fw enron center north enron center south damage restoration overview sorry see email till late stupidly sorted email author po round saturday morning take trhough plan delighted hear little scott sleeping apologize seeing responding email sooner take care p original message kitchen louise sent wednesday june 13 2001 5 48 pm philippe bibi hou ect enron subject fw enron center north enron center south damage restoration overview marcus said wanted see friday going astros problem notice responded email talk phone sometime week end instead friday louise forwarded louise kitchen hou ect 06 13 2001 05 46 pm louise kitchen 06 11 2001 10 53 philippe bibi enron enronxgate enron cc subject fw enron center north enron center south damage restoration overview bloody good effort thought lost lot systems things thanks message got last night phones week end spent week end figuring alternative ways home marcus mum indianappolis new york london finally got home obviously luggage got lost also picking parents golfing every hour god sends one else thinks courses open damage though news nothing exciting lavo ring last week tell everyone saying going back london david port rang friday said many rumours around nice suffice say presume bollocks one mentioned anything maybe last person get consulted matthew scrimshaw made move ebs info figure already know 4 days old never speed emails 5 inbox news scott finally sleeping got whole 7 hours last night back work monday free time week lunch catch gossip get back could never stay home mum lacking requried attributes patience inability spend money nothing apart look scott become demon internet spotter let know lunch regards louise philippe bibi enron enronxgate 06 11 2001 09 17 mark frevert enron enronxgate greg whalley hou ect ect cc mike mcconnell hou ect ect jeffrey shankman enron enronxgate jeffrey mcmahon enron enronxgate raymond bowen enron enronxgate john j lavorato enron enronxgate louise kitchen lon ect ect rebecca mcdonald enron enronxgate kevin hannon enron communications enron communications ken rice enron communications enron communications subject fw enron center north enron center south damage donovan bill cc kean steven subject enron center north enron center south damage ees maint worked together power systems begin repair work 4 00 pm saturday epsc ees maint coordinated pillar henderson elec obtain replacement parts begin repairs 9 30 pm repairs ups c made system bought back line measure extra protection back genset enron ctr north operation reliant energy restored circuit approximately 10 30 pm saturday evening epsc ees maint subs conducted thorough review electrical back systems saturday evening enron network operations began restoration affected systems saturday evening epsc ees maint obtained diesel fuel topped gensets saturday case additional problems due fuel consumption outage building damage limited flooding tunnels water damage flooding portions body shop lv b 1 enron center south 1500 louisiana impact damage summary levels 8 9 received limited amounts water core area elevator shafts exterior curtainwall exposure water systems network cabling entire period response crews contained cleaned water traced building idf closets lvs 3 5 traders floors remained dry throughout duration rains flooding friday saturday lv 6 received water lv 7 response area contained cleaned additional damage beyond tuesday evenings flooding occurred due extreme street flooding water pressure 10 sanitary sewer line tied ecs burst friday evening causing extensive flooding lv b 1 area approximately 4 6 inches water basement response clark way engr able install temporary plug line stop going flood waters penetrating basement clean continued throughout weekend due extreme flooding water pressure water seal reliant vault burst early saturday flooded electrical vault room 24 30 water resulted complete loss power approximately 1 30 pm staurday afternoon back systems engaged operated per design support data ctr traders floors temporary cooling tower went line prior flooding clark process tieing temporary feed back system 7 1 01 prep migration response clark used back water pumps pump clean reliant electrical vault well maintained operation back systems data ctr ahu kept line dehumidifiers blowers modulate airflow data ctr epsc way engr techs use temp humidity probes monitor areas recordings indicated temps lvs 8 engineers mep subs shall conducting thorough system review repirs required systems throughout building coming week summary back systems facilities engage operate designed however due extreme conditons stress placed upon systems facility held extremely well would also like note throughout ordeal beginning friday evening sunday everyone enron networks ees facilitiesclark const way engring fisk electric henderson electric kw pillar hines outstanding job enourmous pressure severe conditions seen downtown houston communication around clock work cool heads managed assess damage develop action restoration plans facilitate repairs monday business let know need details specific issues items regards henry