sj pipe settling steve darrell informed burlington late friday unplanned outage next week two days talk commercial folks monday morning make sure loop anticipate back online september business burlington proceed ahead september business usual also talk sj players help fill gap maintain 800 000 mmbtu lateral burlington thanks kim original message roensch david sent friday august 24 2001 5 28 pm harris steven cc watson kimberly subject sj pipe settling effect burlington low pressure system still flow 800 mmcfd lateral need make low pressure volumes recieved burlington high pressure customers discussed darryl today burlington flowing approximately 130 mmcfd limited 800 mmcfd lateral due gallups condition forwarded david roensch et enron 08 24 2001 04 24 pm steven harris enron enronxgate 08 24 2001 06 08 pm cdt david roensch et chanley earl spalding norm rance byron eisenstein arnold l rice randy stephens ld schoolcraft darrell january steven watson kimberly san juan team gormley john delossantos ernie fajardo leo mccracken mike asante ben matthews ron osborn roger gottsponer morgan mcilwain greg cc lowry phil harris steven soldano louis keller john r david l johnson ots enron enron shafer john subject sj pipe settling importance high conf call set monday morning 9 00 cst discuss force majeure situation 3 unit san juan compressor station 877 795 3687 pin 475577 overview uninvolved date walk san juan station team thursday evening 8 16 noted severe settling issues yard piping existed team working engineering developing action plan address last several months upon visual inspection requested team contact local contractor pipe cover dirt removed immediately allow piping relieve would provide necessary time follow engineering attain feedback status project implement remedies team contractor location following monday 8 20 work removing cover completed monday 8 27 however expected results achieved words piping spring back degree pipe stress concerns eliminated requested structural engineer sent site immediately evaluate integrity piping location thursday morning 8 29 phone conversation phil dickenson trigon structural engineer mentioned immediate concern much displacement could induce high stresses however pipe coating cracks visible wanted opportunity input data model evaluate prior making recommendations offer minimum stand good chance exceeding 5 design factor without reviewing data would commit conclusion asked work evening required provide necessary information regards pipes integrity waiting trigons report notified team asked contact foutz bursham local pipeline contractor get evaluation estimated time would require worst case scenario make repairs replacements 4 5 days requested roswell cdc ernie delossantos determine availability approximately 150 x 42 356 wall 10 pipe 12 ea 42 365 wall 90 1 ea 42 365 wall 45 material available redman supply farmington conclusion mr dickenson called results morning informed us appear exceeding allowable stress levels stress levels calculated dickinson excess yield follows 1 09 smys connection recycle surge line discharge header 1 01 smys elbow immediately outside building wall 10 recycle line recommendation piping cut welded return piping lower stress condition suitable pipe supports subject subsidence provided conference calls engineering spalding eisenstein rance pebdani minnoti set review data mr dickenson decided greg mcilwain location monday conjunction mike mccracken initiate necessary repairs much discussion dickenson regards modeling performed engineering indicated system operational therefore remain loaded early next week repairs made repairs isolated 3 unit downtime expected exceed 2 days 48 hours however furhter evaluation mcilwain confirm timelines anyone questions weekend prior mondays call reached 520 853 3253