2.1. Special requirements for SCADA input: (I) For CPPSM UNIT: DIGITAL SL. NO. OF MONITORING (M) (D) / DESCRIPTION TAG NO. / CONTROL (C) A) CPPSM OUT PUT A CPPSM-V 1 M 1 VOLTAGE CPPSM OUT PUT 2 M 1 CPPSM-A CURRENT PIPELINE OVER 3 M 1 PL-OV PROTECTED PIPELINE UNDER 4 M 1 PL-UV PROTECTED ALL REFERENCE 5 M 1 REFC-F CELLS FAILED REFERENCE CELL-1 6 M 1 REFC1-V VOLTAGE REFERENCE CELL-2 7 M 1 REFC2-V VOLTAGE IN AUTO MODE 8 M 1 9 CPPSM IN MANUAL MODE M 1 CURRENT 10 C 1 CI-ST INTERRUPTER CURRENT 11 C 1 CI-STP INTERRUPTER STOP CURRENT 12 C 1 CI-RST INTERRUPTER RESET
2.1. Special requirements for SCADA input: (I) For CPPSM UNIT: SL. DESCRIPTION MONITORING (M) / CONTROL (C) DIGITAL (D) / A) NO. OF TAG NO. 1 CPPSM OUT PUT VOLTAGE M 1 CPPSM-V 2 CPPSM OUT PUT CURRENT M 1 CPPSM-A 3 PIPELINE OVER PROTECTED M 1 PL-OV 4 PIPELINE UNDER PROTECTED M 1 PL-UV 5 ALL REFERENCE CELLS FAILED M 1 REFC-F 6 REFERENCE CELL-1 VOLTAGE M 1 REFC1-V 7 REFERENCE CELL-2 VOLTAGE M 1 REFC2-V 8 IN AUTO MODE M 1 9 CPPSM IN MANUAL MODE M 1 10 CURRENT INTERRUPTER C 1 CI-ST 11 CURRENT INTERRUPTER STOP C 1 CI-STP 12 CURRENT INTERRUPTER RESET C 1 CI-RST A
08_Design-Basis_CP-system.docx