TABLE 315—Minimum distances from any part of a vehicle, plant or machinery to aerial lines Column 1 Column 2 Column 3 Column 4 Row A U 1500V ≤ traction 66kV< 132kV< Aerial line conductor U 66kV U 132kV U 500kV ≤ ≤ ≤ Row B 2000 mm 2000 mm 4000 mm 6400 mm Minimum distance from the aerial line in all directions 316 Minimum distances between transported loads and aerial lines r. 316 A person must not drive or manoeuvre a vehicle with a load or transport a load so that the load is closer to an aerial line that forms part of a relevant installation set out in Row A in Column 1, 2, 3, 4, 5, 6 or 7 of Table 316 than the relevant minimum distance specified in the corresponding item in Row B in Column 1, 2, 3, 4, 5, 6 or 7 of Table 316. 20 penalty units. TABLE 316—Minimum distances from transported loads to aerial lines Column 1 Column 2 Column 3 Column 4 Column 5 Column 6 Column 7 Alternating current aerial lines Nominal voltage ("U") Row A U 1kV a.c. 1kV< ≤ bare U 66kV ≤ Aerial line conductor and a.c. and U 1500V U 1kV a.c. 1500V < 66kV< 132kV< ≤ ≤ traction insulated U 66kV U U 275kV< U ≤ ≤ ≤ ≤ conductor conductor d.c. 132kV 275kV U 330kV 500kV ≤
TABLE 315—Minimum distances from any part of a vehicle, plant or machinery to aerial lines Column 1 Column 2 Column 3 Column 4 Row A Aerial line U ≤ 1500V traction conductor U ≤ 66kV 66kV< U ≤ 132kV 132kV< U ≤ 500kV Row B Minimum distance from the aerial line in all directions 2000 mm 2000 mm 4000 mm 6400 mm 316 Minimum distances between transported loads and aerial lines r. 316 A person must not drive or manoeuvre a vehicle with a load or transport a load so that the load is closer to an aerial line that forms part of a relevant installation set out in Row A in Column 1, 2, 3, 4, 5, 6 or 7 of Table 316 than the relevant minimum distance specified in the corresponding item in Row B in Column 1, 2, 3, 4, 5, 6 or 7 of Table 316. 20 penalty units. TABLE 316—Minimum distances from transported loads to aerial lines Column 1 Column 2 Column 3 Column 4 Column 5 Column 6 Column 7 Alternating current aerial lines Nominal voltage ("U") Row A Aerial line U ≤ 1kV a.c. bare conductor and U ≤ 1500V traction conductor U ≤ 1kV a.c. insulated conductor 1kV< U ≤ 66kV a.c. and 1500V < U ≤ 66kV d.c. 66kV< U ≤ 132kV 132kV< U ≤ 275kV 275kV< U ≤ 330kV U ≤ 500kV
09-164sr004.docx