Air flow 2-step direction (Swing/Stop) Air Flow Each Group Each Group Air flow operation varies depending on the Direction Setting model. ON/OFF single event timer ON/OFF Timer Each Group Each Group Can set to turn unit ON and/or OFF 30 minutes ~ 18 hours. Button permission level setting (On/Off / setting / Mode button / Fan Button lock Temperature limit setting Each Group Each Group After power reset, the setting value is Various restriction capabilities Viewing/Setting indoor unit option code Viewing/setting indoor unit MAIN address Viewing/setting indoor unit RMC address Service Mode Each Unit Each Unit Viewing indoor unit cycle data Viewing/setting indoor unit temperature compensation during Heating (+2°F +5°F) When an error is currently occurring in the Error system, the afflicted unit and the error code Each Group Each Group are displayed Permit / Prohibit Setting/releasing of simplified locking of Each Group N/A Local Operation remote control buttons Select the quiet mode to lower the fan noise Quiet Mode Each Group N/A level. SIMPLE TOUCH WIRED CONTROLLER (MWR-SH10N) Connection: The wired controller shall control up to 16 SAMSUNG indoor units (defined and as one group). Dimensions: The wired controller shall be approximately 4 x 3 x in size and 13/16” 11/16” 3/4” in color. The wired controller shall have the following features and control capability: The wired controller shall have an internal infrared receiver to allow control of
Air Flow Direction Setting Air flow 2-step direction (Swing/Stop) Air flow operation varies depending on the model. Each Group Each Group ON/OFF Timer ON/OFF single event timer Can set to turn unit ON and/or OFF 30 minutes ~ 18 hours. Each Group Each Group Button lock Button permission level setting (On/Off / setting / Mode button / Fan Temperature limit setting After power reset, the setting value is Various restriction capabilities Each Group Each Group Service Mode Viewing/Setting indoor unit option code Viewing/setting indoor unit MAIN address Viewing/setting indoor unit RMC address Viewing indoor unit cycle data Viewing/setting indoor unit temperature compensation during Heating (+2°F +5°F) Each Unit Each Unit Error When an error is currently occurring in the system, the afflicted unit and the error code are displayed Each Group Each Group Permit / Prohibit Local Operation Setting/releasing of simplified locking of remote control buttons Each Group N/A Quiet Mode Select the quiet mode to lower the fan noise level. Each Group N/A SIMPLE TOUCH WIRED CONTROLLER (MWR-SH10N) Connection: The wired controller shall control up to 16 SAMSUNG indoor units (defined and as one group). Dimensions: The wired controller shall be approximately 4 13/16” x 3 11/16” x 3/4” in size and in color. The wired controller shall have the following features and control capability: The wired controller shall have an internal infrared receiver to allow control of
AC018MXSCCCAA_Guide%20Spec.docx