basetype" : "Integer32",
                    "ranges" : [
                    {
                        "min" : "1",
                        "max" : "64"
                    },
                    ],
                    "range" : {
                        "min" : "1",
                        "max" : "64"
                    },
                },
            },
            "access" : "readonly",
            "description" :
                """The number of the Receptacle. Serves as index for Receptacle table.""",
        }, # column
        "upsRecepStatus" : {
            "nodetype" : "column",
            "moduleName" : "CPQPOWER-MIB",
            "oid" : "1.3.6.1.4.1.232.165.3.10.2.1.2",
            "status" : "current",
            "syntax" : {
                "type" :                 {
                    "basetype" : "Enumeration",
                    "on" : {
                        "nodetype" : "namednumber",
                        "number" : "1"
                    },
                    "off" : {
                        "nodetype" : "namednumber",
                        "number" : "2"
                    },
                    "pendingOff" : {
                        "nodetype" : "namednumber",
                        "number" : "3"
                    },
                    "pendingOn" : {
                        "nodetype" : "namednumber",
                        "number" : "4"
                    },
                    "unknown" : {
                        "nodetype" : "namednumber",
                        "number" : "5"
                    },
                },
            },
            "access" : "readonly",
            "description" :
                """The Recep Status 1=On/Close, 2=Off/Open, 3=On w/Pending Off, 
4=Off w/Pending ON, 5=Unknown.""",
        }, # column
        "upsRecepOffDelaySecs" : {
            "nodetype" : "column",
            "moduleName" : "CPQPOWER-MIB",
            "oid" : "1.3.6.1.4.1.232.165.3.10.2.1.3",
            "status" : "current",
            "syntax" : {
                "type" :                 {
                    "basetype" : "Integer32",
                    "ranges" : [
                    {
                        "min" : "-1",
                        "max" : "2147483647"
                    },
                    ],
                    "range" : {
                        "min" : "-1",
                        "max" : "2147483647"
                    },
                },
            },
            "access" : "readwrite",
            "description" :
                """The Delay until the Receptacle is turned Off.  Setting 
this value to other than -1 will cause the UPS output to 
turn off after the number of seconds (0 is immediately).  
Setting it to -1 will cause an attempt to abort a pending shutdown.
When this object is set while the UPS is On Battery, it is not necessary
to set UpsRecepOnDelaySecs, since the outlet will turn back on 
automatically when power is available again.""",
        }, # column
        "upsRecepOnDelaySecs" : {
            "nodetype" : "column",
            "moduleName" : "CPQPOWER-MIB",
            "oid" : "1.3.6.1.4.1.232.165.3.10.2.1.4",
            "status" : "current",
            "syntax" : {
                "type" :                 {
                    "basetype" : "Integer32",
                    "ranges" : [
                    {
                        "min" : "-1",
                        "max" : "2147483647"
                    },
                    ],
                    "range" : {
                        "min" : "-1",
                        "max" : "2147483647"
                    },
                },
            },
            "access" : "readwrite",
            "description" :
                """ The Delay until the Receptacle is turned On.  Setting 
this value to other than -1 will cause the UPS output to 
turn on after the number of seconds (0 is immediately).  
Setting it to -1 will cause an attempt to abort a pending restart.""",
        }, # column
        "upsRecepAutoOffDelay" : {
            "nodetype" : "column",
            "moduleName" : "CPQPOWER-MIB",
            "oid" : "1.3.6.1.4.1.232.165.3.10.2.1.5",
            "status" : "current",
            "syntax" : {
                "type" :                 {
                    "basetype" : "Integer32",
                    "ranges" : [
                    {
                        "min" : "-1",
                        "max" : "32767"
                    },
                    ],
                    "range" : {
                        "min" : "-1",
                        "max" : "32767"
                    },
                },
            },
            "access" : "readwrite",
            "description" :
                """The delay after going On Battery until the Receptacle is 
automatically turned Off.  A value of -1 means that this Output should 
never be turned Off automatically, but must be turned Off only by command.
Values from 0 to 30 are valid, but probably innappropriate.
The AutoOffDelay can be used to prioritize loads in the event of a prolonged 
power outage; less critical loads will turn off earlier to extend battery 
time for the more critical loads. If the utility power is restored before the 
AutoOff delay counts down to 0 on an outlet, that outlet will not turn Off.""",
        }, # column
        "upsRecepAutoOnDelay" : {
            "nodetype" : "column",
            "moduleName" : "CPQPOWER-MIB",
            "oid" : "1.3.6.1.4.1.232.165.3.10.2.1.6",
            "status" : "current",
            "syntax" : {
                "type" :                 {
                    "basetype" : "Integer32",
                    "ranges" : [
                    {
                        "min" : "-1",
                        "max" : "32767"
                    },
                    ],
                    "range" : {
                        "min" : "-1",
                        "max" : "32767"
                    },
                },
            },
            "access" : "readwrite",
            "description" :
                """Seconds delay after the Outlet is signaled to turn On before the Output is
Automatically turned ON. A value of -1 means that this Output should never
be turned On automatically, but only when specifically commanded to do so.
A value of 0 means that the Receptacle should come On immediately
at power-up or for an On command.""",
        }, # column
        "upsRecepShedSecsWithRestart" : {
            "nodetype" : "column",
            "moduleName" : "CPQPOWER-MIB",
            "oid" : "1.3.6.1.4.1.232.165.3.10.2.1.7",
            "status" : "current",
            "syntax" : {
                "type" :                 {
                    "basetype" : "Integer32",
                    "ranges" : [
                    {
                        "min" : "0",
                        "max" : "2147483647"
                    },
                    ],
                    "range" : {
                        "min" : "0",
                        "max" : "2147483647"
                    },
                },
            },
            "access" : "readwrite",
            "description" :
                """Setting this value will cause the UPS output to turn off 
after the set number of seconds, then restart (after a UPS-defined
'down time') when the utility is again available.  
Unlike UpsRecepOffDelaySecs, which might or might not,
this object always maps to the XCP 0x8A Load Dump & Restart command,
so the desired shutdown and restart behavior is guaranteed to happen.
Once set, this command cannot be aborted.""",
        }, # column
        "upsTopology" : {
            "nodetype" : "node",
            "moduleName" : "CPQPOWER-MIB",
            "oid" : "1.3.6.1.4.1.232.165.3.11",
        }, # node
        "upsTopologyType" : {
            "nodetype" : "scalar",
            "moduleName" : "CPQPOWER-MIB",
            "oid" : "1.3.6.1.4.1.232.165.3.11.1",
            "status" : "current",
            "syntax" : {
                "type" :                 {
                    "basetype" : "Integer32",
                    "ranges" : [
                    {
                        "min" : "0",
                        "max" : "32767"
                    },
                    ],
                    "range" : {
                        "min" : "0",
                        "max" : "32767"
                    },
                },
            },
            "access" : "readonly",
            "description" :
                """Value which denotes the type of UPS by its power topology.  Values are the
same as those described in the XCP Topology block's Overall Topology field.""",
        }, # scalar
        "upsTopoMachineCode" : {
            "nodetype" : "scalar",
            "moduleName" : "CPQPOWER-MIB",
            "oid" : "1.3.6.1.4.1.232.165.3.11.2",
            "status" : "current",
            "syntax" : {
                "type" :                 {
                    "basetype" : "Integer32",
                    "ranges" : [
                    {
                        "min" : "0",
                        "max" : "32767"
                    },
                    ],
                    "range" : {
                        "min" : "0",
                        "max" : "32767"
                    },
                },
            },
            "access" : "readonly",
            "description" :
                """ID Value which denotes the Compaq/HP model of the UPS for software.  Values 
are the same as those described in the XCP Configuration block's Machine Code 
field.""",
        }, # scalar
        "upsTopoUnitNumber" : {
            "nodetype" : "scalar",
            "moduleName" : "CPQPOWER-MIB",
            "oid" : "1.3.6.1.4.1.232.165.3.11.3",
            "status" : "current",
            "syntax" : {
                "type" :                 {
                    "basetype" : "Integer32",
                    "ranges" : [
                    {
                        "min" : "0",
                        "max" : "64"
                    },
                    ],
                    "range" : {
                        "min" : "0",
                        "max" : "64"
                    },
                },
            },
            "access" : "readonly",
            "description" :
                """Identifies which unit and what type of data is being reported.
A value of 0 means that this MIB information comes from the top-level system 
view (eg, manifold module or system bypass cabinet reporting total system 
output).  Standalone units also use a value of 0, since they are the 'full 
system' view.
A value of 1 or higher indicates the number of the module in the system
which is reporting only its own data in the HP MIB objects.""",
        }, # scalar
        "upsTopoPowerStrategy" : {
            "nodetype" : "scalar",
            "moduleName" : "CPQPOWER-MIB",
            "oid" : "1.3.6.1.4.1.232.165.3.11.4",
            "status" : "current",
            "syntax" : {
                "type" :                 {
                    "basetype" : "Enumeration",
                    "highAlert" : {
                        "nodetype" : "namednumber",
                        "number" : "1"
                    },
                    "standard" : {
                        "nodetype" : "namednumber",
                        "number" : "2"
                    },
                    "enableHighEfficiency" : {
                        "nodetype" : "namednumber",
                        "number" : "3"
                    },
                    "immediateHighEfficiency" : {
                        "nodetype" : "namednumber",
                        "number" : "4"
                    },
                },
            },
            "access" : "readwrite",
            "description" :
                """Value which denotes which Power Strategy is currently set for the UPS.
The values are:
highAlert(1) - The UPS shall optimize its operating state to maximize its 
		power-protection levels.  This mode will be held for at most 24 hours.
standard(2) - Balanced, normal power protection strategy. UPS will not enter 
		HE operating mode from this setting.
enableHighEfficiency(3) - The UPS is enabled to enter HE operating mode to 
		optimize its operating state to maximize its efficiency, when 
		conditions change to permit it (as determined by the UPS).
forceHighEfficiency(4) - If this value is permitted to be Set for this UPS,
		and if conditions permit, requires the UPS to enter High Efficiency 
		mode now, without delay (for as long as utility conditions permit).
		After successfully set to forceHighEfficiency(4), 
		UpsTopoPowerStrategy changes to value enableHighEfficiency(3).
UpsOutputSource will indicate if the UPS status is actually operating in 
High Efficiency mode.""",
        }, # scalar
        "pdr" : {
            "nodetype" : "node",
            "moduleName" : "CPQPOWER-MIB",
            "oid" : "1.3.6.1.4.1.232.165.4",
        }, # node
        "pdrIdent" : {
            "nodetype" : "node",
            "moduleName" : "CPQPOWER-MIB",
            "oid" : "1.3.6.1.4.1.232.165.4.1",
        }, # node
        "pdrName" : {
            "nodetype" : "scalar",
            "moduleName" : "CPQPOWER-MIB",
            "oid" : "1.3.6.1.4.1.232.165.4.1.1",
            "status" : "current",
            "syntax" : {
                "type" :                 {
                    "basetype" : "OctetString",
                    "parent module" : {
                        "name" : "RFC1213-MIB",
                        "type" : "DisplayString",
                    },
                    "ranges" : [
                    {
                        "min" : "0",
                        "max" : "63"
                    },
                    ],
                    "range" : {
                        "min" : "0",
                        "max" : "63"
                    },
                },
            },
            "access" : "readwrite",
            "description" :
                """The string identify the device.""",
        }, # scalar
        "pdrModel" : {
            "nodetype" : "scalar",
            "moduleName" : "CPQPOWER-MIB",
            "oid" : "1.3.6.1.4.1.232.165.4.1.2",
            "status" : "current",
            "syntax" : {
                "type" :                 {
                    "basetype" : "OctetString",
                    "parent module" : {
                        "name" : "RFC1213-MIB",
                        "type" : "DisplayString",
                    },
                    "ranges" : [
                    {
                        "min" : "0",
                        "max" : "63"
                    },
                    ],
                    "range" : {
                        "min" : "0",
                        "max" : "63"
                    },
                },
            },
            "access" : "readonly",
            "description" :
                """The Device Model.""",
        }, # scalar
        "pdrManufacturer" : {
            "nodetype" : "scalar",
            "moduleName" : "CPQPOWER-MIB",
            "oid" : "1.3.6.1.4.1.232.165.4.1.3",
            "status" : "current",
            "syntax" : {
                "type" :                 {
                    "basetype" : "OctetString",
                    "parent module" : {
                        "name" : "RFC1213-MIB",
                        "type" : "DisplayString",
                    },
                    "ranges" : [
                    {
                        "min" : "0",
                        "max" : "63"
                    },
                    ],
                    "range" : {
                        "min" : "0",
                        "max" : "63"
                    },
                },
            },
            "access" : "readonly",
            "description" :
                """The Device Manufacturer Name (e.g. Hewlett-Packard).""",
        }, # scalar
        "pdrFirmwareVersion" : {
            "nodetype" : "scalar",
            "moduleName" : "CPQPOWER-MIB",
            "oid" : "1.3.6.1.4.1.232.165.4.1.4",
            "status" : "current",
            "syntax" : {
                "type" :                 {
                    "basetype" : "OctetString",
                    "parent module" : {
                        "name" : "RFC1213-MIB",
                        "type" : "DisplayString",
                    },
                    "ranges" : [
                    {
                        "min" : "0",
                        "max" : "63"
                    },
                    ],
                    "range" : {
                        "min" : "0",
                        "max" : "63"
                    },
                },
            },
            "access" : "readonly",
            "description" :
                """The firmware revision level of the device.""",
        }, # scalar
        "pdrPartNumber" : {
            "nodetype" : "scalar",
            "moduleName" : "CPQPOWER-MIB",
            "oid" : "1.3.6.1.4.1.232.165.4.1.5",
            "status" : "current",
            "syntax" : {
                "type" :                 {
                    "basetype" : "OctetString",
                    "parent module" : {
                        "name" : "RFC1213-MIB",
                        "type" : "DisplayString",
                    },
                    "ranges" : [
                    {
                        "min" : "0",
                        "max" : "63"
                    },
                    ],
                    "range" : {
                        "min" : "0",
                        "max" : "63"
                    },
                },
            },
            "access" : "readonly",
            "description" :
                """The device part number.""",
        }, # scalar
        "pdrSerialNumber" : {
            "nodetype" : "scalar",
            "moduleName" : "CPQPOWER-MIB",
            "oid" : "1.3.6.1.4.1.232.165.4.1.6",
            "status" : "current",
            "syntax" : {
                "type" :                 {
                    "basetype" : "OctetString",
                    "parent module" : {
                        "name" : "RFC1213-MIB",
                        "type" : "DisplayString",
                    },
                    "ranges" : [
                    {
                        "min" : "0",
                        "max" : "63"
                    },
                    ],
                    "range" : {
                        "min" : "0",
                        "max" : "63"
                    },
                },
            },
            "access" : "readonly",
            "description" :
                """The PDR's serial number.""",
        }, # scalar
        "pdrVARating" : {
            "nodetype" : "scalar",
            "moduleName" : "CPQPOWER-MIB",
            "oid" : "1.3.6.1.4.1.232.165.4.1.7",
            "status" : "current",
            "syntax" : {
                "type" :                 {
                    "basetype" : "Integer32",
                    "ranges" : [
                    {
                        "min" : "0",
                        "max" : "2147483647"
                    },
                    ],
                    "range" : {
                        "min" : "0",
                        "max" : "2147483647"
                    },
                },
            },
            "access" : "readonly",
            "description" :
                """The VA Rating of this PDR (all phases)""",
        }, # scalar
        "pdrNominalOutputVoltage" : {
            "nodetype" : "scalar",
            "moduleName" : "CPQPOWER-MIB",
            "oid" : "1.3.6.1.4.1.232.165.4.1.8",
            "status" : "current",
            "syntax" : {
                "type" :                 {
                    "basetype" : "Integer32",
                    "ranges" : [
                    {
                        "min" : "0",
                        "max" : "2147483647"
                    },
                    ],
                    "range" : {
                        "min" : "0",
                        "max" : "2147483647"
                    },
                },
            },
            "access" : "readonly",
            "description" :
                """The nominal Output Voltage may differ from the nominal 
Input Voltage if the PDR has an input transformer""",
        }, # scalar
        "pdrNumPhases" : {
            "nodetype" : "scalar",
            "moduleName" : "CPQPOWER-MIB",
            "oid" : "1.3.6.1.4.1.232.165.4.1.9",
            "status" : "current",
            "syntax" : {
                "type" :                 {
                    "basetype" : "Integer32",
                    "ranges" : [
                    {
                        "min" : "1",
                        "max" : "3"
                    },
                    ],
                    "range" : {
                        "min" : "1",
                        "max" : "3"
                    },
                },
            },
            "access" : "readonly",
            "description" :
                """The number of phases for this PDR""",
        }, # scalar
        "pdrNumPanels" : {
            "nodetype" : "scalar",
            "moduleName" : "CPQPOWER-MIB",
            "oid" : "1.3.6.1.4.1.232.165.4.1.10",
            "status" : "current",
            "syntax" : {
                "type" :                 {
                    "basetype" : "Integer32",
                    "ranges" : [
                    {
                        "min" : "0",
                        "max" : "100"
                    },
                    ],
                    "range" : {
                        "min" : "0",
                        "max" : "100"
                    },
                },
            },
            "access" : "readonly",
            "description" :
                """The number of panels or subfeeds in this PDR""",
        }, # scalar
        "pdrNumBreakers" : {
            "nodetype" : "scalar",
            "moduleName" : "CPQPOWER-MIB",
            "oid" : "1.3.6.1.4.1.232.165.4.1.11",
            "status" : "current",
            "syntax" : {
                "type" :                 {
                    "basetype" : "Integer32",
                    "ranges" : [
                    {
                        "min" : "0",
                        "max" : "100"
                    },
                    ],
                    "range" : {
                        "min" : "0",
                        "max" : "100"
                    },
                },
            },
            "access" : "readonly",
            "description" :
                """The number of breakers in this PDR""",
        }, # scalar
        "pdrPanel" : {
            "nodetype" : "node",
            "moduleName" : "CPQPOWER-MIB",
            "oid" : "1.3.6.1.4.1.232.165.4.2",
        }, # node
        "pdrPanelTable" : {
            "nodetype" : "table",
            "moduleName" : "CPQPOWER-MIB",
            "oid" : "1.3.6.1.4.1.232.165.4.2.1",
            "status" : "current",
            "description" :
                """Aggregate Object with number of entries equal to
pdrNumPanels""",
        }, # table
        "pdrPanelEntry" : {
            "nodetype" : "row",
            "moduleName" : "CPQPOWER-MIB",
            "oid" : "1.3.6.1.4.1.232.165.4.2.1.1",
            "status" : "current",
            "linkage" : [
                "pdrPanelIndex",
            ],
            "description" :
                """The panel table entry containing all power parameters 
for each panel.""",
        }, # row
        "pdrPanelIndex" : {
            "nodetype" : "column",
            "moduleName" : "CPQPOWER-MIB",
            "oid" : "1.3.6.1.4.1.232.165.4.2.1.1.1",
            "status" : "current",
            "syntax" : {
                "type" :                 {
                    "basetype" : "Integer32",
                    "ranges" : [
                    {
                        "min" : "0",
                        "max" : "10"
                    },
                    ],
                    "range" : {
                        "min" : "0",
                        "max" : "10"
                    },
                },
            },
            "access" : "readonly",
            "description" :
                """Index for the pdrPanelEntry table.""",
        }, # column
        "pdrPanelFrequency" : {
            "nodetype" : "column",
            "moduleName" : "CPQPOWER-MIB",
            "oid" : "1.3.6.1.4.1.232.165.4.2.1.1.2",
            "status" : "current",
            "syntax" : {
                "type" :                 {
                    "basetype" : "Integer32",
                    "ranges" : [
                    {
                        "min" : "0",
                        "max" : "2147483647"
                    },
                    ],
                    "range" : {
                        "min" : "0",
                        "max" : "2147483647"
                    },
                },
            },
            "access" : "readonly",
            "description" :
                """The present frequency reading for the panel voltage.""",
        }, # column
        "pdrPanelPower" : {
            "nodetype" : "column",
            "moduleName" : "CPQPOWER-MIB",
            "oid" : "1.3.6.1.4.1.232.165.4.2.1.1.3",
            "status" : "current",
            "syntax" : {
                "type" :                 {
                    "basetype" : "Integer32",
                    "ranges" : [
                    {
                        "min" : "0",
                        "max" : "2147483647"
                    },
                    ],
                    "range" : {
                        "min" : "0",
                        "max" : "2147483647"
                    },
                },
            },
            "access" : "readonly",
            "description" :
                """The present power of the panel.""",
        }, # column
        "pdrPanelRatedCurrent" : {
            "nodetype" : "column",
            "moduleName" : "CPQPOWER-MIB",
            "oid" : "1.3.6.1.4.1.232.165.4.2.1.1.4",
            "status" : "current",
            "syntax" : {
                "type" :                 {
                    "basetype" : "Integer32",
                    "ranges" : [
                    {
                        "min" : "0",
                        "max" : "2147483647"
                    },
                    ],
                    "range" : {
                        "min" : "0",
                        "max" : "2147483647"
                    },
                },
            },
            "access" : "readonly",
            "description" :
                """The present rated current of the panel.""",
        }, # column
        "pdrPanelMonthlyKWH" : {
            "nodetype" : "column",
            "moduleName" : "CPQPOWER-MIB",
            "oid" : "1.3.6.1.4.1.232.165.4.2.1.1.5",
            "status" : "current",
            "syntax" : {
                "type" :                 {
                    "basetype" : "Integer32",
                    "ranges" : [
                    {
                        "min" : "0",
                        "max" : "2147483647"
                    },
                    ],
                    "range" : {
                        "min" : "0",
                        "max" : "2147483647"
                    },
                },
            },
            "access" : "readonly",
            "description" :
                """The accumulated KWH for this panel since the beginning of this 
calendar month or since the last reset.""",
        }, # column
        "pdrPanelYearlyKWH" : {
            "nodetype" : "column",
            "moduleName" : "CPQPOWER-MIB",
            "oid" : "1.3.6.1.4.1.232.165.4.2.1.1.6",
            "status" : "current",
            "syntax" : {
                "type" :                 {
                    "basetype" : "Integer32",
                    "ranges" : [
                    {
                        "min" : "0",
                        "max" : "2147483647"
                    },
                    ],
                    "range" : {
                        "min" : "0",
                        "max" : "2147483647"
                    },
                },
            },
            "access" : "readonly",
            "description" :
                """The accumulated KWH for this panel since the beginning of this 
calendar year or since the last reset.""",
        }, # column
        "pdrPanelTotalKWH" : {
            "nodetype" : "column",
            "moduleName" : "CPQPOWER-MIB",
            "oid" : "1.3.6.1.4.1.232.165.4.2.1.1.7",
            "status" : "current",
            "syntax" : {
                "type" :                 {
                    "basetype" : "Integer32",
                    "ranges" : [
                    {
                        "min" : "0",
                        "max" : "2147483647"
                    },
                    ],
                    "range" : {
                        "min" : "0",
                        "max" : "2147483647"
                    },
                },
            },
            "access" : "readonly",
            "description" :
                """The accumulated KWH for this panel since it was put into service 
or since the last reset.""",
        }, # column
        "pdrPanelVoltageA" : {
            "nodetype" : "column",
            "moduleName" : "CPQPOWER-MIB",
            "oid" : "1.3.6.1.4.1.232.165.4.2.1.1.8",
            "status" : "current",
            "syntax" : {
                "type" :                 {
                    "basetype" : "Integer32",
                    "ranges" : [
                    {
                        "min" : "0",
                        "max" : "2147483647"
                    },
                    ],
                    "range" : {
                        "min" : "0",
                        "max" : "2147483647"
                    },
                },
            },
            "access" : "readonly",
            "description" :
                """The measured panel output voltage.""",
        }, # column
        "pdrPanelVoltageB" : {
            "nodetype" : "column",
            "moduleName" : "CPQPOWER-MIB",
            "oid" : "1.3.6.1.4.1.232.165.4.2.1.1.9",
            "status" : "current",
            "syntax" : {
                "type" :                 {
                    "basetype" : "Integer32",
                    "ranges" : [
                    {
                        "min" : "0",
                        "max" : "2147483647"
                    },
                    ],
                    "range" : {
                        "min" : "0",
                        "max" : "2147483647"
                    },
                },
            },
            "access" : "readonly",
            "description" :
                """The measured panel output voltage.""",
        }, # column
        "pdrPanelVoltageC" : {
            "nodetype" : "column",
            "moduleName" : "CPQPOWER-MIB",
            "oid" : "1.3.6.1.4.1.232.165.4.2.1.1.10",
            "status" : "current",
            "syntax" : {
                "type" :                 {
                    "basetype" : "Integer32",
                    "ranges" : [
                    {
                        "min" : "0",
                        "max" : "2147483647"
                    },
                    ],
                    "range" : {
                        "min" : "0",
                        "max" : "2147483647"
                    },
                },
            },
            "access" : "readonly",
            "description" :
                """The measured panel output voltage.""",
        }, # column
        "pdrPanelCurrentA" : {
            "nodetype" : "column",
            "moduleName" : "CPQPOWER-MIB",
            "oid" : "1.3.6.1.4.1.232.165.4.2.1.1.11",
            "status" : "current",
            "syntax" : {
                "type" :                 {
                    "basetype" : "Integer32",
                    "ranges" : [
                    {
                        "min" : "0",
                        "max" : "2147483647"
                    },
                    ],
                    "range" : {
                        "min" : "0",
                        "max" : "2147483647"
                    },
                },
            },
            "access" : "readonly",
            "description" :
                """The measured panel output current.""",
        }, # column
        "pdrPanelCurrentB" : {
            "nodetype" : "column",
            "moduleName" : "CPQPOWER-MIB",
            "oid" : "1.3.6.1.4.1.232.165.4.2.1.1.12",
            "status" : "current",
            "syntax" : {
                "type" :                 {
                    "basetype" : "Integer32",
                    "ranges" : [
                    {
                        "min" : "0",
                        "max" : "2147483647"
                    },
                    ],
                    "range" : {
                        "min" : "0",
                        "max" : "2147483647"
                    },
                },
            },
            "access" : "readonly",
            "description" :
                """The measured panel output current.""",
        }, # column
        "pdrPanelCurrentC" : {
            "nodetype" : "column",
            "moduleName" : "CPQPOWER-MIB",
            "oid" : "1.3.6.1.4.1.232.165.4.2.1.1.13",
            "status" : "current",
            "syntax" : {
                "type" :                 {
                    "basetype" : "Integer32",
                    "ranges" : [
                    {
                        "min" : "0",
                        "max" : "2147483647"
                    },
                    ],
                    "range" : {
                        "min" : "0",
                        "max" : "2147483647"
                    },
                },
            },
            "access" : "readonly",
            "description" :
                """The measured panel output current.""",
        }, # column
        "pdrPanelLoadA" : {
            "nodetype" : "column",
            "moduleName" : "CPQPOWER-MIB",
            "oid" : "1.3.6.1.4.1.232.165.4.2.1.1.14",
            "status" : "current",
            "syntax" : {
                "type" :                 {
                    "basetype" : "Integer32",
                    "ranges" : [
                    {
                        "min" : "0",
                        "max" : "200"
                    },
                    ],
                    "range" : {
                        "min" : "0",
                        "max" : "200"
                    },
                },
            },
            "access" : "readonly",
            "description" :
                """The percentage of load is the ratio of each output 
current to the rated output current to the panel.""",
        }, # column
        "pdrPanelLoadB" : {
            "nodetype" : "column",
            "moduleName" : "CPQPOWER-MIB",
            "oid" : "1.3.6.1.4.1.232.165.4.2.1.1.15",
            "status" : "current",
            "syntax" : {
                "type" :                 {
                    "basetype" : "Integer32",
                    "ranges" : [
                    {
                        "min" : "0",
                        "max" : "200"
                    },
                    ],
                    "range" : {
                        "min" : "0",
                        "max" : "200"
                    },
                },
            },
            "access" : "readonly",
            "description" :
                """The percentage of load is the ratio of each output  
current to the rated output current to the panel.""",
        }, # column
        "pdrPanelLoadC" : {
            "nodetype" : "column",
            "moduleName" : "CPQPOWER-MIB",
            "oid" : "1.3.6.1.4.1.232.165.4.2.1.1.16",
            "status" : "current",
            "syntax" : {
                "type" :                 {
                    "basetype" : "Integer32",
                    "ranges" : [
                    {
                        "min" : "0",
                        "max" : "200"
                    },
                    ],
                    "range" : {
                        "min" : "0",
                        "max" : "200"
                    },
                },
            },
            "access" : "readonly",
            "description" :
                """The percentage of load is the ratio of each output  
current to the rated output current to the panel.""",
        }, # column
        "pdrBreaker" : {
            "nodetype" : "node",
            "moduleName" : "CPQPOWER-MIB",
            "oid" : "1.3.6.1.4.1.232.165.4.3",
        }, # node
        "pdrBreakerTable" : {
            "nodetype" : "table",
            "moduleName" : "CPQPOWER-MIB",
            "oid" : "1.3.6.1.4.1.232.165.4.3.1",
            "status" : "current",
            "description" :
                """List of breaker table entries.  The number of entries 
is given by pdrNumBreakers for this panel.""",
        }, # table
        "pdrBreakerEntry" : {
            "nodetype" : "row",
            "moduleName" : "CPQPOWER-MIB",
            "oid" : "1.3.6.1.4.1.232.165.4.3.1.1",
            "status" : "current",
            "linkage" : [
                "pdrPanelIndex",
                "pdrBreakerIndex",
            ],
            "description" :
                """An entry containing information applicable to a
particular output breaker of a particular panel.""",
        }, # row
        "pdrBreakerIndex" : {
            "nodetype" : "column",
            "moduleName" : "CPQPOWER-MIB",
            "oid" : "1.3.6.1.4.1.232.165.4.3.1.1.1",
            "status" : "current",
            "syntax" : {
                "type" :                 {
                    "basetype" : "Integer32",
                    "ranges" : [
                    {
                        "min" : "0",
                        "max" : "200"
                    },
                    ],
                    "range" : {
                        "min" : "0",
                        "max" : "200"
                    },
                },
            },
            "access" : "readonly",
            "description" :
                """The index of breakers. 42 breakers in each panel,
arranged in odd and even columns""",
        }, # column
        "pdrBreakerPanel" : {
            "nodetype" : "column",
            "moduleName" : "CPQPOWER-MIB",
            "oid" : "1.3.6.1.4.1.232.165.4.3.1.1.2",
            "status" : "current",
            "syntax" : {
                "type" : { "module" :"", "name" : "Integer32"},
            },
            "access" : "readonly",
            "description" :
                """The index of panel that these breakers are installed on.""",
        }, # column
        "pdrBreakerNumPosition" : {
            "nodetype" : "column",
            "moduleName" : "CPQPOWER-MIB",
            "oid" : "1.3.6.1.4.1.232.165.4.3.1.1.3",
            "status" : "current",
            "syntax" : {
                "type" : { "module" :"", "name" : "Integer32"},
            },
            "access" : "readonly",
            "description" :
                """The position of this breaker in the panel, 1-phase breaker
or n-m breaker for 2-phase or n-m-k breaker for 3-phase.""",
        }, # column
        "pdrBreakerNumPhases" : {
            "nodetype" : "column",
            "moduleName" : "CPQPOWER-MIB",
            "oid" : "1.3.6.1.4.1.232.165.4.3.1.1.4",
            "status" : "current",
            "syntax" : {
                "type" : { "module" :"", "name" : "Integer32"},
            },
            "access" : "readonly",
            "description" :
                """The number of phase for this particular breaker.""",
        }, # column
        "pdrBreakerNumSequence" : {
            "nodetype" : "column",
            "moduleName" : "CPQPOWER-MIB",
            "oid" : "1.3.6.1.4.1.232.165.4.3.1.1.5",
            "status" : "current",
            "syntax" : {
                "type" : { "module" :"", "name" : "Integer32"},
            },
            "access" : "readonly",
            "description" :
                """The sequence of this breaker. i.e. 1 for single phase
1,2 for 2-phase or 1,2,3 for 3-phase.""",
        }, # column
        "pdrBreakerRatedCurrent" : {
            "nodetype" : "column",
            "moduleName" : "CPQPOWER-MIB",
            "oid" : "1.3.6.1.4.1.232.165.4.3.1.1.6",
            "status" : "current",
            "syntax" : {
                "type" : { "module" :"", "name" : "Integer32"},
            },
            "access" : "readonly",
            "description" :
                """The rated current in Amps for this particular breaker.""",
        }, # column
        "pdrBreakerMonthlyKWH" : {
            "nodetype" : "column",
            "moduleName" : "CPQPOWER-MIB",
            "oid" : "1.3.6.1.4.1.232.165.4.3.1.1.7",
            "status" : "current",
            "syntax" : {
                "type" :                 {
                    "basetype" : "Integer32",
                    "ranges" : [
                    {
                        "min" : "0",
                        "max" : "2147483647"
                    },
                    ],
                    "range" : {
                        "min" : "0",
                        "max" : "2147483647"
                    },
                },
            },
            "access" : "readonly",
            "description" :
                """The accumulated KWH for this breaker since the beginning of this 
calendar month or since the last reset.""",
        }, # column
        "pdrBreakerYearlyKWH" : {
            "nodetype" : "column",
            "moduleName" : "CPQPOWER-MIB",
            "oid" : "1.3.6.1.4.1.232.165.4.3.1.1.8",
            "status" : "current",
            "syntax" : {
                "type" :                 {
                    "basetype" : "Integer32",
                    "ranges" : [
                    {
                        "min" : "0",
                        "max" : "2147483647"
                    },
                    ],
                    "range" : {
                        "min" : "0",
                        "max" : "2147483647"
                    },
                },
            },
            "access" : "readonly",
            "description" :
                """The accumulated KWH for this breaker since the beginning of this 
calendar year or since the last reset.""",
        }, # column
        "pdrBreakerTotalKWH" : {
            "nodetype" : "column",
            "moduleName" : "CPQPOWER-MIB",
            "oid" : "1.3.6.1.4.1.232.165.4.3.1.1.9",
            "status" : "current",
            "syntax" : {
                "type" :                 {
                    "basetype" : "Integer32",
                    "ranges" : [
                    {
                        "min" : "0",
                        "max" : "2147483647"
                    },
                    ],
                    "range" : {
                        "min" : "0",
                        "max" : "2147483647"
                    },
                },
            },
            "access" : "readonly",
            "description" :
                """The accumulated KWH for this breaker since it was put into service 
or since the last reset.""",
        }, # column
        "pdrBreakerCurrent" : {
            "nodetype" : "column",
            "moduleName" : "CPQPOWER-MIB",
            "oid" : "1.3.6.1.4.1.232.165.4.3.1.1.10",
            "status" : "current",
            "syntax" : {
                "type" :                 {
                    "basetype" : "Integer32",
                    "ranges" : [
                    {
                        "min" : "0",
                        "max" : "2147483647"
                    },
                    ],
                    "range" : {
                        "min" : "0",
                        "max" : "2147483647"
                    },
                },
            },
            "access" : "readonly",
            "description" :
                """The measured output current for this breaker Current.""",
        }, # column
        "pdrBreakerCurrentPercent" : {
            "nodetype" : "column",
            "moduleName" : "CPQPOWER-MIB",
            "oid" : "1.3.6.1.4.1.232.165.4.3.1.1.11",
            "status" : "current",
            "syntax" : {
                "type" :                 {
                    "basetype" : "Integer32",
                    "ranges" : [
                    {
                        "min" : "0",
                        "max" : "200"
                    },
                    ],
                    "range" : {
                        "min" : "0",
                        "max" : "200"
                    },
                },
            },
            "access" : "readonly",
            "description" :
                """The ratio of output current over rated 
current for each breaker.""",
        }, # column
        "pdrBreakerPower" : {
            "nodetype" : "column",
            "moduleName" : "CPQPOWER-MIB",
            "oid" : "1.3.6.1.4.1.232.165.4.3.1.1.12",
            "status" : "current",
            "syntax" : {
                "type" : { "module" :"", "name" : "Integer32"},
            },
            "access" : "readonly",
            "description" :
                """The power for this breaker in Watts.""",
        }, # column
        "pdrBreakerPercentWarning" : {
            "nodetype" : "column",
            "moduleName" : "CPQPOWER-MIB",
            "oid" : "1.3.6.1.4.1.232.165.4.3.1.1.13",
            "status" : "current",
            "syntax" : {
                "type" :                 {
                    "basetype" : "Integer32",
                    "ranges" : [
                    {
                        "min" : "0",
                        "max" : "200"
                    },
                    ],
                    "range" : {
                        "min" : "0",
                        "max" : "200"
                    },
                },
            },
            "access" : "readonly",
            "description" :
                """The percentage of Warning set for this breaker.""",
        }, # column
        "pdrBreakerPercentOverload" : {
            "nodetype" : "column",
            "moduleName" : "CPQPOWER-MIB",
            "oid" : "1.3.6.1.4.1.232.165.4.3.1.1.14",
            "status" : "current",
            "syntax" : {
                "type" : { "module" :"", "name" : "Integer32"},
            },
            "access" : "readonly",
            "description" :
                """The percentage of Overload set for this breaker.""",
        }, # column
        "mpdu" : {
            "nodetype" : "node",
            "moduleName" : "CPQPOWER-MIB",
            "oid" : "1.3.6.1.4.1.232.165.5",
        }, # node
        "mpduIdent" : {
            "nodetype" : "node",
            "moduleName" : "CPQPOWER-MIB",
            "oid" : "1.3.6.1.4.1.232.165.5.1",
        }, # node
        "mpduNumMPDU" : {
            "nodetype" : "scalar",
            "moduleName" : "CPQPOWER-MIB",
            "oid" : "1.3.6.1.4.1.232.165.5.1.1",
            "status" : "current",
            "syntax" : {
                "type" : { "module" :"", "name" : "Integer32"},
            },
            "access" : "readonly",
            "description" :
                """The number of Modular PDUs (Core) detected.""",
        }, # scalar
        "mpduIdentTable" : {
            "nodetype" : "table",
            "moduleName" : "CPQPOWER-MIB",
            "oid" : "1.3.6.1.4.1.232.165.5.1.2",
            "status" : "current",
            "description" :
                """Indexed by mpduNumMPDU. So aggregate objects for each entry equal to mpduNumMPDU 
before go to the next entry. i.e if 4 MPDU detected, display 4 indexes, 4 
Manufacturers, 4 Models..., start with 1.""",
        }, # table
        "mpduIdentEntry" : {
            "nodetype" : "row",
            "moduleName" : "CPQPOWER-MIB",
            "oid" : "1.3.6.1.4.1.232.165.5.1.2.1",
            "status" : "current",
            "linkage" : [
                "mpduIdentIndex",
            ],
            "description" :
                """The table entry containing the identifications of each MPDU as well 
as names of PDR panel, location of MPDU in a Data Center.""",
        }, # row
        "mpduIdentIndex" : {
            "nodetype" : "column",
            "moduleName" : "CPQPOWER-MIB",
            "oid" : "1.3.6.1.4.1.232.165.5.1.2.1.1",
            "status" : "current",
            "syntax" : {
                "type" :                 {
                    "basetype" : "Integer32",
                    "ranges" : [
                    {
                        "min" : "0",
                        "max" : "100"
                    },
                    ],
                    "range" : {
                        "min" : "0",
                        "max" : "100"
                    },
                },
            },
            "access" : "readonly",
            "description" :
                """Index for the MpduIdentEntry table. Start with 1""",
        }, # column
        "mpduManufacturer" : {
            "nodetype" : "column",
            "moduleName" : "CPQPOWER-MIB",
            "oid" : "1.3.6.1.4.1.232.165.5.1.2.1.2",
            "status" : "current",
            "syntax" : {
                "type" : { "module" :"RFC1213-MIB", "name" : "DisplayString"},
            },
            "access" : "readonly",
            "description" :
                """ The Core PDU manufacturer. StringLength=[21]""",
        }, # column
        "mpduModel" : {
            "nodetype" : "column",
            "moduleName" : "CPQPOWER-MIB",
            "oid" : "1.3.6.1.4.1.232.165.5.1.2.1.3",
            "status" : "current",
            "syntax" : {
                "type" : { "module" :"RFC1213-MIB", "name" : "DisplayString"},
            },
            "access" : "readonly",
            "description" :
                """The Core PDU model, marketing name. StringLength=[40].""",
        }, # column
        "mpduName" : {
            "nodetype" : "column",
            "moduleName" : "CPQPOWER-MIB",
            "oid" : "1.3.6.1.4.1.232.165.5.1.2.1.4",
            "status" : "current",
            "syntax" : {
                "type" : { "module" :"RFC1213-MIB", "name" : "DisplayString"},
            },
            "access" : "readonly",
            "description" :
                """The Core PDU name, descriptive name or hostname. StringLength=[16].""",
        }, # column
        "mpduFirmwareVersion" : {
            "nodetype" : "column",
            "moduleName" : "CPQPOWER-MIB",
            "oid" : "1.3.6.1.4.1.232.165.5.1.2.1.5",
            "status" : "current",
            "syntax" : {
                "type" : { "module" :"RFC1213-MIB", "name" : "DisplayString"},
            },
            "access" : "readonly",
            "description" :
                """The Core PDU firmware version(s). StringLength=[12].""",
        }, # column
        "mpduHardwareVersion" : {
            "nodetype" : "column",
            "moduleName" : "CPQPOWER-MIB",
            "oid" : "1.3.6.1.4.1.232.165.5.1.2.1.6",
            "status" : "current",
            "syntax" : {
                "type" : { "module" :"RFC1213-MIB", "name" : "DisplayString"},
            },
            "access" : "readonly",
            "description" :
                """The Core PDU hardware version. StringLength=[8].""",
        }, # column
        "mpduPartNumber" : {
            "nodetype" : "column",
            "moduleName" : "CPQPOWER-MIB",
            "oid" : "1.3.6.1.4.1.232.165.5.1.2.1.7",
            "status" : "current",
            "syntax" : {
                "type" : { "module" :"RFC1213-MIB", "name" : "DisplayString"},
            },
            "access" : "readonly",
            "description" :
                """The Core PDU part number. StringLength=[21].""",
        }, # column
        "mpduSerialNumber" : {
            "nodetype" : "column",
            "moduleName" : "CPQPOWER-MIB",
            "oid" : "1.3.6.1.4.1.232.165.5.1.2.1.8",
            "status" : "current",
            "syntax" : {
                "type" : { "module" :"RFC1213-MIB", "name" : "DisplayString"},
            },
            "access" : "readonly",
            "description" :
                """The PDU external serial number. StringLength=[21].""",
        }, # column
        "mpduUUID" : {
            "nodetype" : "column",
            "moduleName" : "CPQPOWER-MIB",
            "oid" : "1.3.6.1.4.1.232.165.5.1.2.1.9",
            "status" : "current",
            "syntax" : {
                "type" : { "module" :"RFC1213-MIB", "name" : "DisplayString"},
            },
            "access" : "readonly",
            "description" :
                """The PDU's UUID equals PN add SN then canonical conversion. StringLength=[37].""",
        }, # column
        "mpduIP" : {
            "nodetype" : "column",
            "moduleName" : "CPQPOWER-MIB",
            "oid" : "1.3.6.1.4.1.232.165.5.1.2.1.10",
            "status" : "current",
            "syntax" : {
                "type" : { "module" :"RFC1213-MIB", "name" : "DisplayString"},
            },
            "access" : "readonly",
            "description" :
                """The PDU's assigned IP. StringLength=[16].""",
        }, # column
        "mpduMACAddress" : {
            "nodetype" : "column",
            "moduleName" : "CPQPOWER-MIB",
            "oid" : "1.3.6.1.4.1.232.165.5.1.2.1.11",
            "status" : "current",
            "syntax" : {
                "type" : { "module" :"RFC1213-MIB", "name" : "DisplayString"},
            },
            "access" : "readonly",
            "description" :
                """The Core PDU MAC address. StringLength=[18].""",
        }, # column
        "mpduControlStatus" : {
            "nodetype" : "column",
            "moduleName" : "CPQPOWER-MIB",
            "oid" : "1.3.6.1.4.1.232.165.5.1.2.1.12",
            "status" : "current",
            "syntax" : {
                "type" : { "module" :"RFC1213-MIB", "name" : "DisplayString"},
            },
            "access" : "readonly",
            "description" :
                """The Core PDU Control Status: master or slave units.
StringLength=[31].""",
        }, # column
        "mpduRegion" : {
            "nodetype" : "column",
            "moduleName" : "CPQPOWER-MIB",
            "oid" : "1.3.6.1.4.1.232.165.5.1.2.1.13",
            "status" : "current",
            "syntax" : {
                "type" : { "module" :"RFC1213-MIB", "name" : "DisplayString"},
            },
            "access" : "readonly",
            "description" :
                """The PDU's Region: NA, Intl, Japan... StringLength=[7].""",
        }, # column
        "mpduType" : {
            "nodetype" : "column",
            "moduleName" : "CPQPOWER-MIB",
            "oid" : "1.3.6.1.4.1.232.165.5.1.2.1.14",
            "status" : "current",
            "syntax" : {
                "type" : { "module" :"RFC1213-MIB", "name" : "DisplayString"},
            },
            "access" : "readonly",
            "description" :
                """The PDU's Type: Delta, Wye, single, Wye+lowline.
StringLength=[24].""",
        }, # column
        "mpduPowerRating" : {
            "nodetype" : "column",
            "moduleName" : "CPQPOWER-MIB",
            "oid" : "1.3.6.1.4.1.232.165.5.1.2.1.15",
            "status" : "current",
            "syntax" : {
                "type" : { "module" :"RFC1213-MIB", "name" : "DisplayString"},
            },
            "access" : "readonly",
            "description" :
                """The PDU's Power Rating in KVA (Name Plate). Value is presented 
in 1/100 of the KVA. i.e. 1750 means 17.50 KVA""",
        }, # column
        "mpduInputRating" : {
            "nodetype" : "column",
            "moduleName" : "CPQPOWER-MIB",
            "oid" : "1.3.6.1.4.1.232.165.5.1.2.1.16",
            "status" : "current",
            "syntax" : {
                "type" : { "module" :"RFC1213-MIB", "name" : "DisplayString"},
            },
            "access" : "readonly",
            "description" :
                """The PDU's Input Current Rating in A (Name Plate)""",
        }, # column
        "mpduInputPlug" : {
            "nodetype" : "column",
            "moduleName" : "CPQPOWER-MIB",
            "oid" : "1.3.6.1.4.1.232.165.5.1.2.1.17",
            "status" : "current",
            "syntax" : {
                "type" : { "module" :"RFC1213-MIB", "name" : "DisplayString"},
            },
            "access" : "readonly",
            "description" :
                """The PDU's Input Plug: IEC60309 516P6,NEMA L15-30P...
