External Static Pressure (“WC) Model Number Standard Acceptable Range AC018MNHDCH/AA 0.10 0.10 - 0.6 AC024MNHDCH/AA 0.10 0.10 - 0.8 AC030MNHDCH/AA 0.16 0.12 0.8 – AC036MNHDCH/AA 0.16 0.12 0.8 – AC042MNHDCH/AA 0.16 0.12 0.8 – AC048MNHDCH/AA 0.20 0.16 0.8 – The indoor fan shall consist of three (3) speeds, Low, Mid, and High. The fan speed shall be adjustable by optional remote controller or manufacturer provided service software according to external static pressure. The indoor unit shall have a ducted air outlet system and ducted return air system. The indoor unit shall have static pressure scanning for simple setup and optimized comfort settings for the occupant. Filter Return air shall be filtered by means of a standard factory installed return air filter. Optional return filter box (rear placement) is available (see accessories section). Coil The indoor coil shall be of nonferrous construction with slit fins on copper tubing. Aluminum coil fins shall be coated with a hydrophilic/protective coating to promote moisture shedding. The tubing shall have inner grooves for high efficiency heat exchange. All tube joints shall be brazed with phos-copper or silver alloy. The coils shall be pressure tested at the factory. A condensate pan with drain pump shall be provided under the coil. The coil fins are coated with hydrophilic paints. The condensate lift mechanism shall be able to raise drain water 29 inches above the condensate pan with built in check valve and float switch.
External Static Pressure (“WC) Model Number Standard Acceptable Range AC018MNHDCH/AA 0.10 0.10 - 0.6 AC024MNHDCH/AA 0.10 0.10 - 0.8 AC030MNHDCH/AA 0.16 0.12 – 0.8 AC036MNHDCH/AA 0.16 0.12 – 0.8 AC042MNHDCH/AA 0.16 0.12 – 0.8 AC048MNHDCH/AA 0.20 0.16 – 0.8 The indoor fan shall consist of three (3) speeds, Low, Mid, and High. The fan speed shall be adjustable by optional remote controller or manufacturer provided service software according to external static pressure. The indoor unit shall have a ducted air outlet system and ducted return air system. The indoor unit shall have static pressure scanning for simple setup and optimized comfort settings for the occupant. Filter Return air shall be filtered by means of a standard factory installed return air filter. Optional return filter box (rear placement) is available (see accessories section). Coil The indoor coil shall be of nonferrous construction with slit fins on copper tubing. Aluminum coil fins shall be coated with a hydrophilic/protective coating to promote moisture shedding. The tubing shall have inner grooves for high efficiency heat exchange. All tube joints shall be brazed with phos-copper or silver alloy. The coils shall be pressure tested at the factory. A condensate pan with drain pump shall be provided under the coil. The coil fins are coated with hydrophilic paints. The condensate lift mechanism shall be able to raise drain water 29 inches above the condensate pan with built in check valve and float switch.
AC009KXADCHAA_CAC%20Guide%20Spec.docx