Obtain plan from website Yes Is the evacuation plan current? Plan should be dated within last 12 months Check fire risk assessment report (Section 10) for Yes Are any hazardous areas identified in the fire hazardous areas risk assessment still present? Physically inspect the building to ensure fire Yes escape routes are and there is no accumulation of combustible materials Are housekeeping standards within the building acceptable? Compare the signage in the building to that Mostly, a few sign have been removed when decorating referred to in the fire risk assessment, primarily: has occurred. DL to replace. Call Points Fire Action Notices Is the signage in place and adequate? Emergency Exits Fire Extinguishers Complete a sample check within the building (approx. 20%) Numerous self closers were not working, missing or broken logged on CAFM 00277783 – L609 is now a kitchen and requires both heat detection and a FD30 fitting logged CAFM 00277785 – Additional observations L519 has a kitchen in it and requires heat detection this – area needs to be checked further to ensure travel distances are not excessive and signage is required for the fire exit route through the old reception area. The Regulatory Reform (Fire Safety) Order 2005 Yes Does legislation referred to in fire risk The Licensing Act No assessment reflect current standards The Housing Act No
Is the evacuation plan current? Obtain plan from website Plan should be dated within last 12 months Yes Are any hazardous areas identified in the fire risk assessment still present? Check fire risk assessment report (Section 10) for hazardous areas Yes Are housekeeping standards within the building acceptable? Physically inspect the building to ensure fire escape routes are and there is no accumulation of combustible materials Yes Is the signage in place and adequate? Compare the signage in the building to that referred to in the fire risk assessment, primarily: Call Points Fire Action Notices Emergency Exits Fire Extinguishers Complete a sample check within the building (approx. 20%) Mostly, a few sign have been removed when decorating has occurred. DL to replace. Additional observations Numerous self closers were not working, missing or broken – logged on CAFM 00277783 L609 is now a kitchen and requires both heat detection and a FD30 fitting – logged CAFM 00277785 L519 has a kitchen in it and requires heat detection – this area needs to be checked further to ensure travel distances are not excessive and signage is required for the fire exit route through the old reception area. Does legislation referred to in fire risk assessment reflect current standards The Regulatory Reform (Fire Safety) Order 2005 The Licensing Act The Housing Act Yes No No
Allerton-Building-Fire-Risk-Assessment-Review-Record-12-14.docx