The Vendor shall provide monitored generator systems sized to support the data center load with an fuel supply for 72 hours. (M) Vendor Additional Fuel Supply The Vendor shall ensure both Data Center Facilities will continue to have available generator fuel beyond the initial 72 hour on-site supply. (M) Power UPS and Generator Testing Policies and Procedures – The Vendor shall have policies, procedures, and communicate to CTS the schedule for UPS and Generator activation testing. (M) Power Bonding and Grounding – The Vendor shall be responsible for bonding and grounding and ensuring that is has been done properly. (M) Power Utility Power Feeds – The Vendor shall have a minimum of two (2) physically diverse underground power feeds to both Data Center Facilities. (DS) Power Different Substations – Describe if Vendor power feeds originate from different substations. (DS) Power Different Electrical Grids – Describe if Vendor power feeds originate different electrical grids. (MS) Power Runtime UPS at 100% – The Vendor runtime for the UPS shall be at 100% load. Describe the Vendor runtime for the UPS at 100% load, and at what percentage of capacity are both Data Center Facilities at today. (MS) Power Meter and Charge for Power Usage – The Vendor shall charge for power usage. Describe how the Vendor meters and charges for power usage at both Data Center Facilities. Please outline the level of detail that is provided on power usage for both facilities. (MS) Power Power Whips – The Vendor shall provide as many as six power whips in any high-density rack. Describe if the Vendor is able to provide as many as six power whips in any of the high-density racks. Please describe what is available at both Data Center Facilities. (MS) Power Fuel Providers – The Vendor shall have Service Level Agreements with its Fuel Providers to ensure availability of fuel supply as necessary to provide the Services herein. Telecommunications (M) Telecommunications Facilities
The Vendor shall provide monitored generator systems sized to support the data center load with an fuel supply for 72 hours. (M) Vendor Additional Fuel Supply The Vendor shall ensure both Data Center Facilities will continue to have available generator fuel beyond the initial 72 hour on-site supply. (M) Power – UPS and Generator Testing Policies and Procedures The Vendor shall have policies, procedures, and communicate to CTS the schedule for UPS and Generator activation testing. (M) Power – Bonding and Grounding The Vendor shall be responsible for bonding and grounding and ensuring that is has been done properly. (M) Power – Utility Power Feeds The Vendor shall have a minimum of two (2) physically diverse underground power feeds to both Data Center Facilities. (DS) Power – Different Substations Describe if Vendor power feeds originate from different substations. (DS) Power – Different Electrical Grids Describe if Vendor power feeds originate different electrical grids. (MS) Power – Runtime UPS at 100% The Vendor runtime for the UPS shall be at 100% load. Describe the Vendor runtime for the UPS at 100% load, and at what percentage of capacity are both Data Center Facilities at today. (MS) Power – Meter and Charge for Power Usage The Vendor shall charge for power usage. Describe how the Vendor meters and charges for power usage at both Data Center Facilities. Please outline the level of detail that is provided on power usage for both facilities. (MS) Power – Power Whips The Vendor shall provide as many as six power whips in any high-density rack. Describe if the Vendor is able to provide as many as six power whips in any of the high-density racks. Please describe what is available at both Data Center Facilities. (MS) Power – Fuel Providers The Vendor shall have Service Level Agreements with its Fuel Providers to ensure availability of fuel supply as necessary to provide the Services herein. Telecommunications (M) Telecommunications Facilities
A17-RFP-030.docx