IGE/UP/10 Installation of Flued Appliances Local Authority environmental requirements and planning conditions. The Electricity Supply Regulations CHP The CHP shall be designed and independently certified to the following standards: EN 50465 European product standard for combined heating power systems using gas fuel. IEC 61000-6-2 Electromagnetic compatibility (EMC) - Part 6-2: Generic standards - Immunity standard for industrial environments IEC 61000-6-3 Electromagnetic compatibility (EMC) - Part 6-3: Generic standards - Emission standard for residential, commercial and light-industrial environments EN 12601 Reciprocating internal combustion engine driven generating sets. Safety EN 60204-1 Safety of machinery. Electrical equipment of machines. General requirements EN ISO 13849-1 Safety of machinery. Safety-related parts of control systems. General principles for design 2009/142/EC Gas Appliance Directive 92/42/EEC Boiler Efficiency Directive 2014/30/EU Electromagnetic Compatibility (EMC) Directive 2006/42/EC Machinery Directive To reduce local levels of air pollution, the engine emissions shall not exceed the following values: NOX Emissions 0% O2 7.5 mg/kWh Gas Input – NOX Emissions 0% O2 8.8 mg/Nm3 – NOX Emissions 5% O2 6.7 mg/Nm3 – CO Emissions 0% O2 8.6 mg/Nm3 – Emissions data shall be independently verified by a notified body and a test report shall be available for inspection by the engineer on request. OPERATING PARAMETERS The design is based on the following parameters: Ref Description Unit Unit Unit 1 Minimum CHP unit net electrical output at maximum continuous 10 kW 20 kW 25 kW rating (MCR) and at 0.96 power factor 2 Minimum CHP unit heat output to LTHW at maximum output (35°C 25.0 kW 48.5 kW 57.6 kW return temperature) 3 Minimum CHP unit heat output to LTHW at minimum output (35°C 16.4 kW 30.9 kW 30.9 kW return temperature) 4 Nominal CHP unit gas consumption. Gas supplier to confirm 3.29 m3/hr 6.27 m3/hr 7.56 m3/hr calorific value of gas supplied at time of commissioning.
IGE/UP/10 Installation of Flued Appliances Local Authority environmental requirements and planning conditions. The Electricity Supply Regulations CHP The CHP shall be designed and independently certified to the following standards: EN 50465 European product standard for combined heating power systems using gas fuel. IEC 61000-6-2 Electromagnetic compatibility (EMC) - Part 6-2: Generic standards - Immunity standard for industrial environments IEC 61000-6-3 Electromagnetic compatibility (EMC) - Part 6-3: Generic standards - Emission standard for residential, commercial and light-industrial environments EN 12601 Reciprocating internal combustion engine driven generating sets. Safety EN 60204-1 Safety of machinery. Electrical equipment of machines. General requirements EN ISO 13849-1 Safety of machinery. Safety-related parts of control systems. General principles for design 2009/142/EC Gas Appliance Directive 92/42/EEC Boiler Efficiency Directive 2014/30/EU Electromagnetic Compatibility (EMC) Directive 2006/42/EC Machinery Directive To reduce local levels of air pollution, the engine emissions shall not exceed the following values: NOX Emissions – 0% O2 7.5 mg/kWh Gas Input NOX Emissions – 0% O2 8.8 mg/Nm3 NOX Emissions – 5% O2 6.7 mg/Nm3 CO Emissions – 0% O2 8.6 mg/Nm3 Emissions data shall be independently verified by a notified body and a test report shall be available for inspection by the engineer on request. OPERATING PARAMETERS The design is based on the following parameters: Ref Description Unit Unit Unit 1 Minimum CHP unit net electrical output at maximum continuous rating (MCR) and at 0.96 power factor 10 kW 20 kW 25 kW 2 Minimum CHP unit heat output to LTHW at maximum output (35°C return temperature) 25.0 kW 48.5 kW 57.6 kW 3 Minimum CHP unit heat output to LTHW at minimum output (35°C return temperature) 16.4 kW 30.9 kW 30.9 kW 4 Nominal CHP unit gas consumption. Gas supplier to confirm calorific value of gas supplied at time of commissioning. 3.29 m3/hr 6.27 m3/hr 7.56 m3/hr
Adveco-Totem-mCHP-Full-Specification.docx