StringLength=[16].""",
        }, # column
        "mpduNumBreakers" : {
            "nodetype" : "column",
            "moduleName" : "CPQPOWER-MIB",
            "oid" : "1.3.6.1.4.1.232.165.5.1.2.1.18",
            "status" : "current",
            "syntax" : {
                "type" : { "module" :"", "name" : "Integer32"},
            },
            "access" : "readonly",
            "description" :
                """The number of breakers used in each MPDU (6 by default).""",
        }, # column
        "mpduNumOutlet" : {
            "nodetype" : "column",
            "moduleName" : "CPQPOWER-MIB",
            "oid" : "1.3.6.1.4.1.232.165.5.1.2.1.19",
            "status" : "current",
            "syntax" : {
                "type" : { "module" :"", "name" : "Integer32"},
            },
            "access" : "readonly",
            "description" :
                """The number of outlets of each MPDU (6 by default).""",
        }, # column
        "mpduUHeight" : {
            "nodetype" : "column",
            "moduleName" : "CPQPOWER-MIB",
            "oid" : "1.3.6.1.4.1.232.165.5.1.2.1.20",
            "status" : "current",
            "syntax" : {
                "type" : { "module" :"", "name" : "Integer32"},
            },
            "access" : "readonly",
            "description" :
                """The MPDU U Height 1U or 2 U (1U by default).""",
        }, # column
        "mpduRedundantStatus" : {
            "nodetype" : "column",
            "moduleName" : "CPQPOWER-MIB",
            "oid" : "1.3.6.1.4.1.232.165.5.1.2.1.21",
            "status" : "current",
            "syntax" : {
                "type" : { "module" :"RFC1213-MIB", "name" : "DisplayString"},
            },
            "access" : "readonly",
            "description" :
                """Status of Core PDU in paired or not: Stand-alone or Redundant.
StringLength=[12].""",
        }, # column
        "mpduNumSmartExtBar" : {
            "nodetype" : "column",
            "moduleName" : "CPQPOWER-MIB",
            "oid" : "1.3.6.1.4.1.232.165.5.1.2.1.22",
            "status" : "current",
            "syntax" : {
                "type" : { "module" :"", "name" : "Integer32"},
            },
            "access" : "readonly",
            "description" :
                """total number of  detected Smart Sticks connecting to each PDU.""",
        }, # column
        "mpduPanelName" : {
            "nodetype" : "column",
            "moduleName" : "CPQPOWER-MIB",
            "oid" : "1.3.6.1.4.1.232.165.5.1.2.1.23",
            "status" : "current",
            "syntax" : {
                "type" : { "module" :"RFC1213-MIB", "name" : "DisplayString"},
            },
            "access" : "readonly",
            "description" :
                """Name of Panel that was entered by customer in GUI.
StringLength=[50].""",
        }, # column
        "mpduPanelBreakerName" : {
            "nodetype" : "column",
            "moduleName" : "CPQPOWER-MIB",
            "oid" : "1.3.6.1.4.1.232.165.5.1.2.1.24",
            "status" : "current",
            "syntax" : {
                "type" : { "module" :"RFC1213-MIB", "name" : "DisplayString"},
            },
            "access" : "readonly",
            "description" :
                """Name of breakers or Panel Position entered by customer in GUI.
StringLength=[50].""",
        }, # column
        "mpduPanelBreakerRating" : {
            "nodetype" : "column",
            "moduleName" : "CPQPOWER-MIB",
            "oid" : "1.3.6.1.4.1.232.165.5.1.2.1.25",
            "status" : "current",
            "syntax" : {
                "type" : { "module" :"RFC1213-MIB", "name" : "DisplayString"},
            },
            "access" : "readonly",
            "description" :
                """Breaker rating of the PDR Panel.""",
        }, # column
        "mpduACFeedName" : {
            "nodetype" : "column",
            "moduleName" : "CPQPOWER-MIB",
            "oid" : "1.3.6.1.4.1.232.165.5.1.2.1.26",
            "status" : "current",
            "syntax" : {
                "type" : { "module" :"RFC1213-MIB", "name" : "DisplayString"},
            },
            "access" : "readonly",
            "description" :
                """it would be A, B, Red, or White...
StringLength=[50].""",
        }, # column
        "mpduFloorName" : {
            "nodetype" : "column",
            "moduleName" : "CPQPOWER-MIB",
            "oid" : "1.3.6.1.4.1.232.165.5.1.2.1.27",
            "status" : "current",
            "syntax" : {
                "type" : { "module" :"RFC1213-MIB", "name" : "DisplayString"},
            },
            "access" : "readonly",
            "description" :
                """Name of building floor entered by customer in GUI.
StringLength=[50].""",
        }, # column
        "mpduRoomName" : {
            "nodetype" : "column",
            "moduleName" : "CPQPOWER-MIB",
            "oid" : "1.3.6.1.4.1.232.165.5.1.2.1.28",
            "status" : "current",
            "syntax" : {
                "type" : { "module" :"RFC1213-MIB", "name" : "DisplayString"},
            },
            "access" : "readonly",
            "description" :
                """Name of the room entered by customer in GUI. StringLength=[50].""",
        }, # column
        "mpduRow" : {
            "nodetype" : "column",
            "moduleName" : "CPQPOWER-MIB",
            "oid" : "1.3.6.1.4.1.232.165.5.1.2.1.29",
            "status" : "current",
            "syntax" : {
                "type" : { "module" :"RFC1213-MIB", "name" : "DisplayString"},
            },
            "access" : "readonly",
            "description" :
                """Data Center Row entered by customer in GUI.
StringLength=[11].""",
        }, # column
        "mpduRowPosition" : {
            "nodetype" : "column",
            "moduleName" : "CPQPOWER-MIB",
            "oid" : "1.3.6.1.4.1.232.165.5.1.2.1.30",
            "status" : "current",
            "syntax" : {
                "type" : { "module" :"RFC1213-MIB", "name" : "DisplayString"},
            },
            "access" : "readonly",
            "description" :
                """Position in Row entered by customer in GUI. Null will be returned 
if not detected. StringLength=[11].""",
        }, # column
        "mpduRackName" : {
            "nodetype" : "column",
            "moduleName" : "CPQPOWER-MIB",
            "oid" : "1.3.6.1.4.1.232.165.5.1.2.1.31",
            "status" : "current",
            "syntax" : {
                "type" : { "module" :"RFC1213-MIB", "name" : "DisplayString"},
            },
            "access" : "readonly",
            "description" :
                """Name of the Rack entered by customer in GUI. Null will be returned 
if not detected. StringLength=[50].""",
        }, # column
        "mpduRackHeight" : {
            "nodetype" : "column",
            "moduleName" : "CPQPOWER-MIB",
            "oid" : "1.3.6.1.4.1.232.165.5.1.2.1.32",
            "status" : "current",
            "syntax" : {
                "type" : { "module" :"RFC1213-MIB", "name" : "DisplayString"},
            },
            "access" : "readonly",
            "description" :
                """Rack Type (22U, 42U, 50U...). Null will be returned if not detected.
StringLength=[3].""",
        }, # column
        "mpduRackID" : {
            "nodetype" : "column",
            "moduleName" : "CPQPOWER-MIB",
            "oid" : "1.3.6.1.4.1.232.165.5.1.2.1.33",
            "status" : "current",
            "syntax" : {
                "type" : { "module" :"RFC1213-MIB", "name" : "DisplayString"},
            },
            "access" : "readonly",
            "description" :
                """An unique ID to identify a rack, i.e. Rack SN. Null will be returned if 
not detected. StringLength=[50].""",
        }, # column
        "mpduUPosition" : {
            "nodetype" : "column",
            "moduleName" : "CPQPOWER-MIB",
            "oid" : "1.3.6.1.4.1.232.165.5.1.2.1.34",
            "status" : "current",
            "syntax" : {
                "type" : { "module" :"", "name" : "Integer32"},
            },
            "access" : "readonly",
            "description" :
                """PDU Rack bottom U Start position, core U position. Null will be returned if not detected.""",
        }, # column
        "mpduPairedPDUUUID" : {
            "nodetype" : "column",
            "moduleName" : "CPQPOWER-MIB",
            "oid" : "1.3.6.1.4.1.232.165.5.1.2.1.35",
            "status" : "current",
            "syntax" : {
                "type" : { "module" :"RFC1213-MIB", "name" : "DisplayString"},
            },
            "access" : "readonly",
            "description" :
                """UUID of the PDU paired with this one. Null will be returned if not detected.
StringLength=[50].""",
        }, # column
        "mpduPairedPDUIP" : {
            "nodetype" : "column",
            "moduleName" : "CPQPOWER-MIB",
            "oid" : "1.3.6.1.4.1.232.165.5.1.2.1.36",
            "status" : "current",
            "syntax" : {
                "type" : { "module" :"RFC1213-MIB", "name" : "DisplayString"},
            },
            "access" : "readonly",
            "description" :
                """IP address of the PDU paired with this one. Null will be returned if not detected.
StringLength=[16].""",
        }, # column
        "mpduInstalledLocation" : {
            "nodetype" : "column",
            "moduleName" : "CPQPOWER-MIB",
            "oid" : "1.3.6.1.4.1.232.165.5.1.2.1.37",
            "status" : "current",
            "syntax" : {
                "type" : { "module" :"", "name" : "Integer32"},
            },
            "access" : "readonly",
            "description" :
                """0=Left 0U side area or rack frame, 1= Right 0U side area or rack frame, 2= front RETMA rail, 
3=back RETMA rail) - spatial location. A value of -1 will be returned if not detected.""",
        }, # column
        "mpduTotalPowerWatt" : {
            "nodetype" : "column",
            "moduleName" : "CPQPOWER-MIB",
            "oid" : "1.3.6.1.4.1.232.165.5.1.2.1.38",
            "status" : "current",
            "syntax" : {
                "type" : { "module" :"", "name" : "Integer32"},
            },
            "access" : "readonly",
            "description" :
                """The total power for the whole iPDU in Watts.  A value 
of -1 will be returned if the power is unable to be calculated.""",
        }, # column
        "mpduTotalPowerVA" : {
            "nodetype" : "column",
            "moduleName" : "CPQPOWER-MIB",
            "oid" : "1.3.6.1.4.1.232.165.5.1.2.1.39",
            "status" : "current",
            "syntax" : {
                "type" : { "module" :"", "name" : "Integer32"},
            },
            "access" : "readonly",
            "description" :
                """The total power for the whole iPDU in VA.  A value 
of -1 will be returned if the power is unable to be calculated.""",
        }, # column
        "mpduTotalPercentLoad" : {
            "nodetype" : "column",
            "moduleName" : "CPQPOWER-MIB",
            "oid" : "1.3.6.1.4.1.232.165.5.1.2.1.40",
            "status" : "current",
            "syntax" : {
                "type" : { "module" :"", "name" : "Integer32"},
            },
            "access" : "readonly",
            "description" :
                """The whole iPDU's load in percent of rated capacity. Value is 
presented in 1/10 of the percentage i.e. 125 is 12.5%.  A value 
of -1 will be returned if the current is unable to be measured.""",
        }, # column
        "mpduRegionalNominalVoltage" : {
            "nodetype" : "column",
            "moduleName" : "CPQPOWER-MIB",
            "oid" : "1.3.6.1.4.1.232.165.5.1.2.1.41",
            "status" : "current",
            "syntax" : {
                "type" : { "module" :"RFC1213-MIB", "name" : "DisplayString"},
            },
            "access" : "readonly",
            "description" :
                """value is either America(208V), Japan(202V) or blank for International Model""",
        }, # column
        "mpduOutput" : {
            "nodetype" : "node",
            "moduleName" : "CPQPOWER-MIB",
            "oid" : "1.3.6.1.4.1.232.165.5.2",
        }, # node
        "mpduOutputTable" : {
            "nodetype" : "table",
            "moduleName" : "CPQPOWER-MIB",
            "oid" : "1.3.6.1.4.1.232.165.5.2.1",
            "status" : "current",
            "description" :
                """Indexed by mpduNumOutlet. So aggregate objects for each entry equal to (mpduNumMPDU 
multiplies mpduNumOutlet) before go to the next entry. i.e if 4 MPDU detected, 
display 6x4 indexes, 6x4 OutputStatus, 6x4 OutputBreakerRating...start with 1.""",
        }, # table
        "mpduOutputEntry" : {
            "nodetype" : "row",
            "moduleName" : "CPQPOWER-MIB",
            "oid" : "1.3.6.1.4.1.232.165.5.2.1.1",
            "status" : "current",
            "linkage" : [
                "mpduIdentIndex",
                "mpduOutputIndex",
            ],
            "description" :
                """The output table entry containing the voltage, current, PF,
percent load, VA, Watts for the Modular PDU.""",
        }, # row
        "mpduOutputIndex" : {
            "nodetype" : "column",
            "moduleName" : "CPQPOWER-MIB",
            "oid" : "1.3.6.1.4.1.232.165.5.2.1.1.1",
            "status" : "current",
            "syntax" : {
                "type" :                 {
                    "basetype" : "Integer32",
                    "ranges" : [
                    {
                        "min" : "0",
                        "max" : "100"
                    },
                    ],
                    "range" : {
                        "min" : "0",
                        "max" : "100"
                    },
                },
            },
            "access" : "readonly",
            "description" :
                """Index for the MpduOutputEntry table.""",
        }, # column
        "mpduOutputStatus" : {
            "nodetype" : "column",
            "moduleName" : "CPQPOWER-MIB",
            "oid" : "1.3.6.1.4.1.232.165.5.2.1.1.2",
            "status" : "current",
            "syntax" : {
                "type" : { "module" :"RFC1213-MIB", "name" : "DisplayString"},
            },
            "access" : "readonly",
            "description" :
                """The overall status of the device: off, on, problem. StringLength=[7].""",
        }, # column
        "mpduOutputBreakerRating" : {
            "nodetype" : "column",
            "moduleName" : "CPQPOWER-MIB",
            "oid" : "1.3.6.1.4.1.232.165.5.2.1.1.3",
            "status" : "current",
            "syntax" : {
                "type" : { "module" :"", "name" : "Integer32"},
            },
            "access" : "readonly",
            "description" :
                """The rating of each MPDU Output in Ampere.""",
        }, # column
        "mpduOutputSmartDevice" : {
            "nodetype" : "column",
            "moduleName" : "CPQPOWER-MIB",
            "oid" : "1.3.6.1.4.1.232.165.5.2.1.1.4",
            "status" : "current",
            "syntax" : {
                "type" : { "module" :"RFC1213-MIB", "name" : "DisplayString"},
            },
            "access" : "readonly",
            "description" :
                """A smart cord device detected: False, True. StringLength=[5].""",
        }, # column
        "mpduOutputPercentLoad" : {
            "nodetype" : "column",
            "moduleName" : "CPQPOWER-MIB",
            "oid" : "1.3.6.1.4.1.232.165.5.2.1.1.5",
            "status" : "current",
            "syntax" : {
                "type" : { "module" :"", "name" : "Integer32"},
            },
            "access" : "readonly",
            "description" :
                """The MPDU's each output load in percent of rated capacity. Value is 
presented in 1/10 of the percentage i.e. 125 is 12.5%.  A value 
of -1 will be returned if the current is unable to be measured.""",
        }, # column
        "mpduOutputVoltage" : {
            "nodetype" : "column",
            "moduleName" : "CPQPOWER-MIB",
            "oid" : "1.3.6.1.4.1.232.165.5.2.1.1.6",
            "status" : "current",
            "syntax" : {
                "type" : { "module" :"", "name" : "Integer32"},
            },
            "access" : "readonly",
            "description" :
                """The measured output voltage from the PDU meters in volts. Value is 
presented in 1/10 of the Volt i.e. 2095 is 209.5 V.  A value 
of -1 will be returned if the voltage is unable to be measured.""",
        }, # column
        "mpduOutputCurrent" : {
            "nodetype" : "column",
            "moduleName" : "CPQPOWER-MIB",
            "oid" : "1.3.6.1.4.1.232.165.5.2.1.1.7",
            "status" : "current",
            "syntax" : {
                "type" : { "module" :"", "name" : "Integer32"},
            },
            "access" : "readonly",
            "description" :
                """The measured output current from the PDU meters in amps. Value is 
presented in 1/100 of the Ampere i.e. 175 is 1.75 A.  A value 
of -1 will be returned if the current is unable to be measured.""",
        }, # column
        "mpduOutputPowerVA" : {
            "nodetype" : "column",
            "moduleName" : "CPQPOWER-MIB",
            "oid" : "1.3.6.1.4.1.232.165.5.2.1.1.8",
            "status" : "current",
            "syntax" : {
                "type" : { "module" :"", "name" : "Integer32"},
            },
            "access" : "readonly",
            "description" :
                """The total VA load (VI) measured on the PDU in VA.  A value 
of -1 will be returned if the power is unable to be calculated.""",
        }, # column
        "mpduOutputPowerWatt" : {
            "nodetype" : "column",
            "moduleName" : "CPQPOWER-MIB",
            "oid" : "1.3.6.1.4.1.232.165.5.2.1.1.9",
            "status" : "current",
            "syntax" : {
                "type" : { "module" :"", "name" : "Integer32"},
            },
            "access" : "readonly",
            "description" :
                """The total power load measured on the PDU in Watts.  A value 
of -1 will be returned if the power is unable to be calculated.""",
        }, # column
        "mpduOutputPowerFactor" : {
            "nodetype" : "column",
            "moduleName" : "CPQPOWER-MIB",
            "oid" : "1.3.6.1.4.1.232.165.5.2.1.1.10",
            "status" : "current",
            "syntax" : {
                "type" : { "module" :"", "name" : "Integer32"},
            },
            "access" : "readonly",
            "description" :
                """The power factor is presented in 1/100 of the unit i.e.
98 is 0.98.  A value of -1 will be returned if the power factor is unable 
to be measured.""",
        }, # column
        "mpduOutputWarningThreshold" : {
            "nodetype" : "column",
            "moduleName" : "CPQPOWER-MIB",
            "oid" : "1.3.6.1.4.1.232.165.5.2.1.1.11",
            "status" : "current",
            "syntax" : {
                "type" : { "module" :"", "name" : "Integer32"},
            },
            "access" : "readonly",
            "description" :
                """Report the User-set threshhold limit for Warning in percentage""",
        }, # column
        "mpduOutputCriticalThreshold" : {
            "nodetype" : "column",
            "moduleName" : "CPQPOWER-MIB",
            "oid" : "1.3.6.1.4.1.232.165.5.2.1.1.12",
            "status" : "current",
            "syntax" : {
                "type" : { "module" :"", "name" : "Integer32"},
            },
            "access" : "readonly",
            "description" :
                """Report the User-set threshhold limit for Critical in percentage""",
        }, # column
        "mpduOutputPowerWattHour" : {
            "nodetype" : "column",
            "moduleName" : "CPQPOWER-MIB",
            "oid" : "1.3.6.1.4.1.232.165.5.2.1.1.13",
            "status" : "current",
            "syntax" : {
                "type" : { "module" :"", "name" : "Integer32"},
            },
            "access" : "readonly",
            "description" :
                """Support Billing Grade Energy Metering in Watt-Hour.  A value 
of -1 will be returned if the power is unable to be calculated.""",
        }, # column
        "mpduDeviceIdent" : {
            "nodetype" : "node",
            "moduleName" : "CPQPOWER-MIB",
            "oid" : "1.3.6.1.4.1.232.165.5.3",
        }, # node
        "mpduDeviceIdentTable" : {
            "nodetype" : "table",
            "moduleName" : "CPQPOWER-MIB",
            "oid" : "1.3.6.1.4.1.232.165.5.3.1",
            "status" : "current",
            "description" :
                """Indexed by mpduNumOutlet. So aggregate objects for each entry equal 
to (mpduNumMPDU multiplies mpduNumOutlet) before go to the next entry. 
i.e if 4 MPDU detected, display 6x4 indexes, 6x4 mpduDeviceStatus, 6x4 
DeviceUIDStatus...start with 1.""",
        }, # table
        "mpduDeviceIdentEntry" : {
            "nodetype" : "row",
            "moduleName" : "CPQPOWER-MIB",
            "oid" : "1.3.6.1.4.1.232.165.5.3.1.1",
            "status" : "current",
            "linkage" : [
                "mpduIdentIndex",
                "mpduDeviceIdentIndex",
            ],
            "description" :
                """The ident table entry containing the name, model, 
manufacturer, firmware version, part number... for
each smart device, null value for unknown device.""",
        }, # row
        "mpduDeviceIdentIndex" : {
            "nodetype" : "column",
            "moduleName" : "CPQPOWER-MIB",
            "oid" : "1.3.6.1.4.1.232.165.5.3.1.1.1",
            "status" : "current",
            "syntax" : {
                "type" :                 {
                    "basetype" : "Integer32",
                    "ranges" : [
                    {
                        "min" : "0",
                        "max" : "100"
                    },
                    ],
                    "range" : {
                        "min" : "0",
                        "max" : "100"
                    },
                },
            },
            "access" : "readonly",
            "description" :
                """Index is based on the total number of Smart Extension Bars plus
smart devices (with smart power cord i.e. blades) detected.""",
        }, # column
        "mpduDeviceStatus" : {
            "nodetype" : "column",
            "moduleName" : "CPQPOWER-MIB",
            "oid" : "1.3.6.1.4.1.232.165.5.3.1.1.2",
            "status" : "current",
            "syntax" : {
                "type" : { "module" :"RFC1213-MIB", "name" : "DisplayString"},
            },
            "access" : "readonly",
            "description" :
                """The overall status of the device: off, on, problem. StringLength=[8].""",
        }, # column
        "mpduDeviceUIDStatus" : {
            "nodetype" : "column",
            "moduleName" : "CPQPOWER-MIB",
            "oid" : "1.3.6.1.4.1.232.165.5.3.1.1.3",
            "status" : "current",
            "syntax" : {
                "type" : { "module" :"RFC1213-MIB", "name" : "DisplayString"},
            },
            "access" : "readonly",
            "description" :
                """The overall status of the device UID: off, on, blink. StringLength=[8].""",
        }, # column
        "mpduDeviceNumOutlet" : {
            "nodetype" : "column",
            "moduleName" : "CPQPOWER-MIB",
            "oid" : "1.3.6.1.4.1.232.165.5.3.1.1.4",
            "status" : "current",
            "syntax" : {
                "type" : { "module" :"", "name" : "Integer32"},
            },
            "access" : "readonly",
            "description" :
                """The number of outlets of detected the device.  This variable 
indicates the number of rows in the breakers table. Default is 5""",
        }, # column
        "mpduDeviceUHeight" : {
            "nodetype" : "column",
            "moduleName" : "CPQPOWER-MIB",
            "oid" : "1.3.6.1.4.1.232.165.5.3.1.1.5",
            "status" : "current",
            "syntax" : {
                "type" : { "module" :"", "name" : "Integer32"},
            },
            "access" : "readonly",
            "description" :
                """The Unit height of ext bar or device. Some device supports non-integer. 
Present value x100, when read back, divided by 100 to get 2 decimal points.""",
        }, # column
        "mpduDevicePowerRating" : {
            "nodetype" : "column",
            "moduleName" : "CPQPOWER-MIB",
            "oid" : "1.3.6.1.4.1.232.165.5.3.1.1.6",
            "status" : "current",
            "syntax" : {
                "type" : { "module" :"RFC1213-MIB", "name" : "DisplayString"},
            },
            "access" : "readonly",
            "description" :
                """The device's Power Rating in VA. Null will be returned if not detected.
StringLength=[8].""",
        }, # column
        "mpduDeviceManufacturer" : {
            "nodetype" : "column",
            "moduleName" : "CPQPOWER-MIB",
            "oid" : "1.3.6.1.4.1.232.165.5.3.1.1.7",
            "status" : "current",
            "syntax" : {
                "type" : { "module" :"RFC1213-MIB", "name" : "DisplayString"},
            },
            "access" : "readonly",
            "description" :
                """The Device Manufacturer Name (e.g. Hewlett-Packard).
Null will be returned if not detected. StringLength=[16].""",
        }, # column
        "mpduDeviceType" : {
            "nodetype" : "column",
            "moduleName" : "CPQPOWER-MIB",
            "oid" : "1.3.6.1.4.1.232.165.5.3.1.1.8",
            "status" : "current",
            "syntax" : {
                "type" : { "module" :"RFC1213-MIB", "name" : "DisplayString"},
            },
            "access" : "readonly",
            "description" :
                """The Device's Type: Ext Bar, server, or network device...
StringLength=[16].""",
        }, # column
        "mpduDeviceModel" : {
            "nodetype" : "column",
            "moduleName" : "CPQPOWER-MIB",
            "oid" : "1.3.6.1.4.1.232.165.5.3.1.1.9",
            "status" : "current",
            "syntax" : {
                "type" : { "module" :"RFC1213-MIB", "name" : "DisplayString"},
            },
            "access" : "readonly",
            "description" :
                """The Device Model is Managed or Non-managed Ext Bar. 
Null will be returned if not detected. StringLength=[24].""",
        }, # column
        "mpduDeviceName" : {
            "nodetype" : "column",
            "moduleName" : "CPQPOWER-MIB",
            "oid" : "1.3.6.1.4.1.232.165.5.3.1.1.10",
            "status" : "current",
            "syntax" : {
                "type" : { "module" :"RFC1213-MIB", "name" : "DisplayString"},
            },
            "access" : "readonly",
            "description" :
                """The string identify the Device. i.e. 'BAR#1' (descriptive name)
Null will be returned if not detected. StringLength=[32].""",
        }, # column
        "mpduDeviceFirmwareVersion" : {
            "nodetype" : "column",
            "moduleName" : "CPQPOWER-MIB",
            "oid" : "1.3.6.1.4.1.232.165.5.3.1.1.11",
            "status" : "current",
            "syntax" : {
                "type" : { "module" :"RFC1213-MIB", "name" : "DisplayString"},
            },
            "access" : "readonly",
            "description" :
                """The firmware revision level of Sm Ext Bar. Null will be returned if 
not detected. StringLength=[8].""",
        }, # column
        "mpduDeviceHardwareVersion" : {
            "nodetype" : "column",
            "moduleName" : "CPQPOWER-MIB",
            "oid" : "1.3.6.1.4.1.232.165.5.3.1.1.12",
            "status" : "current",
            "syntax" : {
                "type" : { "module" :"RFC1213-MIB", "name" : "DisplayString"},
            },
            "access" : "readonly",
            "description" :
                """The hardware version of Sm Ext Bar. Null will be returned if not 
detected. StringLength=[8].""",
        }, # column
        "mpduDevicePartNumber" : {
            "nodetype" : "column",
            "moduleName" : "CPQPOWER-MIB",
            "oid" : "1.3.6.1.4.1.232.165.5.3.1.1.13",
            "status" : "current",
            "syntax" : {
                "type" : { "module" :"RFC1213-MIB", "name" : "DisplayString"},
            },
            "access" : "readonly",
            "description" :
                """The device's part number. Null will be returned if not detected.
StringLength=[21].""",
        }, # column
        "mpduDeviceSerialNumber" : {
            "nodetype" : "column",
            "moduleName" : "CPQPOWER-MIB",
            "oid" : "1.3.6.1.4.1.232.165.5.3.1.1.14",
            "status" : "current",
            "syntax" : {
                "type" : { "module" :"RFC1213-MIB", "name" : "DisplayString"},
            },
            "access" : "readonly",
            "description" :
                """The device's serial number. Null will be returned if not detected.
StringLength=[21].""",
        }, # column
        "mpduDeviceUUID" : {
            "nodetype" : "column",
            "moduleName" : "CPQPOWER-MIB",
            "oid" : "1.3.6.1.4.1.232.165.5.3.1.1.15",
            "status" : "current",
            "syntax" : {
                "type" : { "module" :"RFC1213-MIB", "name" : "DisplayString"},
            },
            "access" : "readonly",
            "description" :
                """The device's UUID. Null will be returned if not detected.
StringLength=[37].""",
        }, # column
        "mpduDeviceIP" : {
            "nodetype" : "column",
            "moduleName" : "CPQPOWER-MIB",
            "oid" : "1.3.6.1.4.1.232.165.5.3.1.1.16",
            "status" : "current",
            "syntax" : {
                "type" : { "module" :"RFC1213-MIB", "name" : "DisplayString"},
            },
            "access" : "readonly",
            "description" :
                """The device's IP Address. Null will be returned if not detected.
StringLength=[16].""",
        }, # column
        "mpduDeviceMAC" : {
            "nodetype" : "column",
            "moduleName" : "CPQPOWER-MIB",
            "oid" : "1.3.6.1.4.1.232.165.5.3.1.1.17",
            "status" : "current",
            "syntax" : {
                "type" : { "module" :"RFC1213-MIB", "name" : "DisplayString"},
            },
            "access" : "readonly",
            "description" :
                """The device mgmt processor MAC Address. Null will be returned if 
not detected. StringLength=[18].""",
        }, # column
        "mpduDevicePSUSlotNo" : {
            "nodetype" : "column",
            "moduleName" : "CPQPOWER-MIB",
            "oid" : "1.3.6.1.4.1.232.165.5.3.1.1.18",
            "status" : "current",
            "syntax" : {
                "type" : { "module" :"", "name" : "Integer32"},
            },
            "access" : "readonly",
            "description" :
                """Device power supply logical slot number.""",
        }, # column
        "mpduDeviceUPosition" : {
            "nodetype" : "column",
            "moduleName" : "CPQPOWER-MIB",
            "oid" : "1.3.6.1.4.1.232.165.5.3.1.1.19",
            "status" : "current",
            "syntax" : {
                "type" : { "module" :"", "name" : "Integer32"},
            },
            "access" : "readonly",
            "description" :
                """Device U start position.""",
        }, # column
        "mpduDeviceDetectionThreshold" : {
            "nodetype" : "column",
            "moduleName" : "CPQPOWER-MIB",
            "oid" : "1.3.6.1.4.1.232.165.5.3.1.1.20",
            "status" : "current",
            "syntax" : {
                "type" : { "module" :"", "name" : "Integer32"},
            },
            "access" : "readonly",
            "description" :
                """Read device detection threshold between 10 and 50mA.""",
        }, # column
        "mpduSmExtBarOutlet" : {
            "nodetype" : "node",
            "moduleName" : "CPQPOWER-MIB",
            "oid" : "1.3.6.1.4.1.232.165.5.4",
        }, # node
        "mpduSmExtBarOutletTable" : {
            "nodetype" : "table",
            "moduleName" : "CPQPOWER-MIB",
            "oid" : "1.3.6.1.4.1.232.165.5.4.1",
            "status" : "current",
            "description" :
                """Indexed by mpduDeviceNumOutlet. So aggregate objects for each entry equal to 
(mpduNumMPDU multiplies mpduNumOutlet multiplies mpduDeviceNumOutlet) before 
go to the next entry. i.e if 4 MPDU detected, display 5x6x4 indexes, 5x6x4
mpduSmExtBarOutletStatus, 5x6x4 mpduSmExtBarOutletUIDStatus...start with 1.""",
        }, # table
        "mpduSmExtBarOutletEntry" : {
            "nodetype" : "row",
            "moduleName" : "CPQPOWER-MIB",
            "oid" : "1.3.6.1.4.1.232.165.5.4.1.1",
            "status" : "current",
            "linkage" : [
                "mpduIdentIndex",
                "mpduOutputIndex",
                "mpduSmExtBarOutletIndex",
            ],
            "description" :
                """Entries contain status, measurements for each outlet (no PowerVA)
Display null if it can't be measured or no device detected.""",
        }, # row
        "mpduSmExtBarOutletIndex" : {
            "nodetype" : "column",
            "moduleName" : "CPQPOWER-MIB",
            "oid" : "1.3.6.1.4.1.232.165.5.4.1.1.1",
            "status" : "current",
            "syntax" : {
                "type" :                 {
                    "basetype" : "Integer32",
                    "ranges" : [
                    {
                        "min" : "0",
                        "max" : "100"
                    },
                    ],
                    "range" : {
                        "min" : "0",
                        "max" : "100"
                    },
                },
            },
            "access" : "readonly",
            "description" :
                """The Index of Smart Extension Bar.""",
        }, # column
        "mpduSmExtBarOutletStatus" : {
            "nodetype" : "column",
            "moduleName" : "CPQPOWER-MIB",
            "oid" : "1.3.6.1.4.1.232.165.5.4.1.1.2",
            "status" : "current",
            "syntax" : {
                "type" : { "module" :"RFC1213-MIB", "name" : "DisplayString"},
            },
            "access" : "readonly",
            "description" :
                """The overall status of the Smart Extension Bar's outlet: off, on, problem...
StringLength=[3].""",
        }, # column
        "mpduSmExtBarOutletUIDStatus" : {
            "nodetype" : "column",
            "moduleName" : "CPQPOWER-MIB",
            "oid" : "1.3.6.1.4.1.232.165.5.4.1.1.3",
            "status" : "current",
            "syntax" : {
                "type" : { "module" :"RFC1213-MIB", "name" : "DisplayString"},
            },
            "access" : "readonly",
            "description" :
                """The overall status of the Smart Extension Bar's UID: off, on, blink...
StringLength=[8].""",
        }, # column
        "mpduSmExtBarOutletRating" : {
            "nodetype" : "column",
            "moduleName" : "CPQPOWER-MIB",
            "oid" : "1.3.6.1.4.1.232.165.5.4.1.1.4",
            "status" : "current",
            "syntax" : {
                "type" : { "module" :"", "name" : "Integer32"},
            },
            "access" : "readonly",
            "description" :
                """Sm Ext Bar Outlet's Rating in Amp.  A value of -1 will be returned 
if the stick is unable to detect. StringLength=[8].""",
        }, # column
        "mpduSmExtBarOutletVoltage" : {
            "nodetype" : "column",
            "moduleName" : "CPQPOWER-MIB",
            "oid" : "1.3.6.1.4.1.232.165.5.4.1.1.5",
            "status" : "current",
            "syntax" : {
                "type" : { "module" :"", "name" : "Integer32"},
            },
            "access" : "readonly",
            "description" :
                """The SM Ext Bar voltage in volts. Value is presented 1/10 of the Volt 
i.e. 2098 means 209.8 V.  A value of -1 will be returned if the voltage is unable 
to be measured.""",
        }, # column
        "mpduSmExtBarOutletCurrent" : {
            "nodetype" : "column",
            "moduleName" : "CPQPOWER-MIB",
            "oid" : "1.3.6.1.4.1.232.165.5.4.1.1.6",
            "status" : "current",
            "syntax" : {
                "type" : { "module" :"", "name" : "Integer32"},
            },
            "access" : "readonly",
            "description" :
                """The SM Ext Bar current draw in Amps. Value is presented in 1/100 of the Ampere
i.e. 127 means 1.27 A.  A value of -1 will be returned if the current is unable 
 to be measured.""",
        }, # column
        "mpduSmExtBarOutletPowerWatt" : {
            "nodetype" : "column",
            "moduleName" : "CPQPOWER-MIB",
            "oid" : "1.3.6.1.4.1.232.165.5.4.1.1.7",
            "status" : "current",
            "syntax" : {
                "type" : { "module" :"", "name" : "Integer32"},
            },
            "access" : "readonly",
            "description" :
                """The Sm Ext Bar's Power measured in Watts. A value of -1 will be returned if the 
power is unable to be measured.""",
        }, # column
        "mpduSmExtBarOutletPowerFactor" : {
            "nodetype" : "column",
            "moduleName" : "CPQPOWER-MIB",
            "oid" : "1.3.6.1.4.1.232.165.5.4.1.1.8",
            "status" : "current",
            "syntax" : {
                "type" : { "module" :"", "name" : "Integer32"},
            },
            "access" : "readonly",
            "description" :
                """The outlet's power factor in 0.01 unit. It is presented in 1/100 of the unit. 
i.e. 98 means 0.98.  A value of -1 will be returned if the voltage is unable 
  to be measured.""",
        }, # column
        "mpduSmExtBarOutletDeviceName" : {
            "nodetype" : "column",
            "moduleName" : "CPQPOWER-MIB",
            "oid" : "1.3.6.1.4.1.232.165.5.4.1.1.9",
            "status" : "current",
            "syntax" : {
                "type" : { "module" :"RFC1213-MIB", "name" : "DisplayString"},
            },
            "access" : "readonly",
            "description" :
                """The Device (Blade/Server/Storage) Name that connects to this 
Sm Ext Bar Outlet. Null will be returned if not detected. StringLength=[50].""",
        }, # column
        "mpduSmExtBarOutletDeviceUUID" : {
            "nodetype" : "column",
            "moduleName" : "CPQPOWER-MIB",
            "oid" : "1.3.6.1.4.1.232.165.5.4.1.1.10",
            "status" : "current",
            "syntax" : {
                "type" : { "module" :"RFC1213-MIB", "name" : "DisplayString"},
            },
            "access" : "readonly",
            "description" :
                """The Device (Blade/Server/Storage) UUID that connects to this 
Sm Ext Bar Outlet. Null will be returned if not detected. StringLength=[37].""",
        }, # column
        "mpduSmExtBarOutletDeviceProduct" : {
            "nodetype" : "column",
            "moduleName" : "CPQPOWER-MIB",
            "oid" : "1.3.6.1.4.1.232.165.5.4.1.1.11",
            "status" : "current",
            "syntax" : {
                "type" : { "module" :"RFC1213-MIB", "name" : "DisplayString"},
            },
            "access" : "readonly",
            "description" :
                """The Device (Blade/Server/Storage) Model that connects to this 
Sm Ext Bar Outlet. Null will be returned if not detected. StringLength=[40].""",
        }, # column
        "mpduSmExtBarOutletDeviceIP" : {
            "nodetype" : "column",
            "moduleName" : "CPQPOWER-MIB",
            "oid" : "1.3.6.1.4.1.232.165.5.4.1.1.12",
            "status" : "current",
            "syntax" : {
                "type" : { "module" :"RFC1213-MIB", "name" : "DisplayString"},
            },
            "access" : "readonly",
            "description" :
                """The Device (Blade/Server/Storage) IP of iLO that connects to this 
Sm Ext Bar Outlet. Null will be returned if not detected. StringLength=[16].""",
        }, # column
        "mpduSmExtBarOutletAutoDiscovered" : {
            "nodetype" : "column",
            "moduleName" : "CPQPOWER-MIB",
            "oid" : "1.3.6.1.4.1.232.165.5.4.1.1.13",
            "status" : "current",
            "syntax" : {
                "type" : { "module" :"", "name" : "Integer32"},
            },
            "access" : "readonly",
            "description" :
                """Boolean values of 0 or 1. 1 means this Sm Ext Bar Outlet is able to get information 
from a blade with smart power supply (auto discovery is enabled)...""",
        }, # column
        "mpduSmExtBarOutletDeviceMAC" : {
            "nodetype" : "column",
            "moduleName" : "CPQPOWER-MIB",
            "oid" : "1.3.6.1.4.1.232.165.5.4.1.1.14",
            "status" : "current",
            "syntax" : {
                "type" : { "module" :"RFC1213-MIB", "name" : "DisplayString"},
            },
            "access" : "readonly",
            "description" :
                """The Device (Blade/Server/Storage) MAC address that connects to this 
Sm Ext Bar Outlet. Null will be returned if not detected. StringLength=[18].""",
        }, # column
        "mpduSmExtBarOutletDeviceSN" : {
            "nodetype" : "column",
            "moduleName" : "CPQPOWER-MIB",
            "oid" : "1.3.6.1.4.1.232.165.5.4.1.1.15",
            "status" : "current",
            "syntax" : {
                "type" : { "module" :"RFC1213-MIB", "name" : "DisplayString"},
            },
            "access" : "readonly",
            "description" :
                """The Device (Blade/Server/Storage) Serial Number that connects to this 
Sm Ext Bar Outlet. Null will be returned if not detected. StringLength=[21].""",
        }, # column
        "mpduSmExtBarOutletDevicePSSlotNo" : {
            "nodetype" : "column",
            "moduleName" : "CPQPOWER-MIB",
            "oid" : "1.3.6.1.4.1.232.165.5.4.1.1.16",
            "status" : "current",
            "syntax" : {
                "type" : { "module" :"", "name" : "Integer32"},
            },
            "access" : "readonly",
            "description" :
                """The Device (Blade/Server/Storage) Power Supply' Slot Number that connects to this 
Sm Ext Bar Outlet. A value of -1 will be returned if not detected.""",
        }, # column
        "mpduSmExtBarOutletDeviceUPosition" : {
            "nodetype" : "column",
            "moduleName" : "CPQPOWER-MIB",
            "oid" : "1.3.6.1.4.1.232.165.5.4.1.1.17",
            "status" : "current",
            "syntax" : {
                "type" : { "module" :"", "name" : "Integer32"},
            },
            "access" : "readonly",
            "description" :
                """Device U start position. A value of -1 will be returned if not detected.""",
        }, # column
        "mpduSmExtBarOutletDeviceUHeight" : {
            "nodetype" : "column",
            "moduleName" : "CPQPOWER-MIB",
            "oid" : "1.3.6.1.4.1.232.165.5.4.1.1.18",
            "status" : "current",
            "syntax" : {
                "type" : { "module" :"", "name" : "Integer32"},
            },
            "access" : "readonly",
            "description" :
                """Device U height. Enter -1 if not detected. Some device supports non-integer. 
Present value x100, when read back, divided by 100 to get 2 decimal points.""",
        }, # column
        "mpduSmExtBarOutletDeviceInstalledLocation" : {
            "nodetype" : "column",
            "moduleName" : "CPQPOWER-MIB",
            "oid" : "1.3.6.1.4.1.232.165.5.4.1.1.19",
            "status" : "current",
            "syntax" : {
                "type" : { "module" :"", "name" : "Integer32"},
            },
            "access" : "readonly",
            "description" :
                """0=Left 0U side area or rack frame, 1= Right 0U side area or rack frame, 2= front RETMA rail, 
3=back RETMA rail) - spatial location. A value of -1 will be returned if not detected.""",
        }, # column
        "mpduSmExtBarOutletPowerWattHour" : {
            "nodetype" : "column",
            "moduleName" : "CPQPOWER-MIB",
            "oid" : "1.3.6.1.4.1.232.165.5.4.1.1.20",
            "status" : "current",
            "syntax" : {
                "type" : { "module" :"", "name" : "Integer32"},
            },
            "access" : "readonly",
            "description" :
                """The Sm Ext Bar's Power measured in Watt-Hour support Billing Grade Energy Metering. 
