808 Water supply for fire fighting purposes Reg. 808 inserted by (1) This regulation applies if— S.R. No. 105/2009 (a) construction of a Class 1a building is reg. 6, revoked by proposed on the same allotment as a Class 1a S.R. No. building that was destroyed in bushfires 105/2009 reg. 10, new between 1 January 2009 and 31 March 2009 reg. 808 (inclusive); and inserted by S.R. No. 82/2010 reg. 5. Reg. 808(1)(b) (b) the allotment is subject to a Bushfire amended by Management Overlay under the planning S.R. No. 104/2014 scheme approved under the Planning and reg. 10. Environment Act 1987 as in force from time to time applying to that allotment; and (c) a permit is not required under the planning scheme for the construction of the building. (2) A static water supply for fire fighting purposes must be provided on an allotment to which this regulation applies in accordance with this regulation. (3) The static water supply must be— (a) used solely for fire fighting purposes; and (b) able to hold 10 000 litres in onsite static storage located on the allotment; and (c) located within 60m of the building; and (d) situated so as to enable emergency services vehicles access to within 4m of the water supply outlet. (4) If the static water supply is not able to be readily seen from the building or access driveway, a sign
Reg. 808 inserted by S.R. No. 105/2009 reg. 6, revoked by S.R. No. 105/2009 reg. 10, new reg. 808 inserted by S.R. No. 82/2010 reg. 5. 808 Water supply for fire fighting purposes (1) This regulation applies if— (a) construction of a Class 1a building is proposed on the same allotment as a Class 1a building that was destroyed in bushfires between 1 January 2009 and 31 March 2009 (inclusive); and Reg. 808(1)(b) amended by S.R. No. 104/2014 reg. 10. (b) the allotment is subject to a Bushfire Management Overlay under the planning scheme approved under the Planning and Environment Act 1987 as in force from time to time applying to that allotment; and (c) a permit is not required under the planning scheme for the construction of the building. (2) A static water supply for fire fighting purposes must be provided on an allotment to which this regulation applies in accordance with this regulation. (3) The static water supply must be— (a) used solely for fire fighting purposes; and (b) able to hold 10 000 litres in onsite static storage located on the allotment; and (c) located within 60m of the building; and (d) situated so as to enable emergency services vehicles access to within 4m of the water supply outlet. (4) If the static water supply is not able to be readily seen from the building or access driveway, a sign
06-68sr039C.docx