FACP Protection. An automatic smoke detector and a pull station shall be provided at the location of the FACP. Approved Signage. Approved signage shall be provided on the door of the enclosure in which any FACP is located stating Alarm Control Panel”. “Fire Visual. Strobe devices are required to be synchronized when they are in the same room or adjacent spaces within the field of view. Magnetic Locks, Door Releasing Service and Delayed Egress. These shall release upon activation of the fire alarm system. Elevator/Elevator Recall. Elevator recall systems be tied into the fire alarm system if provided. If no fire alarm system exists, installation according to the State of Utah Elevator Commission requirements shall be met. Multi-Occupant Buildings. Buildings where the fire alarm system serves more than one occupancy, individual occupancies shall have as a minimum, one addressable detection device and one notification device in each space, connected to the main FACP. An approved electronic flow bell shall be mounted on the exterior of the building proximate to the location of the fire sprinkler system riser. If the FDC is remote of the riser, an approved weatherproof horn/strobe device shall be installed above and within 20 feet of the FDC. The horn/strobe shall be at a height and location that is visible to responding emergency crews. SUBMITTAL INFORMATION. Drawing Size. Drawings shall be submitted on sheets no less than 24 x 36 inches and shall be drawn to 1/8” or 1/4” scale. A minimum of 2 sets of drawings are required to be Number of Drawing Sets. submitted. An approved set shall be at the jobsite and one set will be retained. Cut Sheets/Specifications. One set of manufacturer’s product information (cut sheets) shall be provided. This is to include information on all devices that are part of or being connected to the fire alarm system. This set will be retained. Peer Review. A peer review of the fire sprinkler system design shall be submitted per IFC, 104.7.2. A list of approved peer reviewers is available from the Fire Marshal. Submittal Content. Include plans, voltage drop rates, battery calculations, and sequence matrix chart. INSPECTIONS AND TESTING.
FACP Protection. An automatic smoke detector and a pull station shall be provided at the location of the FACP. Approved Signage. Approved signage shall be provided on the door of the enclosure in which any FACP is located stating “Fire Alarm Control Panel”. Visual. Strobe devices are required to be synchronized when they are in the same room or adjacent spaces within the field of view. Magnetic Locks, Door Releasing Service and Delayed Egress. These shall release upon activation of the fire alarm system. Elevator/Elevator Recall. Elevator recall systems be tied into the fire alarm system if provided. If no fire alarm system exists, installation according to the State of Utah Elevator Commission requirements shall be met. Multi-Occupant Buildings. Buildings where the fire alarm system serves more than one occupancy, individual occupancies shall have as a minimum, one addressable detection device and one notification device in each space, connected to the main FACP. An approved electronic flow bell shall be mounted on the exterior of the building proximate to the location of the fire sprinkler system riser. If the FDC is remote of the riser, an approved weatherproof horn/strobe device shall be installed above and within 20 feet of the FDC. The horn/strobe shall be at a height and location that is visible to responding emergency crews. SUBMITTAL INFORMATION. Drawing Size. Drawings shall be submitted on sheets no less than 24 x 36 inches and shall be drawn to 1/8” or 1/4” scale. Number of Drawing Sets. A minimum of 2 sets of drawings are required to be submitted. An approved set shall be at the jobsite and one set will be retained. Cut Sheets/Specifications. One set of manufacturer’s product information (cut sheets) shall be provided. This is to include information on all devices that are part of or being connected to the fire alarm system. This set will be retained. Peer Review. A peer review of the fire sprinkler system design shall be submitted per IFC, 104.7.2. A list of approved peer reviewers is available from the Fire Marshal. Submittal Content. Include plans, voltage drop rates, battery calculations, and sequence matrix chart. INSPECTIONS AND TESTING.
bcfd_fire_alarm_packet.docx