A value of -1 will be returned if the power is unable to be measured.""",
        }, # column
        "oups" : {
            "nodetype" : "node",
            "moduleName" : "CPQPOWER-MIB",
            "oid" : "1.3.6.1.4.1.232.165.6",
        }, # node
        "oupsIdent" : {
            "nodetype" : "node",
            "moduleName" : "CPQPOWER-MIB",
            "oid" : "1.3.6.1.4.1.232.165.6.1",
        }, # node
        "oupsIdentManufacturer" : {
            "nodetype" : "scalar",
            "moduleName" : "CPQPOWER-MIB",
            "oid" : "1.3.6.1.4.1.232.165.6.1.1",
            "status" : "current",
            "syntax" : {
                "type" :                 {
                    "basetype" : "OctetString",
                    "parent module" : {
                        "name" : "RFC1213-MIB",
                        "type" : "DisplayString",
                    },
                    "ranges" : [
                    {
                        "min" : "0",
                        "max" : "31"
                    },
                    ],
                    "range" : {
                        "min" : "0",
                        "max" : "31"
                    },
                },
            },
            "access" : "readonly",
            "description" :
                """The UPS Manufacturer Name (e.g. Hewlett-Packard).""",
        }, # scalar
        "oupsIdentModel" : {
            "nodetype" : "scalar",
            "moduleName" : "CPQPOWER-MIB",
            "oid" : "1.3.6.1.4.1.232.165.6.1.2",
            "status" : "current",
            "syntax" : {
                "type" :                 {
                    "basetype" : "OctetString",
                    "parent module" : {
                        "name" : "RFC1213-MIB",
                        "type" : "DisplayString",
                    },
                    "ranges" : [
                    {
                        "min" : "0",
                        "max" : "63"
                    },
                    ],
                    "range" : {
                        "min" : "0",
                        "max" : "63"
                    },
                },
            },
            "access" : "readonly",
            "description" :
                """The UPS Model such as R-1500 G3.""",
        }, # scalar
        "oupsIdentSystemFWVersion" : {
            "nodetype" : "scalar",
            "moduleName" : "CPQPOWER-MIB",
            "oid" : "1.3.6.1.4.1.232.165.6.1.3",
            "status" : "current",
            "syntax" : {
                "type" :                 {
                    "basetype" : "OctetString",
                    "parent module" : {
                        "name" : "RFC1213-MIB",
                        "type" : "DisplayString",
                    },
                    "ranges" : [
                    {
                        "min" : "0",
                        "max" : "63"
                    },
                    ],
                    "range" : {
                        "min" : "0",
                        "max" : "63"
                    },
                },
            },
            "access" : "readonly",
            "description" :
                """Display System firmware version.""",
        }, # scalar
        "oupsIdentPowerModuleFWVersion" : {
            "nodetype" : "scalar",
            "moduleName" : "CPQPOWER-MIB",
            "oid" : "1.3.6.1.4.1.232.165.6.1.4",
            "status" : "current",
            "syntax" : {
                "type" :                 {
                    "basetype" : "OctetString",
                    "parent module" : {
                        "name" : "RFC1213-MIB",
                        "type" : "DisplayString",
                    },
                    "ranges" : [
                    {
                        "min" : "0",
                        "max" : "63"
                    },
                    ],
                    "range" : {
                        "min" : "0",
                        "max" : "63"
                    },
                },
            },
            "access" : "readonly",
            "description" :
                """Display Power Module firmware version.""",
        }, # scalar
        "oupsIdentOemCode" : {
            "nodetype" : "scalar",
            "moduleName" : "CPQPOWER-MIB",
            "oid" : "1.3.6.1.4.1.232.165.6.1.5",
            "status" : "current",
            "syntax" : {
                "type" :                 {
                    "basetype" : "OctetString",
                    "parent module" : {
                        "name" : "RFC1213-MIB",
                        "type" : "DisplayString",
                    },
                    "ranges" : [
                    {
                        "min" : "0",
                        "max" : "63"
                    },
                    ],
                    "range" : {
                        "min" : "0",
                        "max" : "63"
                    },
                },
            },
            "access" : "readonly",
            "description" :
                """A binary code indicating vendor. This should be a ?0x0c? for HP""",
        }, # scalar
        "oupsIdentSerialNumber" : {
            "nodetype" : "scalar",
            "moduleName" : "CPQPOWER-MIB",
            "oid" : "1.3.6.1.4.1.232.165.6.1.6",
            "status" : "current",
            "syntax" : {
                "type" :                 {
                    "basetype" : "OctetString",
                    "parent module" : {
                        "name" : "RFC1213-MIB",
                        "type" : "DisplayString",
                    },
                    "ranges" : [
                    {
                        "min" : "0",
                        "max" : "63"
                    },
                    ],
                    "range" : {
                        "min" : "0",
                        "max" : "63"
                    },
                },
            },
            "access" : "readonly",
            "description" :
                """Get the UPS Serial Number (i.e. B00123456W).""",
        }, # scalar
        "oupsIdentPartNumber" : {
            "nodetype" : "scalar",
            "moduleName" : "CPQPOWER-MIB",
            "oid" : "1.3.6.1.4.1.232.165.6.1.7",
            "status" : "current",
            "syntax" : {
                "type" :                 {
                    "basetype" : "OctetString",
                    "parent module" : {
                        "name" : "RFC1213-MIB",
                        "type" : "DisplayString",
                    },
                    "ranges" : [
                    {
                        "min" : "0",
                        "max" : "63"
                    },
                    ],
                    "range" : {
                        "min" : "0",
                        "max" : "63"
                    },
                },
            },
            "access" : "readonly",
            "description" :
                """Get the UPS Part Number (i.e. 204451-B21).""",
        }, # scalar
        "oupsBattery" : {
            "nodetype" : "node",
            "moduleName" : "CPQPOWER-MIB",
            "oid" : "1.3.6.1.4.1.232.165.6.2",
        }, # node
        "oupsBatTimeRemaining" : {
            "nodetype" : "scalar",
            "moduleName" : "CPQPOWER-MIB",
            "oid" : "1.3.6.1.4.1.232.165.6.2.1",
            "status" : "current",
            "syntax" : {
                "type" :                 {
                    "basetype" : "Integer32",
                    "ranges" : [
                    {
                        "min" : "0",
                        "max" : "2147483647"
                    },
                    ],
                    "range" : {
                        "min" : "0",
                        "max" : "2147483647"
                    },
                },
            },
            "access" : "readonly",
            "description" :
                """Battery run time in seconds before UPS turns off due
to low battery.""",
        }, # scalar
        "oupsBatVoltage" : {
            "nodetype" : "scalar",
            "moduleName" : "CPQPOWER-MIB",
            "oid" : "1.3.6.1.4.1.232.165.6.2.2",
            "status" : "current",
            "syntax" : {
                "type" :                 {
                    "basetype" : "Integer32",
                    "ranges" : [
                    {
                        "min" : "0",
                        "max" : "2147483647"
                    },
                    ],
                    "range" : {
                        "min" : "0",
                        "max" : "2147483647"
                    },
                },
            },
            "access" : "readonly",
            "description" :
                """Read the Total Battery voltage.""",
        }, # scalar
        "oupsBatCapacity" : {
            "nodetype" : "scalar",
            "moduleName" : "CPQPOWER-MIB",
            "oid" : "1.3.6.1.4.1.232.165.6.2.3",
            "status" : "current",
            "syntax" : {
                "type" :                 {
                    "basetype" : "Integer32",
                    "ranges" : [
                    {
                        "min" : "0",
                        "max" : "100"
                    },
                    ],
                    "range" : {
                        "min" : "0",
                        "max" : "100"
                    },
                },
            },
            "access" : "readonly",
            "description" :
                """Battery percent charge.""",
        }, # scalar
        "oupsBatAbmStatus" : {
            "nodetype" : "scalar",
            "moduleName" : "CPQPOWER-MIB",
            "oid" : "1.3.6.1.4.1.232.165.6.2.4",
            "status" : "current",
            "syntax" : {
                "type" :                 {
                    "basetype" : "Enumeration",
                    "batteryCharging" : {
                        "nodetype" : "namednumber",
                        "number" : "1"
                    },
                    "batteryDischarging" : {
                        "nodetype" : "namednumber",
                        "number" : "2"
                    },
                    "batteryResting" : {
                        "nodetype" : "namednumber",
                        "number" : "3"
                    },
                    "batteryTesting" : {
                        "nodetype" : "namednumber",
                        "number" : "4"
                    },
                    "notAvailable" : {
                        "nodetype" : "namednumber",
                        "number" : "5"
                    },
                },
            },
            "access" : "readonly",
            "description" :
                """Gives the status of the Advanced Battery Management; example:
batteryResting(3) is the state when the battery is fully charged and none of 
the other actions (charging/discharging/floating) is being done.""",
        }, # scalar
        "oupsBatTestStatus" : {
            "nodetype" : "scalar",
            "moduleName" : "CPQPOWER-MIB",
            "oid" : "1.3.6.1.4.1.232.165.6.2.5",
            "status" : "current",
            "syntax" : {
                "type" :                 {
                    "basetype" : "Enumeration",
                    "unknown" : {
                        "nodetype" : "namednumber",
                        "number" : "1"
                    },
                    "passed" : {
                        "nodetype" : "namednumber",
                        "number" : "2"
                    },
                    "failed" : {
                        "nodetype" : "namednumber",
                        "number" : "3"
                    },
                    "inProgress" : {
                        "nodetype" : "namednumber",
                        "number" : "4"
                    },
                    "notSupported" : {
                        "nodetype" : "namednumber",
                        "number" : "5"
                    },
                    "inhibited" : {
                        "nodetype" : "namednumber",
                        "number" : "6"
                    },
                },
            },
            "access" : "readonly",
            "description" :
                """Battery Test Status. UPS will support schedule testing only
7, 14, 30, or 60 days. Default is 14 days.""",
        }, # scalar
        "oupsBatLatestTestDate" : {
            "nodetype" : "scalar",
            "moduleName" : "CPQPOWER-MIB",
            "oid" : "1.3.6.1.4.1.232.165.6.2.6",
            "status" : "current",
            "syntax" : {
                "type" :                 {
                    "basetype" : "OctetString",
                    "parent module" : {
                        "name" : "RFC1213-MIB",
                        "type" : "DisplayString",
                    },
                    "ranges" : [
                    {
                        "min" : "0",
                        "max" : "63"
                    },
                    ],
                    "range" : {
                        "min" : "0",
                        "max" : "63"
                    },
                },
            },
            "access" : "readonly",
            "description" :
                """Get time and date of the latest battery test.""",
        }, # scalar
        "oupsBatReplacementDateBP1" : {
            "nodetype" : "scalar",
            "moduleName" : "CPQPOWER-MIB",
            "oid" : "1.3.6.1.4.1.232.165.6.2.7",
            "status" : "current",
            "syntax" : {
                "type" :                 {
                    "basetype" : "OctetString",
                    "parent module" : {
                        "name" : "RFC1213-MIB",
                        "type" : "DisplayString",
                    },
                    "ranges" : [
                    {
                        "min" : "0",
                        "max" : "63"
                    },
                    ],
                    "range" : {
                        "min" : "0",
                        "max" : "63"
                    },
                },
            },
            "access" : "readonly",
            "description" :
                """Get the battery replacement date of BP1.""",
        }, # scalar
        "oupsBatReplacementDateBP2" : {
            "nodetype" : "scalar",
            "moduleName" : "CPQPOWER-MIB",
            "oid" : "1.3.6.1.4.1.232.165.6.2.8",
            "status" : "current",
            "syntax" : {
                "type" :                 {
                    "basetype" : "OctetString",
                    "parent module" : {
                        "name" : "RFC1213-MIB",
                        "type" : "DisplayString",
                    },
                    "ranges" : [
                    {
                        "min" : "0",
                        "max" : "63"
                    },
                    ],
                    "range" : {
                        "min" : "0",
                        "max" : "63"
                    },
                },
            },
            "access" : "readonly",
            "description" :
                """Get the battery replacement date of BP2.""",
        }, # scalar
        "oupsBatToACDelay" : {
            "nodetype" : "scalar",
            "moduleName" : "CPQPOWER-MIB",
            "oid" : "1.3.6.1.4.1.232.165.6.2.9",
            "status" : "current",
            "syntax" : {
                "type" :                 {
                    "basetype" : "Integer32",
                    "ranges" : [
                    {
                        "min" : "0",
                        "max" : "150"
                    },
                    ],
                    "range" : {
                        "min" : "0",
                        "max" : "150"
                    },
                },
            },
            "access" : "readonly",
            "description" :
                """Get delay time switching from Battery mode to AC mode in ms.
Default is 0ms, unit is increased per 100ms""",
        }, # scalar
        "oupsBatChargeDelay" : {
            "nodetype" : "scalar",
            "moduleName" : "CPQPOWER-MIB",
            "oid" : "1.3.6.1.4.1.232.165.6.2.10",
            "status" : "current",
            "syntax" : {
                "type" :                 {
                    "basetype" : "Integer32",
                    "ranges" : [
                    {
                        "min" : "0",
                        "max" : "9999"
                    },
                    ],
                    "range" : {
                        "min" : "0",
                        "max" : "9999"
                    },
                },
            },
            "access" : "readonly",
            "description" :
                """Get battery charge delay in second. Default is 0 (random)
unit is increased per 10sec.""",
        }, # scalar
        "oupsBatNumModules" : {
            "nodetype" : "scalar",
            "moduleName" : "CPQPOWER-MIB",
            "oid" : "1.3.6.1.4.1.232.165.6.2.11",
            "status" : "current",
            "syntax" : {
                "type" :                 {
                    "basetype" : "Integer32",
                    "ranges" : [
                    {
                        "min" : "0",
                        "max" : "2"
                    },
                    ],
                    "range" : {
                        "min" : "0",
                        "max" : "2"
                    },
                },
            },
            "access" : "readonly",
            "description" :
                """Number of battery modules detected by power unit.""",
        }, # scalar
        "oupsBatModel" : {
            "nodetype" : "scalar",
            "moduleName" : "CPQPOWER-MIB",
            "oid" : "1.3.6.1.4.1.232.165.6.2.12",
            "status" : "current",
            "syntax" : {
                "type" :                 {
                    "basetype" : "OctetString",
                    "parent module" : {
                        "name" : "RFC1213-MIB",
                        "type" : "DisplayString",
                    },
                    "ranges" : [
                    {
                        "min" : "0",
                        "max" : "63"
                    },
                    ],
                    "range" : {
                        "min" : "0",
                        "max" : "63"
                    },
                },
            },
            "access" : "readonly",
            "description" :
                """Report 1U, 2U, or 3U Battery Pack, both BPs must be the same model.""",
        }, # scalar
        "oupsBatChargingPowerLevelUtility" : {
            "nodetype" : "scalar",
            "moduleName" : "CPQPOWER-MIB",
            "oid" : "1.3.6.1.4.1.232.165.6.2.13",
            "status" : "current",
            "syntax" : {
                "type" :                 {
                    "basetype" : "OctetString",
                    "parent module" : {
                        "name" : "RFC1213-MIB",
                        "type" : "DisplayString",
                    },
                    "ranges" : [
                    {
                        "min" : "0",
                        "max" : "63"
                    },
                    ],
                    "range" : {
                        "min" : "0",
                        "max" : "63"
                    },
                },
            },
            "access" : "readonly",
            "description" :
                """3 charging power levels: 1100W, 555W, 190W.""",
        }, # scalar
        "oupsBatChargingPowerLevelGenerator" : {
            "nodetype" : "scalar",
            "moduleName" : "CPQPOWER-MIB",
            "oid" : "1.3.6.1.4.1.232.165.6.2.14",
            "status" : "current",
            "syntax" : {
                "type" :                 {
                    "basetype" : "OctetString",
                    "parent module" : {
                        "name" : "RFC1213-MIB",
                        "type" : "DisplayString",
                    },
                    "ranges" : [
                    {
                        "min" : "0",
                        "max" : "63"
                    },
                    ],
                    "range" : {
                        "min" : "0",
                        "max" : "63"
                    },
                },
            },
            "access" : "readonly",
            "description" :
                """4 charging power levels: 1100W, 555W, 190W, No Charge.""",
        }, # scalar
        "oupsBatSharedConfig" : {
            "nodetype" : "scalar",
            "moduleName" : "CPQPOWER-MIB",
            "oid" : "1.3.6.1.4.1.232.165.6.2.15",
            "status" : "current",
            "syntax" : {
                "type" :                 {
                    "basetype" : "OctetString",
                    "parent module" : {
                        "name" : "RFC1213-MIB",
                        "type" : "DisplayString",
                    },
                    "ranges" : [
                    {
                        "min" : "0",
                        "max" : "63"
                    },
                    ],
                    "range" : {
                        "min" : "0",
                        "max" : "63"
                    },
                },
            },
            "access" : "readonly",
            "description" :
                """expect 3 values for shared BP configuration: PU single, PU master, PU slave.""",
        }, # scalar
        "oupsBatPackFWVerBP1" : {
            "nodetype" : "scalar",
            "moduleName" : "CPQPOWER-MIB",
            "oid" : "1.3.6.1.4.1.232.165.6.2.16",
            "status" : "current",
            "syntax" : {
                "type" :                 {
                    "basetype" : "OctetString",
                    "parent module" : {
                        "name" : "RFC1213-MIB",
                        "type" : "DisplayString",
                    },
                    "ranges" : [
                    {
                        "min" : "0",
                        "max" : "63"
                    },
                    ],
                    "range" : {
                        "min" : "0",
                        "max" : "63"
                    },
                },
            },
            "access" : "readonly",
            "description" :
                """Display Battery Pack 1 FW version.""",
        }, # scalar
        "oupsBatPackFWVerBP2" : {
            "nodetype" : "scalar",
            "moduleName" : "CPQPOWER-MIB",
            "oid" : "1.3.6.1.4.1.232.165.6.2.17",
            "status" : "current",
            "syntax" : {
                "type" :                 {
                    "basetype" : "OctetString",
                    "parent module" : {
                        "name" : "RFC1213-MIB",
                        "type" : "DisplayString",
                    },
                    "ranges" : [
                    {
                        "min" : "0",
                        "max" : "63"
                    },
                    ],
                    "range" : {
                        "min" : "0",
                        "max" : "63"
                    },
                },
            },
            "access" : "readonly",
            "description" :
                """Display Battery Pack 2 FW version.""",
        }, # scalar
        "oupsInput" : {
            "nodetype" : "node",
            "moduleName" : "CPQPOWER-MIB",
            "oid" : "1.3.6.1.4.1.232.165.6.3",
        }, # node
        "oupsInputFrequency" : {
            "nodetype" : "scalar",
            "moduleName" : "CPQPOWER-MIB",
            "oid" : "1.3.6.1.4.1.232.165.6.3.1",
            "status" : "current",
            "syntax" : {
                "type" :                 {
                    "basetype" : "Integer32",
                    "ranges" : [
                    {
                        "min" : "0",
                        "max" : "2147483647"
                    },
                    ],
                    "range" : {
                        "min" : "0",
                        "max" : "2147483647"
                    },
                },
            },
            "access" : "readonly",
            "description" :
                """The utility line frequency in tenths of Hz.""",
        }, # scalar
        "oupsInputLineBads" : {
            "nodetype" : "scalar",
            "moduleName" : "CPQPOWER-MIB",
            "oid" : "1.3.6.1.4.1.232.165.6.3.2",
            "status" : "current",
            "syntax" : {
                "type" :                 {
                    "basetype" : "Integer32",
                    "ranges" : [
                    {
                        "min" : "0",
                        "max" : "6"
                    },
                    ],
                    "range" : {
                        "min" : "0",
                        "max" : "6"
                    },
                },
            },
            "access" : "readonly",
            "description" :
                """The number of times the Input was out of tolerance
in voltage or frequency.""",
        }, # scalar
        "oupsInputNumPhases" : {
            "nodetype" : "scalar",
            "moduleName" : "CPQPOWER-MIB",
            "oid" : "1.3.6.1.4.1.232.165.6.3.3",
            "status" : "current",
            "syntax" : {
                "type" :                 {
                    "basetype" : "Integer32",
                    "ranges" : [
                    {
                        "min" : "0",
                        "max" : "6"
                    },
                    ],
                    "range" : {
                        "min" : "0",
                        "max" : "6"
                    },
                },
            },
            "access" : "readonly",
        }, # scalar
        "oupsInputTable" : {
            "nodetype" : "table",
            "moduleName" : "CPQPOWER-MIB",
            "oid" : "1.3.6.1.4.1.232.165.6.3.4",
            "status" : "current",
            "description" :
                """Aggregate Object with number of entries equal to
NumPhases and including the UpsInput group.""",
        }, # table
        "oupsInputEntry" : {
            "nodetype" : "row",
            "moduleName" : "CPQPOWER-MIB",
            "oid" : "1.3.6.1.4.1.232.165.6.3.4.1",
            "status" : "current",
            "linkage" : [
                "oupsInputPhase",
            ],
            "description" :
                """The input table entry containing the current, voltage, etc.""",
        }, # row
        "oupsInputPhase" : {
            "nodetype" : "column",
            "moduleName" : "CPQPOWER-MIB",
            "oid" : "1.3.6.1.4.1.232.165.6.3.4.1.1",
            "status" : "current",
            "syntax" : {
                "type" :                 {
                    "basetype" : "Integer32",
                    "ranges" : [
                    {
                        "min" : "0",
                        "max" : "6"
                    },
                    ],
                    "range" : {
                        "min" : "0",
                        "max" : "6"
                    },
                },
            },
            "access" : "readonly",
            "description" :
                """The number of the phase. Serves as index for input table.""",
        }, # column
        "oupsInputVoltage" : {
            "nodetype" : "column",
            "moduleName" : "CPQPOWER-MIB",
            "oid" : "1.3.6.1.4.1.232.165.6.3.4.1.2",
            "status" : "current",
            "syntax" : {
                "type" :                 {
                    "basetype" : "Integer32",
                    "ranges" : [
                    {
                        "min" : "0",
                        "max" : "2147483647"
                    },
                    ],
                    "range" : {
                        "min" : "0",
                        "max" : "2147483647"
                    },
                },
            },
            "access" : "readonly",
            "description" :
                """The measured input voltage from the UPS meters in volts.""",
        }, # column
        "oupsInputCurrent" : {
            "nodetype" : "column",
            "moduleName" : "CPQPOWER-MIB",
            "oid" : "1.3.6.1.4.1.232.165.6.3.4.1.3",
            "status" : "current",
            "syntax" : {
                "type" :                 {
                    "basetype" : "Integer32",
                    "ranges" : [
                    {
                        "min" : "0",
                        "max" : "2147483647"
                    },
                    ],
                    "range" : {
                        "min" : "0",
                        "max" : "2147483647"
                    },
                },
            },
            "access" : "readonly",
            "description" :
                """The measured input current from the UPS meters in amps.""",
        }, # column
        "oupsInputWatts" : {
            "nodetype" : "column",
            "moduleName" : "CPQPOWER-MIB",
            "oid" : "1.3.6.1.4.1.232.165.6.3.4.1.4",
            "status" : "current",
            "syntax" : {
                "type" :                 {
                    "basetype" : "Integer32",
                    "ranges" : [
                    {
                        "min" : "0",
                        "max" : "2147483647"
                    },
                    ],
                    "range" : {
                        "min" : "0",
                        "max" : "2147483647"
                    },
                },
            },
            "access" : "readonly",
            "description" :
                """The measured input power in watts.""",
        }, # column
        "oupsInputPowerFactor" : {
            "nodetype" : "scalar",
            "moduleName" : "CPQPOWER-MIB",
            "oid" : "1.3.6.1.4.1.232.165.6.3.5",
            "status" : "current",
            "syntax" : {
                "type" :                 {
                    "basetype" : "Integer32",
                    "ranges" : [
                    {
                        "min" : "0",
                        "max" : "2147483647"
                    },
                    ],
                    "range" : {
                        "min" : "0",
                        "max" : "2147483647"
                    },
                },
            },
            "access" : "readonly",
            "description" :
                """The measured real Input power factor with 2 decimals.""",
        }, # scalar
        "oupsInputDBType" : {
            "nodetype" : "scalar",
            "moduleName" : "CPQPOWER-MIB",
            "oid" : "1.3.6.1.4.1.232.165.6.3.6",
            "status" : "current",
            "syntax" : {
                "type" :                 {
                    "basetype" : "OctetString",
                    "parent module" : {
                        "name" : "RFC1213-MIB",
                        "type" : "DisplayString",
                    },
                    "ranges" : [
                    {
                        "min" : "0",
                        "max" : "63"
                    },
                    ],
                    "range" : {
                        "min" : "0",
                        "max" : "63"
                    },
                },
            },
            "access" : "readonly",
            "description" :
                """Read the input Distribution Box type: 1- 480V-Y (US-5W NEMA plugs),
2- 480V-V (US-5W IEC plugs), 3- 415V-Y (EURO-5W IEC plugs),
4- 415V-Y (US/INTL-5W IEC plugs), 5- 380V-Y (China-5W hardwired).""",
        }, # scalar
        "oupsInputUpperVoltage" : {
            "nodetype" : "scalar",
            "moduleName" : "CPQPOWER-MIB",
            "oid" : "1.3.6.1.4.1.232.165.6.3.7",
            "status" : "current",
            "syntax" : {
                "type" :                 {
                    "basetype" : "Integer32",
                    "ranges" : [
                    {
                        "min" : "0",
                        "max" : "999"
                    },
                    ],
                    "range" : {
                        "min" : "0",
                        "max" : "999"
                    },
                },
            },
            "access" : "readonly",
            "description" :
                """Read the upper voltage range, 5 to 10 percent above the nominal voltage.
Factory default is 10 percent.""",
        }, # scalar
        "oupsInputLowerVoltage" : {
            "nodetype" : "scalar",
            "moduleName" : "CPQPOWER-MIB",
            "oid" : "1.3.6.1.4.1.232.165.6.3.8",
            "status" : "current",
            "syntax" : {
                "type" :                 {
                    "basetype" : "Integer32",
                    "ranges" : [
                    {
                        "min" : "0",
                        "max" : "999"
                    },
                    ],
                    "range" : {
                        "min" : "0",
                        "max" : "999"
                    },
                },
            },
            "access" : "readonly",
            "description" :
                """Read the lower voltage range, 5 to 15 percent below the nominal voltage.
Factory default is -15 percent.""",
        }, # scalar
        "oupsGeneratorDetection" : {
            "nodetype" : "scalar",
            "moduleName" : "CPQPOWER-MIB",
            "oid" : "1.3.6.1.4.1.232.165.6.3.9",
            "status" : "current",
            "syntax" : {
                "type" :                 {
                    "basetype" : "Enumeration",
                    "onGenerator" : {
                        "nodetype" : "namednumber",
                        "number" : "1"
                    },
                    "offGenerator" : {
                        "nodetype" : "namednumber",
                        "number" : "2"
                    },
                    "noAction" : {
                        "nodetype" : "namednumber",
                        "number" : "3"
                    },
                },
            },
            "access" : "readwrite",
            "description" :
                """ATS sets a value of 1 to signal UPS that a generator is started so the UPS will  
charge Battery Pack using a different setting while it's on generator (intent to 
save all power to back up for the load).""",
        }, # scalar
        "oupsInputWithGenerator" : {
            "nodetype" : "scalar",
            "moduleName" : "CPQPOWER-MIB",
            "oid" : "1.3.6.1.4.1.232.165.6.3.10",
            "status" : "current",
            "syntax" : {
                "type" :                 {
                    "basetype" : "Enumeration",
                    "woGenerator" : {
                        "nodetype" : "namednumber",
                        "number" : "1"
                    },
                    "withGenerator" : {
                        "nodetype" : "namednumber",
                        "number" : "2"
                    },
                },
            },
            "access" : "readonly",
            "description" :
                """A value of 1 when user known for sure Input has no Generator backup; a value
of 2 tells Input Source could be from either Utility or Generator.""",
        }, # scalar
        "oupsOutput" : {
            "nodetype" : "node",
            "moduleName" : "CPQPOWER-MIB",
            "oid" : "1.3.6.1.4.1.232.165.6.4",
        }, # node
        "oupsOutputLoad" : {
            "nodetype" : "scalar",
            "moduleName" : "CPQPOWER-MIB",
            "oid" : "1.3.6.1.4.1.232.165.6.4.1",
            "status" : "current",
            "syntax" : {
                "type" :                 {
                    "basetype" : "Integer32",
                    "ranges" : [
                    {
                        "min" : "0",
                        "max" : "200"
                    },
                    ],
                    "range" : {
                        "min" : "0",
                        "max" : "200"
                    },
                },
            },
            "access" : "readonly",
            "description" :
                """The total UPS output load in percentage of rated capacity.""",
        }, # scalar
        "oupsOutputFrequency" : {
            "nodetype" : "scalar",
            "moduleName" : "CPQPOWER-MIB",
            "oid" : "1.3.6.1.4.1.232.165.6.4.2",
            "status" : "current",
            "syntax" : {
                "type" :                 {
                    "basetype" : "Integer32",
                    "ranges" : [
                    {
                        "min" : "0",
                        "max" : "2147483647"
                    },
                    ],
                    "range" : {
                        "min" : "0",
                        "max" : "2147483647"
                    },
                },
            },
            "access" : "readonly",
            "description" :
                """The measured UPS output frequency in tenths of Hz.""",
        }, # scalar
        "oupsOutputNumPhases" : {
            "nodetype" : "scalar",
            "moduleName" : "CPQPOWER-MIB",
            "oid" : "1.3.6.1.4.1.232.165.6.4.3",
            "status" : "current",
            "syntax" : {
                "type" :                 {
                    "basetype" : "Integer32",
                    "ranges" : [
                    {
                        "min" : "0",
                        "max" : "6"
                    },
                    ],
                    "range" : {
                        "min" : "0",
                        "max" : "6"
                    },
                },
            },
            "access" : "readonly",
            "description" :
                """The number of metered output phases, serves as the table index.""",
        }, # scalar
        "oupsOutputTable" : {
            "nodetype" : "table",
            "moduleName" : "CPQPOWER-MIB",
            "oid" : "1.3.6.1.4.1.232.165.6.4.4",
            "status" : "current",
            "description" :
                """The Aggregate Object with number of entries equal to NumPhases
and including the UpsOutput group.""",
        }, # table
        "oupsOutputEntry" : {
            "nodetype" : "row",
            "moduleName" : "CPQPOWER-MIB",
            "oid" : "1.3.6.1.4.1.232.165.6.4.4.1",
            "status" : "current",
            "linkage" : [
                "oupsOutputPhase",
            ],
            "description" :
                """Output Table Entry containing voltage, current, etc.""",
        }, # row
        "oupsOutputPhase" : {
            "nodetype" : "column",
            "moduleName" : "CPQPOWER-MIB",
            "oid" : "1.3.6.1.4.1.232.165.6.4.4.1.1",
            "status" : "current",
            "syntax" : {
                "type" :                 {
                    "basetype" : "Integer32",
                    "ranges" : [
                    {
                        "min" : "0",
                        "max" : "6"
                    },
                    ],
                    "range" : {
                        "min" : "0",
                        "max" : "6"
                    },
                },
            },
            "access" : "readonly",
            "description" :
                """The number {1..3} of the output phase.""",
        }, # column
        "oupsOutputVoltage" : {
            "nodetype" : "column",
            "moduleName" : "CPQPOWER-MIB",
            "oid" : "1.3.6.1.4.1.232.165.6.4.4.1.2",
            "status" : "current",
            "syntax" : {
                "type" :                 {
                    "basetype" : "Integer32",
                    "ranges" : [
                    {
                        "min" : "0",
                        "max" : "2147483647"
                    },
                    ],
                    "range" : {
                        "min" : "0",
                        "max" : "2147483647"
                    },
                },
            },
            "access" : "readonly",
            "description" :
                """The measured output voltage from the UPS metering in volts.""",
        }, # column
        "oupsOutputCurrent" : {
            "nodetype" : "column",
            "moduleName" : "CPQPOWER-MIB",
            "oid" : "1.3.6.1.4.1.232.165.6.4.4.1.3",
            "status" : "current",
            "syntax" : {
                "type" :                 {
                    "basetype" : "Integer32",
                    "ranges" : [
                    {
                        "min" : "0",
                        "max" : "2147483647"
                    },
                    ],
                    "range" : {
                        "min" : "0",
                        "max" : "2147483647"
                    },
                },
            },
            "access" : "readonly",
            "description" :
                """The measured UPS output current in amps.""",
        }, # column
        "oupsOutputWatts" : {
            "nodetype" : "column",
            "moduleName" : "CPQPOWER-MIB",
            "oid" : "1.3.6.1.4.1.232.165.6.4.4.1.4",
            "status" : "current",
            "syntax" : {
                "type" :                 {
                    "basetype" : "Integer32",
                    "ranges" : [
                    {
                        "min" : "0",
                        "max" : "2147483647"
                    },
                    ],
                    "range" : {
                        "min" : "0",
                        "max" : "2147483647"
                    },
                },
            },
            "access" : "readonly",
            "description" :
                """The measured real output power in watts.""",
        }, # column
        "oupsOutputLoadPerPhase" : {
            "nodetype" : "column",
            "moduleName" : "CPQPOWER-MIB",
            "oid" : "1.3.6.1.4.1.232.165.6.4.4.1.5",
            "status" : "current",
            "syntax" : {
                "type" :                 {
                    "basetype" : "Integer32",
                    "ranges" : [
                    {
                        "min" : "0",
                        "max" : "200"
                    },
                    ],
                    "range" : {
                        "min" : "0",
                        "max" : "200"
                    },
                },
            },
            "access" : "readonly",
            "description" :
                """The UPS output load per phase in percentage of rated capacity.""",
        }, # column
        "oupsOutputPowerFactor" : {
            "nodetype" : "scalar",
            "moduleName" : "CPQPOWER-MIB",
            "oid" : "1.3.6.1.4.1.232.165.6.4.5",
            "status" : "current",
            "syntax" : {
                "type" :                 {
                    "basetype" : "Integer32",
                    "ranges" : [
                    {
                        "min" : "0",
                        "max" : "2147483647"
                    },
                    ],
                    "range" : {
                        "min" : "0",
                        "max" : "2147483647"
                    },
                },
            },
            "access" : "readonly",
            "description" :
                """The measured real output power factor with 2 decimals.""",
        }, # scalar
        "oupsOutputSource" : {
            "nodetype" : "scalar",
            "moduleName" : "CPQPOWER-MIB",
            "oid" : "1.3.6.1.4.1.232.165.6.4.6",
            "status" : "current",
            "syntax" : {
                "type" :                 {
                    "basetype" : "Enumeration",
                    "acSource" : {
                        "nodetype" : "namednumber",
                        "number" : "1"
                    },
                    "battery" : {
                        "nodetype" : "namednumber",
                        "number" : "2"
                    },
                },
            },
            "access" : "readonly",
            "description" :
                """Indicate the source that UPS operating from when providing output.""",
        }, # scalar
        "oupsMonitor" : {
            "nodetype" : "node",
            "moduleName" : "CPQPOWER-MIB",
            "oid" : "1.3.6.1.4.1.232.165.6.5",
        }, # node
        "oupsMonitorAmbientTemp" : {
            "nodetype" : "scalar",
            "moduleName" : "CPQPOWER-MIB",
            "oid" : "1.3.6.1.4.1.232.165.6.5.1",
            "status" : "current",
            "syntax" : {
                "type" :                 {
                    "basetype" : "Integer32",
                    "ranges" : [
                    {
                        "min" : "-100",
                        "max" : "200"
                    },
                    ],
                    "range" : {
                        "min" : "-100",
                        "max" : "200"
                    },
                },
            },
            "access" : "readonly",
            "description" :
                """The reading of the internal PU Ambient temperature.""",
        }, # scalar
        "oupsMonitorBypassSCRTemp" : {
            "nodetype" : "scalar",
            "moduleName" : "CPQPOWER-MIB",
            "oid" : "1.3.6.1.4.1.232.165.6.5.2",
            "status" : "current",
            "syntax" : {
                "type" :                 {
                    "basetype" : "Integer32",
                    "ranges" : [
                    {
                        "min" : "-100",
                        "max" : "200"
                    },
                    ],
                    "range" : {
                        "min" : "-100",
                        "max" : "200"
                    },
                },
            },
            "access" : "readonly",
            "description" :
                """The reading of the internal PU Bypass SCR temperature.""",
        }, # scalar
        "oupsMonitorDDTemp" : {
            "nodetype" : "scalar",
            "moduleName" : "CPQPOWER-MIB",
            "oid" : "1.3.6.1.4.1.232.165.6.5.3",
            "status" : "current",
            "syntax" : {
                "type" :                 {
                    "basetype" : "Integer32",
                    "ranges" : [
                    {
                        "min" : "-100",
                        "max" : "200"
                    },
                    ],
                    "range" : {
                        "min" : "-100",
                        "max" : "200"
                    },
                },
            },
            "access" : "readonly",
            "description" :
                """The reading of the internal PU DD temperature.""",
        }, # scalar
        "oupsMonitorInverterTemp" : {
            "nodetype" : "scalar",
            "moduleName" : "CPQPOWER-MIB",
            "oid" : "1.3.6.1.4.1.232.165.6.5.4",
            "status" : "current",
            "syntax" : {
                "type" :                 {
                    "basetype" : "Integer32",
                    "ranges" : [
                    {
                        "min" : "-100",
                        "max" : "200"
                    },
                    ],
                    "range" : {
                        "min" : "-100",
                        "max" : "200"
                    },
                },
            },
            "access" : "readonly",
            "description" :
                """The reading of the internal PU DD temperature.""",
        }, # scalar
        "oupsMonitorChargerTemp" : {
            "nodetype" : "scalar",
            "moduleName" : "CPQPOWER-MIB",
            "oid" : "1.3.6.1.4.1.232.165.6.5.5",
            "status" : "current",
            "syntax" : {
                "type" :                 {
                    "basetype" : "Integer32",
                    "ranges" : [
                    {
                        "min" : "-100",
                        "max" : "200"
                    },
                    ],
                    "range" : {
                        "min" : "-100",
                        "max" : "200"
                    },
                },
            },
            "access" : "readonly",
            "description" :
                """The reading of the internal PU Charger temperature.""",
        }, # scalar
        "oupsMonitorBP1Temp" : {
            "nodetype" : "scalar",
            "moduleName" : "CPQPOWER-MIB",
            "oid" : "1.3.6.1.4.1.232.165.6.5.6",
            "status" : "current",
            "syntax" : {
                "type" :                 {
                    "basetype" : "OctetString",
                    "parent module" : {
                        "name" : "RFC1213-MIB",
                        "type" : "DisplayString",
                    },
                    "ranges" : [
                    {
                        "min" : "0",
                        "max" : "63"
                    },
                    ],
                    "range" : {
                        "min" : "0",
                        "max" : "63"
                    },
                },
            },
            "access" : "readonly",
            "description" :
                """Display Battery Pack 1 Temeprature in F. If BP1 not connected the PU will
return 255 and displayed as -not connect-""",
        }, # scalar
        "oupsMonitorBP2Temp" : {
            "nodetype" : "scalar",
            "moduleName" : "CPQPOWER-MIB",
            "oid" : "1.3.6.1.4.1.232.165.6.5.7",
            "status" : "current",
            "syntax" : {
                "type" :                 {
                    "basetype" : "OctetString",
                    "parent module" : {
                        "name" : "RFC1213-MIB",
                        "type" : "DisplayString",
                    },
                    "ranges" : [
                    {
                        "min" : "0",
                        "max" : "63"
                    },
                    ],
                    "range" : {
                        "min" : "0",
                        "max" : "63"
                    },
                },
            },
            "access" : "readonly",
            "description" :
                """Display Battery Pack 2 Temperature in F. If BP2 not connected the PU will
return 255 and displayed as -not connect-""",
        }, # scalar
        "oupsMonitorRestartDelay" : {
            "nodetype" : "scalar",
            "moduleName" : "CPQPOWER-MIB",
            "oid" : "1.3.6.1.4.1.232.165.6.5.8",
            "status" : "current",
            "syntax" : {
                "type" :                 {
                    "basetype" : "Integer32",
                    "ranges" : [
                    {
                        "min" : "1",
                        "max" : "150"
                    },
                    ],
                    "range" : {
                        "min" : "1",
                        "max" : "150"
                    },
                },
            },
            "access" : "readonly",
            "description" :
                """The reading of the AC Turn On Delay (Restart Delay). The value can be
changed via front LCD Menu or inserted Module GUI. Default is 0ms, unit is 
increased per 100ms.""",
        }, # scalar
        "oupsMonitorACCLoadLevel" : {
            "nodetype" : "scalar",
            "moduleName" : "CPQPOWER-MIB",
            "oid" : "1.3.6.1.4.1.232.165.6.5.9",
            "status" : "current",
            "syntax" : {
                "type" :                 {
                    "basetype" : "OctetString",
                    "parent module" : {
                        "name" : "RFC1213-MIB",
                        "type" : "DisplayString",
                    },
                    "ranges" : [
                    {
                        "min" : "0",
                        "max" : "63"
                    },
                    ],
                    "range" : {
                        "min" : "0",
                        "max" : "63"
                    },
                },
            },
            "access" : "readonly",
            "description" :
                """Read the set load level that ACC would be active from 0 to this percentage. 
Default is 20 percent. Select 0 to set it as Always On""",
        }, # scalar
        "oupsMonitorOperatingMode" : {
            "nodetype" : "scalar",
            "moduleName" : "CPQPOWER-MIB",
            "oid" : "1.3.6.1.4.1.232.165.6.5.10",
            "status" : "current",
            "syntax" : {
                "type" :                 {
                    "basetype" : "OctetString",
                    "parent module" : {
                        "name" : "RFC1213-MIB",
                        "type" : "DisplayString",
                    },
                    "ranges" : [
                    {
                        "min" : "0",
                        "max" : "63"
                    },
                    ],
                    "range" : {
                        "min" : "0",
                        "max" : "63"
                    },
                },
            },
            "access" : "readonly",
            "description" :
                """Check if UPS is normal op, or on bypass, on inverter or ACC Active, """,
        }, # scalar
        "oupsMonitorOperationType" : {
            "nodetype" : "scalar",
            "moduleName" : "CPQPOWER-MIB",
            "oid" : "1.3.6.1.4.1.232.165.6.5.11",
            "status" : "current",
            "syntax" : {
                "type" :                 {
                    "basetype" : "OctetString",
                    "parent module" : {
                        "name" : "RFC1213-MIB",
                        "type" : "DisplayString",
                    },
                    "ranges" : [
                    {
                        "min" : "0",
                        "max" : "63"
                    },
                    ],
                    "range" : {
                        "min" : "0",
                        "max" : "63"
                    },
                },
            },
            "access" : "readonly",
            "description" :
                """Check if UPS is operating as an UPS or ACC (PU only, no BP).""",
        }, # scalar
        "oupsTestTrap" : {
            "nodetype" : "scalar",
            "moduleName" : "CPQPOWER-MIB",
            "oid" : "1.3.6.1.4.1.232.165.6.5.12",
            "status" : "current",
            "syntax" : {
                "type" :                 {
                    "basetype" : "Enumeration",
                    "startTestTrap" : {
                        "nodetype" : "namednumber",
                        "number" : "1"
                    },
                },
            },
            "access" : "readwrite",
            "description" :
                """Setting startTestTrap to 1 will initiate a TrapTest
is sent out from Management Module.  All other set values are invalid.""",
        }, # scalar
        "oupsOnGenDuration" : {
            "nodetype" : "scalar",
            "moduleName" : "CPQPOWER-MIB",
            "oid" : "1.3.6.1.4.1.232.165.6.5.13",
            "status" : "current",
            "syntax" : {
                "type" :                 {
                    "basetype" : "Enumeration",
                    "for30Min" : {
                        "nodetype" : "namednumber",
                        "number" : "1"
                    },
                    "for1Hr" : {
                        "nodetype" : "namednumber",
                        "number" : "2"
                    },
                    "for2Hr" : {
                        "nodetype" : "namednumber",
                        "number" : "3"
                    },
                    "for4Hr" : {
                        "nodetype" : "namednumber",
                        "number" : "4"
                    },
                },
            },
            "access" : "readwrite",
            "description" :
                """When read, show the current On-Generator Duration set by user on UPS LCD or GUI .""",
        }, # scalar
        "oupsRuntimeLimitation" : {
            "nodetype" : "scalar",
            "moduleName" : "CPQPOWER-MIB",
            "oid" : "1.3.6.1.4.1.232.165.6.5.14",
            "status" : "current",
            "syntax" : {
                "type" :                 {
                    "basetype" : "Enumeration",
                    "disable" : {
                        "nodetype" : "namednumber",
                        "number" : "1"
                    },
                    "enable" : {
                        "nodetype" : "namednumber",
                        "number" : "2"
                    },
                },
            },
            "access" : "readwrite",
            "description" :
                """show the current setting for Runtime Limitation. When enable, it can last for 70sec or 3min.""",
        }, # scalar
        "oupsRackDiscovery" : {
            "nodetype" : "node",
            "moduleName" : "CPQPOWER-MIB",
            "oid" : "1.3.6.1.4.1.232.165.6.6",
        }, # node
        "oupsRackTagVersion" : {
            "nodetype" : "scalar",
            "moduleName" : "CPQPOWER-MIB",
            "oid" : "1.3.6.1.4.1.232.165.6.6.1",
            "status" : "current",
            "syntax" : {
                "type" :                 {
                    "basetype" : "Integer32",
                    "ranges" : [
                    {
                        "min" : "0",
                        "max" : "10"
                    },
                    ],
                    "range" : {
                        "min" : "0",
                        "max" : "10"
                    },
                },
            },
            "access" : "readonly",
            "description" :
                """Get the 1-wire contact FW version from EEPROM's Tag Version. Initial tag is 01""",
        }, # scalar
        "oupsRackID" : {
            "nodetype" : "scalar",
            "moduleName" : "CPQPOWER-MIB",
            "oid" : "1.3.6.1.4.1.232.165.6.6.2",
            "status" : "current",
            "syntax" : {
                "type" :                 {
                    "basetype" : "OctetString",
                    "parent module" : {
                        "name" : "RFC1213-MIB",
                        "type" : "DisplayString",
                    },
                    "ranges" : [
                    {
                        "min" : "0",
                        "max" : "63"
                    },
                    ],
                    "range" : {
                        "min" : "0",
                        "max" : "63"
                    },
                },
            },
            "access" : "readonly",
            "description" :
                """Get 10-digit Serial Number from the Location Discovery Strip mount in the front of the rack""",
        }, # scalar
        "oupsRackPartNumber" : {
            "nodetype" : "scalar",
            "moduleName" : "CPQPOWER-MIB",
            "oid" : "1.3.6.1.4.1.232.165.6.6.3",
            "status" : "current",
            "syntax" : {
                "type" :                 {
                    "basetype" : "OctetString",
                    "parent module" : {
                        "name" : "RFC1213-MIB",
                        "type" : "DisplayString",
                    },
                    "ranges" : [
                    {
                        "min" : "0",
                        "max" : "63"
                    },
                    ],
                    "range" : {
                        "min" : "0",
                        "max" : "63"
                    },
                },
            },
            "access" : "readonly",
            "description" :
                """Get 10 or 12-digit Part Number xxxxxx-001 from the Location Discovery Strip mount in the front of the rack""",
        }, # scalar
        "oupsRackProductDescription" : {
            "nodetype" : "scalar",
            "moduleName" : "CPQPOWER-MIB",
            "oid" : "1.3.6.1.4.1.232.165.6.6.4",
            "status" : "current",
            "syntax" : {
                "type" :                 {
                    "basetype" : "OctetString",
                    "parent module" : {
                        "name" : "RFC1213-MIB",
                        "type" : "DisplayString",
                    },
                    "ranges" : [
                    {
                        "min" : "0",
                        "max" : "63"
                    },
                    ],
                    "range" : {
                        "min" : "0",
                        "max" : "63"
                    },
                },
            },
            "access" : "readonly",
            "description" :
                """Get spatial data of rack: description of the Rack Name.""",
        }, # scalar
        "oupsRackEncULocation" : {
            "nodetype" : "scalar",
            "moduleName" : "CPQPOWER-MIB",
            "oid" : "1.3.6.1.4.1.232.165.6.6.5",
            "status" : "current",
            "syntax" : {
                "type" :                 {
                    "basetype" : "OctetString",
                    "parent module" : {
                        "name" : "RFC1213-MIB",
                        "type" : "DisplayString",
                    },
                    "ranges" : [
                    {
                        "min" : "0",
                        "max" : "63"
                    },
                    ],
                    "range" : {
                        "min" : "0",
                        "max" : "63"
                    },
                },
            },
            "access" : "readonly",
            "description" :
                """Tell where the Location Discovery Strip is mounted in the rack. B for Back, F for Front, L for Left 
and R for Right.""",
        }, # scalar
        "oupsRackUHeight" : {
            "nodetype" : "scalar",
            "moduleName" : "CPQPOWER-MIB",
            "oid" : "1.3.6.1.4.1.232.165.6.6.6",
            "status" : "current",
            "syntax" : {
                "type" :                 {
                    "basetype" : "Integer32",
                    "ranges" : [
                    {
                        "min" : "0",
                        "max" : "50"
                    },
                    ],
                    "range" : {
                        "min" : "0",
                        "max" : "50"
                    },
                },
            },
            "access" : "readonly",
            "description" :
                """Get spatial data of rack: U-height of the rack can be 36U, 42U, or 47U model.""",
        }, # scalar
        "oupsRackPUUPosition" : {
            "nodetype" : "scalar",
            "moduleName" : "CPQPOWER-MIB",
            "oid" : "1.3.6.1.4.1.232.165.6.6.7",
            "status" : "current",
            "syntax" : {
                "type" :                 {
                    "basetype" : "Integer32",
                    "ranges" : [
                    {
                        "min" : "0",
                        "max" : "50"
                    },
                    ],
                    "range" : {
                        "min" : "0",
                        "max" : "50"
                    },
                },
            },
            "access" : "readonly",
            "description" :
                """Get the U-position of the PU where it is installed in the rack. The U position range is from 1-50.""",
        }, # scalar
        "oupsRackPUUHeight" : {
            "nodetype" : "scalar",
            "moduleName" : "CPQPOWER-MIB",
            "oid" : "1.3.6.1.4.1.232.165.6.6.8",
            "status" : "current",
            "syntax" : {
                "type" :                 {
                    "basetype" : "Integer32",
                    "ranges" : [
                    {
                        "min" : "0",
                        "max" : "10"
                    },
                    ],
                    "range" : {
                        "min" : "0",
                        "max" : "10"
                    },
                },
            },
            "access" : "readonly",
            "description" :
                """Get the U-Height of the Power Unit. PU height is either 1U or 2U.""",
        }, # scalar
        "oupsRackBP1UPosition" : {
            "nodetype" : "scalar",
            "moduleName" : "CPQPOWER-MIB",
            "oid" : "1.3.6.1.4.1.232.165.6.6.9",
            "status" : "current",
            "syntax" : {
                "type" :                 {
                    "basetype" : "Integer32",
                    "ranges" : [
                    {
                        "min" : "0",
                        "max" : "50"
                    },
                    ],
                    "range" : {
                        "min" : "0",
                        "max" : "50"
                    },
                },
            },
            "access" : "readonly",
            "description" :
                """Get the U-Position of the Battery Pack 1, installed right below the PU.
