power use measurements Full indoor unit control with simple contact input (Emergency/Lock) External Contact State output (Operation/Error) for Each Each Interface synchronous control Channel Channel 10 digital outputs (2 reserved) / 8 digital inputs (2 reserved) Control & monitoring zone edition Wireless/wired remote control restriction Central Each Group Each Group Management Temperature limit setting Operation mode restriction User can edit control logic with arithmetic/conditional operators and parameters. User editable Efficient energy saving realization for Each Group Each Group control logic various operation conditions. EHP/ERV/AHU parameters + AND/OR + Arithmetic equation Function Important data is stored in SD memory card (settings, schedules, errors, Data operation data, energy data, user backup/useful Each Group Each Group settings, etc.) history management Record the operation history and error history Specify unoccupied room settings for applicable indoor units Unoccupied Mode Room Control Each - Configuration Fan speed Set temperature Operation ON/OFF Mode: Heat, cool, cool storage, hot water Operation pattern: standard, rotation, efficiency DVM Chiller Enable/disable Water Law Each Each Control Enable/disable quiet mode Forced fan mode Demand/maximum current control (50~100% of design current) VRF BACnet® Gateway 2.5 Input Variables (Control) Output Variables(Monitor)
power use measurements External Contact Interface Full indoor unit control with simple contact input (Emergency/Lock) State output (Operation/Error) for synchronous control 10 digital outputs (2 reserved) / 8 digital inputs (2 reserved) Each Channel Each Channel Central Management Control & monitoring zone edition Wireless/wired remote control restriction Temperature limit setting Operation mode restriction Each Group Each Group User editable control logic User can edit control logic with arithmetic/conditional operators and parameters. Efficient energy saving realization for various operation conditions. EHP/ERV/AHU parameters + AND/OR + Arithmetic equation Function Each Group Each Group Data backup/useful history management Important data is stored in SD memory card (settings, schedules, errors, operation data, energy data, user settings, etc.) Record the operation history and error history Each Group Each Group Unoccupied Room Control Configuration Specify unoccupied room settings for applicable indoor units Mode Fan speed Set temperature Each - DVM Chiller Control Operation ON/OFF Mode: Heat, cool, cool storage, hot water Operation pattern: standard, rotation, efficiency Enable/disable Water Law Enable/disable quiet mode Forced fan mode Demand/maximum current control (50~100% of design current) Each Each VRF BACnet® Gateway 2.5 Input Variables (Control) Output Variables(Monitor)
AG010KSVAFH_DVM%20Chiller%20Guide%20Spec.docx