(7) This regulation does not apply to a building that has a rise in storeys of more than 2 and— (a) where the distance of travel from the entrance doorway of each sole-occupancy unit— (i) to the nearest exit; or (ii) to a point from which travel in different directions to at least 2 exits is available— is not more than 6m; and (b) that has building elements with a resistance level of not less than 60/60/60 separating each sole-occupancy unit from— (i) a public corridor, public lobby or the like; or (ii) a room not within the sole-occupancy unit; or (iii) the landing of an internal isolated stairway; or (iv) another sole-occupancy unit; and (c) any doorways from each sole-occupancy unit that provide access to a public corridor, public stairway, internal non-fire-isolated stairway or the like are protected with a selfclosing fire door having a fire-resistance level of not less than -/30/30; and (d) that has a fire hose reel system in Reg. 710(7)(d) amended by accordance with clause E1.4 of the S.R. Nos 20/2011 BCA Volume One 2013; and reg. 15(2), 51/2014 reg. 6(1).
(7) This regulation does not apply to a building that has a rise in storeys of more than 2 and— (a) where the distance of travel from the entrance doorway of each sole-occupancy unit— (i) to the nearest exit; or (ii) to a point from which travel in different directions to at least 2 exits is available— is not more than 6m; and (b) that has building elements with a level of not less than 60/60/60 separating each sole-occupancy unit from— (i) a public corridor, public lobby or the like; or (ii) a room not within the sole-occupancy unit; or (iii) the landing of an internal stairway; or (iv) another sole-occupancy unit; and (c) any doorways from each sole-occupancy unit that provide access to a public corridor, public stairway, internal non-fire-isolated stairway or the like are protected with a selfclosing fire door having a fire-resistance level of not less than -/30/30; and Reg. 710(7)(d) amended by S.R. Nos 20/2011 reg. 15(2), 51/2014 reg. 6(1). (d) that has a fire hose reel system in accordance with clause E1.4 of the BCA Volume One 2013; and resistance isolated
06-68sr039C.docx