Range is from 1 to 50.""",
        }, # scalar
        "oupsRackBP1UHeight" : {
            "nodetype" : "scalar",
            "moduleName" : "CPQPOWER-MIB",
            "oid" : "1.3.6.1.4.1.232.165.6.6.10",
            "status" : "current",
            "syntax" : {
                "type" :                 {
                    "basetype" : "Integer32",
                    "ranges" : [
                    {
                        "min" : "0",
                        "max" : "10"
                    },
                    ],
                    "range" : {
                        "min" : "0",
                        "max" : "10"
                    },
                },
            },
            "access" : "readonly",
            "description" :
                """Get the U-Height of the BP 1. BP is either 1U, 2U, and 3U""",
        }, # scalar
        "oupsRackBP2UPosition" : {
            "nodetype" : "scalar",
            "moduleName" : "CPQPOWER-MIB",
            "oid" : "1.3.6.1.4.1.232.165.6.6.11",
            "status" : "current",
            "syntax" : {
                "type" :                 {
                    "basetype" : "Integer32",
                    "ranges" : [
                    {
                        "min" : "0",
                        "max" : "50"
                    },
                    ],
                    "range" : {
                        "min" : "0",
                        "max" : "50"
                    },
                },
            },
            "access" : "readonly",
            "description" :
                """Get the U-Position of the Battery Pack 2, installed right below the BP1.
Range is from 1 to 50.""",
        }, # scalar
        "oupsRackBP2UHeight" : {
            "nodetype" : "scalar",
            "moduleName" : "CPQPOWER-MIB",
            "oid" : "1.3.6.1.4.1.232.165.6.6.12",
            "status" : "current",
            "syntax" : {
                "type" :                 {
                    "basetype" : "Integer32",
                    "ranges" : [
                    {
                        "min" : "0",
                        "max" : "10"
                    },
                    ],
                    "range" : {
                        "min" : "0",
                        "max" : "10"
                    },
                },
            },
            "access" : "readonly",
            "description" :
                """Get the U-Height of the BP 2. BP is either 1U, 2U, and 3U""",
        }, # scalar
        "pdu2" : {
            "nodetype" : "node",
            "moduleName" : "CPQPOWER-MIB",
            "oid" : "1.3.6.1.4.1.232.165.7",
        }, # node
        "pdu2Ident" : {
            "nodetype" : "node",
            "moduleName" : "CPQPOWER-MIB",
            "oid" : "1.3.6.1.4.1.232.165.7.1",
        }, # node
        "pdu2NumberPDU" : {
            "nodetype" : "scalar",
            "moduleName" : "CPQPOWER-MIB",
            "oid" : "1.3.6.1.4.1.232.165.7.1.1",
            "status" : "current",
            "syntax" : {
                "type" :                 {
                    "basetype" : "Integer32",
                    "ranges" : [
                    {
                        "min" : "1",
                        "max" : "2"
                    },
                    ],
                    "range" : {
                        "min" : "1",
                        "max" : "2"
                    },
                },
            },
            "access" : "readonly",
            "description" :
                """The number of PDUs detected (in its daisy chain).""",
        }, # scalar
        "pdu2IdentTable" : {
            "nodetype" : "table",
            "moduleName" : "CPQPOWER-MIB",
            "oid" : "1.3.6.1.4.1.232.165.7.1.2",
            "status" : "current",
            "description" :
                """Aggregate Object with number of entries equal to pdu2NumberPDU .""",
        }, # table
        "pdu2IdentEntry" : {
            "nodetype" : "row",
            "moduleName" : "CPQPOWER-MIB",
            "oid" : "1.3.6.1.4.1.232.165.7.1.2.1",
            "status" : "current",
            "linkage" : [
                "pdu2IdentIndex",
            ],
            "description" :
                """The ident table entry containing the name, model, manufacturer, 
firmware version, part number, etc.""",
        }, # row
        "pdu2IdentIndex" : {
            "nodetype" : "column",
            "moduleName" : "CPQPOWER-MIB",
            "oid" : "1.3.6.1.4.1.232.165.7.1.2.1.1",
            "status" : "current",
            "syntax" : {
                "type" :                 {
                    "basetype" : "Integer32",
                    "ranges" : [
                    {
                        "min" : "0",
                        "max" : "100"
                    },
                    ],
                    "range" : {
                        "min" : "0",
                        "max" : "100"
                    },
                },
            },
            "access" : "readonly",
            "description" :
                """Index for the Pdu2IdentEntry table.""",
        }, # column
        "pdu2Name" : {
            "nodetype" : "column",
            "moduleName" : "CPQPOWER-MIB",
            "oid" : "1.3.6.1.4.1.232.165.7.1.2.1.2",
            "status" : "current",
            "syntax" : {
                "type" :                 {
                    "basetype" : "OctetString",
                    "parent module" : {
                        "name" : "RFC1213-MIB",
                        "type" : "DisplayString",
                    },
                    "ranges" : [
                    {
                        "min" : "0",
                        "max" : "63"
                    },
                    ],
                    "range" : {
                        "min" : "0",
                        "max" : "63"
                    },
                },
            },
            "access" : "readonly",
            "description" :
                """The string identify the device in daisy chain. Example PDU A.""",
        }, # column
        "pdu2Model" : {
            "nodetype" : "column",
            "moduleName" : "CPQPOWER-MIB",
            "oid" : "1.3.6.1.4.1.232.165.7.1.2.1.3",
            "status" : "current",
            "syntax" : {
                "type" :                 {
                    "basetype" : "OctetString",
                    "parent module" : {
                        "name" : "RFC1213-MIB",
                        "type" : "DisplayString",
                    },
                    "ranges" : [
                    {
                        "min" : "0",
                        "max" : "63"
                    },
                    ],
                    "range" : {
                        "min" : "0",
                        "max" : "63"
                    },
                },
            },
            "access" : "readonly",
            "description" :
                """The Device Model.""",
        }, # column
        "pdu2Manufacturer" : {
            "nodetype" : "column",
            "moduleName" : "CPQPOWER-MIB",
            "oid" : "1.3.6.1.4.1.232.165.7.1.2.1.4",
            "status" : "current",
            "syntax" : {
                "type" :                 {
                    "basetype" : "OctetString",
                    "parent module" : {
                        "name" : "RFC1213-MIB",
                        "type" : "DisplayString",
                    },
                    "ranges" : [
                    {
                        "min" : "0",
                        "max" : "63"
                    },
                    ],
                    "range" : {
                        "min" : "0",
                        "max" : "63"
                    },
                },
            },
            "access" : "readonly",
            "description" :
                """The Device Manufacturer Name (e.g. Hewlett-Packard).""",
        }, # column
        "pdu2FirmwareVersion" : {
            "nodetype" : "column",
            "moduleName" : "CPQPOWER-MIB",
            "oid" : "1.3.6.1.4.1.232.165.7.1.2.1.5",
            "status" : "current",
            "syntax" : {
                "type" :                 {
                    "basetype" : "OctetString",
                    "parent module" : {
                        "name" : "RFC1213-MIB",
                        "type" : "DisplayString",
                    },
                    "ranges" : [
                    {
                        "min" : "0",
                        "max" : "63"
                    },
                    ],
                    "range" : {
                        "min" : "0",
                        "max" : "63"
                    },
                },
            },
            "access" : "readonly",
            "description" :
                """The firmware revision level of the device.""",
        }, # column
        "pdu2PartNumber" : {
            "nodetype" : "column",
            "moduleName" : "CPQPOWER-MIB",
            "oid" : "1.3.6.1.4.1.232.165.7.1.2.1.6",
            "status" : "current",
            "syntax" : {
                "type" :                 {
                    "basetype" : "OctetString",
                    "parent module" : {
                        "name" : "RFC1213-MIB",
                        "type" : "DisplayString",
                    },
                    "ranges" : [
                    {
                        "min" : "0",
                        "max" : "63"
                    },
                    ],
                    "range" : {
                        "min" : "0",
                        "max" : "63"
                    },
                },
            },
            "access" : "readonly",
            "description" :
                """The device part number. Example AF400A.""",
        }, # column
        "pdu2SerialNumber" : {
            "nodetype" : "column",
            "moduleName" : "CPQPOWER-MIB",
            "oid" : "1.3.6.1.4.1.232.165.7.1.2.1.7",
            "status" : "current",
            "syntax" : {
                "type" :                 {
                    "basetype" : "OctetString",
                    "parent module" : {
                        "name" : "RFC1213-MIB",
                        "type" : "DisplayString",
                    },
                    "ranges" : [
                    {
                        "min" : "0",
                        "max" : "63"
                    },
                    ],
                    "range" : {
                        "min" : "0",
                        "max" : "63"
                    },
                },
            },
            "access" : "readonly",
            "description" :
                """The device serial number, 10- or 16-digit.""",
        }, # column
        "pdu2Status" : {
            "nodetype" : "column",
            "moduleName" : "CPQPOWER-MIB",
            "oid" : "1.3.6.1.4.1.232.165.7.1.2.1.8",
            "status" : "current",
            "syntax" : {
                "type" :                 {
                    "basetype" : "Enumeration",
                    "other" : {
                        "nodetype" : "namednumber",
                        "number" : "1"
                    },
                    "ok" : {
                        "nodetype" : "namednumber",
                        "number" : "2"
                    },
                    "degraded" : {
                        "nodetype" : "namednumber",
                        "number" : "3"
                    },
                    "failed" : {
                        "nodetype" : "namednumber",
                        "number" : "4"
                    },
                },
            },
            "access" : "readonly",
            "description" :
                """The overall status of the device.  A value of OK(2) indicates the device is operating normally.
A value of degraded(3) indicates the device is operating with warning indicators.  A value of
failed(4) indicates the device is operating with critical indicators.""",
        }, # column
        "pdu2Controllable" : {
            "nodetype" : "column",
            "moduleName" : "CPQPOWER-MIB",
            "oid" : "1.3.6.1.4.1.232.165.7.1.2.1.9",
            "status" : "current",
            "syntax" : {
                "type" :                 {
                    "basetype" : "Enumeration",
                    "yes" : {
                        "nodetype" : "namednumber",
                        "number" : "1"
                    },
                    "no" : {
                        "nodetype" : "namednumber",
                        "number" : "2"
                    },
                },
            },
            "access" : "readonly",
            "description" :
                """This object indicates whether or not the device is controllable.""",
        }, # column
        "pdu2InputPhaseCount" : {
            "nodetype" : "column",
            "moduleName" : "CPQPOWER-MIB",
            "oid" : "1.3.6.1.4.1.232.165.7.1.2.1.10",
            "status" : "current",
            "syntax" : {
                "type" :                 {
                    "basetype" : "Integer32",
                    "ranges" : [
                    {
                        "min" : "0",
                        "max" : "63"
                    },
                    ],
                    "range" : {
                        "min" : "0",
                        "max" : "63"
                    },
                },
            },
            "access" : "readonly",
            "description" :
                """The number of input phase on this pdu 1,2,3.""",
        }, # column
        "pdu2GroupCount" : {
            "nodetype" : "column",
            "moduleName" : "CPQPOWER-MIB",
            "oid" : "1.3.6.1.4.1.232.165.7.1.2.1.11",
            "status" : "current",
            "syntax" : {
                "type" :                 {
                    "basetype" : "Integer32",
                    "ranges" : [
                    {
                        "min" : "0",
                        "max" : "63"
                    },
                    ],
                    "range" : {
                        "min" : "0",
                        "max" : "63"
                    },
                },
            },
            "access" : "readonly",
            "description" :
                """The number of groups (breakers) on this pdu.""",
        }, # column
        "pdu2OutletCount" : {
            "nodetype" : "column",
            "moduleName" : "CPQPOWER-MIB",
            "oid" : "1.3.6.1.4.1.232.165.7.1.2.1.12",
            "status" : "current",
            "syntax" : {
                "type" :                 {
                    "basetype" : "Integer32",
                    "ranges" : [
                    {
                        "min" : "0",
                        "max" : "63"
                    },
                    ],
                    "range" : {
                        "min" : "0",
                        "max" : "63"
                    },
                },
            },
            "access" : "readonly",
            "description" :
                """The number of outlets in this PDU.""",
        }, # column
        "pdu2Input" : {
            "nodetype" : "node",
            "moduleName" : "CPQPOWER-MIB",
            "oid" : "1.3.6.1.4.1.232.165.7.2",
        }, # node
        "pdu2InputTable" : {
            "nodetype" : "table",
            "moduleName" : "CPQPOWER-MIB",
            "oid" : "1.3.6.1.4.1.232.165.7.2.1",
            "status" : "current",
            "description" :
                """Aggregate Object with number of entries equal to pdu2NumberPDU .""",
        }, # table
        "pdu2InputEntry" : {
            "nodetype" : "row",
            "moduleName" : "CPQPOWER-MIB",
            "oid" : "1.3.6.1.4.1.232.165.7.2.1.1",
            "status" : "current",
            "linkage" : [
                "pdu2IdentIndex",
            ],
            "description" :
                """The ident table entry containing the VA, Watts, WH, etc.""",
        }, # row
        "pdu2InputType" : {
            "nodetype" : "column",
            "moduleName" : "CPQPOWER-MIB",
            "oid" : "1.3.6.1.4.1.232.165.7.2.1.1.1",
            "status" : "current",
            "syntax" : {
                "type" :                 {
                    "basetype" : "Enumeration",
                    "singlePhase" : {
                        "nodetype" : "namednumber",
                        "number" : "1"
                    },
                    "splitPhase" : {
                        "nodetype" : "namednumber",
                        "number" : "2"
                    },
                    "threePhaseDelta" : {
                        "nodetype" : "namednumber",
                        "number" : "3"
                    },
                    "threePhaseWye" : {
                        "nodetype" : "namednumber",
                        "number" : "4"
                    },
                },
            },
            "access" : "readonly",
            "description" :
                """Type of input - single phase, split phase, three phase delta, or three
phase wye.""",
        }, # column
        "pdu2InputFrequency" : {
            "nodetype" : "column",
            "moduleName" : "CPQPOWER-MIB",
            "oid" : "1.3.6.1.4.1.232.165.7.2.1.1.2",
            "status" : "current",
            "syntax" : {
                "type" :                 {
                    "basetype" : "Integer32",
                    "ranges" : [
                    {
                        "min" : "0",
                        "max" : "2147483647"
                    },
                    ],
                    "range" : {
                        "min" : "0",
                        "max" : "2147483647"
                    },
                },
            },
            "access" : "readonly",
            "description" :
                """The measured input frequency from the PDU meters in tenths of Hz.""",
        }, # column
        "pdu2InputFrequencyStatus" : {
            "nodetype" : "column",
            "moduleName" : "CPQPOWER-MIB",
            "oid" : "1.3.6.1.4.1.232.165.7.2.1.1.3",
            "status" : "current",
            "syntax" : {
                "type" :                 {
                    "basetype" : "Enumeration",
                    "good" : {
                        "nodetype" : "namednumber",
                        "number" : "1"
                    },
                    "outOfRange" : {
                        "nodetype" : "namednumber",
                        "number" : "2"
                    },
                },
            },
            "access" : "readonly",
            "description" :
                """Status of the measured input frequency relative to the nominal frequency and the admitted tolerance.""",
        }, # column
        "pdu2InputPowerVA" : {
            "nodetype" : "column",
            "moduleName" : "CPQPOWER-MIB",
            "oid" : "1.3.6.1.4.1.232.165.7.2.1.1.4",
            "status" : "current",
            "syntax" : {
                "type" : { "module" :"", "name" : "Integer32"},
            },
            "access" : "readonly",
            "description" :
                """A total input VA of all phases.  Units are VA.  A negative value indicates
that this object is not available.""",
        }, # column
        "pdu2InputPowerWatts" : {
            "nodetype" : "column",
            "moduleName" : "CPQPOWER-MIB",
            "oid" : "1.3.6.1.4.1.232.165.7.2.1.1.5",
            "status" : "current",
            "syntax" : {
                "type" : { "module" :"", "name" : "Integer32"},
            },
            "access" : "readonly",
            "description" :
                """A total input Watts of all phases.  Units are Watts.  A negative value indicates
that this object is not available.""",
        }, # column
        "pdu2InputPowerWattHour" : {
            "nodetype" : "column",
            "moduleName" : "CPQPOWER-MIB",
            "oid" : "1.3.6.1.4.1.232.165.7.2.1.1.6",
            "status" : "current",
            "syntax" : {
                "type" : { "module" :"", "name" : "Integer32"},
            },
            "access" : "readonly",
            "description" :
                """A total input Watt-Hour value for all phases.  Units are WH. This value can be reset to 0 
using GUI. In that case, the pdu2InputPowerWattHourTimer will be reset as well  
A negative value indicates that this object is not available.""",
        }, # column
        "pdu2InputPowerWattHourTimer" : {
            "nodetype" : "column",
            "moduleName" : "CPQPOWER-MIB",
            "oid" : "1.3.6.1.4.1.232.165.7.2.1.1.7",
            "status" : "current",
            "syntax" : {
                "type" :                 {
                    "basetype" : "OctetString",
                    "parent module" : {
                        "name" : "RFC1213-MIB",
                        "type" : "DisplayString",
                    },
                    "ranges" : [
                    {
                        "min" : "0",
                        "max" : "22"
                    },
                    ],
                    "range" : {
                        "min" : "0",
                        "max" : "22"
                    },
                },
            },
            "access" : "readonly",
            "description" :
                """A Timestamp of when the Total Input WH was last reset.""",
        }, # column
        "pdu2InputPowerFactor" : {
            "nodetype" : "column",
            "moduleName" : "CPQPOWER-MIB",
            "oid" : "1.3.6.1.4.1.232.165.7.2.1.1.8",
            "status" : "current",
            "syntax" : {
                "type" : { "module" :"", "name" : "Integer32"},
            },
            "access" : "readonly",
            "description" :
                """An input PF value.  Units are in thousandths, for example a power factor
of 0.958 would be returned as 958, and 0.92 would be returned as 920.  
A negative value indicates that this object is not available.""",
        }, # column
        "pdu2InputPowerVAR" : {
            "nodetype" : "column",
            "moduleName" : "CPQPOWER-MIB",
            "oid" : "1.3.6.1.4.1.232.165.7.2.1.1.9",
            "status" : "current",
            "syntax" : {
                "type" : { "module" :"", "name" : "Integer32"},
            },
            "access" : "readonly",
            "description" :
                """An input VAR value.  Units are VAR.  A negative value indicates
that this object is not available.""",
        }, # column
        "pdu2InputPhaseTable" : {
            "nodetype" : "table",
            "moduleName" : "CPQPOWER-MIB",
            "oid" : "1.3.6.1.4.1.232.165.7.2.2",
            "status" : "current",
            "description" :
                """Aggregate Object with number of entries equal to number of PDUs (pdu2NumberPDU) and
number of input phase (pdu2InputPhaseCount).""",
        }, # table
        "pdu2InputPhaseEntry" : {
            "nodetype" : "row",
            "moduleName" : "CPQPOWER-MIB",
            "oid" : "1.3.6.1.4.1.232.165.7.2.2.1",
            "status" : "current",
            "linkage" : [
                "pdu2IdentIndex",
                "pdu2InputPhaseIndex",
            ],
            "description" :
                """The input table entry containing the voltage, current, frequency, power for each phase.
Entries are given with number of pdu and number of input phase 1, 2, or 3.""",
        }, # row
        "pdu2InputPhaseIndex" : {
            "nodetype" : "column",
            "moduleName" : "CPQPOWER-MIB",
            "oid" : "1.3.6.1.4.1.232.165.7.2.2.1.1",
            "status" : "current",
            "syntax" : {
                "type" :                 {
                    "basetype" : "Integer32",
                    "ranges" : [
                    {
                        "min" : "0",
                        "max" : "100"
                    },
                    ],
                    "range" : {
                        "min" : "0",
                        "max" : "100"
                    },
                },
            },
            "access" : "readonly",
            "description" :
                """Index for the Pdu2InputEntry table.""",
        }, # column
        "pdu2InputPhaseVoltageMeasType" : {
            "nodetype" : "column",
            "moduleName" : "CPQPOWER-MIB",
            "oid" : "1.3.6.1.4.1.232.165.7.2.2.1.2",
            "status" : "current",
            "syntax" : {
                "type" :                 {
                    "basetype" : "Enumeration",
                    "singlePhase" : {
                        "nodetype" : "namednumber",
                        "number" : "1"
                    },
                    "phase1toN" : {
                        "nodetype" : "namednumber",
                        "number" : "2"
                    },
                    "phase2toN" : {
                        "nodetype" : "namednumber",
                        "number" : "3"
                    },
                    "phase3toN" : {
                        "nodetype" : "namednumber",
                        "number" : "4"
                    },
                    "phase1to2" : {
                        "nodetype" : "namednumber",
                        "number" : "5"
                    },
                    "phase2to3" : {
                        "nodetype" : "namednumber",
                        "number" : "6"
                    },
                    "phase3to1" : {
                        "nodetype" : "namednumber",
                        "number" : "7"
                    },
                },
            },
            "access" : "readonly",
            "description" :
                """Value indicates what input voltage is being measured in this table row - single phase
voltage, phase 1 to neutral, phase 2 to neutral, phase 3 to neutral, phase 1 to phase 2,
phase 2 to phase 3, or phase 3 to phase 1.""",
        }, # column
        "pdu2InputPhaseVoltage" : {
            "nodetype" : "column",
            "moduleName" : "CPQPOWER-MIB",
            "oid" : "1.3.6.1.4.1.232.165.7.2.2.1.3",
            "status" : "current",
            "syntax" : {
                "type" : { "module" :"", "name" : "Integer32"},
            },
            "access" : "readonly",
            "description" :
                """An input voltage measurement value.  Units are millivolts.""",
        }, # column
        "pdu2InputPhaseVoltageThStatus" : {
            "nodetype" : "column",
            "moduleName" : "CPQPOWER-MIB",
            "oid" : "1.3.6.1.4.1.232.165.7.2.2.1.4",
            "status" : "current",
            "syntax" : {
                "type" :                 {
                    "basetype" : "Enumeration",
                    "good" : {
                        "nodetype" : "namednumber",
                        "number" : "1"
                    },
                    "lowWarning" : {
                        "nodetype" : "namednumber",
                        "number" : "2"
                    },
                    "lowCritical" : {
                        "nodetype" : "namednumber",
                        "number" : "3"
                    },
                    "highWarning" : {
                        "nodetype" : "namednumber",
                        "number" : "4"
                    },
                    "highCritical" : {
                        "nodetype" : "namednumber",
                        "number" : "5"
                    },
                },
            },
            "access" : "readonly",
            "description" :
                """Status of the measured input voltage relative to the configured thresholds.""",
        }, # column
        "pdu2InputPhaseVoltageThLowerWarning" : {
            "nodetype" : "column",
            "moduleName" : "CPQPOWER-MIB",
            "oid" : "1.3.6.1.4.1.232.165.7.2.2.1.5",
            "status" : "current",
            "syntax" : {
                "type" :                 {
                    "basetype" : "Integer32",
                    "ranges" : [
                    {
                        "min" : "-1",
                        "max" : "500000"
                    },
                    ],
                    "range" : {
                        "min" : "-1",
                        "max" : "500000"
                    },
                },
            },
            "access" : "readonly",
            "description" :
                """Lower warning threshold.  Units are millivolts.  A negative value indicates
that this object is not available.""",
        }, # column
        "pdu2InputPhaseVoltageThLowerCritical" : {
            "nodetype" : "column",
            "moduleName" : "CPQPOWER-MIB",
            "oid" : "1.3.6.1.4.1.232.165.7.2.2.1.6",
            "status" : "current",
            "syntax" : {
                "type" :                 {
                    "basetype" : "Integer32",
                    "ranges" : [
                    {
                        "min" : "-1",
                        "max" : "500000"
                    },
                    ],
                    "range" : {
                        "min" : "-1",
                        "max" : "500000"
                    },
                },
            },
            "access" : "readonly",
            "description" :
                """Lower critical threshold.  Units are millivolts.  A negative value indicates
that this object is not available.""",
        }, # column
        "pdu2InputPhaseVoltageThUpperWarning" : {
            "nodetype" : "column",
            "moduleName" : "CPQPOWER-MIB",
            "oid" : "1.3.6.1.4.1.232.165.7.2.2.1.7",
            "status" : "current",
            "syntax" : {
                "type" :                 {
                    "basetype" : "Integer32",
                    "ranges" : [
                    {
                        "min" : "-1",
                        "max" : "500000"
                    },
                    ],
                    "range" : {
                        "min" : "-1",
                        "max" : "500000"
                    },
                },
            },
            "access" : "readonly",
            "description" :
                """Upper warning threshold.  Units are millivolts.  A negative value indicates
that this object is not available.""",
        }, # column
        "pdu2InputPhaseVoltageThUpperCritical" : {
            "nodetype" : "column",
            "moduleName" : "CPQPOWER-MIB",
            "oid" : "1.3.6.1.4.1.232.165.7.2.2.1.8",
            "status" : "current",
            "syntax" : {
                "type" :                 {
                    "basetype" : "Integer32",
                    "ranges" : [
                    {
                        "min" : "-1",
                        "max" : "500000"
                    },
                    ],
                    "range" : {
                        "min" : "-1",
                        "max" : "500000"
                    },
                },
            },
            "access" : "readonly",
            "description" :
                """Upper critical threshold.  Units are millivolts.  A negative value indicates
that this object is not available.""",
        }, # column
        "pdu2InputPhaseCurrentMeasType" : {
            "nodetype" : "column",
            "moduleName" : "CPQPOWER-MIB",
            "oid" : "1.3.6.1.4.1.232.165.7.2.2.1.9",
            "status" : "current",
            "syntax" : {
                "type" :                 {
                    "basetype" : "Enumeration",
                    "singlePhase" : {
                        "nodetype" : "namednumber",
                        "number" : "1"
                    },
                    "neutral" : {
                        "nodetype" : "namednumber",
                        "number" : "2"
                    },
                    "phase1" : {
                        "nodetype" : "namednumber",
                        "number" : "3"
                    },
                    "phase2" : {
                        "nodetype" : "namednumber",
                        "number" : "4"
                    },
                    "phase3" : {
                        "nodetype" : "namednumber",
                        "number" : "5"
                    },
                },
            },
            "access" : "readonly",
            "description" :
                """Which input wire is being measured in this table row - single phase, neutral, phase 1,
phase 2, or phase 3.""",
        }, # column
        "pdu2InputPhaseCurrentRating" : {
            "nodetype" : "column",
            "moduleName" : "CPQPOWER-MIB",
            "oid" : "1.3.6.1.4.1.232.165.7.2.2.1.10",
            "status" : "current",
            "syntax" : {
                "type" : { "module" :"", "name" : "Integer32"},
            },
            "access" : "readonly",
            "description" :
                """Rated current capacity of the input.  A negative value indicates that
the hardware current capacity is unknown.  Units are milliamps.""",
        }, # column
        "pdu2InputPhaseCurrent" : {
            "nodetype" : "column",
            "moduleName" : "CPQPOWER-MIB",
            "oid" : "1.3.6.1.4.1.232.165.7.2.2.1.11",
            "status" : "current",
            "syntax" : {
                "type" : { "module" :"", "name" : "Integer32"},
            },
            "access" : "readonly",
            "description" :
                """An input current measurement value.  Units are milliamps.""",
        }, # column
        "pdu2InputPhaseCurrentThStatus" : {
            "nodetype" : "column",
            "moduleName" : "CPQPOWER-MIB",
            "oid" : "1.3.6.1.4.1.232.165.7.2.2.1.12",
            "status" : "current",
            "syntax" : {
                "type" :                 {
                    "basetype" : "Enumeration",
                    "good" : {
                        "nodetype" : "namednumber",
                        "number" : "1"
                    },
                    "lowWarning" : {
                        "nodetype" : "namednumber",
                        "number" : "2"
                    },
                    "lowCritical" : {
                        "nodetype" : "namednumber",
                        "number" : "3"
                    },
                    "highWarning" : {
                        "nodetype" : "namednumber",
                        "number" : "4"
                    },
                    "highCritical" : {
                        "nodetype" : "namednumber",
                        "number" : "5"
                    },
                },
            },
            "access" : "readonly",
            "description" :
                """Status of the measured input current relative to the configured thresholds.""",
        }, # column
        "pdu2InputPhaseCurrentThLowerWarning" : {
            "nodetype" : "column",
            "moduleName" : "CPQPOWER-MIB",
            "oid" : "1.3.6.1.4.1.232.165.7.2.2.1.13",
            "status" : "current",
            "syntax" : {
                "type" :                 {
                    "basetype" : "Integer32",
                    "ranges" : [
                    {
                        "min" : "-1",
                        "max" : "100000"
                    },
                    ],
                    "range" : {
                        "min" : "-1",
                        "max" : "100000"
                    },
                },
            },
            "access" : "readonly",
            "description" :
                """Lower warning threshold.  Units are milliamps.  A negative value indicates
that this object is not available.""",
        }, # column
        "pdu2InputPhaseCurrentThLowerCritical" : {
            "nodetype" : "column",
            "moduleName" : "CPQPOWER-MIB",
            "oid" : "1.3.6.1.4.1.232.165.7.2.2.1.14",
            "status" : "current",
            "syntax" : {
                "type" :                 {
                    "basetype" : "Integer32",
                    "ranges" : [
                    {
                        "min" : "-1",
                        "max" : "100000"
                    },
                    ],
                    "range" : {
                        "min" : "-1",
                        "max" : "100000"
                    },
                },
            },
            "access" : "readonly",
            "description" :
                """Lower critical threshold.  Units are milliamps.  A negative value indicates
that this object is not available.""",
        }, # column
        "pdu2InputPhaseCurrentThUpperWarning" : {
            "nodetype" : "column",
            "moduleName" : "CPQPOWER-MIB",
            "oid" : "1.3.6.1.4.1.232.165.7.2.2.1.15",
            "status" : "current",
            "syntax" : {
                "type" :                 {
                    "basetype" : "Integer32",
                    "ranges" : [
                    {
                        "min" : "-1",
                        "max" : "100000"
                    },
                    ],
                    "range" : {
                        "min" : "-1",
                        "max" : "100000"
                    },
                },
            },
            "access" : "readonly",
            "description" :
                """Upper warning threshold.  Units are milliamps.  A negative value indicates
that this object is not available.""",
        }, # column
        "pdu2InputPhaseCurrentThUpperCritical" : {
            "nodetype" : "column",
            "moduleName" : "CPQPOWER-MIB",
            "oid" : "1.3.6.1.4.1.232.165.7.2.2.1.16",
            "status" : "current",
            "syntax" : {
                "type" :                 {
                    "basetype" : "Integer32",
                    "ranges" : [
                    {
                        "min" : "-1",
                        "max" : "100000"
                    },
                    ],
                    "range" : {
                        "min" : "-1",
                        "max" : "100000"
                    },
                },
            },
            "access" : "readonly",
            "description" :
                """Upper critical threshold.  Units are milliamps.  A negative value indicates
that this object is not available.""",
        }, # column
        "pdu2InputPhaseCurrentCrestFactor" : {
            "nodetype" : "column",
            "moduleName" : "CPQPOWER-MIB",
            "oid" : "1.3.6.1.4.1.232.165.7.2.2.1.17",
            "status" : "current",
            "syntax" : {
                "type" : { "module" :"", "name" : "Integer32"},
            },
            "access" : "readonly",
            "description" :
                """Current crest factor.  Units are in milli, for example a crest factor of
1.414 will be returned as 1414.  A negative value indicates
         that this object is not available.""",
        }, # column
        "pdu2InputPhaseCurrentPercentLoad" : {
            "nodetype" : "column",
            "moduleName" : "CPQPOWER-MIB",
            "oid" : "1.3.6.1.4.1.232.165.7.2.2.1.18",
            "status" : "current",
            "syntax" : {
                "type" : { "module" :"", "name" : "Integer32"},
            },
            "access" : "readonly",
            "description" :
                """Current percent load, based on the rated current capacity.  Units are
percentage, for example 80% will be returned as 80.  A negative
value indicates that this object is not available.""",
        }, # column
        "pdu2InputPhasePowerMeasType" : {
            "nodetype" : "column",
            "moduleName" : "CPQPOWER-MIB",
            "oid" : "1.3.6.1.4.1.232.165.7.2.2.1.19",
            "status" : "current",
            "syntax" : {
                "type" :                 {
                    "basetype" : "Enumeration",
                    "singlePhase" : {
                        "nodetype" : "namednumber",
                        "number" : "1"
                    },
                    "neutral" : {
                        "nodetype" : "namednumber",
                        "number" : "2"
                    },
                    "phase1" : {
                        "nodetype" : "namednumber",
                        "number" : "3"
                    },
                    "phase2" : {
                        "nodetype" : "namednumber",
                        "number" : "4"
                    },
                    "phase3" : {
                        "nodetype" : "namednumber",
                        "number" : "5"
                    },
                },
            },
            "access" : "readonly",
            "description" :
                """Which input wire is being measured in this table row - single phase, neutral, phase 1,
phase 2, or phase 3.""",
        }, # column
        "pdu2InputPhasePowerVA" : {
            "nodetype" : "column",
            "moduleName" : "CPQPOWER-MIB",
            "oid" : "1.3.6.1.4.1.232.165.7.2.2.1.20",
            "status" : "current",
            "syntax" : {
                "type" : { "module" :"", "name" : "Integer32"},
            },
            "access" : "readonly",
            "description" :
                """An input VA value.  Units are VA.  A negative value indicates
that this object is not available.""",
        }, # column
        "pdu2InputPhasePowerWatts" : {
            "nodetype" : "column",
            "moduleName" : "CPQPOWER-MIB",
            "oid" : "1.3.6.1.4.1.232.165.7.2.2.1.21",
            "status" : "current",
            "syntax" : {
                "type" : { "module" :"", "name" : "Integer32"},
            },
            "access" : "readonly",
            "description" :
                """An input Watts value.  Units are Watts.  A negative value indicates
that this object is not available.""",
        }, # column
        "pdu2InputPhasePowerWattHour" : {
            "nodetype" : "column",
            "moduleName" : "CPQPOWER-MIB",
            "oid" : "1.3.6.1.4.1.232.165.7.2.2.1.22",
            "status" : "current",
            "syntax" : {
                "type" : { "module" :"", "name" : "Integer32"},
            },
            "access" : "readonly",
            "description" :
                """A Watt-Hour value for each Input phase.  Units are WH. This value can be reset to 0 
using GUI. In that case, the pdu2InputPhasePowerWattHourTimer will be reset as well    
A negative value indicates that this object is not available.""",
        }, # column
        "pdu2InputPhasePowerWattHourTimer" : {
            "nodetype" : "column",
            "moduleName" : "CPQPOWER-MIB",
            "oid" : "1.3.6.1.4.1.232.165.7.2.2.1.23",
            "status" : "current",
            "syntax" : {
                "type" :                 {
                    "basetype" : "OctetString",
                    "parent module" : {
                        "name" : "RFC1213-MIB",
                        "type" : "DisplayString",
                    },
                    "ranges" : [
                    {
                        "min" : "0",
                        "max" : "22"
                    },
                    ],
                    "range" : {
                        "min" : "0",
                        "max" : "22"
                    },
                },
            },
            "access" : "readonly",
            "description" :
                """Timestamp of when input Watt-hours (inputWh) was last reset.""",
        }, # column
        "pdu2InputPhasePowerFactor" : {
            "nodetype" : "column",
            "moduleName" : "CPQPOWER-MIB",
            "oid" : "1.3.6.1.4.1.232.165.7.2.2.1.24",
            "status" : "current",
            "syntax" : {
                "type" : { "module" :"", "name" : "Integer32"},
            },
            "access" : "readonly",
            "description" :
                """An input PF value.  Units are in thousandths, for example a power factor
of 0.958 would be returned as 958, and 0.92 would be returned 
 as 920.  A negative value indicates that this object is not available.""",
        }, # column
        "pdu2InputPhasePowerVAR" : {
            "nodetype" : "column",
            "moduleName" : "CPQPOWER-MIB",
            "oid" : "1.3.6.1.4.1.232.165.7.2.2.1.25",
            "status" : "current",
            "syntax" : {
                "type" : { "module" :"", "name" : "Integer32"},
            },
            "access" : "readonly",
            "description" :
                """An input VAR value.  Units are VAR.  A negative value indicates
that this object is not available.""",
        }, # column
        "pdu2Group" : {
            "nodetype" : "node",
            "moduleName" : "CPQPOWER-MIB",
            "oid" : "1.3.6.1.4.1.232.165.7.3",
        }, # node
        "pdu2GroupTable" : {
            "nodetype" : "table",
            "moduleName" : "CPQPOWER-MIB",
            "oid" : "1.3.6.1.4.1.232.165.7.3.1",
            "status" : "current",
            "description" :
                """Aggregate Object with number of entries equal to number of PDUs
and number of breakers (pdu2GroupCount).""",
        }, # table
        "pdu2GroupEntry" : {
            "nodetype" : "row",
            "moduleName" : "CPQPOWER-MIB",
            "oid" : "1.3.6.1.4.1.232.165.7.3.1.1",
            "status" : "current",
            "linkage" : [
                "pdu2IdentIndex",
                "pdu2GroupIndex",
            ],
            "description" :
                """The input table entry containing the name, voltages, currents, power, etc.""",
        }, # row
        "pdu2GroupIndex" : {
            "nodetype" : "column",
            "moduleName" : "CPQPOWER-MIB",
            "oid" : "1.3.6.1.4.1.232.165.7.3.1.1.1",
            "status" : "current",
            "syntax" : {
                "type" :                 {
                    "basetype" : "Integer32",
                    "ranges" : [
                    {
                        "min" : "0",
                        "max" : "100"
                    },
                    ],
                    "range" : {
                        "min" : "0",
                        "max" : "100"
                    },
                },
            },
            "access" : "readonly",
            "description" :
                """Index for the Pdu2GroupEntry table.""",
        }, # column
        "pdu2GroupName" : {
            "nodetype" : "column",
            "moduleName" : "CPQPOWER-MIB",
            "oid" : "1.3.6.1.4.1.232.165.7.3.1.1.2",
            "status" : "current",
            "syntax" : {
                "type" :                 {
                    "basetype" : "OctetString",
                    "parent module" : {
                        "name" : "RFC1213-MIB",
                        "type" : "DisplayString",
                    },
                    "ranges" : [
                    {
                        "min" : "1",
                        "max" : "31"
                    },
                    ],
                    "range" : {
                        "min" : "1",
                        "max" : "31"
                    },
                },
            },
            "access" : "readonly",
            "description" :
                """A descriptive name for the group.""",
        }, # column
        "pdu2GroupType" : {
            "nodetype" : "column",
            "moduleName" : "CPQPOWER-MIB",
            "oid" : "1.3.6.1.4.1.232.165.7.3.1.1.3",
            "status" : "current",
            "syntax" : {
                "type" :                 {
                    "basetype" : "Enumeration",
                    "breaker1pole" : {
                        "nodetype" : "namednumber",
                        "number" : "2"
                    },
                    "breaker2pole" : {
                        "nodetype" : "namednumber",
                        "number" : "3"
                    },
                    "breaker3pole" : {
                        "nodetype" : "namednumber",
                        "number" : "4"
                    },
                    "outletSection" : {
                        "nodetype" : "namednumber",
                        "number" : "5"
                    },
                },
            },
            "access" : "readonly",
            "description" :
                """The type of the group. (5) has no breaker""",
        }, # column
        "pdu2GroupVoltageMeasType" : {
            "nodetype" : "column",
            "moduleName" : "CPQPOWER-MIB",
            "oid" : "1.3.6.1.4.1.232.165.7.3.1.1.4",
            "status" : "current",
            "syntax" : {
                "type" :                 {
                    "basetype" : "Enumeration",
                    "singlePhase" : {
                        "nodetype" : "namednumber",
                        "number" : "1"
                    },
                    "phase1toN" : {
                        "nodetype" : "namednumber",
                        "number" : "2"
                    },
                    "phase2toN" : {
                        "nodetype" : "namednumber",
                        "number" : "3"
                    },
                    "phase3toN" : {
                        "nodetype" : "namednumber",
                        "number" : "4"
                    },
                    "phase1to2" : {
                        "nodetype" : "namednumber",
                        "number" : "5"
                    },
                    "phase2to3" : {
                        "nodetype" : "namednumber",
                        "number" : "6"
                    },
                    "phase3to1" : {
                        "nodetype" : "namednumber",
                        "number" : "7"
                    },
                },
            },
            "access" : "readonly",
            "description" :
                """Value indicates what input voltage is being measured in this table row - single phase
voltage, phase 1 to neutral, phase 2 to neutral, phase 3 to neutral, phase 1 to phase 2,
phase 2 to phase 3, or phase 3 to phase 1.""",
        }, # column
        "pdu2GroupVoltage" : {
            "nodetype" : "column",
            "moduleName" : "CPQPOWER-MIB",
            "oid" : "1.3.6.1.4.1.232.165.7.3.1.1.5",
            "status" : "current",
            "syntax" : {
                "type" : { "module" :"", "name" : "Integer32"},
            },
            "access" : "readonly",
            "description" :
                """Units are millivolts.""",
        }, # column
        "pdu2GroupVoltageThStatus" : {
            "nodetype" : "column",
            "moduleName" : "CPQPOWER-MIB",
            "oid" : "1.3.6.1.4.1.232.165.7.3.1.1.6",
            "status" : "current",
            "syntax" : {
                "type" :                 {
                    "basetype" : "Enumeration",
                    "good" : {
                        "nodetype" : "namednumber",
                        "number" : "1"
                    },
                    "lowWarning" : {
                        "nodetype" : "namednumber",
                        "number" : "2"
                    },
                    "lowCritical" : {
                        "nodetype" : "namednumber",
                        "number" : "3"
                    },
                    "highWarning" : {
                        "nodetype" : "namednumber",
                        "number" : "4"
                    },
                    "highCritical" : {
                        "nodetype" : "namednumber",
                        "number" : "5"
                    },
                },
            },
            "access" : "readonly",
            "description" :
                """Status of the measured group voltage relative to the configured thresholds.""",
        }, # column
        "pdu2GroupVoltageThLowerWarning" : {
            "nodetype" : "column",
            "moduleName" : "CPQPOWER-MIB",
            "oid" : "1.3.6.1.4.1.232.165.7.3.1.1.7",
            "status" : "current",
            "syntax" : {
                "type" :                 {
                    "basetype" : "Integer32",
                    "ranges" : [
                    {
                        "min" : "-1",
                        "max" : "500000"
                    },
                    ],
                    "range" : {
                        "min" : "-1",
                        "max" : "500000"
                    },
                },
            },
            "access" : "readonly",
            "description" :
                """Lower warning threshold.  Units are millivolts.  A negative value indicates
that this object is not available.""",
        }, # column
        "pdu2GroupVoltageThLowerCritical" : {
            "nodetype" : "column",
            "moduleName" : "CPQPOWER-MIB",
            "oid" : "1.3.6.1.4.1.232.165.7.3.1.1.8",
            "status" : "current",
            "syntax" : {
                "type" :                 {
                    "basetype" : "Integer32",
                    "ranges" : [
                    {
                        "min" : "-1",
                        "max" : "500000"
                    },
                    ],
                    "range" : {
                        "min" : "-1",
                        "max" : "500000"
                    },
                },
            },
            "access" : "readonly",
            "description" :
                """Lower critical threshold.  Units are millivolts.  A negative value indicates
that this object is not available.""",
        }, # column
        "pdu2GroupVoltageThUpperWarning" : {
            "nodetype" : "column",
            "moduleName" : "CPQPOWER-MIB",
            "oid" : "1.3.6.1.4.1.232.165.7.3.1.1.9",
            "status" : "current",
            "syntax" : {
                "type" :                 {
                    "basetype" : "Integer32",
                    "ranges" : [
                    {
                        "min" : "-1",
                        "max" : "500000"
                    },
                    ],
                    "range" : {
                        "min" : "-1",
                        "max" : "500000"
                    },
                },
            },
            "access" : "readonly",
            "description" :
                """Upper warning threshold.  Units are millivolts.  A negative value indicates
that this object is not available.""",
        }, # column
        "pdu2GroupVoltageThUpperCritical" : {
            "nodetype" : "column",
            "moduleName" : "CPQPOWER-MIB",
            "oid" : "1.3.6.1.4.1.232.165.7.3.1.1.10",
            "status" : "current",
            "syntax" : {
                "type" :                 {
                    "basetype" : "Integer32",
                    "ranges" : [
                    {
                        "min" : "-1",
                        "max" : "500000"
                    },
                    ],
                    "range" : {
                        "min" : "-1",
                        "max" : "500000"
                    },
                },
            },
            "access" : "readonly",
            "description" :
                """Upper critical threshold.  Units are millivolts.  A negative value indicates
that this object is not available.""",
        }, # column
        "pdu2groupCurrentRating" : {
            "nodetype" : "column",
            "moduleName" : "CPQPOWER-MIB",
            "oid" : "1.3.6.1.4.1.232.165.7.3.1.1.11",
            "status" : "current",
            "syntax" : {
                "type" : { "module" :"", "name" : "Integer32"},
            },
            "access" : "readonly",
            "description" :
                """Rated current capacity of the group.  Units are milliamps.  A negative 
value indicates that the hardware current capacity is unknown (it
will always be unknown for custom groups).""",
        }, # column
        "pdu2GroupCurrent" : {
            "nodetype" : "column",
            "moduleName" : "CPQPOWER-MIB",
            "oid" : "1.3.6.1.4.1.232.165.7.3.1.1.12",
            "status" : "current",
            "syntax" : {
                "type" : { "module" :"", "name" : "Integer32"},
            },
            "access" : "readonly",
            "description" :
                """A group current measurement value.  Units are milliamps.""",
        }, # column
        "pdu2GroupCurrentThStatus" : {
            "nodetype" : "column",
            "moduleName" : "CPQPOWER-MIB",
            "oid" : "1.3.6.1.4.1.232.165.7.3.1.1.13",
            "status" : "current",
            "syntax" : {
                "type" :                 {
                    "basetype" : "Enumeration",
                    "good" : {
                        "nodetype" : "namednumber",
                        "number" : "1"
                    },
                    "lowWarning" : {
                        "nodetype" : "namednumber",
                        "number" : "2"
                    },
                    "lowCritical" : {
                        "nodetype" : "namednumber",
                        "number" : "3"
                    },
                    "highWarning" : {
                        "nodetype" : "namednumber",
                        "number" : "4"
                    },
                    "highCritical" : {
                        "nodetype" : "namednumber",
                        "number" : "5"
                    },
                },
            },
            "access" : "readonly",
            "description" :
                """Status of the measured group current relative to the configured thresholds.""",
        }, # column
        "pdu2GroupCurrentThLowerWarning" : {
            "nodetype" : "column",
            "moduleName" : "CPQPOWER-MIB",
            "oid" : "1.3.6.1.4.1.232.165.7.3.1.1.14",
            "status" : "current",
            "syntax" : {
                "type" :                 {
                    "basetype" : "Integer32",
                    "ranges" : [
                    {
                        "min" : "-1",
                        "max" : "100000"
                    },
                    ],
                    "range" : {
                        "min" : "-1",
                        "max" : "100000"
                    },
                },
            },
            "access" : "readonly",
            "description" :
                """Lower warning threshold.  Units are milliamps.  A negative value indicates
that this object is not available.""",
        }, # column
        "pdu2GroupCurrentThLowerCritical" : {
            "nodetype" : "column",
            "moduleName" : "CPQPOWER-MIB",
            "oid" : "1.3.6.1.4.1.232.165.7.3.1.1.15",
            "status" : "current",
            "syntax" : {
                "type" :                 {
                    "basetype" : "Integer32",
                    "ranges" : [
                    {
                        "min" : "-1",
                        "max" : "100000"
                    },
                    ],
                    "range" : {
                        "min" : "-1",
                        "max" : "100000"
                    },
                },
            },
            "access" : "readonly",
            "description" :
                """Lower critical threshold.  Units are milliamps.  A negative value indicates
that this object is not available.""",
        }, # column
        "pdu2GroupCurrentThUpperWarning" : {
            "nodetype" : "column",
            "moduleName" : "CPQPOWER-MIB",
            "oid" : "1.3.6.1.4.1.232.165.7.3.1.1.16",
            "status" : "current",
            "syntax" : {
                "type" :                 {
                    "basetype" : "Integer32",
                    "ranges" : [
                    {
                        "min" : "-1",
                        "max" : "100000"
                    },
                    ],
                    "range" : {
                        "min" : "-1",
                        "max" : "100000"
                    },
                },
            },
            "access" : "readonly",
            "description" :
                """Upper warning threshold.  Units are milliamps.  A negative value indicates
that this object is not available.""",
        }, # column
        "pdu2GroupCurrentThUpperCritical" : {
            "nodetype" : "column",
            "moduleName" : "CPQPOWER-MIB",
            "oid" : "1.3.6.1.4.1.232.165.7.3.1.1.17",
            "status" : "current",
            "syntax" : {
                "type" :                 {
                    "basetype" : "Integer32",
                    "ranges" : [
                    {
                        "min" : "-1",
                        "max" : "100000"
                    },
                    ],
                    "range" : {
                        "min" : "-1",
                        "max" : "100000"
                    },
                },
            },
            "access" : "readonly",
            "description" :
                """Upper critical threshold.  Units are milliamps.  A negative value indicates
that this object is not available.""",
        }, # column
        "pdu2GroupCurrentCrestFactor" : {
            "nodetype" : "column",
            "moduleName" : "CPQPOWER-MIB",
            "oid" : "1.3.6.1.4.1.232.165.7.3.1.1.18",
            "status" : "current",
            "syntax" : {
                "type" : { "module" :"", "name" : "Integer32"},
            },
            "access" : "readonly",
            "description" :
                """Current crest factor.  Units are in milli, for example a crest factor of
1.414 will be returned as 1414.  A negative value indicates
         that this object is not available.""",
        }, # column
        "pdu2GroupCurrentPercentLoad" : {
            "nodetype" : "column",
            "moduleName" : "CPQPOWER-MIB",
            "oid" : "1.3.6.1.4.1.232.165.7.3.1.1.19",
            "status" : "current",
            "syntax" : {
                "type" : { "module" :"", "name" : "Integer32"},
            },
            "access" : "readonly",
            "description" :
                """Current percent load, based on the rated current capacity.  Units are
percentage, for example 80% will be returned as 80.  A negative
value indicates that this object is not available.""",
        }, # column
        "pdu2GroupPowerVA" : {
            "nodetype" : "column",
            "moduleName" : "CPQPOWER-MIB",
            "oid" : "1.3.6.1.4.1.232.165.7.3.1.1.20",
            "status" : "current",
            "syntax" : {
                "type" : { "module" :"", "name" : "Integer32"},
            },
            "access" : "readonly",
            "description" :
                """A group VA value.  Units are VA.  A negative value indicates
that this object is not available.""",
        }, # column
        "pdu2GroupPowerWatts" : {
            "nodetype" : "column",
            "moduleName" : "CPQPOWER-MIB",
            "oid" : "1.3.6.1.4.1.232.165.7.3.1.1.21",
            "status" : "current",
            "syntax" : {
                "type" : { "module" :"", "name" : "Integer32"},
            },
            "access" : "readonly",
            "description" :
                """A group Watts value.  Units are Watts.  A negative value indicates
that this object is not available.""",
        }, # column
        "pdu2GroupPowerWattHour" : {
            "nodetype" : "column",
            "moduleName" : "CPQPOWER-MIB",
            "oid" : "1.3.6.1.4.1.232.165.7.3.1.1.22",
            "status" : "current",
            "syntax" : {
                "type" : { "module" :"", "name" : "Integer32"},
            },
            "access" : "readonly",
            "description" :
                """A Watt-Hour value for each section.  Units are WH. This value can be reset to 0 
using GUI. In that case, the pdu2GroupPowerWattHourTimer will be reset as well.    
