performance after repair shall be at least as good as that of the existing provision. Any controls shall be left as existing, with minimal work required Retained unless needed in order to complete other Works that form part of the project, and the overall performance shall be no worse than the existing performance. Any element requiring work’ be left as existing. ‘no Subject to paragraphs 1.1.1.3, 1.1.1.4 in this Technical and Section 1.5 in the GDB, in respect of work to Refurbished Buildings, the required level of compliance with this Technical Annex is set out in the RSoW. Generally the requirements in this Technical Annex, refer to all parts of the Works except any building elements or services that are designated Repaired, Retained or work’ in the RSoW, or spaces designated in the ‘no ‘Untouched’ School-specific SoA. General Philosophy and Strategy The following section outlines the general philosophy and strategy for the controls and relevant associated systems. The purpose and requirements of the controls systems is as follows. Occupant comfort to maintain the environmental internal conditions that are – appropriate to the activity within the space. Energy and carbon emissions to reduce energy consumption and carbon – emissions through efficient use of installed Building Services systems. Space flexibility to ensure the environmental conditions of the internal – spaces are flexible where required. Safe operation to ensure the Building Services systems are safe to operate – and maintain. Information to inform the end users about the environmental conditions that – affect their thermal comfort. This also extends to informing the end users about energy consumption and carbon emissions. The Contractor shall ensure that: the Building Services control systems in schools are fit for purpose and appropriate to the proposed application
performance after repair shall be at least as good as that of the existing provision. Any Retained controls shall be left as existing, with minimal work required unless needed in order to complete other Works that form part of the project, and the overall performance shall be no worse than the existing performance. Any element requiring ‘no work’ be left as existing. Subject to paragraphs 1.1.1.3, 1.1.1.4 in this Technical and Section 1.5 in the GDB, in respect of work to Refurbished Buildings, the required level of compliance with this Technical Annex is set out in the RSoW. Generally the requirements in this Technical Annex, refer to all parts of the Works except any building elements or services that are designated Repaired, Retained or ‘no work’ in the RSoW, or spaces designated ‘Untouched’ in the School-specific SoA. General Philosophy and Strategy The following section outlines the general philosophy and strategy for the controls and relevant associated systems. The purpose and requirements of the controls systems is as follows. Occupant comfort – to maintain the environmental internal conditions that are appropriate to the activity within the space. Energy and carbon emissions – to reduce energy consumption and carbon emissions through efficient use of installed Building Services systems. Space flexibility – to ensure the environmental conditions of the internal spaces are flexible where required. Safe operation – to ensure the Building Services systems are safe to operate and maintain. Information – to inform the end users about the environmental conditions that affect their thermal comfort. This also extends to informing the end users about energy consumption and carbon emissions. The Contractor shall ensure that: the Building Services control systems in schools are fit for purpose and appropriate to the proposed application
Annex_2I_Controls__Technical_Annex_.docx