Cool/Dry mode: 46°F - 64°F Heat mode: 64°F - 86°F Fan Speed Models with 3 air flow speed settings: High Each Each Setting /Mid/Low Group Group Air flow 2-step direction (Swing/Stop) Air Flow Direct setting at a specific angle. Each Each Direction Setting Group Group Air flow operation varies depending on the Remote control with the public IP address Web Server Each Each No management software required – Function Group Group management Wireless/wired remote controller restriction Accessible level / Dynamic user Each Each Specify the scope of control and monitoring unit security Group Group on a per-user Management 3 accessible levels: Admin/Manager/User When an error is currently occurring in the the afflicted unit and the error code are Each Each Error Group Group Error notification via email Up to 256 schedule settings Schedule Each Each Operation Group Group Weekly and daily schedule setting Power distribution to 256 indoor units. Remote data query in 1-day units Power File saving in Microsoft Excel format. Each Each Distribution Group Group Power distribution data storage for one year System MIM-B16 or MIM-B16N required for power use measurements Full indoor unit control with simple contact input (Emergency/Lock) External Contact State output (Operation/Error) for synchronous Each Each Interface control Channel Channel 10 digital outputs (2 reserved) / 8 digital inputs (2 reserved) Control & monitoring zone edition Wireless/wired remote control restriction Smart Central Each Each Management Group Group Temperature limit setting Operation mode restriction User can edit control logic with operators and parameters. User editable Each Each control logic Group Group Efficient energy saving realization for various conditions.
Cool/Dry mode: 46°F - 64°F Heat mode: 64°F - 86°F Fan Speed Setting Models with 3 air flow speed settings: High /Mid/Low Each Group Each Group Air Flow Direction Setting Air flow 2-step direction (Swing/Stop) Direct setting at a specific angle. Air flow operation varies depending on the Each Group Each Group Web Server Function Remote control with the public IP address No management software required – management Each Group Each Group Accessible level / Dynamic user security Management Wireless/wired remote controller restriction Specify the scope of control and monitoring unit on a per-user 3 accessible levels: Admin/Manager/User Each Group Each Group Error When an error is currently occurring in the the afflicted unit and the error code are Error notification via email Each Group Each Group Schedule Operation Up to 256 schedule settings Weekly and daily schedule setting Each Group Each Group Power Distribution System Power distribution to 256 indoor units. Remote data query in 1-day units File saving in Microsoft Excel format. Power distribution data storage for one year MIM-B16 or MIM-B16N required for power use measurements Each Group Each Group External Contact Interface Full indoor unit control with simple contact input (Emergency/Lock) State output (Operation/Error) for synchronous control 10 digital outputs (2 reserved) / 8 digital inputs (2 reserved) Each Channel Each Channel Smart Central Management Control & monitoring zone edition Wireless/wired remote control restriction Temperature limit setting Operation mode restriction Each Group Each Group User editable control logic User can edit control logic with operators and parameters. Efficient energy saving realization for various conditions. Each Group Each Group
AC009KXADCHAA_CAC%20Guide%20Spec.docx