A negative value indicates that this object is not available.""",
        }, # column
        "pdu2GroupPowerWattHourTimer" : {
            "nodetype" : "column",
            "moduleName" : "CPQPOWER-MIB",
            "oid" : "1.3.6.1.4.1.232.165.7.3.1.1.23",
            "status" : "current",
            "syntax" : {
                "type" :                 {
                    "basetype" : "OctetString",
                    "parent module" : {
                        "name" : "RFC1213-MIB",
                        "type" : "DisplayString",
                    },
                    "ranges" : [
                    {
                        "min" : "0",
                        "max" : "22"
                    },
                    ],
                    "range" : {
                        "min" : "0",
                        "max" : "22"
                    },
                },
            },
            "access" : "readonly",
            "description" :
                """Timestamp of when group Watt-hours (groupWh) was last reset.""",
        }, # column
        "pdu2GroupPowerFactor" : {
            "nodetype" : "column",
            "moduleName" : "CPQPOWER-MIB",
            "oid" : "1.3.6.1.4.1.232.165.7.3.1.1.24",
            "status" : "current",
            "syntax" : {
                "type" : { "module" :"", "name" : "Integer32"},
            },
            "access" : "readonly",
            "description" :
                """A group PF value.  Units are in thousandths, for example a power factor
of 0.958 would be returned as 958, and 0.92 would be returned as 920.  
A negative value indicates that this object is not available.""",
        }, # column
        "pdu2GroupPowerVAR" : {
            "nodetype" : "column",
            "moduleName" : "CPQPOWER-MIB",
            "oid" : "1.3.6.1.4.1.232.165.7.3.1.1.25",
            "status" : "current",
            "syntax" : {
                "type" : { "module" :"", "name" : "Integer32"},
            },
            "access" : "readonly",
            "description" :
                """A group VAR value.  Units are VAR.  A negative value indicates
that this object is not available.""",
        }, # column
        "pdu2GroupOutletCount" : {
            "nodetype" : "column",
            "moduleName" : "CPQPOWER-MIB",
            "oid" : "1.3.6.1.4.1.232.165.7.3.1.1.26",
            "status" : "current",
            "syntax" : {
                "type" :                 {
                    "basetype" : "Integer32",
                    "ranges" : [
                    {
                        "min" : "0",
                        "max" : "63"
                    },
                    ],
                    "range" : {
                        "min" : "0",
                        "max" : "63"
                    },
                },
            },
            "access" : "readonly",
            "description" :
                """The number of outlets in each group (breaker).""",
        }, # column
        "pdu2GroupBreakerStatus" : {
            "nodetype" : "column",
            "moduleName" : "CPQPOWER-MIB",
            "oid" : "1.3.6.1.4.1.232.165.7.3.1.1.27",
            "status" : "current",
            "syntax" : {
                "type" :                 {
                    "basetype" : "Enumeration",
                    "notApplicable" : {
                        "nodetype" : "namednumber",
                        "number" : "1"
                    },
                    "breakerOn" : {
                        "nodetype" : "namednumber",
                        "number" : "2"
                    },
                    "breakerOff" : {
                        "nodetype" : "namednumber",
                        "number" : "3"
                    },
                },
            },
            "access" : "readonly",
            "description" :
                """Only applicable to groups with breaker.  Indicates whether a breaker is turned
off or on.""",
        }, # column
        "pdu2Environment" : {
            "nodetype" : "node",
            "moduleName" : "CPQPOWER-MIB",
            "oid" : "1.3.6.1.4.1.232.165.7.4",
        }, # node
        "pdu2EnvProbeTable" : {
            "nodetype" : "table",
            "moduleName" : "CPQPOWER-MIB",
            "oid" : "1.3.6.1.4.1.232.165.7.4.1",
            "status" : "current",
            "description" :
                """A list of environment probe (1 per PDU) for temperature, humidity, and contacts.  
The number of entries is given by number of PDUs in daisy chain.""",
        }, # table
        "pdu2EnvProbeEntry" : {
            "nodetype" : "row",
            "moduleName" : "CPQPOWER-MIB",
            "oid" : "1.3.6.1.4.1.232.165.7.4.1.1",
            "status" : "current",
            "linkage" : [
                "pdu2IdentIndex",
            ],
            "description" :
                """Aggregate entries equal to number of PDUs.""",
        }, # row
        "pdu2TemperatureScale" : {
            "nodetype" : "column",
            "moduleName" : "CPQPOWER-MIB",
            "oid" : "1.3.6.1.4.1.232.165.7.4.1.1.1",
            "status" : "current",
            "syntax" : {
                "type" :                 {
                    "basetype" : "Enumeration",
                    "celsius" : {
                        "nodetype" : "namednumber",
                        "number" : "1"
                    },
                    "fahrenheit" : {
                        "nodetype" : "namednumber",
                        "number" : "2"
                    },
                },
            },
            "access" : "readonly",
            "description" :
                """Scale used to return temperature objects.""",
        }, # column
        "pdu2TemperatureCount" : {
            "nodetype" : "column",
            "moduleName" : "CPQPOWER-MIB",
            "oid" : "1.3.6.1.4.1.232.165.7.4.1.1.2",
            "status" : "current",
            "syntax" : {
                "type" : { "module" :"", "name" : "Integer32"},
            },
            "access" : "readonly",
            "description" :
                """Max number of temperature measurements (1 per probe).""",
        }, # column
        "pdu2HumidityCount" : {
            "nodetype" : "column",
            "moduleName" : "CPQPOWER-MIB",
            "oid" : "1.3.6.1.4.1.232.165.7.4.1.1.3",
            "status" : "current",
            "syntax" : {
                "type" : { "module" :"", "name" : "Integer32"},
            },
            "access" : "readonly",
            "description" :
                """Max number of humidity measurements  (1 per probe).""",
        }, # column
        "pdu2ContactCount" : {
            "nodetype" : "column",
            "moduleName" : "CPQPOWER-MIB",
            "oid" : "1.3.6.1.4.1.232.165.7.4.1.1.4",
            "status" : "current",
            "syntax" : {
                "type" : { "module" :"", "name" : "Integer32"},
            },
            "access" : "readonly",
            "description" :
                """Max number of contact sensors  (1 per probe).""",
        }, # column
        "pdu2TemperatureTable" : {
            "nodetype" : "table",
            "moduleName" : "CPQPOWER-MIB",
            "oid" : "1.3.6.1.4.1.232.165.7.4.2",
            "status" : "current",
            "description" :
                """A list of temperature probe measurements.  The number of entries are
given by number of pdu and pdu2TemperatureCount.""",
        }, # table
        "pdu2TemperatureEntry" : {
            "nodetype" : "row",
            "moduleName" : "CPQPOWER-MIB",
            "oid" : "1.3.6.1.4.1.232.165.7.4.2.1",
            "status" : "current",
            "linkage" : [
                "pdu2IdentIndex",
                "pdu2TemperatureIndex",
            ],
            "description" :
                """An entry for a temperature measurement.""",
        }, # row
        "pdu2TemperatureIndex" : {
            "nodetype" : "column",
            "moduleName" : "CPQPOWER-MIB",
            "oid" : "1.3.6.1.4.1.232.165.7.4.2.1.1",
            "status" : "current",
            "syntax" : {
                "type" :                 {
                    "basetype" : "Integer32",
                    "ranges" : [
                    {
                        "min" : "1",
                        "max" : "2"
                    },
                    ],
                    "range" : {
                        "min" : "1",
                        "max" : "2"
                    },
                },
            },
            "access" : "readonly",
            "description" :
                """A unique value for each temperature probe measurement.  Its value
ranges from 1 to temperatureCount.""",
        }, # column
        "pdu2TemperatureName" : {
            "nodetype" : "column",
            "moduleName" : "CPQPOWER-MIB",
            "oid" : "1.3.6.1.4.1.232.165.7.4.2.1.2",
            "status" : "current",
            "syntax" : {
                "type" :                 {
                    "basetype" : "OctetString",
                    "parent module" : {
                        "name" : "RFC1213-MIB",
                        "type" : "DisplayString",
                    },
                    "ranges" : [
                    {
                        "min" : "1",
                        "max" : "31"
                    },
                    ],
                    "range" : {
                        "min" : "1",
                        "max" : "31"
                    },
                },
            },
            "access" : "readonly",
            "description" :
                """A descriptive name for the temperature probe.""",
        }, # column
        "pdu2TemperatureProbeStatus" : {
            "nodetype" : "column",
            "moduleName" : "CPQPOWER-MIB",
            "oid" : "1.3.6.1.4.1.232.165.7.4.2.1.3",
            "status" : "current",
            "syntax" : {
                "type" :                 {
                    "basetype" : "Enumeration",
                    "disconnected" : {
                        "nodetype" : "namednumber",
                        "number" : "1"
                    },
                    "connected" : {
                        "nodetype" : "namednumber",
                        "number" : "2"
                    },
                    "bad" : {
                        "nodetype" : "namednumber",
                        "number" : "3"
                    },
                },
            },
            "access" : "readonly",
            "description" :
                """Indicates whether a probe is connected or not.""",
        }, # column
        "pdu2TemperatureValue" : {
            "nodetype" : "column",
            "moduleName" : "CPQPOWER-MIB",
            "oid" : "1.3.6.1.4.1.232.165.7.4.2.1.4",
            "status" : "current",
            "syntax" : {
                "type" : { "module" :"", "name" : "Integer32"},
            },
            "access" : "readonly",
            "description" :
                """Units are in tenths of a degree (either Fahrenheit or Celsius). 
Divide by ten to get degrees.""",
        }, # column
        "pdu2TemperatureThStatus" : {
            "nodetype" : "column",
            "moduleName" : "CPQPOWER-MIB",
            "oid" : "1.3.6.1.4.1.232.165.7.4.2.1.5",
            "status" : "current",
            "syntax" : {
                "type" :                 {
                    "basetype" : "Enumeration",
                    "good" : {
                        "nodetype" : "namednumber",
                        "number" : "1"
                    },
                    "lowWarning" : {
                        "nodetype" : "namednumber",
                        "number" : "2"
                    },
                    "lowCritical" : {
                        "nodetype" : "namednumber",
                        "number" : "3"
                    },
                    "highWarning" : {
                        "nodetype" : "namednumber",
                        "number" : "4"
                    },
                    "highCritical" : {
                        "nodetype" : "namednumber",
                        "number" : "5"
                    },
                },
            },
            "access" : "readonly",
            "description" :
                """Status of the measured temperature relative to the configured thresholds.""",
        }, # column
        "pdu2TemperatureThLowerWarning" : {
            "nodetype" : "column",
            "moduleName" : "CPQPOWER-MIB",
            "oid" : "1.3.6.1.4.1.232.165.7.4.2.1.6",
            "status" : "current",
            "syntax" : {
                "type" :                 {
                    "basetype" : "Integer32",
                    "ranges" : [
                    {
                        "min" : "-1",
                        "max" : "150000"
                    },
                    ],
                    "range" : {
                        "min" : "-1",
                        "max" : "150000"
                    },
                },
            },
            "access" : "readonly",
            "description" :
                """Lower warning threshold.  Units are tenths of a degree.  A negative value
indicates that this object is not available.""",
        }, # column
        "pdu2TemperatureThLowerCritical" : {
            "nodetype" : "column",
            "moduleName" : "CPQPOWER-MIB",
            "oid" : "1.3.6.1.4.1.232.165.7.4.2.1.7",
            "status" : "current",
            "syntax" : {
                "type" :                 {
                    "basetype" : "Integer32",
                    "ranges" : [
                    {
                        "min" : "-1",
                        "max" : "150000"
                    },
                    ],
                    "range" : {
                        "min" : "-1",
                        "max" : "150000"
                    },
                },
            },
            "access" : "readonly",
            "description" :
                """Lower critical threshold.  Units are tenths of a degree.  A negative value
indicates that this object is not available.""",
        }, # column
        "pdu2TemperatureThUpperWarning" : {
            "nodetype" : "column",
            "moduleName" : "CPQPOWER-MIB",
            "oid" : "1.3.6.1.4.1.232.165.7.4.2.1.8",
            "status" : "current",
            "syntax" : {
                "type" :                 {
                    "basetype" : "Integer32",
                    "ranges" : [
                    {
                        "min" : "-1",
                        "max" : "150000"
                    },
                    ],
                    "range" : {
                        "min" : "-1",
                        "max" : "150000"
                    },
                },
            },
            "access" : "readonly",
            "description" :
                """Upper warning threshold.  Units are tenths of a degree.  A negative value
indicates that this object is not available.""",
        }, # column
        "pdu2TemperatureThUpperCritical" : {
            "nodetype" : "column",
            "moduleName" : "CPQPOWER-MIB",
            "oid" : "1.3.6.1.4.1.232.165.7.4.2.1.9",
            "status" : "current",
            "syntax" : {
                "type" :                 {
                    "basetype" : "Integer32",
                    "ranges" : [
                    {
                        "min" : "-1",
                        "max" : "150000"
                    },
                    ],
                    "range" : {
                        "min" : "-1",
                        "max" : "150000"
                    },
                },
            },
            "access" : "readonly",
            "description" :
                """Upper critical threshold.  Units are tenths of a degree.  A negative value
indicates that this object is not available.""",
        }, # column
        "pdu2HumidityTable" : {
            "nodetype" : "table",
            "moduleName" : "CPQPOWER-MIB",
            "oid" : "1.3.6.1.4.1.232.165.7.4.3",
            "status" : "current",
            "description" :
                """A list of humidity probe measurements.  The number of entries are
given by number of pdu and pdu2HumidityCount.""",
        }, # table
        "pdu2HumidityEntry" : {
            "nodetype" : "row",
            "moduleName" : "CPQPOWER-MIB",
            "oid" : "1.3.6.1.4.1.232.165.7.4.3.1",
            "status" : "current",
            "linkage" : [
                "pdu2IdentIndex",
                "pdu2HumidityIndex",
            ],
            "description" :
                """An entry for a humidity measurement.""",
        }, # row
        "pdu2HumidityIndex" : {
            "nodetype" : "column",
            "moduleName" : "CPQPOWER-MIB",
            "oid" : "1.3.6.1.4.1.232.165.7.4.3.1.1",
            "status" : "current",
            "syntax" : {
                "type" :                 {
                    "basetype" : "Integer32",
                    "ranges" : [
                    {
                        "min" : "1",
                        "max" : "2"
                    },
                    ],
                    "range" : {
                        "min" : "1",
                        "max" : "2"
                    },
                },
            },
            "access" : "readonly",
            "description" :
                """A unique value for each humidity probe measurement.  Its value
ranges from 1 to pdu2HumidityCount per pdu.""",
        }, # column
        "pdu2HumidityName" : {
            "nodetype" : "column",
            "moduleName" : "CPQPOWER-MIB",
            "oid" : "1.3.6.1.4.1.232.165.7.4.3.1.2",
            "status" : "current",
            "syntax" : {
                "type" :                 {
                    "basetype" : "OctetString",
                    "parent module" : {
                        "name" : "RFC1213-MIB",
                        "type" : "DisplayString",
                    },
                    "ranges" : [
                    {
                        "min" : "1",
                        "max" : "31"
                    },
                    ],
                    "range" : {
                        "min" : "1",
                        "max" : "31"
                    },
                },
            },
            "access" : "readonly",
            "description" :
                """A descriptive name for the humidity probe.""",
        }, # column
        "pdu2HumidityProbeStatus" : {
            "nodetype" : "column",
            "moduleName" : "CPQPOWER-MIB",
            "oid" : "1.3.6.1.4.1.232.165.7.4.3.1.3",
            "status" : "current",
            "syntax" : {
                "type" :                 {
                    "basetype" : "Enumeration",
                    "disconnected" : {
                        "nodetype" : "namednumber",
                        "number" : "1"
                    },
                    "connected" : {
                        "nodetype" : "namednumber",
                        "number" : "2"
                    },
                    "bad" : {
                        "nodetype" : "namednumber",
                        "number" : "3"
                    },
                },
            },
            "access" : "readonly",
            "description" :
                """Indicates whether a probe is connected or not.""",
        }, # column
        "pdu2HumidityValue" : {
            "nodetype" : "column",
            "moduleName" : "CPQPOWER-MIB",
            "oid" : "1.3.6.1.4.1.232.165.7.4.3.1.4",
            "status" : "current",
            "syntax" : {
                "type" : { "module" :"", "name" : "Integer32"},
            },
            "access" : "readonly",
            "description" :
                """Units are tenths of a percent relative humidity.  Divide the value by 10 to get %RH.""",
        }, # column
        "pdu2HumidityThStatus" : {
            "nodetype" : "column",
            "moduleName" : "CPQPOWER-MIB",
            "oid" : "1.3.6.1.4.1.232.165.7.4.3.1.5",
            "status" : "current",
            "syntax" : {
                "type" :                 {
                    "basetype" : "Enumeration",
                    "good" : {
                        "nodetype" : "namednumber",
                        "number" : "1"
                    },
                    "lowWarning" : {
                        "nodetype" : "namednumber",
                        "number" : "2"
                    },
                    "lowCritical" : {
                        "nodetype" : "namednumber",
                        "number" : "3"
                    },
                    "highWarning" : {
                        "nodetype" : "namednumber",
                        "number" : "4"
                    },
                    "highCritical" : {
                        "nodetype" : "namednumber",
                        "number" : "5"
                    },
                },
            },
            "access" : "readonly",
            "description" :
                """Status of the measured humidity relative to the configured thresholds.""",
        }, # column
        "pdu2HumidityThLowerWarning" : {
            "nodetype" : "column",
            "moduleName" : "CPQPOWER-MIB",
            "oid" : "1.3.6.1.4.1.232.165.7.4.3.1.6",
            "status" : "current",
            "syntax" : {
                "type" :                 {
                    "basetype" : "Integer32",
                    "ranges" : [
                    {
                        "min" : "-1",
                        "max" : "1000"
                    },
                    ],
                    "range" : {
                        "min" : "-1",
                        "max" : "1000"
                    },
                },
            },
            "access" : "readonly",
            "description" :
                """Lower warning threshold.  Units are 0.1 %RH.  A negative value
indicates that this object is not available.""",
        }, # column
        "pdu2HumidityThLowerCritical" : {
            "nodetype" : "column",
            "moduleName" : "CPQPOWER-MIB",
            "oid" : "1.3.6.1.4.1.232.165.7.4.3.1.7",
            "status" : "current",
            "syntax" : {
                "type" :                 {
                    "basetype" : "Integer32",
                    "ranges" : [
                    {
                        "min" : "-1",
                        "max" : "1000"
                    },
                    ],
                    "range" : {
                        "min" : "-1",
                        "max" : "1000"
                    },
                },
            },
            "access" : "readonly",
            "description" :
                """Lower critical threshold.  Units are 0.1 %RH.  A negative value
indicates that this object is not available.""",
        }, # column
        "pdu2HumidityThUpperWarning" : {
            "nodetype" : "column",
            "moduleName" : "CPQPOWER-MIB",
            "oid" : "1.3.6.1.4.1.232.165.7.4.3.1.8",
            "status" : "current",
            "syntax" : {
                "type" :                 {
                    "basetype" : "Integer32",
                    "ranges" : [
                    {
                        "min" : "-1",
                        "max" : "1000"
                    },
                    ],
                    "range" : {
                        "min" : "-1",
                        "max" : "1000"
                    },
                },
            },
            "access" : "readonly",
            "description" :
                """Upper warning threshold.  Units are 0.1 %RH.  A negative value
indicates that this object is not available.""",
        }, # column
        "pdu2HumidityThUpperCritical" : {
            "nodetype" : "column",
            "moduleName" : "CPQPOWER-MIB",
            "oid" : "1.3.6.1.4.1.232.165.7.4.3.1.9",
            "status" : "current",
            "syntax" : {
                "type" :                 {
                    "basetype" : "Integer32",
                    "ranges" : [
                    {
                        "min" : "-1",
                        "max" : "1000"
                    },
                    ],
                    "range" : {
                        "min" : "-1",
                        "max" : "1000"
                    },
                },
            },
            "access" : "readonly",
            "description" :
                """Upper critical threshold.  Units are 0.1 %RH.  A negative value
indicates that this object is not available.""",
        }, # column
        "pdu2ContactTable" : {
            "nodetype" : "table",
            "moduleName" : "CPQPOWER-MIB",
            "oid" : "1.3.6.1.4.1.232.165.7.4.4",
            "status" : "current",
            "description" :
                """A list of contact sensors.  The number of entries are
given by number of pdu and pdu2ContactCount.""",
        }, # table
        "pdu2ContactEntry" : {
            "nodetype" : "row",
            "moduleName" : "CPQPOWER-MIB",
            "oid" : "1.3.6.1.4.1.232.165.7.4.4.1",
            "status" : "current",
            "linkage" : [
                "pdu2IdentIndex",
                "pdu2ContactIndex",
            ],
            "description" :
                """An entry for a contact sensor""",
        }, # row
        "pdu2ContactIndex" : {
            "nodetype" : "column",
            "moduleName" : "CPQPOWER-MIB",
            "oid" : "1.3.6.1.4.1.232.165.7.4.4.1.1",
            "status" : "current",
            "syntax" : {
                "type" :                 {
                    "basetype" : "Integer32",
                    "ranges" : [
                    {
                        "min" : "1",
                        "max" : "3"
                    },
                    ],
                    "range" : {
                        "min" : "1",
                        "max" : "3"
                    },
                },
            },
            "access" : "readonly",
            "description" :
                """A unique value for each contact sensor.  Its value ranges from 1 to
contactCount.""",
        }, # column
        "pdu2ContactName" : {
            "nodetype" : "column",
            "moduleName" : "CPQPOWER-MIB",
            "oid" : "1.3.6.1.4.1.232.165.7.4.4.1.2",
            "status" : "current",
            "syntax" : {
                "type" :                 {
                    "basetype" : "OctetString",
                    "parent module" : {
                        "name" : "RFC1213-MIB",
                        "type" : "DisplayString",
                    },
                    "ranges" : [
                    {
                        "min" : "1",
                        "max" : "31"
                    },
                    ],
                    "range" : {
                        "min" : "1",
                        "max" : "31"
                    },
                },
            },
            "access" : "readonly",
            "description" :
                """A descriptive name for the contact sensor.""",
        }, # column
        "pdu2ContactProbeStatus" : {
            "nodetype" : "column",
            "moduleName" : "CPQPOWER-MIB",
            "oid" : "1.3.6.1.4.1.232.165.7.4.4.1.3",
            "status" : "current",
            "syntax" : {
                "type" :                 {
                    "basetype" : "Enumeration",
                    "disconnected" : {
                        "nodetype" : "namednumber",
                        "number" : "1"
                    },
                    "connected" : {
                        "nodetype" : "namednumber",
                        "number" : "2"
                    },
                    "bad" : {
                        "nodetype" : "namednumber",
                        "number" : "3"
                    },
                },
            },
            "access" : "readonly",
            "description" :
                """Indicates whether a probe is connected or not.
Will not be returned  if the contact sensor is internal to the ePDU,
in that case only contactState should be read.""",
        }, # column
        "pdu2ContactState" : {
            "nodetype" : "column",
            "moduleName" : "CPQPOWER-MIB",
            "oid" : "1.3.6.1.4.1.232.165.7.4.4.1.4",
            "status" : "current",
            "syntax" : {
                "type" :                 {
                    "basetype" : "Enumeration",
                    "contactOpen" : {
                        "nodetype" : "namednumber",
                        "number" : "1"
                    },
                    "contactClosed" : {
                        "nodetype" : "namednumber",
                        "number" : "2"
                    },
                    "contactBad" : {
                        "nodetype" : "namednumber",
                        "number" : "3"
                    },
                },
            },
            "access" : "readonly",
            "description" :
                """The state of the contact sensor.""",
        }, # column
        "pdu2Outlet" : {
            "nodetype" : "node",
            "moduleName" : "CPQPOWER-MIB",
            "oid" : "1.3.6.1.4.1.232.165.7.5",
        }, # node
        "pdu2OutletTable" : {
            "nodetype" : "table",
            "moduleName" : "CPQPOWER-MIB",
            "oid" : "1.3.6.1.4.1.232.165.7.5.1",
            "status" : "current",
            "description" :
                """Aggregate Object with number of entries equal to Number of PDU (pdu2IdentIndex)
and Number of outlet per PDU (pdu2OutletIndex).""",
        }, # table
        "pdu2OutletEntry" : {
            "nodetype" : "row",
            "moduleName" : "CPQPOWER-MIB",
            "oid" : "1.3.6.1.4.1.232.165.7.5.1.1",
            "status" : "current",
            "linkage" : [
                "pdu2IdentIndex",
                "pdu2OutletIndex",
            ],
            "description" :
                """The Outlet table entry containing the type, voltage, current etc.""",
        }, # row
        "pdu2OutletIndex" : {
            "nodetype" : "column",
            "moduleName" : "CPQPOWER-MIB",
            "oid" : "1.3.6.1.4.1.232.165.7.5.1.1.1",
            "status" : "current",
            "syntax" : {
                "type" :                 {
                    "basetype" : "Integer32",
                    "ranges" : [
                    {
                        "min" : "0",
                        "max" : "100"
                    },
                    ],
                    "range" : {
                        "min" : "0",
                        "max" : "100"
                    },
                },
            },
            "access" : "readonly",
            "description" :
                """Index for each outlet, value from 1 to the number of outlets per PDU.""",
        }, # column
        "pdu2OutletName" : {
            "nodetype" : "column",
            "moduleName" : "CPQPOWER-MIB",
            "oid" : "1.3.6.1.4.1.232.165.7.5.1.1.2",
            "status" : "current",
            "syntax" : {
                "type" :                 {
                    "basetype" : "OctetString",
                    "parent module" : {
                        "name" : "RFC1213-MIB",
                        "type" : "DisplayString",
                    },
                    "ranges" : [
                    {
                        "min" : "1",
                        "max" : "31"
                    },
                    ],
                    "range" : {
                        "min" : "1",
                        "max" : "31"
                    },
                },
            },
            "access" : "readonly",
            "description" :
                """A descriptive name for the outlet.""",
        }, # column
        "pdu2OutletType" : {
            "nodetype" : "column",
            "moduleName" : "CPQPOWER-MIB",
            "oid" : "1.3.6.1.4.1.232.165.7.5.1.1.3",
            "status" : "current",
            "syntax" : {
                "type" :                 {
                    "basetype" : "Enumeration",
                    "iecC13" : {
                        "nodetype" : "namednumber",
                        "number" : "1"
                    },
                    "iecC19" : {
                        "nodetype" : "namednumber",
                        "number" : "2"
                    },
                    "uk" : {
                        "nodetype" : "namednumber",
                        "number" : "10"
                    },
                    "french" : {
                        "nodetype" : "namednumber",
                        "number" : "11"
                    },
                    "schuko" : {
                        "nodetype" : "namednumber",
                        "number" : "12"
                    },
                    "nema515" : {
                        "nodetype" : "namednumber",
                        "number" : "20"
                    },
                    "nema51520" : {
                        "nodetype" : "namednumber",
                        "number" : "21"
                    },
                    "nema520" : {
                        "nodetype" : "namednumber",
                        "number" : "22"
                    },
                    "nemaL520" : {
                        "nodetype" : "namednumber",
                        "number" : "23"
                    },
                    "nemaL530" : {
                        "nodetype" : "namednumber",
                        "number" : "24"
                    },
                    "nema615" : {
                        "nodetype" : "namednumber",
                        "number" : "25"
                    },
                    "nema620" : {
                        "nodetype" : "namednumber",
                        "number" : "26"
                    },
                    "nemaL620" : {
                        "nodetype" : "namednumber",
                        "number" : "27"
                    },
                    "nemaL630" : {
                        "nodetype" : "namednumber",
                        "number" : "28"
                    },
                    "nemaL715" : {
                        "nodetype" : "namednumber",
                        "number" : "29"
                    },
                    "rf203p277" : {
                        "nodetype" : "namednumber",
                        "number" : "30"
                    },
                },
            },
            "access" : "readonly",
            "description" :
                """Type of this outlet - C13, C19.""",
        }, # column
        "pdu2OutletCurrentRating" : {
            "nodetype" : "column",
            "moduleName" : "CPQPOWER-MIB",
            "oid" : "1.3.6.1.4.1.232.165.7.5.1.1.4",
            "status" : "current",
            "syntax" : {
                "type" : { "module" :"", "name" : "Integer32"},
            },
            "access" : "readonly",
            "description" :
                """Rated current capacity of this outlet.  Units are milliamps.  A negative 
value indicates that the hardware current capacity is unknown.""",
        }, # column
        "pdu2OutletCurrent" : {
            "nodetype" : "column",
            "moduleName" : "CPQPOWER-MIB",
            "oid" : "1.3.6.1.4.1.232.165.7.5.1.1.5",
            "status" : "current",
            "syntax" : {
                "type" : { "module" :"", "name" : "Integer32"},
            },
            "access" : "readonly",
            "description" :
                """A outlet current measurement value.  Units are milliamps.""",
        }, # column
        "pdu2OutletCurrentThStatus" : {
            "nodetype" : "column",
            "moduleName" : "CPQPOWER-MIB",
            "oid" : "1.3.6.1.4.1.232.165.7.5.1.1.6",
            "status" : "current",
            "syntax" : {
                "type" :                 {
                    "basetype" : "Enumeration",
                    "good" : {
                        "nodetype" : "namednumber",
                        "number" : "1"
                    },
                    "lowWarning" : {
                        "nodetype" : "namednumber",
                        "number" : "2"
                    },
                    "lowCritical" : {
                        "nodetype" : "namednumber",
                        "number" : "3"
                    },
                    "highWarning" : {
                        "nodetype" : "namednumber",
                        "number" : "4"
                    },
                    "highCritical" : {
                        "nodetype" : "namednumber",
                        "number" : "5"
                    },
                },
            },
            "access" : "readonly",
            "description" :
                """Status of the measured outlet current relative to the configured thresholds.""",
        }, # column
        "pdu2OutletCurrentThLowerWarning" : {
            "nodetype" : "column",
            "moduleName" : "CPQPOWER-MIB",
            "oid" : "1.3.6.1.4.1.232.165.7.5.1.1.7",
            "status" : "current",
            "syntax" : {
                "type" :                 {
                    "basetype" : "Integer32",
                    "ranges" : [
                    {
                        "min" : "-1",
                        "max" : "100000"
                    },
                    ],
                    "range" : {
                        "min" : "-1",
                        "max" : "100000"
                    },
                },
            },
            "access" : "readonly",
            "description" :
                """Lower warning threshold.  Units are milliamps.  A negative value indicates
that this object is not available.""",
        }, # column
        "pdu2OutletCurrentThLowerCritical" : {
            "nodetype" : "column",
            "moduleName" : "CPQPOWER-MIB",
            "oid" : "1.3.6.1.4.1.232.165.7.5.1.1.8",
            "status" : "current",
            "syntax" : {
                "type" :                 {
                    "basetype" : "Integer32",
                    "ranges" : [
                    {
                        "min" : "-1",
                        "max" : "100000"
                    },
                    ],
                    "range" : {
                        "min" : "-1",
                        "max" : "100000"
                    },
                },
            },
            "access" : "readonly",
            "description" :
                """Lower critical threshold.  Units are milliamps.  A negative value indicates
that this object is not available.""",
        }, # column
        "pdu2OutletCurrentThUpperWarning" : {
            "nodetype" : "column",
            "moduleName" : "CPQPOWER-MIB",
            "oid" : "1.3.6.1.4.1.232.165.7.5.1.1.9",
            "status" : "current",
            "syntax" : {
                "type" :                 {
                    "basetype" : "Integer32",
                    "ranges" : [
                    {
                        "min" : "-1",
                        "max" : "100000"
                    },
                    ],
                    "range" : {
                        "min" : "-1",
                        "max" : "100000"
                    },
                },
            },
            "access" : "readonly",
            "description" :
                """Upper warning threshold.  Units are milliamps.  A negative value indicates
that this object is not available.""",
        }, # column
        "pdu2OutletCurrentThUpperCritical" : {
            "nodetype" : "column",
            "moduleName" : "CPQPOWER-MIB",
            "oid" : "1.3.6.1.4.1.232.165.7.5.1.1.10",
            "status" : "current",
            "syntax" : {
                "type" :                 {
                    "basetype" : "Integer32",
                    "ranges" : [
                    {
                        "min" : "-1",
                        "max" : "100000"
                    },
                    ],
                    "range" : {
                        "min" : "-1",
                        "max" : "100000"
                    },
                },
            },
            "access" : "readonly",
            "description" :
                """Upper critical threshold.  Units are milliamps.  A negative value indicates
that this object is not available.""",
        }, # column
        "pdu2OutletCurrentCrestFactor" : {
            "nodetype" : "column",
            "moduleName" : "CPQPOWER-MIB",
            "oid" : "1.3.6.1.4.1.232.165.7.5.1.1.11",
            "status" : "current",
            "syntax" : {
                "type" : { "module" :"", "name" : "Integer32"},
            },
            "access" : "readonly",
            "description" :
                """Current crest factor.  Units are in milli, for example a crest factor of
1.414 will be returned as 1414.  A negative value indicates
         that this object is not available.""",
        }, # column
        "pdu2OutletCurrentPercentLoad" : {
            "nodetype" : "column",
            "moduleName" : "CPQPOWER-MIB",
            "oid" : "1.3.6.1.4.1.232.165.7.5.1.1.12",
            "status" : "current",
            "syntax" : {
                "type" : { "module" :"", "name" : "Integer32"},
            },
            "access" : "readonly",
            "description" :
                """Current percent load, based on the rated current capacity.  Units are
percentage, for example 80% will be returned as 80.  A negative
value indicates that this object is not available.""",
        }, # column
        "pdu2OutletVA" : {
            "nodetype" : "column",
            "moduleName" : "CPQPOWER-MIB",
            "oid" : "1.3.6.1.4.1.232.165.7.5.1.1.13",
            "status" : "current",
            "syntax" : {
                "type" : { "module" :"", "name" : "Integer32"},
            },
            "access" : "readonly",
            "description" :
                """A outlet VA value.  Units are VA.  A negative value indicates
that this object is not available.""",
        }, # column
        "pdu2OutletWatts" : {
            "nodetype" : "column",
            "moduleName" : "CPQPOWER-MIB",
            "oid" : "1.3.6.1.4.1.232.165.7.5.1.1.14",
            "status" : "current",
            "syntax" : {
                "type" : { "module" :"", "name" : "Integer32"},
            },
            "access" : "readonly",
            "description" :
                """A outlet Watts value.  Units are Watts.  A negative value indicates
that this object is not available.""",
        }, # column
        "pdu2OutletWh" : {
            "nodetype" : "column",
            "moduleName" : "CPQPOWER-MIB",
            "oid" : "1.3.6.1.4.1.232.165.7.5.1.1.15",
            "status" : "current",
            "syntax" : {
                "type" : { "module" :"", "name" : "Integer32"},
            },
            "access" : "readonly",
            "description" :
                """A Watt-Hour value for each outlet.  Units are WH.
This object is writable so that it can be reset to 0.  When it is
written to, the pdu2OutletWhTimer will be reset updated as well    
A negative value indicates that this object is not available.""",
        }, # column
        "pdu2OutletWhTimer" : {
            "nodetype" : "column",
            "moduleName" : "CPQPOWER-MIB",
            "oid" : "1.3.6.1.4.1.232.165.7.5.1.1.16",
            "status" : "current",
            "syntax" : {
                "type" :                 {
                    "basetype" : "OctetString",
                    "parent module" : {
                        "name" : "RFC1213-MIB",
                        "type" : "DisplayString",
                    },
                    "ranges" : [
                    {
                        "min" : "0",
                        "max" : "22"
                    },
                    ],
                    "range" : {
                        "min" : "0",
                        "max" : "22"
                    },
                },
            },
            "access" : "readonly",
            "description" :
                """Timestamp (date and time) of outlet Watt-hours was last reset.""",
        }, # column
        "pdu2OutletPowerFactor" : {
            "nodetype" : "column",
            "moduleName" : "CPQPOWER-MIB",
            "oid" : "1.3.6.1.4.1.232.165.7.5.1.1.17",
            "status" : "current",
            "syntax" : {
                "type" : { "module" :"", "name" : "Integer32"},
            },
            "access" : "readonly",
            "description" :
                """An outlet PF value.  Units are in thousandths, for example a power factor
of 0.958 would be returned as 958, and 0.92 would be returned 
         as 920.  A negative value indicates that this object is not available.""",
        }, # column
        "pdu2OutletVAR" : {
            "nodetype" : "column",
            "moduleName" : "CPQPOWER-MIB",
            "oid" : "1.3.6.1.4.1.232.165.7.5.1.1.18",
            "status" : "current",
            "syntax" : {
                "type" : { "module" :"", "name" : "Integer32"},
            },
            "access" : "readonly",
            "description" :
                """An outlet VAR value.  Units are VAR.  A negative value indicates
that this object is not available.""",
        }, # column
        "pdu2OutletControlTable" : {
            "nodetype" : "table",
            "moduleName" : "CPQPOWER-MIB",
            "oid" : "1.3.6.1.4.1.232.165.7.5.2",
            "status" : "current",
            "description" :
                """Aggregate Object with number of entries equal to Number of PDU (pdu2IdentIndex) 
and Number of outlets per PDU (pdu2OutletIndex).""",
        }, # table
        "pdu2OutletControlEntry" : {
            "nodetype" : "row",
            "moduleName" : "CPQPOWER-MIB",
            "oid" : "1.3.6.1.4.1.232.165.7.5.2.1",
            "status" : "current",
            "linkage" : [
                "pdu2IdentIndex",
                "pdu2OutletIndex",
            ],
            "description" :
                """The Outlet table entry containing the type, voltage, current etc.""",
        }, # row
        "pdu2OutletControlStatus" : {
            "nodetype" : "column",
            "moduleName" : "CPQPOWER-MIB",
            "oid" : "1.3.6.1.4.1.232.165.7.5.2.1.1",
            "status" : "current",
            "syntax" : {
                "type" :                 {
                    "basetype" : "Enumeration",
                    "off" : {
                        "nodetype" : "namednumber",
                        "number" : "1"
                    },
                    "on" : {
                        "nodetype" : "namednumber",
                        "number" : "2"
                    },
                    "pendingOff" : {
                        "nodetype" : "namednumber",
                        "number" : "3"
                    },
                    "pendingOn" : {
                        "nodetype" : "namednumber",
                        "number" : "4"
                    },
                },
            },
            "access" : "readonly",
            "description" :
                """current state of a control outlet.""",
        }, # column
        "pdu2OutletControlOffCmd" : {
            "nodetype" : "column",
            "moduleName" : "CPQPOWER-MIB",
            "oid" : "1.3.6.1.4.1.232.165.7.5.2.1.2",
            "status" : "current",
            "syntax" : {
                "type" :                 {
                    "basetype" : "Integer32",
                    "ranges" : [
                    {
                        "min" : "-1",
                        "max" : "99999"
                    },
                    ],
                    "range" : {
                        "min" : "-1",
                        "max" : "99999"
                    },
                },
            },
            "access" : "readwrite",
            "description" :
                """When write, once issued, the outlet will turn Off immediately.
0-n: Time in seconds until the outlet command is issued
-1: Cancel a pending outlet Off command
 When read, returns -1 if no command is pending, or the current downcount in 
seconds of a pending command.""",
        }, # column
        "pdu2OutletControlOnCmd" : {
            "nodetype" : "column",
            "moduleName" : "CPQPOWER-MIB",
            "oid" : "1.3.6.1.4.1.232.165.7.5.2.1.3",
            "status" : "current",
            "syntax" : {
                "type" :                 {
                    "basetype" : "Integer32",
                    "ranges" : [
                    {
                        "min" : "-1",
                        "max" : "99999"
                    },
                    ],
                    "range" : {
                        "min" : "-1",
                        "max" : "99999"
                    },
                },
            },
            "access" : "readwrite",
            "description" :
                """When write, once issued, the outlet will turn On immediately.
0-n: Time in seconds until the outlet command is issued
-1: Cancel a pending outlet On command
 When read, returns -1 if no command is pending, or the current downcount in 
seconds of a pending command.""",
        }, # column
        "pdu2OutletControlRebootCmd" : {
            "nodetype" : "column",
            "moduleName" : "CPQPOWER-MIB",
            "oid" : "1.3.6.1.4.1.232.165.7.5.2.1.4",
            "status" : "current",
            "syntax" : {
                "type" :                 {
                    "basetype" : "Integer32",
                    "ranges" : [
                    {
                        "min" : "-1",
                        "max" : "99999"
                    },
                    ],
                    "range" : {
                        "min" : "-1",
                        "max" : "99999"
                    },
                },
            },
            "access" : "readwrite",
            "description" :
                """When write, for outlets that are On prior to this Reboot command, they will 
switch Off immediately when the command is issued, remain Off for 
outletControlRebootOffTime seconds, and then turn back On.
