B. Partial Owner Occupancy: Owner may occupy completed areas of building before Substantial Completion. Cooperate with Owner during TAB operations to minimize conflicts with Owner's operations. 1.8 COORDINATION A. Notice: Provide seven days' advance notice for each test. Include scheduled test dates and times. B. Perform TAB after leakage and pressure tests on air and water distribution systems have been satisfactorily completed. 1.9 WARRANTY A. National Project Performance Guarantee: Provide a guarantee forms stating that TAB firm comply and guarantee the following provisions: 1. The certified TAB firm has tested and balanced systems according to the Contract Documents. 2. Systems are balanced to optimum performance capabilities within design and installation limits. PART 2 - PRODUCTS 2.1 TEST INSTRUMENTS A. Utilize test instruments and equipment for TAB work required, of type, precision, and capacity as recommended by the Commissioning Authority. B. All equipment shall be properly calibrated with certification providing that recent calibration has taken place. PART 3 - EXECUTION 3.1 EXAMINATION A. Examine installed work and conditions under which testing is to be done to ensure that work has been completed, cleaned and is operable. Do not proceed with TAB work until unsatisfactory conditions have been corrected in manner acceptable to Tester B. Examine the Contract Documents to become familiar with Project requirements and to discover conditions in systems' designs that may preclude proper TAB of
B. Partial Owner Occupancy: Owner may occupy completed areas of building before Substantial Completion. Cooperate with Owner during TAB operations to minimize conflicts with Owner's operations. 1.8 COORDINATION A. Notice: Provide seven days' advance notice for each test. Include scheduled test dates and times. B. Perform TAB after leakage and pressure tests on air and water distribution systems have been satisfactorily completed. 1.9 WARRANTY A. National Project Performance Guarantee: Provide a guarantee forms stating that TAB firm comply and guarantee the following provisions: 1. The certified TAB firm has tested and balanced systems according to the Contract Documents. 2. Systems are balanced to optimum performance capabilities within design and installation limits. PART 2 - PRODUCTS 2.1 TEST INSTRUMENTS A. Utilize test instruments and equipment for TAB work required, of type, precision, and capacity as recommended by the Commissioning Authority. B. All equipment shall be properly calibrated with certification providing that recent calibration has taken place. PART 3 - EXECUTION 3.1 EXAMINATION A. Examine installed work and conditions under which testing is to be done to ensure that work has been completed, cleaned and is operable. Do not proceed with TAB work until unsatisfactory conditions have been corrected in manner acceptable to Tester B. Examine the Contract Documents to become familiar with Project requirements and to discover conditions in systems' designs that may preclude proper TAB of
ANNEXURE-A-FINAL-TECHNICAL-SPECIFICATIONS.docx