Any other aboveground storage or > 60,000 L handling Combustible N/A Aboveground tank(s) within a multi-story > 1,000 L liquids with a building flashpoint < 93oC Storage areas with any of the following > 10,000 L attributes: co-located with fire-risk hazardous chemicals or toxic substances above minor storage mechanically ventilated located within or attached to a building, or tanks > 6m in diameter. Any other package store > 100,000 L Any other aboveground storage or > 500,000 L handling Flammable and PG I All > 500 kg reactive solids – PG II Activities that involve: > 1,000 kg DG classes 4.1, or elevated temperature or pressure, or 4.2 or 4.3 PG III chemical reactions that cause a temperature rise or generate a gas. Storage areas with any of the following > 2,500 kg attributes: co-located with fire-risk hazardous chemicals above minor storage mechanically ventilated, or located within or attached to a building. Any other aboveground storage or > 10,000 kg handling Oxidising PG I All > 500 L/kg substances DG – PG II Activities that involve: > 1,000 L/kg class 5.1 elevated temperature or pressure, or chemical reactions that cause a
Any other aboveground storage or handling > 60,000 L Combustible liquids with a flashpoint < 93oC N/A Aboveground tank(s) within a multi-story building > 1,000 L Storage areas with any of the following attributes: co-located with fire-risk hazardous chemicals or toxic substances above minor storage mechanically ventilated located within or attached to a building, or tanks > 6m in diameter. > 10,000 L Any other package store > 100,000 L Any other aboveground storage or handling > 500,000 L Flammable and reactive solids – DG classes 4.1, 4.2 or 4.3 PG I All > 500 kg PG II or PG III Activities that involve: elevated temperature or pressure, or chemical reactions that cause a temperature rise or generate a gas. > 1,000 kg Storage areas with any of the following attributes: co-located with fire-risk hazardous chemicals above minor storage mechanically ventilated, or located within or attached to a building. > 2,500 kg Any other aboveground storage or handling > 10,000 kg Oxidising substances – DG class 5.1 PG I All > 500 L/kg PG II Activities that involve: elevated temperature or pressure, or chemical reactions that cause a > 1,000 L/kg
9.4.5-Industry-design.docx