 For outlets that are Off prior to the Reboot command, they will turn On after 
a delay of outletControlRebootOffTime seconds from when the command is issued.
 0-n : Time in seconds until the Reboot command is issued
 -1 : Cancel a pending outlet Reboot command 

When read, returns -1 if no command is pending, or the current downcount in 
seconds of a pending command.""",
        }, # column
        "pdu2OutletControlPowerOnState" : {
            "nodetype" : "column",
            "moduleName" : "CPQPOWER-MIB",
            "oid" : "1.3.6.1.4.1.232.165.7.5.2.1.5",
            "status" : "current",
            "syntax" : {
                "type" :                 {
                    "basetype" : "Enumeration",
                    "off" : {
                        "nodetype" : "namednumber",
                        "number" : "1"
                    },
                    "on" : {
                        "nodetype" : "namednumber",
                        "number" : "2"
                    },
                    "lastState" : {
                        "nodetype" : "namednumber",
                        "number" : "3"
                    },
                },
            },
            "access" : "readwrite",
            "description" :
                """Determines the outlet state when power is applied to the unit.
1 : not restart at device startup
2 : should sequence back ON in line with outletControlSequenceTime
3 : should take the state the outlet had when power was lost.
If the state was ON, should sequence back ON in line with outletControlSequenceTime.""",
        }, # column
        "pdu2OutletControlSequenceDelay" : {
            "nodetype" : "column",
            "moduleName" : "CPQPOWER-MIB",
            "oid" : "1.3.6.1.4.1.232.165.7.5.2.1.6",
            "status" : "current",
            "syntax" : {
                "type" :                 {
                    "basetype" : "Integer32",
                    "ranges" : [
                    {
                        "min" : "-1",
                        "max" : "99999"
                    },
                    ],
                    "range" : {
                        "min" : "-1",
                        "max" : "99999"
                    },
                },
            },
            "access" : "readwrite",
            "description" :
                """Time delay in seconds from when a Global Sequence On command is issued to
when the command is executed on this outlet.  This delay is also used as a power-on
delay. Set to -1 to exclude this outlet from Global Sequence On commands.""",
        }, # column
        "pdu2OutletControlRebootOffTime" : {
            "nodetype" : "column",
            "moduleName" : "CPQPOWER-MIB",
            "oid" : "1.3.6.1.4.1.232.165.7.5.2.1.7",
            "status" : "current",
            "syntax" : {
                "type" :                 {
                    "basetype" : "Integer32",
                    "ranges" : [
                    {
                        "min" : "-1",
                        "max" : "99999"
                    },
                    ],
                    "range" : {
                        "min" : "-1",
                        "max" : "99999"
                    },
                },
            },
            "access" : "readwrite",
            "description" :
                """Time delay in seconds that the outlet should remain in the Off state when executing a Reboot command.""",
        }, # column
        "pdu2OutletControlSwitchable" : {
            "nodetype" : "column",
            "moduleName" : "CPQPOWER-MIB",
            "oid" : "1.3.6.1.4.1.232.165.7.5.2.1.8",
            "status" : "current",
            "syntax" : {
                "type" :                 {
                    "basetype" : "Enumeration",
                    "switchable" : {
                        "nodetype" : "namednumber",
                        "number" : "1"
                    },
                    "notSwitchable" : {
                        "nodetype" : "namednumber",
                        "number" : "2"
                    },
                },
            },
            "access" : "readwrite",
            "description" :
                """Determines the outlet capability to be controlled On/Off from the communication channels.
1 : control On/Off enabled
2 : control On/Off disabled.""",
        }, # column
        "pdu2OutletControlShutoffDelay" : {
            "nodetype" : "column",
            "moduleName" : "CPQPOWER-MIB",
            "oid" : "1.3.6.1.4.1.232.165.7.5.2.1.9",
            "status" : "current",
            "syntax" : {
                "type" :                 {
                    "basetype" : "Integer32",
                    "ranges" : [
                    {
                        "min" : "-1",
                        "max" : "99999"
                    },
                    ],
                    "range" : {
                        "min" : "-1",
                        "max" : "99999"
                    },
                },
            },
            "access" : "readwrite",
            "description" :
                """Time delay in seconds that could be taken in account before shutting of the outlet.
An application which need to shutoff properly an outlet will read this parameter first
then write it to the command pdu2OutletControlOffCmd.""",
        }, # column
        "hpdu" : {
            "nodetype" : "node",
            "moduleName" : "CPQPOWER-MIB",
            "oid" : "1.3.6.1.4.1.232.165.9",
        }, # node
        "hpduIdent" : {
            "nodetype" : "node",
            "moduleName" : "CPQPOWER-MIB",
            "oid" : "1.3.6.1.4.1.232.165.9.1",
        }, # node
        "hpduNumPhase" : {
            "nodetype" : "scalar",
            "moduleName" : "CPQPOWER-MIB",
            "oid" : "1.3.6.1.4.1.232.165.9.1.1",
            "status" : "current",
            "syntax" : {
                "type" :                 {
                    "basetype" : "Integer32",
                    "ranges" : [
                    {
                        "min" : "0",
                        "max" : "100"
                    },
                    ],
                    "range" : {
                        "min" : "0",
                        "max" : "100"
                    },
                },
            },
            "access" : "readonly",
            "description" :
                """for 3 phases""",
        }, # scalar
        "hpduIdentTable" : {
            "nodetype" : "table",
            "moduleName" : "CPQPOWER-MIB",
            "oid" : "1.3.6.1.4.1.232.165.9.1.2",
            "status" : "current",
            "description" :
                """Indexed by 1 Hpdu unit.""",
        }, # table
        "hpduIdentEntry" : {
            "nodetype" : "row",
            "moduleName" : "CPQPOWER-MIB",
            "oid" : "1.3.6.1.4.1.232.165.9.1.2.1",
            "status" : "current",
            "linkage" : [
                "hpduIdentIndex",
            ],
            "description" :
                """The table entry containing the identifications of HPDU""",
        }, # row
        "hpduIdentIndex" : {
            "nodetype" : "column",
            "moduleName" : "CPQPOWER-MIB",
            "oid" : "1.3.6.1.4.1.232.165.9.1.2.1.1",
            "status" : "current",
            "syntax" : {
                "type" :                 {
                    "basetype" : "Integer32",
                    "ranges" : [
                    {
                        "min" : "0",
                        "max" : "100"
                    },
                    ],
                    "range" : {
                        "min" : "0",
                        "max" : "100"
                    },
                },
            },
            "access" : "readonly",
            "description" :
                """Index for the MpduIdentEntry table. Start with 1""",
        }, # column
        "hpduManufacturer" : {
            "nodetype" : "column",
            "moduleName" : "CPQPOWER-MIB",
            "oid" : "1.3.6.1.4.1.232.165.9.1.2.1.2",
            "status" : "current",
            "syntax" : {
                "type" : { "module" :"RFC1213-MIB", "name" : "DisplayString"},
            },
            "access" : "readonly",
            "description" :
                """ The Core PDU manufacturer. StringLength=[21]""",
        }, # column
        "hpduModel" : {
            "nodetype" : "column",
            "moduleName" : "CPQPOWER-MIB",
            "oid" : "1.3.6.1.4.1.232.165.9.1.2.1.3",
            "status" : "current",
            "syntax" : {
                "type" : { "module" :"RFC1213-MIB", "name" : "DisplayString"},
            },
            "access" : "readonly",
            "description" :
                """The Core PDU model, marketing name. StringLength=[40].""",
        }, # column
        "hpduName" : {
            "nodetype" : "column",
            "moduleName" : "CPQPOWER-MIB",
            "oid" : "1.3.6.1.4.1.232.165.9.1.2.1.4",
            "status" : "current",
            "syntax" : {
                "type" : { "module" :"RFC1213-MIB", "name" : "DisplayString"},
            },
            "access" : "readonly",
            "description" :
                """The Core PDU name, descriptive name or hostname. StringLength=[16].""",
        }, # column
        "hpduFirmwareVersion" : {
            "nodetype" : "column",
            "moduleName" : "CPQPOWER-MIB",
            "oid" : "1.3.6.1.4.1.232.165.9.1.2.1.5",
            "status" : "current",
            "syntax" : {
                "type" : { "module" :"RFC1213-MIB", "name" : "DisplayString"},
            },
            "access" : "readonly",
            "description" :
                """The Core PDU firmware version(s). StringLength=[12].""",
        }, # column
        "hpduHardwareVersion" : {
            "nodetype" : "column",
            "moduleName" : "CPQPOWER-MIB",
            "oid" : "1.3.6.1.4.1.232.165.9.1.2.1.6",
            "status" : "current",
            "syntax" : {
                "type" : { "module" :"RFC1213-MIB", "name" : "DisplayString"},
            },
            "access" : "readonly",
            "description" :
                """The Core PDU hardware version. StringLength=[8].""",
        }, # column
        "hpduPartNumber" : {
            "nodetype" : "column",
            "moduleName" : "CPQPOWER-MIB",
            "oid" : "1.3.6.1.4.1.232.165.9.1.2.1.7",
            "status" : "current",
            "syntax" : {
                "type" : { "module" :"RFC1213-MIB", "name" : "DisplayString"},
            },
            "access" : "readonly",
            "description" :
                """The Core PDU part number. StringLength=[21].""",
        }, # column
        "hpduSerialNumber" : {
            "nodetype" : "column",
            "moduleName" : "CPQPOWER-MIB",
            "oid" : "1.3.6.1.4.1.232.165.9.1.2.1.8",
            "status" : "current",
            "syntax" : {
                "type" : { "module" :"RFC1213-MIB", "name" : "DisplayString"},
            },
            "access" : "readonly",
            "description" :
                """The PDU external serial number. StringLength=[21].""",
        }, # column
        "hpduUUID" : {
            "nodetype" : "column",
            "moduleName" : "CPQPOWER-MIB",
            "oid" : "1.3.6.1.4.1.232.165.9.1.2.1.9",
            "status" : "current",
            "syntax" : {
                "type" : { "module" :"RFC1213-MIB", "name" : "DisplayString"},
            },
            "access" : "readonly",
            "description" :
                """The PDU's UUID equals PN add SN, canonical conversion. StringLength=[37].""",
        }, # column
        "hpduType" : {
            "nodetype" : "column",
            "moduleName" : "CPQPOWER-MIB",
            "oid" : "1.3.6.1.4.1.232.165.9.1.2.1.10",
            "status" : "current",
            "syntax" : {
                "type" : { "module" :"RFC1213-MIB", "name" : "DisplayString"},
            },
            "access" : "readonly",
            "description" :
                """The PDU's Type: Delta, Wye, single, Wye+lowline.
StringLength=[24].""",
        }, # column
        "hpduPowerRating" : {
            "nodetype" : "column",
            "moduleName" : "CPQPOWER-MIB",
            "oid" : "1.3.6.1.4.1.232.165.9.1.2.1.11",
            "status" : "current",
            "syntax" : {
                "type" : { "module" :"RFC1213-MIB", "name" : "DisplayString"},
            },
            "access" : "readonly",
            "description" :
                """The PDU's Power Rating in KVA (Name Plate). Value is presented 
in 1/100 of the KVA. i.e. 1750 means 17.50 KVA""",
        }, # column
        "hpduInputRating" : {
            "nodetype" : "column",
            "moduleName" : "CPQPOWER-MIB",
            "oid" : "1.3.6.1.4.1.232.165.9.1.2.1.12",
            "status" : "current",
            "syntax" : {
                "type" : { "module" :"RFC1213-MIB", "name" : "DisplayString"},
            },
            "access" : "readonly",
            "description" :
                """The PDU's Input Current Rating in A (Name Plate)""",
        }, # column
        "hpduRegionalNominalVoltage" : {
            "nodetype" : "column",
            "moduleName" : "CPQPOWER-MIB",
            "oid" : "1.3.6.1.4.1.232.165.9.1.2.1.13",
            "status" : "current",
            "syntax" : {
                "type" : { "module" :"RFC1213-MIB", "name" : "DisplayString"},
            },
            "access" : "readonly",
            "description" :
                """value is either America(208V), Japan(202V) or blank for International Model""",
        }, # column
        "hpduNumOutputBreakers" : {
            "nodetype" : "column",
            "moduleName" : "CPQPOWER-MIB",
            "oid" : "1.3.6.1.4.1.232.165.9.1.2.1.14",
            "status" : "current",
            "syntax" : {
                "type" :                 {
                    "basetype" : "Integer32",
                    "ranges" : [
                    {
                        "min" : "0",
                        "max" : "10"
                    },
                    ],
                    "range" : {
                        "min" : "0",
                        "max" : "10"
                    },
                },
            },
            "access" : "readonly",
            "description" :
                """The number of outlets with breakers of each hpdu.""",
        }, # column
        "hpduNumMonitoredOutlet" : {
            "nodetype" : "column",
            "moduleName" : "CPQPOWER-MIB",
            "oid" : "1.3.6.1.4.1.232.165.9.1.2.1.15",
            "status" : "current",
            "syntax" : {
                "type" :                 {
                    "basetype" : "Integer32",
                    "ranges" : [
                    {
                        "min" : "0",
                        "max" : "10"
                    },
                    ],
                    "range" : {
                        "min" : "0",
                        "max" : "10"
                    },
                },
            },
            "access" : "readonly",
            "description" :
                """The number of measured outlets (with CT, VT) of each hpdu.""",
        }, # column
        "hpduFanStatus" : {
            "nodetype" : "column",
            "moduleName" : "CPQPOWER-MIB",
            "oid" : "1.3.6.1.4.1.232.165.9.1.2.1.16",
            "status" : "current",
            "syntax" : {
                "type" : { "module" :"RFC1213-MIB", "name" : "DisplayString"},
            },
            "access" : "readonly",
            "description" :
                """Report fan status: OK or FAIL""",
        }, # column
        "hpduInput" : {
            "nodetype" : "node",
            "moduleName" : "CPQPOWER-MIB",
            "oid" : "1.3.6.1.4.1.232.165.9.2",
        }, # node
        "hpduInputTable" : {
            "nodetype" : "table",
            "moduleName" : "CPQPOWER-MIB",
            "oid" : "1.3.6.1.4.1.232.165.9.2.1",
            "status" : "current",
            "description" :
                """Indexed by hpduNumPhase.""",
        }, # table
        "hpduInputEntry" : {
            "nodetype" : "row",
            "moduleName" : "CPQPOWER-MIB",
            "oid" : "1.3.6.1.4.1.232.165.9.2.1.1",
            "status" : "current",
            "linkage" : [
                "hpduInputIndex",
            ],
            "description" :
                """The Input table entry containing the voltage, current, PF,
percent load, VA, Watts for the HPDU.""",
        }, # row
        "hpduInputIndex" : {
            "nodetype" : "column",
            "moduleName" : "CPQPOWER-MIB",
            "oid" : "1.3.6.1.4.1.232.165.9.2.1.1.1",
            "status" : "current",
            "syntax" : {
                "type" :                 {
                    "basetype" : "Integer32",
                    "ranges" : [
                    {
                        "min" : "0",
                        "max" : "100"
                    },
                    ],
                    "range" : {
                        "min" : "0",
                        "max" : "100"
                    },
                },
            },
            "access" : "readonly",
            "description" :
                """Index for the hpduInputEntry table.""",
        }, # column
        "hpduInputStatus" : {
            "nodetype" : "column",
            "moduleName" : "CPQPOWER-MIB",
            "oid" : "1.3.6.1.4.1.232.165.9.2.1.1.2",
            "status" : "current",
            "syntax" : {
                "type" : { "module" :"RFC1213-MIB", "name" : "DisplayString"},
            },
            "access" : "readonly",
            "description" :
                """The overall status of the Input: off, on, problem. StringLength=[7].""",
        }, # column
        "hpduInputBreakerRating" : {
            "nodetype" : "column",
            "moduleName" : "CPQPOWER-MIB",
            "oid" : "1.3.6.1.4.1.232.165.9.2.1.1.3",
            "status" : "current",
            "syntax" : {
                "type" : { "module" :"", "name" : "Integer32"},
            },
            "access" : "readonly",
            "description" :
                """The rating of each hpdu Input in Ampere.""",
        }, # column
        "hpduInputVoltage" : {
            "nodetype" : "column",
            "moduleName" : "CPQPOWER-MIB",
            "oid" : "1.3.6.1.4.1.232.165.9.2.1.1.4",
            "status" : "current",
            "syntax" : {
                "type" : { "module" :"", "name" : "Integer32"},
            },
            "access" : "readonly",
            "description" :
                """The measured Input voltage from the PDU meters in volts. Value is 
presented in 1/10 of the Volt i.e. 2095 is 209.5 V.  A value 
of -1 will be returned if the voltage is unable to be measured.""",
        }, # column
        "hpduInputCurrent" : {
            "nodetype" : "column",
            "moduleName" : "CPQPOWER-MIB",
            "oid" : "1.3.6.1.4.1.232.165.9.2.1.1.5",
            "status" : "current",
            "syntax" : {
                "type" : { "module" :"", "name" : "Integer32"},
            },
            "access" : "readonly",
            "description" :
                """The measured Input current from the PDU meters in amps. Value is 
presented in 1/100 of the Ampere i.e. 175 is 1.75 A.  A value 
of -1 will be returned if the current is unable to be measured.""",
        }, # column
        "hpduInputPowerVA" : {
            "nodetype" : "column",
            "moduleName" : "CPQPOWER-MIB",
            "oid" : "1.3.6.1.4.1.232.165.9.2.1.1.6",
            "status" : "current",
            "syntax" : {
                "type" : { "module" :"", "name" : "Integer32"},
            },
            "access" : "readonly",
            "description" :
                """The total Input Power measured in VA.  A value 
of -1 will be returned if the power is unable to be calculated.""",
        }, # column
        "hpduInputPowerWatt" : {
            "nodetype" : "column",
            "moduleName" : "CPQPOWER-MIB",
            "oid" : "1.3.6.1.4.1.232.165.9.2.1.1.7",
            "status" : "current",
            "syntax" : {
                "type" : { "module" :"", "name" : "Integer32"},
            },
            "access" : "readonly",
            "description" :
                """The total Input power measured in Watts.  A value 
of -1 will be returned if the power is unable to be calculated.""",
        }, # column
        "hpduInputPowerFactor" : {
            "nodetype" : "column",
            "moduleName" : "CPQPOWER-MIB",
            "oid" : "1.3.6.1.4.1.232.165.9.2.1.1.8",
            "status" : "current",
            "syntax" : {
                "type" : { "module" :"", "name" : "Integer32"},
            },
            "access" : "readonly",
            "description" :
                """The Input power factor is presented in 1/100 of the unit i.e.
98 is 0.98.  A value of -1 will be returned if the power factor is unable 
to be measured.""",
        }, # column
        "hpduInputWarningThreshold" : {
            "nodetype" : "column",
            "moduleName" : "CPQPOWER-MIB",
            "oid" : "1.3.6.1.4.1.232.165.9.2.1.1.9",
            "status" : "current",
            "syntax" : {
                "type" : { "module" :"", "name" : "Integer32"},
            },
            "access" : "readonly",
            "description" :
                """Report the User-setting Input threshhold limit for Warning in percentage""",
        }, # column
        "hpduInputCriticalThreshold" : {
            "nodetype" : "column",
            "moduleName" : "CPQPOWER-MIB",
            "oid" : "1.3.6.1.4.1.232.165.9.2.1.1.10",
            "status" : "current",
            "syntax" : {
                "type" : { "module" :"", "name" : "Integer32"},
            },
            "access" : "readonly",
            "description" :
                """Report the User-setting Input threshhold limit for Critical in percentage""",
        }, # column
        "hpduInputPowerWattHour" : {
            "nodetype" : "column",
            "moduleName" : "CPQPOWER-MIB",
            "oid" : "1.3.6.1.4.1.232.165.9.2.1.1.11",
            "status" : "current",
            "syntax" : {
                "type" : { "module" :"", "name" : "Integer32"},
            },
            "access" : "readonly",
            "description" :
                """Support Billing Grade Energy Metering in Watt-Hour.  A value 
of -1 will be returned if the power is unable to be calculated.""",
        }, # column
        "hpduInputTotalEnergySince" : {
            "nodetype" : "column",
            "moduleName" : "CPQPOWER-MIB",
            "oid" : "1.3.6.1.4.1.232.165.9.2.1.1.12",
            "status" : "current",
            "syntax" : {
                "type" : { "module" :"RFC1213-MIB", "name" : "DisplayString"},
            },
            "access" : "readonly",
            "description" :
                """Display the date and time that starts to accumulate the per Load segment energy in WH. 
Date and Time can be set by user on GUI.""",
        }, # column
        "hpduInputEnergyMeteringTotalHours" : {
            "nodetype" : "column",
            "moduleName" : "CPQPOWER-MIB",
            "oid" : "1.3.6.1.4.1.232.165.9.2.1.1.13",
            "status" : "current",
            "syntax" : {
                "type" : { "module" :"", "name" : "Integer32"},
            },
            "access" : "readonly",
            "description" :
                """Total hours of collecting measurement data.  A value 
of -1 will be returned if the value is unable to be calculated.""",
        }, # column
        "hpduOutlet" : {
            "nodetype" : "node",
            "moduleName" : "CPQPOWER-MIB",
            "oid" : "1.3.6.1.4.1.232.165.9.3",
        }, # node
        "hpduOutletTable" : {
            "nodetype" : "table",
            "moduleName" : "CPQPOWER-MIB",
            "oid" : "1.3.6.1.4.1.232.165.9.3.1",
            "status" : "current",
            "description" :
                """Indexed by hpduNumMonitoredOutlet and hpduNumPhase . So aggregate objects for each entry 
equal to (hpduNumMonitoredOutlet x hpduNumPhase). Start with 1.""",
        }, # table
        "hpduOutletEntry" : {
            "nodetype" : "row",
            "moduleName" : "CPQPOWER-MIB",
            "oid" : "1.3.6.1.4.1.232.165.9.3.1.1",
            "status" : "current",
            "linkage" : [
                "hpduNumMonitoredOutlet",
                "hpduNumPhase",
                "hpduOutletIndex",
            ],
            "description" :
                """The Outlet table entry containing the voltage, current, PF,
percent load, VA, Watts for the Modular PDU.""",
        }, # row
        "hpduOutletIndex" : {
            "nodetype" : "column",
            "moduleName" : "CPQPOWER-MIB",
            "oid" : "1.3.6.1.4.1.232.165.9.3.1.1.1",
            "status" : "current",
            "syntax" : {
                "type" :                 {
                    "basetype" : "Integer32",
                    "ranges" : [
                    {
                        "min" : "0",
                        "max" : "100"
                    },
                    ],
                    "range" : {
                        "min" : "0",
                        "max" : "100"
                    },
                },
            },
            "access" : "readonly",
            "description" :
                """Index for the hpduOutletEntry table.""",
        }, # column
        "hpduOutletStatus" : {
            "nodetype" : "column",
            "moduleName" : "CPQPOWER-MIB",
            "oid" : "1.3.6.1.4.1.232.165.9.3.1.1.2",
            "status" : "current",
            "syntax" : {
                "type" : { "module" :"RFC1213-MIB", "name" : "DisplayString"},
            },
            "access" : "readonly",
            "description" :
                """The overall status of the breaker: off, on, problem. StringLength=[7].""",
        }, # column
        "hpduOutletBreakerRating" : {
            "nodetype" : "column",
            "moduleName" : "CPQPOWER-MIB",
            "oid" : "1.3.6.1.4.1.232.165.9.3.1.1.3",
            "status" : "current",
            "syntax" : {
                "type" : { "module" :"", "name" : "Integer32"},
            },
            "access" : "readonly",
            "description" :
                """The rating of each hpdu Outlet in Ampere.""",
        }, # column
        "hpduOutletPercentLoad" : {
            "nodetype" : "column",
            "moduleName" : "CPQPOWER-MIB",
            "oid" : "1.3.6.1.4.1.232.165.9.3.1.1.4",
            "status" : "current",
            "syntax" : {
                "type" : { "module" :"", "name" : "Integer32"},
            },
            "access" : "readonly",
            "description" :
                """The hpdu's each Outlet load in percent of rated capacity. Value is 
presented in 1/10 of the percentage i.e. 125 is 12.5%.  A value 
of -1 will be returned if the current is unable to be measured.""",
        }, # column
        "hpduOutletVoltage" : {
            "nodetype" : "column",
            "moduleName" : "CPQPOWER-MIB",
            "oid" : "1.3.6.1.4.1.232.165.9.3.1.1.5",
            "status" : "current",
            "syntax" : {
                "type" : { "module" :"", "name" : "Integer32"},
            },
            "access" : "readonly",
            "description" :
                """The measured Outlet voltage from the PDU meters in volts. Value is 
presented in 1/10 of the Volt i.e. 2095 is 209.5 V.  A value 
of -1 will be returned if the voltage is unable to be measured.""",
        }, # column
        "hpduOutletCurrent" : {
            "nodetype" : "column",
            "moduleName" : "CPQPOWER-MIB",
            "oid" : "1.3.6.1.4.1.232.165.9.3.1.1.6",
            "status" : "current",
            "syntax" : {
                "type" : { "module" :"", "name" : "Integer32"},
            },
            "access" : "readonly",
            "description" :
                """The measured Outlet current from the PDU meters in amps. Value is 
presented in 1/100 of the Ampere i.e. 175 is 1.75 A.  A value 
of -1 will be returned if the current is unable to be measured.""",
        }, # column
        "hpduOutletPowerVA" : {
            "nodetype" : "column",
            "moduleName" : "CPQPOWER-MIB",
            "oid" : "1.3.6.1.4.1.232.165.9.3.1.1.7",
            "status" : "current",
            "syntax" : {
                "type" : { "module" :"", "name" : "Integer32"},
            },
            "access" : "readonly",
            "description" :
                """The total VA load (VI) measured on the PDU in VA.  A value 
of -1 will be returned if the power is unable to be calculated.""",
        }, # column
        "hpduOutletPowerWatt" : {
            "nodetype" : "column",
            "moduleName" : "CPQPOWER-MIB",
            "oid" : "1.3.6.1.4.1.232.165.9.3.1.1.8",
            "status" : "current",
            "syntax" : {
                "type" : { "module" :"", "name" : "Integer32"},
            },
            "access" : "readonly",
            "description" :
                """The total power load measured on the PDU in Watts.  A value 
of -1 will be returned if the power is unable to be calculated.""",
        }, # column
        "hpduOutletPowerFactor" : {
            "nodetype" : "column",
            "moduleName" : "CPQPOWER-MIB",
            "oid" : "1.3.6.1.4.1.232.165.9.3.1.1.9",
            "status" : "current",
            "syntax" : {
                "type" : { "module" :"", "name" : "Integer32"},
            },
            "access" : "readonly",
            "description" :
                """The power factor is presented in 1/100 of the unit i.e.
98 is 0.98.  A value of -1 will be returned if the power factor is unable 
to be measured.""",
        }, # column
        "hpduOutletWarningThreshold" : {
            "nodetype" : "column",
            "moduleName" : "CPQPOWER-MIB",
            "oid" : "1.3.6.1.4.1.232.165.9.3.1.1.10",
            "status" : "current",
            "syntax" : {
                "type" : { "module" :"", "name" : "Integer32"},
            },
            "access" : "readonly",
            "description" :
                """Report the User-set threshhold limit for Warning in percentage""",
        }, # column
        "hpduOutletCriticalThreshold" : {
            "nodetype" : "column",
            "moduleName" : "CPQPOWER-MIB",
            "oid" : "1.3.6.1.4.1.232.165.9.3.1.1.11",
            "status" : "current",
            "syntax" : {
                "type" : { "module" :"", "name" : "Integer32"},
            },
            "access" : "readonly",
            "description" :
                """Report the User-set threshhold limit for Critical in percentage""",
        }, # column
        "hpduOutletPowerWattHour" : {
            "nodetype" : "column",
            "moduleName" : "CPQPOWER-MIB",
            "oid" : "1.3.6.1.4.1.232.165.9.3.1.1.12",
            "status" : "current",
            "syntax" : {
                "type" : { "module" :"", "name" : "Integer32"},
            },
            "access" : "readonly",
            "description" :
                """Support Billing Grade Energy Metering in Watt-Hour.  A value 
of -1 will be returned if the power is unable to be calculated.""",
        }, # column
        "hpduOutletTotalEnergySince" : {
            "nodetype" : "column",
            "moduleName" : "CPQPOWER-MIB",
            "oid" : "1.3.6.1.4.1.232.165.9.3.1.1.13",
            "status" : "current",
            "syntax" : {
                "type" : { "module" :"RFC1213-MIB", "name" : "DisplayString"},
            },
            "access" : "readonly",
            "description" :
                """Display the date and time that starts to accumulate the per Load segment energy in WH. 
Date and Time can be set by user on GUI.""",
        }, # column
        "hpduOutletEnergyMeteringTotalHours" : {
            "nodetype" : "column",
            "moduleName" : "CPQPOWER-MIB",
            "oid" : "1.3.6.1.4.1.232.165.9.3.1.1.14",
            "status" : "current",
            "syntax" : {
                "type" : { "module" :"", "name" : "Integer32"},
            },
            "access" : "readonly",
            "description" :
                """Total hours of collecting measurement data.  A value 
of -1 will be returned if the value is unable to be calculated.""",
        }, # column
        "pdu3" : {
            "nodetype" : "node",
            "moduleName" : "CPQPOWER-MIB",
            "oid" : "1.3.6.1.4.1.232.165.11",
        }, # node
        "pdu3Ident" : {
            "nodetype" : "node",
            "moduleName" : "CPQPOWER-MIB",
            "oid" : "1.3.6.1.4.1.232.165.11.1",
        }, # node
        "pdu3NumberPDU" : {
            "nodetype" : "scalar",
            "moduleName" : "CPQPOWER-MIB",
            "oid" : "1.3.6.1.4.1.232.165.11.1.1",
            "status" : "current",
            "syntax" : {
                "type" :                 {
                    "basetype" : "Integer32",
                    "ranges" : [
                    {
                        "min" : "1",
                        "max" : "2"
                    },
                    ],
                    "range" : {
                        "min" : "1",
                        "max" : "2"
                    },
                },
            },
            "access" : "readonly",
            "description" :
                """The number of PDUs detected (in its daisy chain).""",
        }, # scalar
        "pdu3IdentTable" : {
            "nodetype" : "table",
            "moduleName" : "CPQPOWER-MIB",
            "oid" : "1.3.6.1.4.1.232.165.11.1.2",
            "status" : "current",
            "description" :
                """Aggregate Object with number of entries equal to pdu3NumberPDU .""",
        }, # table
        "pdu3IdentEntry" : {
            "nodetype" : "row",
            "moduleName" : "CPQPOWER-MIB",
            "oid" : "1.3.6.1.4.1.232.165.11.1.2.1",
            "status" : "current",
            "linkage" : [
                "pdu3IdentIndex",
            ],
            "description" :
                """The ident table entry containing the name, model, manufacturer, 
firmware version, part number, etc.""",
        }, # row
        "pdu3IdentIndex" : {
            "nodetype" : "column",
            "moduleName" : "CPQPOWER-MIB",
            "oid" : "1.3.6.1.4.1.232.165.11.1.2.1.1",
            "status" : "current",
            "syntax" : {
                "type" :                 {
                    "basetype" : "Integer32",
                    "ranges" : [
                    {
                        "min" : "0",
                        "max" : "100"
                    },
                    ],
                    "range" : {
                        "min" : "0",
                        "max" : "100"
                    },
                },
            },
            "access" : "readonly",
            "description" :
                """Index for the Pdu3IdentEntry table.""",
        }, # column
        "pdu3Name" : {
            "nodetype" : "column",
            "moduleName" : "CPQPOWER-MIB",
            "oid" : "1.3.6.1.4.1.232.165.11.1.2.1.2",
            "status" : "current",
            "syntax" : {
                "type" :                 {
                    "basetype" : "OctetString",
                    "parent module" : {
                        "name" : "RFC1213-MIB",
                        "type" : "DisplayString",
                    },
                    "ranges" : [
                    {
                        "min" : "0",
                        "max" : "63"
                    },
                    ],
                    "range" : {
                        "min" : "0",
                        "max" : "63"
                    },
                },
            },
            "access" : "readonly",
            "description" :
                """The string identify the device in daisy chain. Example PDU A.""",
        }, # column
        "pdu3Model" : {
            "nodetype" : "column",
            "moduleName" : "CPQPOWER-MIB",
            "oid" : "1.3.6.1.4.1.232.165.11.1.2.1.3",
            "status" : "current",
            "syntax" : {
                "type" :                 {
                    "basetype" : "OctetString",
                    "parent module" : {
                        "name" : "RFC1213-MIB",
                        "type" : "DisplayString",
                    },
                    "ranges" : [
                    {
                        "min" : "0",
                        "max" : "63"
                    },
                    ],
                    "range" : {
                        "min" : "0",
                        "max" : "63"
                    },
                },
            },
            "access" : "readonly",
            "description" :
                """The Device Model.""",
        }, # column
        "pdu3Manufacturer" : {
            "nodetype" : "column",
            "moduleName" : "CPQPOWER-MIB",
            "oid" : "1.3.6.1.4.1.232.165.11.1.2.1.4",
            "status" : "current",
            "syntax" : {
                "type" :                 {
                    "basetype" : "OctetString",
                    "parent module" : {
                        "name" : "RFC1213-MIB",
                        "type" : "DisplayString",
                    },
                    "ranges" : [
                    {
                        "min" : "0",
                        "max" : "63"
                    },
                    ],
                    "range" : {
                        "min" : "0",
                        "max" : "63"
                    },
                },
            },
            "access" : "readonly",
            "description" :
                """The Device Manufacturer Name (e.g. Hewlett-Packard).""",
        }, # column
        "pdu3FirmwareVersion" : {
            "nodetype" : "column",
            "moduleName" : "CPQPOWER-MIB",
            "oid" : "1.3.6.1.4.1.232.165.11.1.2.1.5",
            "status" : "current",
            "syntax" : {
                "type" :                 {
                    "basetype" : "OctetString",
                    "parent module" : {
                        "name" : "RFC1213-MIB",
                        "type" : "DisplayString",
                    },
                    "ranges" : [
                    {
                        "min" : "0",
                        "max" : "63"
                    },
                    ],
                    "range" : {
                        "min" : "0",
                        "max" : "63"
                    },
                },
            },
            "access" : "readonly",
            "description" :
                """The firmware revision level of the device.""",
        }, # column
        "pdu3FirmwareVersionTimeStamp" : {
            "nodetype" : "column",
            "moduleName" : "CPQPOWER-MIB",
            "oid" : "1.3.6.1.4.1.232.165.11.1.2.1.6",
            "status" : "current",
            "syntax" : {
                "type" : { "module" :"RFC1213-MIB", "name" : "DisplayString"},
            },
            "access" : "readonly",
            "description" :
                """Timestamp of when the PDU firmware was last updated""",
        }, # column
        "pdu3PartNumber" : {
            "nodetype" : "column",
            "moduleName" : "CPQPOWER-MIB",
            "oid" : "1.3.6.1.4.1.232.165.11.1.2.1.7",
            "status" : "current",
            "syntax" : {
                "type" :                 {
                    "basetype" : "OctetString",
                    "parent module" : {
                        "name" : "RFC1213-MIB",
                        "type" : "DisplayString",
                    },
                    "ranges" : [
                    {
                        "min" : "0",
                        "max" : "63"
                    },
                    ],
                    "range" : {
                        "min" : "0",
                        "max" : "63"
                    },
                },
            },
            "access" : "readonly",
            "description" :
                """The device part number. Example AF400A.""",
        }, # column
        "pdu3SerialNumber" : {
            "nodetype" : "column",
            "moduleName" : "CPQPOWER-MIB",
            "oid" : "1.3.6.1.4.1.232.165.11.1.2.1.8",
            "status" : "current",
            "syntax" : {
                "type" :                 {
                    "basetype" : "OctetString",
                    "parent module" : {
                        "name" : "RFC1213-MIB",
                        "type" : "DisplayString",
                    },
                    "ranges" : [
                    {
                        "min" : "0",
                        "max" : "63"
                    },
                    ],
                    "range" : {
                        "min" : "0",
                        "max" : "63"
                    },
                },
            },
            "access" : "readonly",
            "description" :
                """The device serial number, 10- or 16-digit.""",
        }, # column
        "pdu3Status" : {
            "nodetype" : "column",
            "moduleName" : "CPQPOWER-MIB",
            "oid" : "1.3.6.1.4.1.232.165.11.1.2.1.9",
            "status" : "current",
            "syntax" : {
                "type" :                 {
                    "basetype" : "Enumeration",
                    "other" : {
                        "nodetype" : "namednumber",
                        "number" : "1"
                    },
                    "ok" : {
                        "nodetype" : "namednumber",
                        "number" : "2"
                    },
                    "degraded" : {
                        "nodetype" : "namednumber",
                        "number" : "3"
                    },
                    "failed" : {
                        "nodetype" : "namednumber",
                        "number" : "4"
                    },
                },
            },
            "access" : "readonly",
            "description" :
                """The overall status of the device.  A value of OK(2) indicates the device is operating normally.
A value of degraded(3) indicates the device is operating with warning indicators.  A value of
failed(4) indicates the device is operating with critical indicators.""",
        }, # column
        "pdu3Controllable" : {
            "nodetype" : "column",
            "moduleName" : "CPQPOWER-MIB",
            "oid" : "1.3.6.1.4.1.232.165.11.1.2.1.10",
            "status" : "current",
            "syntax" : {
                "type" :                 {
                    "basetype" : "Enumeration",
                    "yes" : {
                        "nodetype" : "namednumber",
                        "number" : "1"
                    },
                    "no" : {
                        "nodetype" : "namednumber",
                        "number" : "2"
                    },
                },
            },
            "access" : "readonly",
            "description" :
                """This object indicates whether or not the device is controllable.""",
        }, # column
        "pdu3InputPhaseCount" : {
            "nodetype" : "column",
            "moduleName" : "CPQPOWER-MIB",
            "oid" : "1.3.6.1.4.1.232.165.11.1.2.1.11",
            "status" : "current",
            "syntax" : {
                "type" :                 {
                    "basetype" : "Integer32",
                    "ranges" : [
                    {
                        "min" : "0",
                        "max" : "63"
                    },
                    ],
                    "range" : {
                        "min" : "0",
                        "max" : "63"
                    },
                },
            },
            "access" : "readonly",
            "description" :
                """The number of input phase on this pdu 1,2,3.""",
        }, # column
        "pdu3GroupCount" : {
            "nodetype" : "column",
            "moduleName" : "CPQPOWER-MIB",
            "oid" : "1.3.6.1.4.1.232.165.11.1.2.1.12",
            "status" : "current",
            "syntax" : {
                "type" :                 {
                    "basetype" : "Integer32",
                    "ranges" : [
                    {
                        "min" : "0",
                        "max" : "63"
                    },
                    ],
                    "range" : {
                        "min" : "0",
                        "max" : "63"
                    },
                },
            },
            "access" : "readonly",
            "description" :
                """The number of groups (breakers) on this pdu.""",
        }, # column
        "pdu3OutletCount" : {
            "nodetype" : "column",
            "moduleName" : "CPQPOWER-MIB",
            "oid" : "1.3.6.1.4.1.232.165.11.1.2.1.13",
            "status" : "current",
            "syntax" : {
                "type" :                 {
                    "basetype" : "Integer32",
                    "ranges" : [
                    {
                        "min" : "0",
                        "max" : "63"
                    },
                    ],
                    "range" : {
                        "min" : "0",
                        "max" : "63"
                    },
                },
            },
            "access" : "readonly",
            "description" :
                """The number of outlets in this PDU.""",
        }, # column
        "pdu3MACAddress" : {
            "nodetype" : "column",
            "moduleName" : "CPQPOWER-MIB",
            "oid" : "1.3.6.1.4.1.232.165.11.1.2.1.14",
            "status" : "current",
            "syntax" : {
                "type" : { "module" :"RFC1213-MIB", "name" : "DisplayString"},
            },
            "access" : "readonly",
            "description" :
                """The assigned MAC address for this PDU.""",
        }, # column
        "pdu3IPv4Address" : {
            "nodetype" : "column",
            "moduleName" : "CPQPOWER-MIB",
            "oid" : "1.3.6.1.4.1.232.165.11.1.2.1.15",
            "status" : "current",
            "syntax" : {
                "type" : { "module" :"RFC1213-MIB", "name" : "DisplayString"},
            },
            "access" : "readonly",
            "description" :
                """The current IPv4 Address. 
A value of 0.0.0.0 indicates an error or an unset option.""",
        }, # column
        "pdu3IPv6Address" : {
            "nodetype" : "column",
            "moduleName" : "CPQPOWER-MIB",
            "oid" : "1.3.6.1.4.1.232.165.11.1.2.1.16",
            "status" : "current",
            "syntax" : {
                "type" : { "module" :"RFC1213-MIB", "name" : "DisplayString"},
            },
            "access" : "readonly",
            "description" :
                """The current IPv6 Address.
A vale of 0.0.0.0.0.0 indicates an error or an unset option.""",
        }, # column
        "pdu3ConfigTable" : {
            "nodetype" : "table",
            "moduleName" : "CPQPOWER-MIB",
            "oid" : "1.3.6.1.4.1.232.165.11.1.3",
            "status" : "current",
            "description" :
                """Aggregate Object with number of entries equal to pdu3NumberPDU .""",
        }, # table
        "pdu3ConfigEntry" : {
            "nodetype" : "row",
            "moduleName" : "CPQPOWER-MIB",
            "oid" : "1.3.6.1.4.1.232.165.11.1.3.1",
            "status" : "current",
            "linkage" : [
                "pdu3ConfigIndex",
            ],
            "description" :
                """Read Configuration data from the PDU being queried.""",
        }, # row
        "pdu3ConfigIndex" : {
            "nodetype" : "column",
            "moduleName" : "CPQPOWER-MIB",
            "oid" : "1.3.6.1.4.1.232.165.11.1.3.1.1",
            "status" : "current",
            "syntax" : {
                "type" :                 {
                    "basetype" : "Integer32",
                    "ranges" : [
                    {
                        "min" : "0",
                        "max" : "20"
                    },
                    ],
                    "range" : {
                        "min" : "0",
                        "max" : "20"
                    },
                },
            },
            "access" : "readonly",
            "description" :
                """The index of PDU configuration entry.""",
        }, # column
        "pdu3ConfigSsh" : {
            "nodetype" : "column",
            "moduleName" : "CPQPOWER-MIB",
            "oid" : "1.3.6.1.4.1.232.165.11.1.3.1.2",
            "status" : "current",
            "syntax" : {
                "type" :                 {
                    "basetype" : "Enumeration",
                    "off" : {
                        "nodetype" : "namednumber",
                        "number" : "0"
                    },
                    "on" : {
                        "nodetype" : "namednumber",
                        "number" : "1"
                    },
                },
            },
            "access" : "readonly",
            "description" :
                """Setting this OID to off(0) will disable the SSH conneciton.
Setting this OID to on(1) will enable the SSH connection.""",
        }, # column
        "pdu3ConfigFtps" : {
            "nodetype" : "column",
            "moduleName" : "CPQPOWER-MIB",
            "oid" : "1.3.6.1.4.1.232.165.11.1.3.1.3",
            "status" : "current",
            "syntax" : {
                "type" :                 {
                    "basetype" : "Enumeration",
                    "off" : {
                        "nodetype" : "namednumber",
                        "number" : "0"
                    },
                    "on" : {
                        "nodetype" : "namednumber",
                        "number" : "1"
                    },
                },
            },
            "access" : "readonly",
            "description" :
                """Setting this OID to off(0) will disable the FTPS connection.
Setting this OID to on(1) will enable the FTPS connection.""",
        }, # column
        "pdu3ConfigHttp" : {
            "nodetype" : "column",
            "moduleName" : "CPQPOWER-MIB",
            "oid" : "1.3.6.1.4.1.232.165.11.1.3.1.4",
            "status" : "current",
            "syntax" : {
                "type" :                 {
                    "basetype" : "Enumeration",
                    "off" : {
                        "nodetype" : "namednumber",
                        "number" : "0"
                    },
                    "on" : {
                        "nodetype" : "namednumber",
                        "number" : "1"
                    },
                },
            },
            "access" : "readonly",
            "description" :
                """Setting this OID to off(0) will disable the HTTP connection.
Setting this OID to on(1) will enable the HTTP connection.""",
        }, # column
        "pdu3ConfigHttps" : {
            "nodetype" : "column",
            "moduleName" : "CPQPOWER-MIB",
            "oid" : "1.3.6.1.4.1.232.165.11.1.3.1.5",
            "status" : "current",
            "syntax" : {
                "type" :                 {
                    "basetype" : "Enumeration",
                    "off" : {
                        "nodetype" : "namednumber",
                        "number" : "0"
                    },
                    "on" : {
                        "nodetype" : "namednumber",
                        "number" : "1"
                    },
                },
            },
            "access" : "readonly",
            "description" :
                """Setting this OID to off(0) will disable the HTTPS connection.
Setting this OID to on(1) will enable the HTTPS connection.""",
        }, # column
        "pdu3ConfigIPv4IPv6Switch" : {
            "nodetype" : "column",
            "moduleName" : "CPQPOWER-MIB",
            "oid" : "1.3.6.1.4.1.232.165.11.1.3.1.6",
            "status" : "current",
            "syntax" : {
                "type" :                 {
                    "basetype" : "Enumeration",
                    "iPv4" : {
                        "nodetype" : "namednumber",
                        "number" : "1"
                    },
                    "iPv6" : {
                        "nodetype" : "namednumber",
                        "number" : "2"
                    },
                    "iPv4IPv6" : {
                        "nodetype" : "namednumber",
                        "number" : "3"
                    },
                },
            },
            "access" : "readonly",
            "description" :
                """Setting this OID to IPv4(1) will enable the IPv4 configuration.
Setting this OID to IPv6(2) will enable the IPv6 configuration.
Setting this OID to IPv4&IPv6(3) will enable both IPv4 and IPv6 configuration.""",
        }, # column
        "pdu3ConfigRedfishAPI" : {
            "nodetype" : "column",
            "moduleName" : "CPQPOWER-MIB",
            "oid" : "1.3.6.1.4.1.232.165.11.1.3.1.7",
            "status" : "current",
            "syntax" : {
                "type" :                 {
                    "basetype" : "Enumeration",
                    "off" : {
                        "nodetype" : "namednumber",
                        "number" : "0"
                    },
                    "on" : {
                        "nodetype" : "namednumber",
                        "number" : "1"
                    },
                },
            },
            "access" : "readwrite",
            "description" :
                """Setting this OID to off(0) will disable the Redfish API.
