(II) For CPTRU: DIGITAL (D) NO. OF SL. G (M) / DESCRIPTION No. ANALOGUE TAG NO. (C) (A) 1 CPTR OUT PUT VOLTAGE M AI 1 CPTR-V CPTR OUT PUT CURRENT AI CPTR-A 2 M 1 PIPELINE OVER DI PL-OV 3 M 1 PROTECTED PIPELINE UNDER 4 M 1 DI PL-UV PROTECTED ALL REFERENCE 5 M DI 1 REFC-F CELLS FAILED REFERENCE CELL-1 6 M AI 1 REFC1-V VOLTAGE REFERENCE CELL-2 7 M AI 1 REFC2-V VOLTAGE CPTR IN AUTO MODE DI CPTR-AU 8 M 1 9 CPTR IN MANUAL MODE M DI 1 CURRENT 10 C 1 DO CI-ST INTERRUPTER START CURRENT 11 C DO 1 CI-STP INTERRUPTER STOP 12 C 1 CURRENT INTERRUPTER DO CI-RST
(II) For CPTRU: SL. No. DESCRIPTION G (M) (C) DIGITAL (D) / ANALOGUE (A) NO. OF TAG NO. 1 CPTR OUT PUT VOLTAGE M AI 1 CPTR-V 2 CPTR OUT PUT CURRENT M AI 1 CPTR-A 3 PIPELINE OVER PROTECTED M DI 1 PL-OV 4 PIPELINE UNDER PROTECTED M DI 1 PL-UV 5 ALL REFERENCE CELLS FAILED M DI 1 REFC-F 6 REFERENCE CELL-1 VOLTAGE M AI 1 REFC1-V 7 REFERENCE CELL-2 VOLTAGE M AI 1 REFC2-V 8 CPTR IN AUTO MODE M DI 1 CPTR-AU 9 CPTR IN MANUAL MODE M DI 1 10 CURRENT INTERRUPTER START C DO 1 CI-ST 11 CURRENT INTERRUPTER STOP C DO 1 CI-STP 12 CURRENT INTERRUPTER C DO 1 CI-RST
08_Design-Basis_CP-system.docx