VertiCool Aurora Indoor Vertical Air Conditioning System ENGINEERING SPECIFICATION DATA UNITS Part 1 General – 1.01 Related Documents A. Drawings and general provisions of the contract, including General and Supplementary Conditions and other Division 1 specification sections, apply to this section. General Description A. Furnish and install an indoor vertical air conditioner system designed to control space temperature and humidity levels. It shall have the performance, electrical characteristics, and air path configurations as defined in the product schedule for the space to be conditioned. B. The unit(s) shall be a VertiCool Aurora modular water-cooled model manufactured by United CoolAir, York, Pennsylvania. C. The unit(s) shall be installed as a floor mounted [Single Package] [Split] system. D. All systems shall be shipped with a full factory refrigerant charge and be ready to wire once the unit has been placed on site. E. A wiring diagram shall be affixed to each unit. A printed Installation, Operation and Maintenance Manual shall be provided with each unit. All units shall be suitably labeled for safety purposes and for access. Quality Assurance Unit and refrigeration system(s) shall comply with ASHRAE 15, Safety Standard for Mechanical Refrigeration.
VertiCool Aurora Indoor Vertical Air Conditioning System ENGINEERING SPECIFICATION DATA UNITS Part 1 – General 1.01 Related Documents A. Drawings and general provisions of the contract, including General and Supplementary Conditions and other Division 1 specification sections, apply to this section. General Description A. Furnish and install an indoor vertical air conditioner system designed to control space temperature and humidity levels. It shall have the performance, electrical characteristics, and air path configurations as defined in the product schedule for the space to be conditioned. B. The unit(s) shall be a VertiCool Aurora modular water-cooled model manufactured by United CoolAir, York, Pennsylvania. C. The unit(s) shall be installed as a floor mounted [Single Package] [Split] system. D. All systems shall be shipped with a full factory refrigerant charge and be ready to wire once the unit has been placed on site. E. A wiring diagram shall be affixed to each unit. A printed Installation, Operation and Maintenance Manual shall be provided with each unit. All units shall be suitably labeled for safety purposes and for access. Quality Assurance Unit and refrigeration system(s) shall comply with ASHRAE 15, Safety Standard for Mechanical Refrigeration.
Aurora-Engineering-Guide-Spec_Water-Cooled_0618.docx