Setting this OID to on(1) will enable the Redfish API.""",
        }, # column
        "pdu3ConfigOledDispalyOrientation" : {
            "nodetype" : "column",
            "moduleName" : "CPQPOWER-MIB",
            "oid" : "1.3.6.1.4.1.232.165.11.1.3.1.8",
            "status" : "current",
            "syntax" : {
                "type" :                 {
                    "basetype" : "Enumeration",
                    "displayNormal" : {
                        "nodetype" : "namednumber",
                        "number" : "1"
                    },
                    "displayReverse" : {
                        "nodetype" : "namednumber",
                        "number" : "2"
                    },
                },
            },
            "access" : "readwrite",
            "description" :
                """Indicates the intended physical orientation of OLED display.
displayNormal(1) indicates normal orientation.
displayReverse(2) indicates upside down orientation.""",
        }, # column
        "pdu3ConfigEnergyReset" : {
            "nodetype" : "column",
            "moduleName" : "CPQPOWER-MIB",
            "oid" : "1.3.6.1.4.1.232.165.11.1.3.1.9",
            "status" : "current",
            "syntax" : {
                "type" :                 {
                    "basetype" : "Enumeration",
                    "noOperation" : {
                        "nodetype" : "namednumber",
                        "number" : "1"
                    },
                    "reset" : {
                        "nodetype" : "namednumber",
                        "number" : "2"
                    },
                    "notSupported" : {
                        "nodetype" : "namednumber",
                        "number" : "3"
                    },
                },
            },
            "access" : "readwrite",
            "description" :
                """Setting this OID to reset(2) will cause the device energy meter value 
to be reset to zero. Getting this OID in models that support this feature
will do nothing and return the noOperation(1) value. Models that do not
supported this feature will respond to this OID with a value of notSupported(3).
Attempts to set this OID in these models will fail.""",
        }, # column
        "pdu3ConfigNetworkManagementCardReset" : {
            "nodetype" : "column",
            "moduleName" : "CPQPOWER-MIB",
            "oid" : "1.3.6.1.4.1.232.165.11.1.3.1.10",
            "status" : "current",
            "syntax" : {
                "type" :                 {
                    "basetype" : "Enumeration",
                    "noOperation" : {
                        "nodetype" : "namednumber",
                        "number" : "0"
                    },
                    "reset" : {
                        "nodetype" : "namednumber",
                        "number" : "1"
                    },
                },
            },
            "access" : "readwrite",
            "description" :
                """Getting this OID will return noOperation(0).
Getting this OID to reset(1) will reset NMC.""",
        }, # column
        "pdu3ConfigDaisyChainStatus" : {
            "nodetype" : "column",
            "moduleName" : "CPQPOWER-MIB",
            "oid" : "1.3.6.1.4.1.232.165.11.1.3.1.11",
            "status" : "current",
            "syntax" : {
                "type" :                 {
                    "basetype" : "Enumeration",
                    "daisychain" : {
                        "nodetype" : "namednumber",
                        "number" : "0"
                    },
                },
            },
            "access" : "readwrite",
            "description" :
                """Setting this OID to daisychain(0) will enable daisychain mode.""",
        }, # column
        "pdu3Input" : {
            "nodetype" : "node",
            "moduleName" : "CPQPOWER-MIB",
            "oid" : "1.3.6.1.4.1.232.165.11.2",
        }, # node
        "pdu3InputTable" : {
            "nodetype" : "table",
            "moduleName" : "CPQPOWER-MIB",
            "oid" : "1.3.6.1.4.1.232.165.11.2.1",
            "status" : "current",
            "description" :
                """Aggregate Object with number of entries equal to pdu3NumberPDU .""",
        }, # table
        "pdu3InputEntry" : {
            "nodetype" : "row",
            "moduleName" : "CPQPOWER-MIB",
            "oid" : "1.3.6.1.4.1.232.165.11.2.1.1",
            "status" : "current",
            "linkage" : [
                "pdu3IdentIndex",
            ],
            "description" :
                """The ident table entry containing the VA, Watts, WH, etc.""",
        }, # row
        "pdu3InputType" : {
            "nodetype" : "column",
            "moduleName" : "CPQPOWER-MIB",
            "oid" : "1.3.6.1.4.1.232.165.11.2.1.1.1",
            "status" : "current",
            "syntax" : {
                "type" :                 {
                    "basetype" : "Enumeration",
                    "singlePhase" : {
                        "nodetype" : "namednumber",
                        "number" : "1"
                    },
                    "splitPhase" : {
                        "nodetype" : "namednumber",
                        "number" : "2"
                    },
                    "threePhaseDelta" : {
                        "nodetype" : "namednumber",
                        "number" : "3"
                    },
                    "threePhaseWye" : {
                        "nodetype" : "namednumber",
                        "number" : "4"
                    },
                },
            },
            "access" : "readonly",
            "description" :
                """Type of input - single phase, split phase, three phase delta, or three
phase wye.""",
        }, # column
        "pdu3InputFrequency" : {
            "nodetype" : "column",
            "moduleName" : "CPQPOWER-MIB",
            "oid" : "1.3.6.1.4.1.232.165.11.2.1.1.2",
            "status" : "current",
            "syntax" : {
                "type" :                 {
                    "basetype" : "Integer32",
                    "ranges" : [
                    {
                        "min" : "0",
                        "max" : "2147483647"
                    },
                    ],
                    "range" : {
                        "min" : "0",
                        "max" : "2147483647"
                    },
                },
            },
            "access" : "readonly",
            "description" :
                """The measured input frequency from the PDU meters in tenths of Hz.""",
        }, # column
        "pdu3InputFrequencyStatus" : {
            "nodetype" : "column",
            "moduleName" : "CPQPOWER-MIB",
            "oid" : "1.3.6.1.4.1.232.165.11.2.1.1.3",
            "status" : "current",
            "syntax" : {
                "type" :                 {
                    "basetype" : "Enumeration",
                    "good" : {
                        "nodetype" : "namednumber",
                        "number" : "1"
                    },
                    "outOfRange" : {
                        "nodetype" : "namednumber",
                        "number" : "2"
                    },
                },
            },
            "access" : "readonly",
            "description" :
                """Status of the measured input frequency relative to the nominal frequency and the admitted tolerance.""",
        }, # column
        "pdu3InputPowerVA" : {
            "nodetype" : "column",
            "moduleName" : "CPQPOWER-MIB",
            "oid" : "1.3.6.1.4.1.232.165.11.2.1.1.4",
            "status" : "current",
            "syntax" : {
                "type" : { "module" :"", "name" : "Integer32"},
            },
            "access" : "readonly",
            "description" :
                """A total input VA of all phases.  Units are 0.001 VA.  A negative value indicates
that this object is not available.""",
        }, # column
        "pdu3InputPowerWatts" : {
            "nodetype" : "column",
            "moduleName" : "CPQPOWER-MIB",
            "oid" : "1.3.6.1.4.1.232.165.11.2.1.1.5",
            "status" : "current",
            "syntax" : {
                "type" : { "module" :"", "name" : "Integer32"},
            },
            "access" : "readonly",
            "description" :
                """A total input Watts of all phases.  Units are 0.001 Watts.  A negative value indicates
that this object is not available.""",
        }, # column
        "pdu3InputTotalEnergy" : {
            "nodetype" : "column",
            "moduleName" : "CPQPOWER-MIB",
            "oid" : "1.3.6.1.4.1.232.165.11.2.1.1.6",
            "status" : "current",
            "syntax" : {
                "type" : { "module" :"", "name" : "Integer32"},
            },
            "access" : "readonly",
            "description" :
                """A total input Watt-Hour value for all phases.  Units are KWh. This value is accumulated since PDU in service.   
A negative value indicates that this object is not available.""",
        }, # column
        "pdu3InputPowerWattHourTimer" : {
            "nodetype" : "column",
            "moduleName" : "CPQPOWER-MIB",
            "oid" : "1.3.6.1.4.1.232.165.11.2.1.1.7",
            "status" : "current",
            "syntax" : {
                "type" :                 {
                    "basetype" : "OctetString",
                    "parent module" : {
                        "name" : "RFC1213-MIB",
                        "type" : "DisplayString",
                    },
                    "ranges" : [
                    {
                        "min" : "0",
                        "max" : "22"
                    },
                    ],
                    "range" : {
                        "min" : "0",
                        "max" : "22"
                    },
                },
            },
            "access" : "readonly",
            "description" :
                """A Timestamp of when the Total Input WH was last reset.""",
        }, # column
        "pdu3InputResettableEnergy" : {
            "nodetype" : "column",
            "moduleName" : "CPQPOWER-MIB",
            "oid" : "1.3.6.1.4.1.232.165.11.2.1.1.8",
            "status" : "current",
            "syntax" : {
                "type" : { "module" :"", "name" : "Integer32"},
            },
            "access" : "readonly",
            "description" :
                """A total input Watt-Hour value for all phases.  Units are 0.001 Wh. This value can be reset to 0 
using GUI. In that case, the pdu3InputPowerWattHourTimer will be reset as well  
A negative value indicates that this object is not available.""",
        }, # column
        "pdu3InputPowerFactor" : {
            "nodetype" : "column",
            "moduleName" : "CPQPOWER-MIB",
            "oid" : "1.3.6.1.4.1.232.165.11.2.1.1.9",
            "status" : "current",
            "syntax" : {
                "type" : { "module" :"", "name" : "Integer32"},
            },
            "access" : "readonly",
            "description" :
                """An input PF value.  Units are in thousandths, for example a power factor
of 0.958 would be returned as 958, and 0.92 would be returned as 920.  
A negative value indicates that this object is not available.""",
        }, # column
        "pdu3InputPowerVAR" : {
            "nodetype" : "column",
            "moduleName" : "CPQPOWER-MIB",
            "oid" : "1.3.6.1.4.1.232.165.11.2.1.1.10",
            "status" : "current",
            "syntax" : {
                "type" : { "module" :"", "name" : "Integer32"},
            },
            "access" : "readonly",
            "description" :
                """An input VAR value.  Units are 0.001 VAR.  A negative value indicates
that this object is not available.""",
        }, # column
        "pdu3InputPhaseTable" : {
            "nodetype" : "table",
            "moduleName" : "CPQPOWER-MIB",
            "oid" : "1.3.6.1.4.1.232.165.11.2.2",
            "status" : "current",
            "description" :
                """Aggregate Object with number of entries equal to number of PDUs (pdu3NumberPDU) and
number of input phase (pdu3InputPhaseCount).""",
        }, # table
        "pdu3InputPhaseEntry" : {
            "nodetype" : "row",
            "moduleName" : "CPQPOWER-MIB",
            "oid" : "1.3.6.1.4.1.232.165.11.2.2.1",
            "status" : "current",
            "linkage" : [
                "pdu3IdentIndex",
                "pdu3InputPhaseIndex",
            ],
            "description" :
                """The input table entry containing the voltage, current, frequency, power for each phase.
Entries are given with number of pdu and number of input phase 1, 2, or 3.""",
        }, # row
        "pdu3InputPhaseIndex" : {
            "nodetype" : "column",
            "moduleName" : "CPQPOWER-MIB",
            "oid" : "1.3.6.1.4.1.232.165.11.2.2.1.1",
            "status" : "current",
            "syntax" : {
                "type" :                 {
                    "basetype" : "Integer32",
                    "ranges" : [
                    {
                        "min" : "0",
                        "max" : "100"
                    },
                    ],
                    "range" : {
                        "min" : "0",
                        "max" : "100"
                    },
                },
            },
            "access" : "readonly",
            "description" :
                """Index for the Pdu3InputEntry table.""",
        }, # column
        "pdu3InputPhaseVoltageMeasType" : {
            "nodetype" : "column",
            "moduleName" : "CPQPOWER-MIB",
            "oid" : "1.3.6.1.4.1.232.165.11.2.2.1.2",
            "status" : "current",
            "syntax" : {
                "type" :                 {
                    "basetype" : "Enumeration",
                    "singlePhase" : {
                        "nodetype" : "namednumber",
                        "number" : "1"
                    },
                    "phase1toN" : {
                        "nodetype" : "namednumber",
                        "number" : "2"
                    },
                    "phase2toN" : {
                        "nodetype" : "namednumber",
                        "number" : "3"
                    },
                    "phase3toN" : {
                        "nodetype" : "namednumber",
                        "number" : "4"
                    },
                    "phase1to2" : {
                        "nodetype" : "namednumber",
                        "number" : "5"
                    },
                    "phase2to3" : {
                        "nodetype" : "namednumber",
                        "number" : "6"
                    },
                    "phase3to1" : {
                        "nodetype" : "namednumber",
                        "number" : "7"
                    },
                },
            },
            "access" : "readonly",
            "description" :
                """Value indicates what input voltage is being measured in this table row - single phase
voltage, phase 1 to neutral, phase 2 to neutral, phase 3 to neutral, phase 1 to phase 2,
phase 2 to phase 3, or phase 3 to phase 1.""",
        }, # column
        "pdu3InputPhaseVoltage" : {
            "nodetype" : "column",
            "moduleName" : "CPQPOWER-MIB",
            "oid" : "1.3.6.1.4.1.232.165.11.2.2.1.3",
            "status" : "current",
            "syntax" : {
                "type" : { "module" :"", "name" : "Integer32"},
            },
            "access" : "readonly",
            "description" :
                """An input voltage measurement value. Return value is divided by 10.""",
        }, # column
        "pdu3InputPhaseVoltageThStatus" : {
            "nodetype" : "column",
            "moduleName" : "CPQPOWER-MIB",
            "oid" : "1.3.6.1.4.1.232.165.11.2.2.1.4",
            "status" : "current",
            "syntax" : {
                "type" :                 {
                    "basetype" : "Enumeration",
                    "good" : {
                        "nodetype" : "namednumber",
                        "number" : "1"
                    },
                    "lowWarning" : {
                        "nodetype" : "namednumber",
                        "number" : "2"
                    },
                    "lowCritical" : {
                        "nodetype" : "namednumber",
                        "number" : "3"
                    },
                    "highWarning" : {
                        "nodetype" : "namednumber",
                        "number" : "4"
                    },
                    "highCritical" : {
                        "nodetype" : "namednumber",
                        "number" : "5"
                    },
                },
            },
            "access" : "readonly",
            "description" :
                """Status of the measured input voltage relative to the configured thresholds.""",
        }, # column
        "pdu3InputPhaseVoltageThLowerWarning" : {
            "nodetype" : "column",
            "moduleName" : "CPQPOWER-MIB",
            "oid" : "1.3.6.1.4.1.232.165.11.2.2.1.5",
            "status" : "current",
            "syntax" : {
                "type" :                 {
                    "basetype" : "Integer32",
                    "ranges" : [
                    {
                        "min" : "-1",
                        "max" : "500000"
                    },
                    ],
                    "range" : {
                        "min" : "-1",
                        "max" : "500000"
                    },
                },
            },
            "access" : "readonly",
            "description" :
                """Lower warning threshold.  Return value is divided by 10. A negative value indicates
that this object is not available.""",
        }, # column
        "pdu3InputPhaseVoltageThLowerCritical" : {
            "nodetype" : "column",
            "moduleName" : "CPQPOWER-MIB",
            "oid" : "1.3.6.1.4.1.232.165.11.2.2.1.6",
            "status" : "current",
            "syntax" : {
                "type" :                 {
                    "basetype" : "Integer32",
                    "ranges" : [
                    {
                        "min" : "-1",
                        "max" : "500000"
                    },
                    ],
                    "range" : {
                        "min" : "-1",
                        "max" : "500000"
                    },
                },
            },
            "access" : "readonly",
            "description" :
                """Lower critical threshold.  Return value is divided by 10. A negative value indicates
that this object is not available.""",
        }, # column
        "pdu3InputPhaseVoltageThUpperWarning" : {
            "nodetype" : "column",
            "moduleName" : "CPQPOWER-MIB",
            "oid" : "1.3.6.1.4.1.232.165.11.2.2.1.7",
            "status" : "current",
            "syntax" : {
                "type" :                 {
                    "basetype" : "Integer32",
                    "ranges" : [
                    {
                        "min" : "-1",
                        "max" : "500000"
                    },
                    ],
                    "range" : {
                        "min" : "-1",
                        "max" : "500000"
                    },
                },
            },
            "access" : "readonly",
            "description" :
                """Upper warning threshold.  Return value is divided by 10. A negative value indicates
that this object is not available.""",
        }, # column
        "pdu3InputPhaseVoltageThUpperCritical" : {
            "nodetype" : "column",
            "moduleName" : "CPQPOWER-MIB",
            "oid" : "1.3.6.1.4.1.232.165.11.2.2.1.8",
            "status" : "current",
            "syntax" : {
                "type" :                 {
                    "basetype" : "Integer32",
                    "ranges" : [
                    {
                        "min" : "-1",
                        "max" : "500000"
                    },
                    ],
                    "range" : {
                        "min" : "-1",
                        "max" : "500000"
                    },
                },
            },
            "access" : "readonly",
            "description" :
                """Upper critical threshold.  Return value is divided by 10. A negative value indicates
that this object is not available.""",
        }, # column
        "pdu3InputPhaseCurrentMeasType" : {
            "nodetype" : "column",
            "moduleName" : "CPQPOWER-MIB",
            "oid" : "1.3.6.1.4.1.232.165.11.2.2.1.9",
            "status" : "current",
            "syntax" : {
                "type" :                 {
                    "basetype" : "Enumeration",
                    "singlePhase" : {
                        "nodetype" : "namednumber",
                        "number" : "1"
                    },
                    "neutral" : {
                        "nodetype" : "namednumber",
                        "number" : "2"
                    },
                    "phase1" : {
                        "nodetype" : "namednumber",
                        "number" : "3"
                    },
                    "phase2" : {
                        "nodetype" : "namednumber",
                        "number" : "4"
                    },
                    "phase3" : {
                        "nodetype" : "namednumber",
                        "number" : "5"
                    },
                },
            },
            "access" : "readonly",
            "description" :
                """Which input wire is being measured in this table row - single phase, neutral, phase 1,
phase 2, or phase 3.""",
        }, # column
        "pdu3InputPhaseCurrentRating" : {
            "nodetype" : "column",
            "moduleName" : "CPQPOWER-MIB",
            "oid" : "1.3.6.1.4.1.232.165.11.2.2.1.10",
            "status" : "current",
            "syntax" : {
                "type" : { "module" :"", "name" : "Integer32"},
            },
            "access" : "readonly",
            "description" :
                """Rated current capacity of the input.  A negative value indicates that
the hardware current capacity is unknown. Return value is divided by 100.""",
        }, # column
        "pdu3InputPhaseCurrent" : {
            "nodetype" : "column",
            "moduleName" : "CPQPOWER-MIB",
            "oid" : "1.3.6.1.4.1.232.165.11.2.2.1.11",
            "status" : "current",
            "syntax" : {
                "type" : { "module" :"", "name" : "Integer32"},
            },
            "access" : "readonly",
            "description" :
                """An input current measurement value. Return value is divided by 100.""",
        }, # column
        "pdu3InputPhaseCurrentThStatus" : {
            "nodetype" : "column",
            "moduleName" : "CPQPOWER-MIB",
            "oid" : "1.3.6.1.4.1.232.165.11.2.2.1.12",
            "status" : "current",
            "syntax" : {
                "type" :                 {
                    "basetype" : "Enumeration",
                    "good" : {
                        "nodetype" : "namednumber",
                        "number" : "1"
                    },
                    "lowWarning" : {
                        "nodetype" : "namednumber",
                        "number" : "2"
                    },
                    "lowCritical" : {
                        "nodetype" : "namednumber",
                        "number" : "3"
                    },
                    "highWarning" : {
                        "nodetype" : "namednumber",
                        "number" : "4"
                    },
                    "highCritical" : {
                        "nodetype" : "namednumber",
                        "number" : "5"
                    },
                },
            },
            "access" : "readonly",
            "description" :
                """Status of the measured input current relative to the configured thresholds.""",
        }, # column
        "pdu3InputPhaseCurrentThLowerWarning" : {
            "nodetype" : "column",
            "moduleName" : "CPQPOWER-MIB",
            "oid" : "1.3.6.1.4.1.232.165.11.2.2.1.13",
            "status" : "current",
            "syntax" : {
                "type" :                 {
                    "basetype" : "Integer32",
                    "ranges" : [
                    {
                        "min" : "-1",
                        "max" : "100000"
                    },
                    ],
                    "range" : {
                        "min" : "-1",
                        "max" : "100000"
                    },
                },
            },
            "access" : "readonly",
            "description" :
                """Lower warning threshold.  Return value is divided by 100.  A negative value indicates
that this object is not available.""",
        }, # column
        "pdu3InputPhaseCurrentThLowerCritical" : {
            "nodetype" : "column",
            "moduleName" : "CPQPOWER-MIB",
            "oid" : "1.3.6.1.4.1.232.165.11.2.2.1.14",
            "status" : "current",
            "syntax" : {
                "type" :                 {
                    "basetype" : "Integer32",
                    "ranges" : [
                    {
                        "min" : "-1",
                        "max" : "100000"
                    },
                    ],
                    "range" : {
                        "min" : "-1",
                        "max" : "100000"
                    },
                },
            },
            "access" : "readonly",
            "description" :
                """Lower critical threshold.  Return value is divided by 100.  A negative value indicates
that this object is not available.""",
        }, # column
        "pdu3InputPhaseCurrentThUpperWarning" : {
            "nodetype" : "column",
            "moduleName" : "CPQPOWER-MIB",
            "oid" : "1.3.6.1.4.1.232.165.11.2.2.1.15",
            "status" : "current",
            "syntax" : {
                "type" :                 {
                    "basetype" : "Integer32",
                    "ranges" : [
                    {
                        "min" : "-1",
                        "max" : "100000"
                    },
                    ],
                    "range" : {
                        "min" : "-1",
                        "max" : "100000"
                    },
                },
            },
            "access" : "readonly",
            "description" :
                """Upper warning threshold. Return value is divided by 100.  A negative value indicates
that this object is not available.""",
        }, # column
        "pdu3InputPhaseCurrentThUpperCritical" : {
            "nodetype" : "column",
            "moduleName" : "CPQPOWER-MIB",
            "oid" : "1.3.6.1.4.1.232.165.11.2.2.1.16",
            "status" : "current",
            "syntax" : {
                "type" :                 {
                    "basetype" : "Integer32",
                    "ranges" : [
                    {
                        "min" : "-1",
                        "max" : "100000"
                    },
                    ],
                    "range" : {
                        "min" : "-1",
                        "max" : "100000"
                    },
                },
            },
            "access" : "readonly",
            "description" :
                """Upper critical threshold. Return value is divided by 100.  A negative value indicates
that this object is not available.""",
        }, # column
        "pdu3InputPhaseCurrentPercentLoad" : {
            "nodetype" : "column",
            "moduleName" : "CPQPOWER-MIB",
            "oid" : "1.3.6.1.4.1.232.165.11.2.2.1.17",
            "status" : "current",
            "syntax" : {
                "type" : { "module" :"", "name" : "Integer32"},
            },
            "access" : "readonly",
            "description" :
                """Current percent load, based on the rated current capacity.  Units are
percentage, for example 80.9 % will be returned as 809.  A negative
value indicates that this object is not available.""",
        }, # column
        "pdu3InputPhasePowerMeasType" : {
            "nodetype" : "column",
            "moduleName" : "CPQPOWER-MIB",
            "oid" : "1.3.6.1.4.1.232.165.11.2.2.1.18",
            "status" : "current",
            "syntax" : {
                "type" :                 {
                    "basetype" : "Enumeration",
                    "singlePhase" : {
                        "nodetype" : "namednumber",
                        "number" : "1"
                    },
                    "neutral" : {
                        "nodetype" : "namednumber",
                        "number" : "2"
                    },
                    "phase1" : {
                        "nodetype" : "namednumber",
                        "number" : "3"
                    },
                    "phase2" : {
                        "nodetype" : "namednumber",
                        "number" : "4"
                    },
                    "phase3" : {
                        "nodetype" : "namednumber",
                        "number" : "5"
                    },
                },
            },
            "access" : "readonly",
            "description" :
                """Which input wire is being measured in this table row - single phase, neutral, phase 1,
phase 2, or phase 3.""",
        }, # column
        "pdu3InputPhasePowerVA" : {
            "nodetype" : "column",
            "moduleName" : "CPQPOWER-MIB",
            "oid" : "1.3.6.1.4.1.232.165.11.2.2.1.19",
            "status" : "current",
            "syntax" : {
                "type" : { "module" :"", "name" : "Integer32"},
            },
            "access" : "readonly",
            "description" :
                """An input VA value.  Units are VA.  A negative value indicates
that this object is not available.""",
        }, # column
        "pdu3InputPhasePowerWatts" : {
            "nodetype" : "column",
            "moduleName" : "CPQPOWER-MIB",
            "oid" : "1.3.6.1.4.1.232.165.11.2.2.1.20",
            "status" : "current",
            "syntax" : {
                "type" : { "module" :"", "name" : "Integer32"},
            },
            "access" : "readonly",
            "description" :
                """An input Watts value.  Units are Watts.  A negative value indicates
that this object is not available.""",
        }, # column
        "pdu3InputPhasePowerWattHour" : {
            "nodetype" : "column",
            "moduleName" : "CPQPOWER-MIB",
            "oid" : "1.3.6.1.4.1.232.165.11.2.2.1.21",
            "status" : "current",
            "syntax" : {
                "type" : { "module" :"", "name" : "Integer32"},
            },
            "access" : "readonly",
            "description" :
                """A kWatt-Hour value for each Input phase.  Units are kWh. This value can be reset to 0 
using GUI. In that case, the pdu3InputPhasePowerWattHourTimer will be reset as well    
A negative value indicates that this object is not available.""",
        }, # column
        "pdu3InputPhasePowerWattHourTimer" : {
            "nodetype" : "column",
            "moduleName" : "CPQPOWER-MIB",
            "oid" : "1.3.6.1.4.1.232.165.11.2.2.1.22",
            "status" : "current",
            "syntax" : {
                "type" :                 {
                    "basetype" : "OctetString",
                    "parent module" : {
                        "name" : "RFC1213-MIB",
                        "type" : "DisplayString",
                    },
                    "ranges" : [
                    {
                        "min" : "0",
                        "max" : "22"
                    },
                    ],
                    "range" : {
                        "min" : "0",
                        "max" : "22"
                    },
                },
            },
            "access" : "readonly",
            "description" :
                """Timestamp of when input phase kWatt-hours (kWh) was last reset.""",
        }, # column
        "pdu3InputPhasePowerFactor" : {
            "nodetype" : "column",
            "moduleName" : "CPQPOWER-MIB",
            "oid" : "1.3.6.1.4.1.232.165.11.2.2.1.23",
            "status" : "current",
            "syntax" : {
                "type" : { "module" :"", "name" : "Integer32"},
            },
            "access" : "readonly",
            "description" :
                """An input PF value.  Return value is divided by 100, for example a power factor
of 0.95 would be returned as 95.  A negative value indicates that this object is not available.""",
        }, # column
        "pdu3InputPhasePowerVAR" : {
            "nodetype" : "column",
            "moduleName" : "CPQPOWER-MIB",
            "oid" : "1.3.6.1.4.1.232.165.11.2.2.1.24",
            "status" : "current",
            "syntax" : {
                "type" : { "module" :"", "name" : "Integer32"},
            },
            "access" : "readonly",
            "description" :
                """An input VA Reactive value.  Units are in VAR.  A negative value indicates
that this object is not available.""",
        }, # column
        "pdu3Group" : {
            "nodetype" : "node",
            "moduleName" : "CPQPOWER-MIB",
            "oid" : "1.3.6.1.4.1.232.165.11.3",
        }, # node
        "pdu3GroupTable" : {
            "nodetype" : "table",
            "moduleName" : "CPQPOWER-MIB",
            "oid" : "1.3.6.1.4.1.232.165.11.3.1",
            "status" : "current",
            "description" :
                """Aggregate Object with number of entries equal to number of PDUs
and number of breakers (pdu3GroupCount).""",
        }, # table
        "pdu3GroupEntry" : {
            "nodetype" : "row",
            "moduleName" : "CPQPOWER-MIB",
            "oid" : "1.3.6.1.4.1.232.165.11.3.1.1",
            "status" : "current",
            "linkage" : [
                "pdu3IdentIndex",
                "pdu3GroupIndex",
            ],
            "description" :
                """The input table entry containing the name, voltages, currents, power, etc.""",
        }, # row
        "pdu3GroupIndex" : {
            "nodetype" : "column",
            "moduleName" : "CPQPOWER-MIB",
            "oid" : "1.3.6.1.4.1.232.165.11.3.1.1.1",
            "status" : "current",
            "syntax" : {
                "type" :                 {
                    "basetype" : "Integer32",
                    "ranges" : [
                    {
                        "min" : "0",
                        "max" : "100"
                    },
                    ],
                    "range" : {
                        "min" : "0",
                        "max" : "100"
                    },
                },
            },
            "access" : "readonly",
            "description" :
                """Index for the Pdu3GroupEntry table.""",
        }, # column
        "pdu3GroupName" : {
            "nodetype" : "column",
            "moduleName" : "CPQPOWER-MIB",
            "oid" : "1.3.6.1.4.1.232.165.11.3.1.1.2",
            "status" : "current",
            "syntax" : {
                "type" :                 {
                    "basetype" : "OctetString",
                    "parent module" : {
                        "name" : "RFC1213-MIB",
                        "type" : "DisplayString",
                    },
                    "ranges" : [
                    {
                        "min" : "1",
                        "max" : "31"
                    },
                    ],
                    "range" : {
                        "min" : "1",
                        "max" : "31"
                    },
                },
            },
            "access" : "readonly",
            "description" :
                """A descriptive name for the group.""",
        }, # column
        "pdu3GroupType" : {
            "nodetype" : "column",
            "moduleName" : "CPQPOWER-MIB",
            "oid" : "1.3.6.1.4.1.232.165.11.3.1.1.3",
            "status" : "current",
            "syntax" : {
                "type" :                 {
                    "basetype" : "Enumeration",
                    "breaker1pole" : {
                        "nodetype" : "namednumber",
                        "number" : "2"
                    },
                    "breaker2pole" : {
                        "nodetype" : "namednumber",
                        "number" : "3"
                    },
                    "breaker3pole" : {
                        "nodetype" : "namednumber",
                        "number" : "4"
                    },
                    "outletSection" : {
                        "nodetype" : "namednumber",
                        "number" : "5"
                    },
                },
            },
            "access" : "readonly",
            "description" :
                """The type of the group. (5) has no breaker""",
        }, # column
        "pdu3GroupVoltageMeasType" : {
            "nodetype" : "column",
            "moduleName" : "CPQPOWER-MIB",
            "oid" : "1.3.6.1.4.1.232.165.11.3.1.1.4",
            "status" : "current",
            "syntax" : {
                "type" :                 {
                    "basetype" : "Enumeration",
                    "singlePhase" : {
                        "nodetype" : "namednumber",
                        "number" : "1"
                    },
                    "phase1toN" : {
                        "nodetype" : "namednumber",
                        "number" : "2"
                    },
                    "phase2toN" : {
                        "nodetype" : "namednumber",
                        "number" : "3"
                    },
                    "phase3toN" : {
                        "nodetype" : "namednumber",
                        "number" : "4"
                    },
                    "phase1to2" : {
                        "nodetype" : "namednumber",
                        "number" : "5"
                    },
                    "phase2to3" : {
                        "nodetype" : "namednumber",
                        "number" : "6"
                    },
                    "phase3to1" : {
                        "nodetype" : "namednumber",
                        "number" : "7"
                    },
                },
            },
            "access" : "readonly",
            "description" :
                """Value indicates what input voltage is being measured in this table row - single phase
voltage, phase 1 to neutral, phase 2 to neutral, phase 3 to neutral, phase 1 to phase 2,
phase 2 to phase 3, or phase 3 to phase 1.""",
        }, # column
        "pdu3GroupVoltage" : {
            "nodetype" : "column",
            "moduleName" : "CPQPOWER-MIB",
            "oid" : "1.3.6.1.4.1.232.165.11.3.1.1.5",
            "status" : "current",
            "syntax" : {
                "type" : { "module" :"", "name" : "Integer32"},
            },
            "access" : "readonly",
            "description" :
                """Return value is divided by 10 to get one decimal point, unit is in Volt.""",
        }, # column
        "pdu3GroupVoltageThStatus" : {
            "nodetype" : "column",
            "moduleName" : "CPQPOWER-MIB",
            "oid" : "1.3.6.1.4.1.232.165.11.3.1.1.6",
            "status" : "current",
            "syntax" : {
                "type" :                 {
                    "basetype" : "Enumeration",
                    "good" : {
                        "nodetype" : "namednumber",
                        "number" : "1"
                    },
                    "lowWarning" : {
                        "nodetype" : "namednumber",
                        "number" : "2"
                    },
                    "lowCritical" : {
                        "nodetype" : "namednumber",
                        "number" : "3"
                    },
                    "highWarning" : {
                        "nodetype" : "namednumber",
                        "number" : "4"
                    },
                    "highCritical" : {
                        "nodetype" : "namednumber",
                        "number" : "5"
                    },
                },
            },
            "access" : "readonly",
            "description" :
                """Status of the measured group voltage relative to the configured thresholds.""",
        }, # column
        "pdu3GroupVoltageThLowerWarning" : {
            "nodetype" : "column",
            "moduleName" : "CPQPOWER-MIB",
            "oid" : "1.3.6.1.4.1.232.165.11.3.1.1.7",
            "status" : "current",
            "syntax" : {
                "type" :                 {
                    "basetype" : "Integer32",
                    "ranges" : [
                    {
                        "min" : "-1",
                        "max" : "500000"
                    },
                    ],
                    "range" : {
                        "min" : "-1",
                        "max" : "500000"
                    },
                },
            },
            "access" : "readonly",
            "description" :
                """Lower warning threshold.  Return value is divided by 10 to get one decimal point, 
unit is in Volt.  A negative value indicates that this object is not available.""",
        }, # column
        "pdu3GroupVoltageThLowerCritical" : {
            "nodetype" : "column",
            "moduleName" : "CPQPOWER-MIB",
            "oid" : "1.3.6.1.4.1.232.165.11.3.1.1.8",
            "status" : "current",
            "syntax" : {
                "type" :                 {
                    "basetype" : "Integer32",
                    "ranges" : [
                    {
                        "min" : "-1",
                        "max" : "500000"
                    },
                    ],
                    "range" : {
                        "min" : "-1",
                        "max" : "500000"
                    },
                },
            },
            "access" : "readonly",
            "description" :
                """Lower critical threshold.  Return value is divided by 10 to get one decimal point, 
unit is in Volt.  A negative value indicates that this object is not available.""",
        }, # column
        "pdu3GroupVoltageThUpperWarning" : {
            "nodetype" : "column",
            "moduleName" : "CPQPOWER-MIB",
            "oid" : "1.3.6.1.4.1.232.165.11.3.1.1.9",
            "status" : "current",
            "syntax" : {
                "type" :                 {
                    "basetype" : "Integer32",
                    "ranges" : [
                    {
                        "min" : "-1",
                        "max" : "500000"
                    },
                    ],
                    "range" : {
                        "min" : "-1",
                        "max" : "500000"
                    },
                },
            },
            "access" : "readonly",
            "description" :
                """Upper warning threshold.  Return value is divided by 10 to get one decimal point, 
unit is in Volt.  A negative value indicates that this object is not available.""",
        }, # column
        "pdu3GroupVoltageThUpperCritical" : {
            "nodetype" : "column",
            "moduleName" : "CPQPOWER-MIB",
            "oid" : "1.3.6.1.4.1.232.165.11.3.1.1.10",
            "status" : "current",
            "syntax" : {
                "type" :                 {
                    "basetype" : "Integer32",
                    "ranges" : [
                    {
                        "min" : "-1",
                        "max" : "500000"
                    },
                    ],
                    "range" : {
                        "min" : "-1",
                        "max" : "500000"
                    },
                },
            },
            "access" : "readonly",
            "description" :
                """Upper critical threshold.  Return value is divided by 10 to get one decimal point, 
unit is in Volt.  A negative value indicates that this object is not available.""",
        }, # column
        "pdu3groupCurrentRating" : {
            "nodetype" : "column",
            "moduleName" : "CPQPOWER-MIB",
            "oid" : "1.3.6.1.4.1.232.165.11.3.1.1.11",
            "status" : "current",
            "syntax" : {
                "type" : { "module" :"", "name" : "Integer32"},
            },
            "access" : "readonly",
            "description" :
                """Rated current capacity of the group.  Return value is divided by 100 to get two decimal points, 
unit is in Amps.  A negative value indicates that the hardware current capacity is unknown (it
 will always be unknown for custom groups).""",
        }, # column
        "pdu3GroupCurrent" : {
            "nodetype" : "column",
            "moduleName" : "CPQPOWER-MIB",
            "oid" : "1.3.6.1.4.1.232.165.11.3.1.1.12",
            "status" : "current",
            "syntax" : {
                "type" : { "module" :"", "name" : "Integer32"},
            },
            "access" : "readonly",
            "description" :
                """A group current measurement value. Return value is divided by 100 to get two decimal points.""",
        }, # column
        "pdu3GroupCurrentThStatus" : {
            "nodetype" : "column",
            "moduleName" : "CPQPOWER-MIB",
            "oid" : "1.3.6.1.4.1.232.165.11.3.1.1.13",
            "status" : "current",
            "syntax" : {
                "type" :                 {
                    "basetype" : "Enumeration",
                    "good" : {
                        "nodetype" : "namednumber",
                        "number" : "1"
                    },
                    "lowWarning" : {
                        "nodetype" : "namednumber",
                        "number" : "2"
                    },
                    "lowCritical" : {
                        "nodetype" : "namednumber",
                        "number" : "3"
                    },
                    "highWarning" : {
                        "nodetype" : "namednumber",
                        "number" : "4"
                    },
                    "highCritical" : {
                        "nodetype" : "namednumber",
                        "number" : "5"
                    },
                },
            },
            "access" : "readonly",
            "description" :
                """Status of the measured group current relative to the configured thresholds.""",
        }, # column
        "pdu3GroupCurrentThLowerWarning" : {
            "nodetype" : "column",
            "moduleName" : "CPQPOWER-MIB",
            "oid" : "1.3.6.1.4.1.232.165.11.3.1.1.14",
            "status" : "current",
            "syntax" : {
                "type" :                 {
                    "basetype" : "Integer32",
                    "ranges" : [
                    {
                        "min" : "-1",
                        "max" : "100000"
                    },
                    ],
                    "range" : {
                        "min" : "-1",
                        "max" : "100000"
                    },
                },
            },
            "access" : "readonly",
            "description" :
                """Lower warning threshold.  Return value is divided by 100 to get two decimal points.  A negative value indicates
that this object is not available.""",
        }, # column
        "pdu3GroupCurrentThLowerCritical" : {
            "nodetype" : "column",
            "moduleName" : "CPQPOWER-MIB",
            "oid" : "1.3.6.1.4.1.232.165.11.3.1.1.15",
            "status" : "current",
            "syntax" : {
                "type" :                 {
                    "basetype" : "Integer32",
                    "ranges" : [
                    {
                        "min" : "-1",
                        "max" : "100000"
                    },
                    ],
                    "range" : {
                        "min" : "-1",
                        "max" : "100000"
                    },
                },
            },
            "access" : "readonly",
            "description" :
                """Lower critical threshold.  Return value is divided by 100 to get two decimal points.  A negative value indicates
that this object is not available.""",
        }, # column
        "pdu3GroupCurrentThUpperWarning" : {
            "nodetype" : "column",
            "moduleName" : "CPQPOWER-MIB",
            "oid" : "1.3.6.1.4.1.232.165.11.3.1.1.16",
            "status" : "current",
            "syntax" : {
                "type" :                 {
                    "basetype" : "Integer32",
                    "ranges" : [
                    {
                        "min" : "-1",
                        "max" : "100000"
                    },
                    ],
                    "range" : {
                        "min" : "-1",
                        "max" : "100000"
                    },
                },
            },
            "access" : "readonly",
            "description" :
                """Upper warning threshold.  Return value is divided by 100 to get two decimal points.  A negative value indicates
that this object is not available.""",
        }, # column
        "pdu3GroupCurrentThUpperCritical" : {
            "nodetype" : "column",
            "moduleName" : "CPQPOWER-MIB",
            "oid" : "1.3.6.1.4.1.232.165.11.3.1.1.17",
            "status" : "current",
            "syntax" : {
                "type" :                 {
                    "basetype" : "Integer32",
                    "ranges" : [
                    {
                        "min" : "-1",
                        "max" : "100000"
                    },
                    ],
                    "range" : {
                        "min" : "-1",
                        "max" : "100000"
                    },
                },
            },
            "access" : "readonly",
            "description" :
                """Upper critical threshold. Return value is divided by 100 to get two decimal points.  A negative value indicates
that this object is not available.""",
        }, # column
        "pdu3GroupCurrentPercentLoad" : {
            "nodetype" : "column",
            "moduleName" : "CPQPOWER-MIB",
            "oid" : "1.3.6.1.4.1.232.165.11.3.1.1.18",
            "status" : "current",
            "syntax" : {
                "type" : { "module" :"", "name" : "Integer32"},
            },
            "access" : "readonly",
            "description" :
                """Current percent load, based on the rated current capacity.  Units are
percentage, for example 80.9 % will be returned as 809.  A negative
value indicates that this object is not available.""",
        }, # column
        "pdu3GroupPowerVA" : {
            "nodetype" : "column",
            "moduleName" : "CPQPOWER-MIB",
            "oid" : "1.3.6.1.4.1.232.165.11.3.1.1.19",
            "status" : "current",
            "syntax" : {
                "type" : { "module" :"", "name" : "Integer32"},
            },
            "access" : "readonly",
            "description" :
                """A group VA value.  Units are VA.  A negative value indicates
that this object is not available.""",
        }, # column
        "pdu3GroupPowerWatts" : {
            "nodetype" : "column",
            "moduleName" : "CPQPOWER-MIB",
            "oid" : "1.3.6.1.4.1.232.165.11.3.1.1.20",
            "status" : "current",
            "syntax" : {
                "type" : { "module" :"", "name" : "Integer32"},
            },
            "access" : "readonly",
            "description" :
                """A group power value.  Units are Watts.  A negative value indicates
that this object is not available.""",
        }, # column
        "pdu3GroupPowerWattHour" : {
            "nodetype" : "column",
            "moduleName" : "CPQPOWER-MIB",
            "oid" : "1.3.6.1.4.1.232.165.11.3.1.1.21",
            "status" : "current",
            "syntax" : {
                "type" : { "module" :"", "name" : "Integer32"},
            },
            "access" : "readonly",
            "description" :
                """An energy consumption value for each load segment.  Units are kWh. This value can be reset to 0 
using GUI. In that case, the pdu3GroupPowerWattHourTimer will be reset as well.    
A negative value indicates that this object is not available.""",
        }, # column
        "pdu3GroupPowerWattHourTimer" : {
            "nodetype" : "column",
            "moduleName" : "CPQPOWER-MIB",
            "oid" : "1.3.6.1.4.1.232.165.11.3.1.1.22",
            "status" : "current",
            "syntax" : {
                "type" :                 {
                    "basetype" : "OctetString",
                    "parent module" : {
                        "name" : "RFC1213-MIB",
                        "type" : "DisplayString",
                    },
                    "ranges" : [
                    {
                        "min" : "0",
                        "max" : "22"
                    },
                    ],
                    "range" : {
                        "min" : "0",
                        "max" : "22"
                    },
                },
            },
            "access" : "readonly",
            "description" :
                """Timestamp when group kilo Watt-hours (group kWh) is reset.""",
        }, # column
        "pdu3GroupPowerFactor" : {
            "nodetype" : "column",
            "moduleName" : "CPQPOWER-MIB",
            "oid" : "1.3.6.1.4.1.232.165.11.3.1.1.23",
            "status" : "current",
            "syntax" : {
                "type" : { "module" :"", "name" : "Integer32"},
            },
            "access" : "readonly",
            "description" :
                """A group PF value.  Return value is divided by 100, for example a power factor of 0.95 would be returned as 95.  
A negative value indicates that this object is not available.""",
        }, # column
        "pdu3GroupPowerVAR" : {
            "nodetype" : "column",
            "moduleName" : "CPQPOWER-MIB",
            "oid" : "1.3.6.1.4.1.232.165.11.3.1.1.24",
            "status" : "current",
            "syntax" : {
                "type" : { "module" :"", "name" : "Integer32"},
            },
            "access" : "readonly",
            "description" :
                """A measurement for group/load segment power reactive. Units are VAR.  A negative value indicates
that this object is not available.""",
        }, # column
        "pdu3GroupOutletCount" : {
            "nodetype" : "column",
            "moduleName" : "CPQPOWER-MIB",
            "oid" : "1.3.6.1.4.1.232.165.11.3.1.1.25",
            "status" : "current",
            "syntax" : {
                "type" :                 {
                    "basetype" : "Integer32",
                    "ranges" : [
                    {
                        "min" : "0",
                        "max" : "63"
                    },
                    ],
                    "range" : {
                        "min" : "0",
                        "max" : "63"
                    },
                },
            },
            "access" : "readonly",
            "description" :
                """The number of outlets in each group (breaker).""",
        }, # column
        "pdu3GroupBreakerStatus" : {
            "nodetype" : "column",
            "moduleName" : "CPQPOWER-MIB",
            "oid" : "1.3.6.1.4.1.232.165.11.3.1.1.26",
            "status" : "current",
            "syntax" : {
                "type" :                 {
                    "basetype" : "Enumeration",
                    "notApplicable" : {
                        "nodetype" : "namednumber",
                        "number" : "1"
                    },
                    "breakerOn" : {
                        "nodetype" : "namednumber",
                        "number" : "2"
                    },
                    "breakerOff" : {
                        "nodetype" : "namednumber",
                        "number" : "3"
                    },
                },
            },
            "access" : "readonly",
            "description" :
                """Only applicable to groups with breaker.  Indicates whether a breaker is turned
off or on.""",
        }, # column
        "pdu3Environment" : {
            "nodetype" : "node",
            "moduleName" : "CPQPOWER-MIB",
            "oid" : "1.3.6.1.4.1.232.165.11.4",
        }, # node
        "pdu3EnvProbeTable" : {
            "nodetype" : "table",
            "moduleName" : "CPQPOWER-MIB",
            "oid" : "1.3.6.1.4.1.232.165.11.4.1",
            "status" : "current",
            "description" :
                """A list of environment probe (1 per PDU) for temperature, humidity, and contacts.  
