Fan Performance Data: Fan performance curves with flow, static pressure and horsepower. Fan volumetric flow rate, fan nozzle outlet velocity, induced flow rate, total volumetric flow rate, windband outlet velocity, and discharge plume height at indicated wind speed. Sound Performance Data: Fan sound power levels in eight octave bands and, overall sound power level or sone values. ratings and electrical characteristics. Furnished specialty components. Specified accessories. Dimensioned standard drawings indicating dimensions, weights, and attachments to other work. Specifier: If Contractor will be required to provide engineering drawings and calculations for vibration, seismic, or high wind design, insert requirements here. INFORMATIONAL SUBMITTALS Source quality-control reports. Field quality-control reports. ISO-9001 certificate. CLOSEOUT SUBMITTALS Operation and Maintenance Data: Include routine maintenance, adjustment requirements, safety information, and troubleshooting guide. QUALITY ASSURANCE Manufacturer Qualifications: Approved ISO 9001-compliant manufacturer listed in this Section with minimum 10 years' experience in manufacture of similar products in successful use in similar applications, and with an ASME NQA-1 compliant Program. Specifier: Retain paragraph below if Owner allows substitutions but requires strict control over qualifying of substitutions. Approval of Comparable Products: Submit the following in accordance with project substitution requirements, within time allowed for substitution review: Product data, including certified independent test data indicating compliance with requirements. Project references: Minimum of 5 installations not less than 5 years old, with Owner contact information. Sample warranty. Substitutions following award of contract are not allowed except as stipulated in Division 01 General Requirements. Approved manufacturers must meet separate requirements of Submittals Article. AMCA Compliance: Provide fan types tested in accordance with AMCA Standard 210 (air performance), AMCA Standard 260 (Induced Flow Fans) and AMCA Standard 300 (sound performance) in an AMCA-accredited laboratory.
Fan Performance Data: Fan performance curves with flow, static pressure and horsepower. Fan volumetric flow rate, fan nozzle outlet velocity, induced flow rate, total volumetric flow rate, windband outlet velocity, and discharge plume height at indicated wind speed. Sound Performance Data: Fan sound power levels in eight octave bands and, overall sound power level or sone values. ratings and electrical characteristics. Furnished specialty components. Specified accessories. Dimensioned standard drawings indicating dimensions, weights, and attachments to other work. Specifier: If Contractor will be required to provide engineering drawings and calculations for vibration, seismic, or high wind design, insert requirements here. INFORMATIONAL SUBMITTALS Source quality-control reports. Field quality-control reports. ISO-9001 certificate. CLOSEOUT SUBMITTALS Operation and Maintenance Data: Include routine maintenance, adjustment requirements, safety information, and troubleshooting guide. QUALITY ASSURANCE Manufacturer Qualifications: Approved ISO 9001-compliant manufacturer listed in this Section with minimum 10 years' experience in manufacture of similar products in successful use in similar applications, and with an ASME NQA-1 compliant Program. Specifier: Retain paragraph below if Owner allows substitutions but requires strict control over qualifying of substitutions. Approval of Comparable Products: Submit the following in accordance with project substitution requirements, within time allowed for substitution review: Product data, including certified independent test data indicating compliance with requirements. Project references: Minimum of 5 installations not less than 5 years old, with Owner contact information. Sample warranty. Substitutions following award of contract are not allowed except as stipulated in Division 01 General Requirements. Approved manufacturers must meet separate requirements of Submittals Article. AMCA Compliance: Provide fan types tested in accordance with AMCA Standard 210 (air performance), AMCA Standard 260 (Induced Flow Fans) and AMCA Standard 300 (sound performance) in an AMCA-accredited laboratory.
baife-specification-233423.02-centrifugal-roof-ventilators.docx