of a power failure. Can power local detectors and warning appliances. Allows for programming open/close obstruction cycling should the sensing edge encounter a stationary obstruction in the opening during AC power, alarm signal closing. Manual Operation/Labeled Fire Doors: Manual Chain Hoist: Provide combination chain / controlled closing system operator including endless steel chain, geared reduction unit and chain keeper. Provide a wall mounted Push To Close station located at floor level. Integral to the unit is a locking mechanism to hold the door at any position of travel during normal door operation mode and a governor to control automatic closing speed. Provide a combination close operation / automatic drop test cable located at floor level. Integral to the unit is a locking mechanism to hold the door at any position of travel during normal door operation mode and a governor to control automatic closing speed. Manual Crank Hoist: Provide combination crank / controlled closing system operator including removable hand crank and geared reduction unit. Provide a wall mounted Push To station located at floor level. Integral to the unit is a locking mechanism to hold the door at any position of travel during normal door operation mode and a governor to control automatic closing speed. Provide a wall mounted combination operation / automatic drop test cable located at floor level. Integral to the unit is a locking mechanism to hold the door at any position of travel during normal door operation mode and a governor to control automatic closing speed. Manual Push-Up with Conventional Spring Release System: Provide lift handles on bottom bar and pole with hook. Automatic closure shall maintain an average closing speed of not less than 6 inches (152 mm) nor more than 24 inches (610 mm) per second during automatic closing per NFPA 80. Resetting of spring tension and mechanical dropouts by a trained door systems technician is required. Automatic closure shall be activated by fusible link. Automatic closure shall be activated by a local smoke/fire detector by means of a fail-safe releasing device. Automatic closure shall be activated by a central smoke/fire alarm system by means of a fail-safe releasing device. Fire Detectors: Provide Photoelectric Smoke/Heat Detector: UL listed. Provide Ionization Smoke Detector: UL listed. Fire Emergency Annunciator: Provide ADA compliant horn/strobe fire emergency annunciator to give advanced warning that the fire door is to close. Warning signal to activate upon alarm signal.
of a power failure. Can power local detectors and warning appliances. Allows for programming open/close obstruction cycling should the sensing edge encounter a stationary obstruction in the opening during AC power, alarm signal closing. Manual Operation/Labeled Fire Doors: Manual Chain Hoist: Provide combination chain / controlled closing system operator including endless steel chain, geared reduction unit and chain keeper. Provide a wall mounted Push To Close station located at floor level. Integral to the unit is a locking mechanism to hold the door at any position of travel during normal door operation mode and a governor to control automatic closing speed. Provide a combination close operation / automatic drop test cable located at floor level. Integral to the unit is a locking mechanism to hold the door at any position of travel during normal door operation mode and a governor to control automatic closing speed. Manual Crank Hoist: Provide combination crank / controlled closing system operator including removable hand crank and geared reduction unit. Provide a wall mounted Push To station located at floor level. Integral to the unit is a locking mechanism to hold the door at any position of travel during normal door operation mode and a governor to control automatic closing speed. Provide a wall mounted combination operation / automatic drop test cable located at floor level. Integral to the unit is a locking mechanism to hold the door at any position of travel during normal door operation mode and a governor to control automatic closing speed. Manual Push-Up with Conventional Spring Release System: Provide lift handles on bottom bar and pole with hook. Automatic closure shall maintain an average closing speed of not less than 6 inches (152 mm) nor more than 24 inches (610 mm) per second during automatic closing per NFPA 80. Resetting of spring tension and mechanical dropouts by a trained door systems technician is required. Automatic closure shall be activated by fusible link. Automatic closure shall be activated by a local smoke/fire detector by means of a fail-safe releasing device. Automatic closure shall be activated by a central smoke/fire alarm system by means of a fail-safe releasing device. Fire Detectors: Provide Photoelectric Smoke/Heat Detector: UL listed. Provide Ionization Smoke Detector: UL listed. Fire Emergency Annunciator: Provide ADA compliant horn/strobe fire emergency annunciator to give advanced warning that the fire door is to close. Warning signal to activate upon alarm signal.
08330clo.docx