The number of entries is given by number of PDUs in daisy chain.""",
        }, # table
        "pdu3EnvProbeEntry" : {
            "nodetype" : "row",
            "moduleName" : "CPQPOWER-MIB",
            "oid" : "1.3.6.1.4.1.232.165.11.4.1.1",
            "status" : "current",
            "linkage" : [
                "pdu3IdentIndex",
            ],
            "description" :
                """Aggregate entries equal to number of PDUs.""",
        }, # row
        "pdu3TemperatureScale" : {
            "nodetype" : "column",
            "moduleName" : "CPQPOWER-MIB",
            "oid" : "1.3.6.1.4.1.232.165.11.4.1.1.1",
            "status" : "current",
            "syntax" : {
                "type" :                 {
                    "basetype" : "Enumeration",
                    "celsius" : {
                        "nodetype" : "namednumber",
                        "number" : "1"
                    },
                    "fahrenheit" : {
                        "nodetype" : "namednumber",
                        "number" : "2"
                    },
                },
            },
            "access" : "readonly",
            "description" :
                """Scale used to return temperature objects.""",
        }, # column
        "pdu3TemperatureCount" : {
            "nodetype" : "column",
            "moduleName" : "CPQPOWER-MIB",
            "oid" : "1.3.6.1.4.1.232.165.11.4.1.1.2",
            "status" : "current",
            "syntax" : {
                "type" : { "module" :"", "name" : "Integer32"},
            },
            "access" : "readonly",
            "description" :
                """Max number of temperature measurements (1 per probe).""",
        }, # column
        "pdu3HumidityCount" : {
            "nodetype" : "column",
            "moduleName" : "CPQPOWER-MIB",
            "oid" : "1.3.6.1.4.1.232.165.11.4.1.1.3",
            "status" : "current",
            "syntax" : {
                "type" : { "module" :"", "name" : "Integer32"},
            },
            "access" : "readonly",
            "description" :
                """Max number of humidity measurements  (1 per probe).""",
        }, # column
        "pdu3ContactCount" : {
            "nodetype" : "column",
            "moduleName" : "CPQPOWER-MIB",
            "oid" : "1.3.6.1.4.1.232.165.11.4.1.1.4",
            "status" : "current",
            "syntax" : {
                "type" : { "module" :"", "name" : "Integer32"},
            },
            "access" : "readonly",
            "description" :
                """Max number of contact sensors  (1 per probe).""",
        }, # column
        "pdu3TemperatureTable" : {
            "nodetype" : "table",
            "moduleName" : "CPQPOWER-MIB",
            "oid" : "1.3.6.1.4.1.232.165.11.4.2",
            "status" : "current",
            "description" :
                """A list of temperature probe measurements.  The number of entries are
given by number of pdu and pdu3TemperatureCount.""",
        }, # table
        "pdu3TemperatureEntry" : {
            "nodetype" : "row",
            "moduleName" : "CPQPOWER-MIB",
            "oid" : "1.3.6.1.4.1.232.165.11.4.2.1",
            "status" : "current",
            "linkage" : [
                "pdu3IdentIndex",
                "pdu3TemperatureIndex",
            ],
            "description" :
                """An entry for a temperature measurement.""",
        }, # row
        "pdu3TemperatureIndex" : {
            "nodetype" : "column",
            "moduleName" : "CPQPOWER-MIB",
            "oid" : "1.3.6.1.4.1.232.165.11.4.2.1.1",
            "status" : "current",
            "syntax" : {
                "type" :                 {
                    "basetype" : "Integer32",
                    "ranges" : [
                    {
                        "min" : "1",
                        "max" : "2"
                    },
                    ],
                    "range" : {
                        "min" : "1",
                        "max" : "2"
                    },
                },
            },
            "access" : "readonly",
            "description" :
                """A unique value for each temperature probe measurement.  Its value
ranges from 1 to temperatureCount.""",
        }, # column
        "pdu3TemperatureName" : {
            "nodetype" : "column",
            "moduleName" : "CPQPOWER-MIB",
            "oid" : "1.3.6.1.4.1.232.165.11.4.2.1.2",
            "status" : "current",
            "syntax" : {
                "type" :                 {
                    "basetype" : "OctetString",
                    "parent module" : {
                        "name" : "RFC1213-MIB",
                        "type" : "DisplayString",
                    },
                    "ranges" : [
                    {
                        "min" : "1",
                        "max" : "31"
                    },
                    ],
                    "range" : {
                        "min" : "1",
                        "max" : "31"
                    },
                },
            },
            "access" : "readonly",
            "description" :
                """A descriptive name for the temperature probe.""",
        }, # column
        "pdu3TemperatureProbeStatus" : {
            "nodetype" : "column",
            "moduleName" : "CPQPOWER-MIB",
            "oid" : "1.3.6.1.4.1.232.165.11.4.2.1.3",
            "status" : "current",
            "syntax" : {
                "type" :                 {
                    "basetype" : "Enumeration",
                    "disconnected" : {
                        "nodetype" : "namednumber",
                        "number" : "1"
                    },
                    "connected" : {
                        "nodetype" : "namednumber",
                        "number" : "2"
                    },
                    "bad" : {
                        "nodetype" : "namednumber",
                        "number" : "3"
                    },
                },
            },
            "access" : "readonly",
            "description" :
                """Indicates whether a probe is connected or not.""",
        }, # column
        "pdu3TemperatureValue" : {
            "nodetype" : "column",
            "moduleName" : "CPQPOWER-MIB",
            "oid" : "1.3.6.1.4.1.232.165.11.4.2.1.4",
            "status" : "current",
            "syntax" : {
                "type" : { "module" :"", "name" : "Integer32"},
            },
            "access" : "readonly",
            "description" :
                """Units are in tenths of a degree (either Fahrenheit or Celsius). 
Return value is divided by 10 to get degrees.""",
        }, # column
        "pdu3TemperatureThStatus" : {
            "nodetype" : "column",
            "moduleName" : "CPQPOWER-MIB",
            "oid" : "1.3.6.1.4.1.232.165.11.4.2.1.5",
            "status" : "current",
            "syntax" : {
                "type" :                 {
                    "basetype" : "Enumeration",
                    "good" : {
                        "nodetype" : "namednumber",
                        "number" : "1"
                    },
                    "lowWarning" : {
                        "nodetype" : "namednumber",
                        "number" : "2"
                    },
                    "lowCritical" : {
                        "nodetype" : "namednumber",
                        "number" : "3"
                    },
                    "highWarning" : {
                        "nodetype" : "namednumber",
                        "number" : "4"
                    },
                    "highCritical" : {
                        "nodetype" : "namednumber",
                        "number" : "5"
                    },
                },
            },
            "access" : "readonly",
            "description" :
                """Status of the measured temperature relative to the configured thresholds.""",
        }, # column
        "pdu3TemperatureThLowerWarning" : {
            "nodetype" : "column",
            "moduleName" : "CPQPOWER-MIB",
            "oid" : "1.3.6.1.4.1.232.165.11.4.2.1.6",
            "status" : "current",
            "syntax" : {
                "type" :                 {
                    "basetype" : "Integer32",
                    "ranges" : [
                    {
                        "min" : "-1",
                        "max" : "150000"
                    },
                    ],
                    "range" : {
                        "min" : "-1",
                        "max" : "150000"
                    },
                },
            },
            "access" : "readonly",
            "description" :
                """Lower warning threshold.  Return value is divided by 10 to get degree.  A negative value
indicates that this object is not available.""",
        }, # column
        "pdu3TemperatureThLowerCritical" : {
            "nodetype" : "column",
            "moduleName" : "CPQPOWER-MIB",
            "oid" : "1.3.6.1.4.1.232.165.11.4.2.1.7",
            "status" : "current",
            "syntax" : {
                "type" :                 {
                    "basetype" : "Integer32",
                    "ranges" : [
                    {
                        "min" : "-1",
                        "max" : "150000"
                    },
                    ],
                    "range" : {
                        "min" : "-1",
                        "max" : "150000"
                    },
                },
            },
            "access" : "readonly",
            "description" :
                """Lower critical threshold. Return value is divided by 10 to get degree.  A negative value
indicates that this object is not available.""",
        }, # column
        "pdu3TemperatureThUpperWarning" : {
            "nodetype" : "column",
            "moduleName" : "CPQPOWER-MIB",
            "oid" : "1.3.6.1.4.1.232.165.11.4.2.1.8",
            "status" : "current",
            "syntax" : {
                "type" :                 {
                    "basetype" : "Integer32",
                    "ranges" : [
                    {
                        "min" : "-1",
                        "max" : "150000"
                    },
                    ],
                    "range" : {
                        "min" : "-1",
                        "max" : "150000"
                    },
                },
            },
            "access" : "readonly",
            "description" :
                """Upper warning threshold. Return value is divided by 10 to get degree.  A negative value
indicates that this object is not available.""",
        }, # column
        "pdu3TemperatureThUpperCritical" : {
            "nodetype" : "column",
            "moduleName" : "CPQPOWER-MIB",
            "oid" : "1.3.6.1.4.1.232.165.11.4.2.1.9",
            "status" : "current",
            "syntax" : {
                "type" :                 {
                    "basetype" : "Integer32",
                    "ranges" : [
                    {
                        "min" : "-1",
                        "max" : "150000"
                    },
                    ],
                    "range" : {
                        "min" : "-1",
                        "max" : "150000"
                    },
                },
            },
            "access" : "readonly",
            "description" :
                """Upper critical threshold. Return value is divided by 10 to get degree.  A negative value
indicates that this object is not available.""",
        }, # column
        "pdu3HumidityTable" : {
            "nodetype" : "table",
            "moduleName" : "CPQPOWER-MIB",
            "oid" : "1.3.6.1.4.1.232.165.11.4.3",
            "status" : "current",
            "description" :
                """A list of humidity probe measurements.  The number of entries are
given by number of pdu and pdu3HumidityCount.""",
        }, # table
        "pdu3HumidityEntry" : {
            "nodetype" : "row",
            "moduleName" : "CPQPOWER-MIB",
            "oid" : "1.3.6.1.4.1.232.165.11.4.3.1",
            "status" : "current",
            "linkage" : [
                "pdu3IdentIndex",
                "pdu3HumidityIndex",
            ],
            "description" :
                """An entry for a humidity measurement.""",
        }, # row
        "pdu3HumidityIndex" : {
            "nodetype" : "column",
            "moduleName" : "CPQPOWER-MIB",
            "oid" : "1.3.6.1.4.1.232.165.11.4.3.1.1",
            "status" : "current",
            "syntax" : {
                "type" :                 {
                    "basetype" : "Integer32",
                    "ranges" : [
                    {
                        "min" : "1",
                        "max" : "2"
                    },
                    ],
                    "range" : {
                        "min" : "1",
                        "max" : "2"
                    },
                },
            },
            "access" : "readonly",
            "description" :
                """A unique value for each humidity probe measurement.  Its value
ranges from 1 to pdu3HumidityCount per pdu.""",
        }, # column
        "pdu3HumidityName" : {
            "nodetype" : "column",
            "moduleName" : "CPQPOWER-MIB",
            "oid" : "1.3.6.1.4.1.232.165.11.4.3.1.2",
            "status" : "current",
            "syntax" : {
                "type" :                 {
                    "basetype" : "OctetString",
                    "parent module" : {
                        "name" : "RFC1213-MIB",
                        "type" : "DisplayString",
                    },
                    "ranges" : [
                    {
                        "min" : "1",
                        "max" : "31"
                    },
                    ],
                    "range" : {
                        "min" : "1",
                        "max" : "31"
                    },
                },
            },
            "access" : "readonly",
            "description" :
                """A descriptive name for the humidity probe.""",
        }, # column
        "pdu3HumidityProbeStatus" : {
            "nodetype" : "column",
            "moduleName" : "CPQPOWER-MIB",
            "oid" : "1.3.6.1.4.1.232.165.11.4.3.1.3",
            "status" : "current",
            "syntax" : {
                "type" :                 {
                    "basetype" : "Enumeration",
                    "disconnected" : {
                        "nodetype" : "namednumber",
                        "number" : "1"
                    },
                    "connected" : {
                        "nodetype" : "namednumber",
                        "number" : "2"
                    },
                    "bad" : {
                        "nodetype" : "namednumber",
                        "number" : "3"
                    },
                },
            },
            "access" : "readonly",
            "description" :
                """Indicates whether a probe is connected or not.""",
        }, # column
        "pdu3HumidityValue" : {
            "nodetype" : "column",
            "moduleName" : "CPQPOWER-MIB",
            "oid" : "1.3.6.1.4.1.232.165.11.4.3.1.4",
            "status" : "current",
            "syntax" : {
                "type" : { "module" :"", "name" : "Integer32"},
            },
            "access" : "readonly",
            "description" :
                """Units are tenths of a percent relative humidity. Return value is divided by 10 to get %RH.""",
        }, # column
        "pdu3HumidityThStatus" : {
            "nodetype" : "column",
            "moduleName" : "CPQPOWER-MIB",
            "oid" : "1.3.6.1.4.1.232.165.11.4.3.1.5",
            "status" : "current",
            "syntax" : {
                "type" :                 {
                    "basetype" : "Enumeration",
                    "good" : {
                        "nodetype" : "namednumber",
                        "number" : "1"
                    },
                    "lowWarning" : {
                        "nodetype" : "namednumber",
                        "number" : "2"
                    },
                    "lowCritical" : {
                        "nodetype" : "namednumber",
                        "number" : "3"
                    },
                    "highWarning" : {
                        "nodetype" : "namednumber",
                        "number" : "4"
                    },
                    "highCritical" : {
                        "nodetype" : "namednumber",
                        "number" : "5"
                    },
                },
            },
            "access" : "readonly",
            "description" :
                """Status of the measured humidity relative to the configured thresholds.""",
        }, # column
        "pdu3HumidityThLowerWarning" : {
            "nodetype" : "column",
            "moduleName" : "CPQPOWER-MIB",
            "oid" : "1.3.6.1.4.1.232.165.11.4.3.1.6",
            "status" : "current",
            "syntax" : {
                "type" :                 {
                    "basetype" : "Integer32",
                    "ranges" : [
                    {
                        "min" : "-1",
                        "max" : "1000"
                    },
                    ],
                    "range" : {
                        "min" : "-1",
                        "max" : "1000"
                    },
                },
            },
            "access" : "readonly",
            "description" :
                """Lower warning threshold. Return value is divided by 10 to get %RH.  A negative value
indicates that this object is not available.""",
        }, # column
        "pdu3HumidityThLowerCritical" : {
            "nodetype" : "column",
            "moduleName" : "CPQPOWER-MIB",
            "oid" : "1.3.6.1.4.1.232.165.11.4.3.1.7",
            "status" : "current",
            "syntax" : {
                "type" :                 {
                    "basetype" : "Integer32",
                    "ranges" : [
                    {
                        "min" : "-1",
                        "max" : "1000"
                    },
                    ],
                    "range" : {
                        "min" : "-1",
                        "max" : "1000"
                    },
                },
            },
            "access" : "readonly",
            "description" :
                """Lower critical threshold. Return value is divided by 10 to get %RH.  A negative value
indicates that this object is not available.""",
        }, # column
        "pdu3HumidityThUpperWarning" : {
            "nodetype" : "column",
            "moduleName" : "CPQPOWER-MIB",
            "oid" : "1.3.6.1.4.1.232.165.11.4.3.1.8",
            "status" : "current",
            "syntax" : {
                "type" :                 {
                    "basetype" : "Integer32",
                    "ranges" : [
                    {
                        "min" : "-1",
                        "max" : "1000"
                    },
                    ],
                    "range" : {
                        "min" : "-1",
                        "max" : "1000"
                    },
                },
            },
            "access" : "readonly",
            "description" :
                """Upper warning threshold. Return value is divided by 10 to get %RH.  A negative value
indicates that this object is not available.""",
        }, # column
        "pdu3HumidityThUpperCritical" : {
            "nodetype" : "column",
            "moduleName" : "CPQPOWER-MIB",
            "oid" : "1.3.6.1.4.1.232.165.11.4.3.1.9",
            "status" : "current",
            "syntax" : {
                "type" :                 {
                    "basetype" : "Integer32",
                    "ranges" : [
                    {
                        "min" : "-1",
                        "max" : "1000"
                    },
                    ],
                    "range" : {
                        "min" : "-1",
                        "max" : "1000"
                    },
                },
            },
            "access" : "readonly",
            "description" :
                """Upper critical threshold. Return value is divided by 10 to get %RH.  A negative value
indicates that this object is not available.""",
        }, # column
        "pdu3ContactTable" : {
            "nodetype" : "table",
            "moduleName" : "CPQPOWER-MIB",
            "oid" : "1.3.6.1.4.1.232.165.11.4.4",
            "status" : "current",
            "description" :
                """A list of contact sensors.  The number of entries are
given by number of pdu and pdu3ContactCount.""",
        }, # table
        "pdu3ContactEntry" : {
            "nodetype" : "row",
            "moduleName" : "CPQPOWER-MIB",
            "oid" : "1.3.6.1.4.1.232.165.11.4.4.1",
            "status" : "current",
            "linkage" : [
                "pdu3IdentIndex",
                "pdu3ContactIndex",
            ],
            "description" :
                """An entry for a contact sensor""",
        }, # row
        "pdu3ContactIndex" : {
            "nodetype" : "column",
            "moduleName" : "CPQPOWER-MIB",
            "oid" : "1.3.6.1.4.1.232.165.11.4.4.1.1",
            "status" : "current",
            "syntax" : {
                "type" :                 {
                    "basetype" : "Integer32",
                    "ranges" : [
                    {
                        "min" : "1",
                        "max" : "3"
                    },
                    ],
                    "range" : {
                        "min" : "1",
                        "max" : "3"
                    },
                },
            },
            "access" : "readonly",
            "description" :
                """A unique value for each contact sensor.  Its value ranges from 1 to
contactCount.""",
        }, # column
        "pdu3ContactName" : {
            "nodetype" : "column",
            "moduleName" : "CPQPOWER-MIB",
            "oid" : "1.3.6.1.4.1.232.165.11.4.4.1.2",
            "status" : "current",
            "syntax" : {
                "type" :                 {
                    "basetype" : "OctetString",
                    "parent module" : {
                        "name" : "RFC1213-MIB",
                        "type" : "DisplayString",
                    },
                    "ranges" : [
                    {
                        "min" : "1",
                        "max" : "31"
                    },
                    ],
                    "range" : {
                        "min" : "1",
                        "max" : "31"
                    },
                },
            },
            "access" : "readonly",
            "description" :
                """A descriptive name for the contact sensor.""",
        }, # column
        "pdu3ContactProbeStatus" : {
            "nodetype" : "column",
            "moduleName" : "CPQPOWER-MIB",
            "oid" : "1.3.6.1.4.1.232.165.11.4.4.1.3",
            "status" : "current",
            "syntax" : {
                "type" :                 {
                    "basetype" : "Enumeration",
                    "disconnected" : {
                        "nodetype" : "namednumber",
                        "number" : "1"
                    },
                    "connected" : {
                        "nodetype" : "namednumber",
                        "number" : "2"
                    },
                    "bad" : {
                        "nodetype" : "namednumber",
                        "number" : "3"
                    },
                },
            },
            "access" : "readonly",
            "description" :
                """Indicates whether a probe is connected or not.
Will not be returned  if the contact sensor is internal to the ePDU,
in that case only contactState should be read.""",
        }, # column
        "pdu3ContactState" : {
            "nodetype" : "column",
            "moduleName" : "CPQPOWER-MIB",
            "oid" : "1.3.6.1.4.1.232.165.11.4.4.1.4",
            "status" : "current",
            "syntax" : {
                "type" :                 {
                    "basetype" : "Enumeration",
                    "contactOpen" : {
                        "nodetype" : "namednumber",
                        "number" : "1"
                    },
                    "contactClosed" : {
                        "nodetype" : "namednumber",
                        "number" : "2"
                    },
                    "contactBad" : {
                        "nodetype" : "namednumber",
                        "number" : "3"
                    },
                },
            },
            "access" : "readonly",
            "description" :
                """The state of the contact sensor.""",
        }, # column
        "pdu3Outlet" : {
            "nodetype" : "node",
            "moduleName" : "CPQPOWER-MIB",
            "oid" : "1.3.6.1.4.1.232.165.11.5",
        }, # node
        "pdu3OutletTable" : {
            "nodetype" : "table",
            "moduleName" : "CPQPOWER-MIB",
            "oid" : "1.3.6.1.4.1.232.165.11.5.1",
            "status" : "current",
            "description" :
                """Aggregate Object with number of entries equal to Number of PDU (pdu3IdentIndex)
and Number of outlet per PDU (pdu3OutletIndex).""",
        }, # table
        "pdu3OutletEntry" : {
            "nodetype" : "row",
            "moduleName" : "CPQPOWER-MIB",
            "oid" : "1.3.6.1.4.1.232.165.11.5.1.1",
            "status" : "current",
            "linkage" : [
                "pdu3IdentIndex",
                "pdu3OutletIndex",
            ],
            "description" :
                """The Outlet table entry containing the type, voltage, current etc.""",
        }, # row
        "pdu3OutletIndex" : {
            "nodetype" : "column",
            "moduleName" : "CPQPOWER-MIB",
            "oid" : "1.3.6.1.4.1.232.165.11.5.1.1.1",
            "status" : "current",
            "syntax" : {
                "type" :                 {
                    "basetype" : "Integer32",
                    "ranges" : [
                    {
                        "min" : "0",
                        "max" : "100"
                    },
                    ],
                    "range" : {
                        "min" : "0",
                        "max" : "100"
                    },
                },
            },
            "access" : "readonly",
            "description" :
                """Index for each outlet, value from 1 to the number of outlets per PDU.""",
        }, # column
        "pdu3OutletName" : {
            "nodetype" : "column",
            "moduleName" : "CPQPOWER-MIB",
            "oid" : "1.3.6.1.4.1.232.165.11.5.1.1.2",
            "status" : "current",
            "syntax" : {
                "type" :                 {
                    "basetype" : "OctetString",
                    "parent module" : {
                        "name" : "RFC1213-MIB",
                        "type" : "DisplayString",
                    },
                    "ranges" : [
                    {
                        "min" : "1",
                        "max" : "31"
                    },
                    ],
                    "range" : {
                        "min" : "1",
                        "max" : "31"
                    },
                },
            },
            "access" : "readonly",
            "description" :
                """A descriptive name for the outlet.""",
        }, # column
        "pdu3OutletType" : {
            "nodetype" : "column",
            "moduleName" : "CPQPOWER-MIB",
            "oid" : "1.3.6.1.4.1.232.165.11.5.1.1.3",
            "status" : "current",
            "syntax" : {
                "type" :                 {
                    "basetype" : "Enumeration",
                    "iecC13" : {
                        "nodetype" : "namednumber",
                        "number" : "1"
                    },
                    "iecC19" : {
                        "nodetype" : "namednumber",
                        "number" : "2"
                    },
                    "uk" : {
                        "nodetype" : "namednumber",
                        "number" : "10"
                    },
                    "french" : {
                        "nodetype" : "namednumber",
                        "number" : "11"
                    },
                    "schuko" : {
                        "nodetype" : "namednumber",
                        "number" : "12"
                    },
                    "nema515" : {
                        "nodetype" : "namednumber",
                        "number" : "20"
                    },
                    "nema51520" : {
                        "nodetype" : "namednumber",
                        "number" : "21"
                    },
                    "nema520" : {
                        "nodetype" : "namednumber",
                        "number" : "22"
                    },
                    "nemaL520" : {
                        "nodetype" : "namednumber",
                        "number" : "23"
                    },
                    "nemaL530" : {
                        "nodetype" : "namednumber",
                        "number" : "24"
                    },
                    "nema615" : {
                        "nodetype" : "namednumber",
                        "number" : "25"
                    },
                    "nema620" : {
                        "nodetype" : "namednumber",
                        "number" : "26"
                    },
                    "nemaL620" : {
                        "nodetype" : "namednumber",
                        "number" : "27"
                    },
                    "nemaL630" : {
                        "nodetype" : "namednumber",
                        "number" : "28"
                    },
                    "nemaL715" : {
                        "nodetype" : "namednumber",
                        "number" : "29"
                    },
                    "rf203p277" : {
                        "nodetype" : "namednumber",
                        "number" : "30"
                    },
                },
            },
            "access" : "readonly",
            "description" :
                """Type of this outlet - C13, C19.""",
        }, # column
        "pdu3OutletCurrentRating" : {
            "nodetype" : "column",
            "moduleName" : "CPQPOWER-MIB",
            "oid" : "1.3.6.1.4.1.232.165.11.5.1.1.4",
            "status" : "current",
            "syntax" : {
                "type" : { "module" :"", "name" : "Integer32"},
            },
            "access" : "readonly",
            "description" :
                """Rated current capacity of this outlet. Return value is divided by 100 to get amps.  A negative 
value indicates that the hardware current capacity is unknown.""",
        }, # column
        "pdu3OutletCurrent" : {
            "nodetype" : "column",
            "moduleName" : "CPQPOWER-MIB",
            "oid" : "1.3.6.1.4.1.232.165.11.5.1.1.5",
            "status" : "current",
            "syntax" : {
                "type" : { "module" :"", "name" : "Integer32"},
            },
            "access" : "readonly",
            "description" :
                """A outlet current measurement value. Return value is divided by 100 to get amps.""",
        }, # column
        "pdu3OutletActivePowerThStatus" : {
            "nodetype" : "column",
            "moduleName" : "CPQPOWER-MIB",
            "oid" : "1.3.6.1.4.1.232.165.11.5.1.1.6",
            "status" : "current",
            "syntax" : {
                "type" :                 {
                    "basetype" : "Enumeration",
                    "good" : {
                        "nodetype" : "namednumber",
                        "number" : "1"
                    },
                    "lowWarning" : {
                        "nodetype" : "namednumber",
                        "number" : "2"
                    },
                    "lowCritical" : {
                        "nodetype" : "namednumber",
                        "number" : "3"
                    },
                    "highWarning" : {
                        "nodetype" : "namednumber",
                        "number" : "4"
                    },
                    "highCritical" : {
                        "nodetype" : "namednumber",
                        "number" : "5"
                    },
                },
            },
            "access" : "readonly",
            "description" :
                """Status of the measured outlet active power relative to the configured thresholds.""",
        }, # column
        "pdu3OutletActivePowerThLowerWarning" : {
            "nodetype" : "column",
            "moduleName" : "CPQPOWER-MIB",
            "oid" : "1.3.6.1.4.1.232.165.11.5.1.1.7",
            "status" : "current",
            "syntax" : {
                "type" :                 {
                    "basetype" : "Integer32",
                    "ranges" : [
                    {
                        "min" : "-1",
                        "max" : "10000"
                    },
                    ],
                    "range" : {
                        "min" : "-1",
                        "max" : "10000"
                    },
                },
            },
            "access" : "readonly",
            "description" :
                """Lower warning threshold.  Units are Watts(W).  A negative value indicates
that this object is not available.""",
        }, # column
        "pdu3OutletActivePowerThLowerCritical" : {
            "nodetype" : "column",
            "moduleName" : "CPQPOWER-MIB",
            "oid" : "1.3.6.1.4.1.232.165.11.5.1.1.8",
            "status" : "current",
            "syntax" : {
                "type" :                 {
                    "basetype" : "Integer32",
                    "ranges" : [
                    {
                        "min" : "-1",
                        "max" : "10000"
                    },
                    ],
                    "range" : {
                        "min" : "-1",
                        "max" : "10000"
                    },
                },
            },
            "access" : "readonly",
            "description" :
                """Lower critical threshold.  Units are Watts(W).  A negative value indicates
that this object is not available.""",
        }, # column
        "pdu3OutletActivePowerThUpperWarning" : {
            "nodetype" : "column",
            "moduleName" : "CPQPOWER-MIB",
            "oid" : "1.3.6.1.4.1.232.165.11.5.1.1.9",
            "status" : "current",
            "syntax" : {
                "type" :                 {
                    "basetype" : "Integer32",
                    "ranges" : [
                    {
                        "min" : "-1",
                        "max" : "10000"
                    },
                    ],
                    "range" : {
                        "min" : "-1",
                        "max" : "10000"
                    },
                },
            },
            "access" : "readonly",
            "description" :
                """Upper warning threshold.  Units are Watts(W).  A negative value indicates
that this object is not available.""",
        }, # column
        "pdu3OutletActivePowerThUpperCritical" : {
            "nodetype" : "column",
            "moduleName" : "CPQPOWER-MIB",
            "oid" : "1.3.6.1.4.1.232.165.11.5.1.1.10",
            "status" : "current",
            "syntax" : {
                "type" :                 {
                    "basetype" : "Integer32",
                    "ranges" : [
                    {
                        "min" : "-1",
                        "max" : "10000"
                    },
                    ],
                    "range" : {
                        "min" : "-1",
                        "max" : "10000"
                    },
                },
            },
            "access" : "readonly",
            "description" :
                """Upper critical threshold.  Units are Watts(W).  A negative value indicates
that this object is not available.""",
        }, # column
        "pdu3OutletCurrentPercentLoad" : {
            "nodetype" : "column",
            "moduleName" : "CPQPOWER-MIB",
            "oid" : "1.3.6.1.4.1.232.165.11.5.1.1.11",
            "status" : "current",
            "syntax" : {
                "type" : { "module" :"", "name" : "Integer32"},
            },
            "access" : "readonly",
            "description" :
                """Current percent load, based on the rated current capacity.  Units are
percentage, for example 80.5% will be returned as 805.  A negative
value indicates that this object is not available.""",
        }, # column
        "pdu3OutletVA" : {
            "nodetype" : "column",
            "moduleName" : "CPQPOWER-MIB",
            "oid" : "1.3.6.1.4.1.232.165.11.5.1.1.12",
            "status" : "current",
            "syntax" : {
                "type" : { "module" :"", "name" : "Integer32"},
            },
            "access" : "readonly",
            "description" :
                """A outlet power VA value.  Units are VA.  A negative value indicates
that this object is not available.""",
        }, # column
        "pdu3OutletWatts" : {
            "nodetype" : "column",
            "moduleName" : "CPQPOWER-MIB",
            "oid" : "1.3.6.1.4.1.232.165.11.5.1.1.13",
            "status" : "current",
            "syntax" : {
                "type" : { "module" :"", "name" : "Integer32"},
            },
            "access" : "readonly",
            "description" :
                """A outlet power in Watts value.  Units are Watts.  A negative value indicates
that this object is not available.""",
        }, # column
        "pdu3OutletWh" : {
            "nodetype" : "column",
            "moduleName" : "CPQPOWER-MIB",
            "oid" : "1.3.6.1.4.1.232.165.11.5.1.1.14",
            "status" : "current",
            "syntax" : {
                "type" : { "module" :"", "name" : "Integer32"},
            },
            "access" : "readonly",
            "description" :
                """An energy in kWatt-Hour value for each outlet.  Units are kWh.
This object is writable so that it can be reset to 0.  When it is
written to, the pdu3OutletWhTimer will be reset updated as well    
A negative value indicates that this object is not available.""",
        }, # column
        "pdu3OutletWhTimer" : {
            "nodetype" : "column",
            "moduleName" : "CPQPOWER-MIB",
            "oid" : "1.3.6.1.4.1.232.165.11.5.1.1.15",
            "status" : "current",
            "syntax" : {
                "type" :                 {
                    "basetype" : "OctetString",
                    "parent module" : {
                        "name" : "RFC1213-MIB",
                        "type" : "DisplayString",
                    },
                    "ranges" : [
                    {
                        "min" : "0",
                        "max" : "22"
                    },
                    ],
                    "range" : {
                        "min" : "0",
                        "max" : "22"
                    },
                },
            },
            "access" : "readonly",
            "description" :
                """Timestamp (date and time) of outlet energy in kWh is reset.""",
        }, # column
        "pdu3OutletPowerFactor" : {
            "nodetype" : "column",
            "moduleName" : "CPQPOWER-MIB",
            "oid" : "1.3.6.1.4.1.232.165.11.5.1.1.16",
            "status" : "current",
            "syntax" : {
                "type" : { "module" :"", "name" : "Integer32"},
            },
            "access" : "readonly",
            "description" :
                """An outlet PF value.  Return value is divided by 100, for example a power factor
of 0.95 would be returned as 95. A negative value indicates that this object is not available.""",
        }, # column
        "pdu3OutletVAR" : {
            "nodetype" : "column",
            "moduleName" : "CPQPOWER-MIB",
            "oid" : "1.3.6.1.4.1.232.165.11.5.1.1.17",
            "status" : "current",
            "syntax" : {
                "type" : { "module" :"", "name" : "Integer32"},
            },
            "access" : "readonly",
            "description" :
                """An outlet power reactive in VAR value.  Units are VAR.  A negative value indicates
that this object is not available.""",
        }, # column
        "pdu3OutletControlTable" : {
            "nodetype" : "table",
            "moduleName" : "CPQPOWER-MIB",
            "oid" : "1.3.6.1.4.1.232.165.11.5.2",
            "status" : "current",
            "description" :
                """Aggregate Object with number of entries equal to Number of PDU (pdu3IdentIndex) 
and Number of outlets per PDU (pdu3OutletIndex).""",
        }, # table
        "pdu3OutletControlEntry" : {
            "nodetype" : "row",
            "moduleName" : "CPQPOWER-MIB",
            "oid" : "1.3.6.1.4.1.232.165.11.5.2.1",
            "status" : "current",
            "linkage" : [
                "pdu3IdentIndex",
                "pdu3OutletIndex",
            ],
            "description" :
                """The Outlet table entry containing the type, voltage, current etc.""",
        }, # row
        "pdu3OutletControlStatus" : {
            "nodetype" : "column",
            "moduleName" : "CPQPOWER-MIB",
            "oid" : "1.3.6.1.4.1.232.165.11.5.2.1.1",
            "status" : "current",
            "syntax" : {
                "type" :                 {
                    "basetype" : "Enumeration",
                    "off" : {
                        "nodetype" : "namednumber",
                        "number" : "1"
                    },
                    "on" : {
                        "nodetype" : "namednumber",
                        "number" : "2"
                    },
                    "pendingOff" : {
                        "nodetype" : "namednumber",
                        "number" : "3"
                    },
                    "pendingOn" : {
                        "nodetype" : "namednumber",
                        "number" : "4"
                    },
                },
            },
            "access" : "readonly",
            "description" :
                """current state of a control outlet.""",
        }, # column
        "pdu3OutletControlOffCmd" : {
            "nodetype" : "column",
            "moduleName" : "CPQPOWER-MIB",
            "oid" : "1.3.6.1.4.1.232.165.11.5.2.1.2",
            "status" : "current",
            "syntax" : {
                "type" :                 {
                    "basetype" : "Integer32",
                    "ranges" : [
                    {
                        "min" : "-1",
                        "max" : "99999"
                    },
                    ],
                    "range" : {
                        "min" : "-1",
                        "max" : "99999"
                    },
                },
            },
            "access" : "readwrite",
            "description" :
                """When write, once issued, the outlet will turn Off immediately.
0-n: Time in seconds until the outlet command is issued
-1: Cancel a pending outlet Off command
 When read, returns -1 if no command is pending, or the current downcount in 
seconds of a pending command.""",
        }, # column
        "pdu3OutletControlOnCmd" : {
            "nodetype" : "column",
            "moduleName" : "CPQPOWER-MIB",
            "oid" : "1.3.6.1.4.1.232.165.11.5.2.1.3",
            "status" : "current",
            "syntax" : {
                "type" :                 {
                    "basetype" : "Integer32",
                    "ranges" : [
                    {
                        "min" : "-1",
                        "max" : "99999"
                    },
                    ],
                    "range" : {
                        "min" : "-1",
                        "max" : "99999"
                    },
                },
            },
            "access" : "readwrite",
            "description" :
                """When write, once issued, the outlet will turn On immediately.
0-n: Time in seconds until the outlet command is issued
-1: Cancel a pending outlet On command
 When read, returns -1 if no command is pending, or the current downcount in 
seconds of a pending command.""",
        }, # column
        "pdu3OutletControlRebootCmd" : {
            "nodetype" : "column",
            "moduleName" : "CPQPOWER-MIB",
            "oid" : "1.3.6.1.4.1.232.165.11.5.2.1.4",
            "status" : "current",
            "syntax" : {
                "type" :                 {
                    "basetype" : "Integer32",
                    "ranges" : [
                    {
                        "min" : "-1",
                        "max" : "99999"
                    },
                    ],
                    "range" : {
                        "min" : "-1",
                        "max" : "99999"
                    },
                },
            },
            "access" : "readwrite",
            "description" :
                """When write, for outlets that are On prior to this Reboot command, they will 
switch Off immediately when the command is issued, remain Off for 
outletControlRebootOffTime seconds, and then turn back On.
 For outlets that are Off prior to the Reboot command, they will turn On after 
a delay of outletControlRebootOffTime seconds from when the command is issued.
 0-n : Time in seconds until the Reboot command is issued
 -1 : Cancel a pending outlet Reboot command 

When read, returns -1 if no command is pending, or the current downcount in 
seconds of a pending command.""",
        }, # column
        "pdu3OutletControlPowerOnState" : {
            "nodetype" : "column",
            "moduleName" : "CPQPOWER-MIB",
            "oid" : "1.3.6.1.4.1.232.165.11.5.2.1.5",
            "status" : "current",
            "syntax" : {
                "type" :                 {
                    "basetype" : "Enumeration",
                    "off" : {
                        "nodetype" : "namednumber",
                        "number" : "1"
                    },
                    "on" : {
                        "nodetype" : "namednumber",
                        "number" : "2"
                    },
                    "lastState" : {
                        "nodetype" : "namednumber",
                        "number" : "3"
                    },
                },
            },
            "access" : "readwrite",
            "description" :
                """Determines the outlet state when power is applied to the unit.
1 : not restart at device startup
2 : should sequence back ON in line with outletControlSequenceTime
3 : should take the state the outlet had when power was lost.
If the state was ON, should sequence back ON in line with outletControlSequenceTime.""",
        }, # column
        "pdu3OutletControlSequenceDelay" : {
            "nodetype" : "column",
            "moduleName" : "CPQPOWER-MIB",
            "oid" : "1.3.6.1.4.1.232.165.11.5.2.1.6",
            "status" : "current",
            "syntax" : {
                "type" :                 {
                    "basetype" : "Integer32",
                    "ranges" : [
                    {
                        "min" : "-1",
                        "max" : "99999"
                    },
                    ],
                    "range" : {
                        "min" : "-1",
                        "max" : "99999"
                    },
                },
            },
            "access" : "readwrite",
            "description" :
                """Time delay in seconds from when a Global Sequence On command is issued to
when the command is executed on this outlet.  This delay is also used as a power-on
delay. Set to -1 to exclude this outlet from Global Sequence On commands.""",
        }, # column
        "pdu3OutletControlRebootOffTime" : {
            "nodetype" : "column",
            "moduleName" : "CPQPOWER-MIB",
            "oid" : "1.3.6.1.4.1.232.165.11.5.2.1.7",
            "status" : "current",
            "syntax" : {
                "type" :                 {
                    "basetype" : "Integer32",
                    "ranges" : [
                    {
                        "min" : "-1",
                        "max" : "99999"
                    },
                    ],
                    "range" : {
                        "min" : "-1",
                        "max" : "99999"
                    },
                },
            },
            "access" : "readwrite",
            "description" :
                """Time delay in seconds that the outlet should remain in the Off state when executing a Reboot command.""",
        }, # column
        "pdu3OutletControlSwitchable" : {
            "nodetype" : "column",
            "moduleName" : "CPQPOWER-MIB",
            "oid" : "1.3.6.1.4.1.232.165.11.5.2.1.8",
            "status" : "current",
            "syntax" : {
                "type" :                 {
                    "basetype" : "Enumeration",
                    "switchable" : {
                        "nodetype" : "namednumber",
                        "number" : "1"
                    },
                    "notSwitchable" : {
                        "nodetype" : "namednumber",
                        "number" : "2"
                    },
                },
            },
            "access" : "readwrite",
            "description" :
                """Determines the outlet capability to be controlled On/Off from the communication channels.
1 : control On/Off enabled
2 : control On/Off disabled.""",
        }, # column
        "pdu3OutletControlShutoffDelay" : {
            "nodetype" : "column",
            "moduleName" : "CPQPOWER-MIB",
            "oid" : "1.3.6.1.4.1.232.165.11.5.2.1.9",
            "status" : "current",
            "syntax" : {
                "type" :                 {
                    "basetype" : "Integer32",
                    "ranges" : [
                    {
                        "min" : "-1",
                        "max" : "99999"
                    },
                    ],
                    "range" : {
                        "min" : "-1",
                        "max" : "99999"
                    },
                },
            },
            "access" : "readwrite",
            "description" :
                """Time delay in seconds that could be taken in account before shutting of the outlet.
An application which need to shutoff properly an outlet will read this parameter first
then write it to the command pdu3OutletControlOffCmd.""",
        }, # column
    }, # nodes

    "notifications" : {
        "trapCritical" : {
            "nodetype" : "notification",
            "moduleName" : "CPQPOWER-MIB",
            "oid" : "1.3.6.1.4.1.232.165.0.1",
            "status" : "current",
            "objects" : {
                "sysName" : {
                    "nodetype" : "object",
                    "module" : "RFC1213-MIB"
                },
                "trapCode" : {
                    "nodetype" : "object",
                    "module" : "CPQPOWER-MIB"
                },
                "trapDescription" : {
                    "nodetype" : "object",
                    "module" : "CPQPOWER-MIB"
                },
                "trapDeviceName" : {
                    "nodetype" : "object",
                    "module" : "CPQPOWER-MIB"
                },
                "trapDeviceDetails" : {
                    "nodetype" : "object",
                    "module" : "CPQPOWER-MIB"
                },
                "trapDeviceMgmtUrl" : {
                    "nodetype" : "object",
                    "module" : "CPQPOWER-MIB"
                },
            },
            "description" :
                """A critical alarm has occurred. Action: Check the Trap Details for more information.""",
        }, # notification
        "trapWarning" : {
            "nodetype" : "notification",
            "moduleName" : "CPQPOWER-MIB",
            "oid" : "1.3.6.1.4.1.232.165.0.2",
            "status" : "current",
            "objects" : {
                "sysName" : {
                    "nodetype" : "object",
                    "module" : "RFC1213-MIB"
                },
                "trapCode" : {
                    "nodetype" : "object",
                    "module" : "CPQPOWER-MIB"
                },
                "trapDescription" : {
                    "nodetype" : "object",
                    "module" : "CPQPOWER-MIB"
                },
                "trapDeviceName" : {
                    "nodetype" : "object",
                    "module" : "CPQPOWER-MIB"
                },
                "trapDeviceDetails" : {
                    "nodetype" : "object",
                    "module" : "CPQPOWER-MIB"
                },
                "trapDeviceMgmtUrl" : {
                    "nodetype" : "object",
                    "module" : "CPQPOWER-MIB"
                },
            },
            "description" :
                """A warning alarm has occurred. Action: Check the Trap Details for more information.""",
        }, # notification
        "trapInformation" : {
            "nodetype" : "notification",
            "moduleName" : "CPQPOWER-MIB",
            "oid" : "1.3.6.1.4.1.232.165.0.3",
            "status" : "current",
            "objects" : {
                "sysName" : {
                    "nodetype" : "object",
                    "module" : "RFC1213-MIB"
                },
                "trapCode" : {
                    "nodetype" : "object",
                    "module" : "CPQPOWER-MIB"
                },
                "trapDescription" : {
                    "nodetype" : "object",
                    "module" : "CPQPOWER-MIB"
                },
                "trapDeviceName" : {
                    "nodetype" : "object",
                    "module" : "CPQPOWER-MIB"
                },
                "trapDeviceDetails" : {
                    "nodetype" : "object",
                    "module" : "CPQPOWER-MIB"
                },
                "trapDeviceMgmtUrl" : {
                    "nodetype" : "object",
                    "module" : "CPQPOWER-MIB"
                },
            },
            "description" :
                """An informational alarm has occurred. Action: Check the Trap Details for more information.""",
        }, # notification
        "trapCleared" : {
            "nodetype" : "notification",
            "moduleName" : "CPQPOWER-MIB",
            "oid" : "1.3.6.1.4.1.232.165.0.4",
            "status" : "current",
            "objects" : {
                "sysName" : {
                    "nodetype" : "object",
                    "module" : "RFC1213-MIB"
                },
                "trapCode" : {
                    "nodetype" : "object",
                    "module" : "CPQPOWER-MIB"
                },
                "trapDescription" : {
                    "nodetype" : "object",
                    "module" : "CPQPOWER-MIB"
                },
                "trapDeviceName" : {
                    "nodetype" : "object",
                    "module" : "CPQPOWER-MIB"
                },
                "trapDeviceDetails" : {
                    "nodetype" : "object",
                    "module" : "CPQPOWER-MIB"
                },
                "trapDeviceMgmtUrl" : {
                    "nodetype" : "object",
                    "module" : "CPQPOWER-MIB"
                },
            },
            "description" :
                """An alarm has cleared. Action: Check the Trap Details for more information.""",
        }, # notification
        "trapTest" : {
            "nodetype" : "notification",
            "moduleName" : "CPQPOWER-MIB",
            "oid" : "1.3.6.1.4.1.232.165.0.5",
            "status" : "current",
            "objects" : {
                "sysName" : {
                    "nodetype" : "object",
                    "module" : "RFC1213-MIB"
                },
                "trapCode" : {
                    "nodetype" : "object",
                    "module" : "CPQPOWER-MIB"
                },
                "trapDescription" : {
                    "nodetype" : "object",
                    "module" : "CPQPOWER-MIB"
                },
                "trapDeviceName" : {
                    "nodetype" : "object",
                    "module" : "CPQPOWER-MIB"
                },
                "trapDeviceDetails" : {
                    "nodetype" : "object",
                    "module" : "CPQPOWER-MIB"
                },
                "trapDeviceMgmtUrl" : {
                    "nodetype" : "object",
                    "module" : "CPQPOWER-MIB"
                },
            },
            "description" :
                """Test trap sent to a trap receiver to check proper reception of traps""",
        }, # notification
        "deviceTrapInitialization" : {
            "nodetype" : "notification",
            "moduleName" : "CPQPOWER-MIB",
            "oid" : "1.3.6.1.4.1.232.165.0.6",
            "status" : "current",
            "objects" : {
                "sysName" : {
                    "nodetype" : "object",
                    "module" : "RFC1213-MIB"
                },
                "deviceIdentName" : {
                    "nodetype" : "object",
                    "module" : "CPQPOWER-MIB"
                },
            },
            "description" :
                """This trap is sent each time a power device is initialized.""",
        }, # notification
    }, # notifications

}
