station room with insulators on either ends and with at least from wall 1.5” clearance Shall provide a bus bar with at least 6 sets of 10 mm diameter holes and respective SS hexagonal head nuts & bolts set with copper washer on both side Shall terminate all cables by Copper lugs Shall electroplate the Earth bus bar and connect to both the electrodes through welding Shall electroplate the top of Electrodes and the Earth Plate, withthe length of the electroplated head being at least 66cm from the top cap of the Earth Electrode. Shall have Earth Pits for each electrode at each of the locations, where the minimum size of the Earth Pit will be 1.5ft x 1.5 ft x 2.5 ft subject to availability of space in that site Shall construct the earth pit by brick works with wall thickness of 5 inch and a galvanized steel door on top of the pit Copper Wire/PVC pipe of 1 inch diametershall be installed along the building with necessary clamps, royal bolts & other fixings at every 2 (two) meters so that they are fixed firmly and properly insulated, and run until they reach the wall of the Earth Pit Indicative Diagram 10 Service Center for The Service Center shall have the following capabilities, at a Desktop PCs and other minimum, in terms of tools and equipment, in order to perform Peripherals the support services for desktop PCs and its peripherals - Sufficient toolkit for desktop maintenance considering that the computer has lots of components that are sensitive to electrostatic discharge; at a minimum it should include screwdriver, zip ties, hex driver, tweezers, isopropyl alcohol, lint free cloth, canned air/vacuum, grounding strap, temperature probe etc. Hardware and software diagnostic toolkits to increase testing accuracy for resolved defects and troubleshoot issues more efficiently Multimeters that provide accurate measurements of voltage
station room with insulators on either ends and with at least 1.5” clearance from wall Shall provide a bus bar with at least 6 sets of 10 mm diameter holes and respective SS hexagonal head nuts & bolts set with copper washer on both side Shall terminate all cables by Copper lugs Shall electroplate the Earth bus bar and connect to both the electrodes through welding Shall electroplate the top of Electrodes and the Earth Plate, withthe length of the electroplated head being at least 66cm from the top cap of the Earth Electrode. Shall have Earth Pits for each electrode at each of the locations, where the minimum size of the Earth Pit will be 1.5ft x 1.5 ft x 2.5 ft subject to availability of space in that site Shall construct the earth pit by brick works with wall thickness of 5 inch and a galvanized steel door on top of the pit Copper Wire/PVC pipe of 1 inch diametershall be installed along the building with necessary clamps, royal bolts & other fixings at every 2 (two) meters so that they are fixed firmly and properly insulated, and run until they reach the wall of the Earth Pit Indicative Diagram 10 Service Center for Desktop PCs and other Peripherals The Service Center shall have the following capabilities, at a minimum, in terms of tools and equipment, in order to perform the support services for desktop PCs and its peripherals - Sufficient toolkit for desktop maintenance considering that the computer has lots of components that are sensitive to electrostatic discharge; at a minimum it should include screwdriver, zip ties, hex driver, tweezers, isopropyl alcohol, lint free cloth, canned air/vacuum, grounding strap, temperature probe etc. Hardware and software diagnostic toolkits to increase testing accuracy for resolved defects and troubleshoot issues more efficiently Multimeters that provide accurate measurements of voltage
96040ICB%20Document%20Package%20GD-26.docx