(with protection system) N=5.0kvt Electric n=1650d/min. control box Air fan L=10000m3/hour 4 Ea. 1 (with 850 Pa protection Voltage=380V system) Frequency=50Hz Heating section, electric colorific installation Electric control box 5 Ea. 1 N=67.0 kvt (with protection system) Duct fan RS 100x50 L3 -Fan is of rectangular shape: 1000x500 mm - Engine power: 2,96 Kwt - Number of revolutions: 1361 rev/min Electric - Power source: 380V, 50Hz control box - Air flow rate 12000 m3/hour 6 Ea. 1 DIN EN ISO 5801 (with - air pressure created by fan (max) :1000 Pa protection - Protection class IP 54 system) - heat resistant isolation class: F - the duct fan is designed for connecting to the ventilation line in the workshop Electric control box 7 Water heating combi installed on the wall, power Ea. 1 (with 22.5 Kwt protection system) Duct fan “BKM 400” -Fan is of round shape: - Engine power: 0,46 kwt - Number of revolutions: 1361 rev/min - Power source: 220-240V,50Hz Electric -Air flow rate 1434 m3/hour control box - air pressure created by fan (max) :1000 Pa 8 Ea. 1 GOST 9725-82 (with - Protection class IP 44 protection - heat resistant isolation class: F system) - The fan shall be equipped with packaged electronic circuit for automatic control of temperature in the domestic building - the duct fan is designed for connecting to the ventilation line of the domestic building N=0.49 kvt Electric n=1100 d/dəq control box Air handling unit MPA 1800 E3 9 set 1 L=1224 m3/hour (with Voltage=220V protection Frequency=50Hz system) Electric V=200, N=2.0 kvt control box Electric water heater 10 Ea. 1 Voltage=220V (with Frequency=50Hz protection system)
(with protection system) 4 Air fan Ea. 1 N=5.0kvt n=1650d/min. L=10000m3/hour 850 Pa Voltage=380V Frequency=50Hz Electric control box (with protection system) 5 Heating section, electric colorific installation Ea. 1 N=67.0 kvt Electric control box (with protection system) 6 Duct fan RS 100x50 L3 -Fan is of rectangular shape: 1000x500 mm - Engine power: 2,96 Kwt - Number of revolutions: 1361 rev/min - Power source: 380V, 50Hz - Air flow rate 12000 m3/hour - air pressure created by fan (max) :1000 Pa - Protection class IP 54 - heat resistant isolation class: F - the duct fan is designed for connecting to the ventilation line in the workshop Ea. 1 DIN EN ISO 5801 Electric control box (with protection system) 7 Water heating combi installed on the wall, power 22.5 Kwt Ea. 1 Electric control box (with protection system) 8 Duct fan “BKM 400” -Fan is of round shape: - Engine power: 0,46 kwt - Number of revolutions: 1361 rev/min - Power source: 220-240V,50Hz -Air flow rate 1434 m3/hour - air pressure created by fan (max) :1000 Pa - Protection class IP 44 - heat resistant isolation class: F - The fan shall be equipped with packaged electronic circuit for automatic control of temperature in the domestic building - the duct fan is designed for connecting to the ventilation line of the domestic building Ea. 1 GOST 9725-82 Electric control box (with protection system) 9 Air handling unit MPA 1800 E3 set 1 N=0.49 kvt n=1100 d/dəq L=1224 m3/hour Voltage=220V Frequency=50Hz Electric control box (with protection system) 10 Electric water heater Ea. 1 V=200, N=2.0 kvt Voltage=220V Frequency=50Hz Electric control box (with protection system)
05.06.2018-26078-18.Notice-Equipment.docx