r. r. 808 809 be protected from the effects of radiant heat and flame. (7) If the static water supply is above ground, the following additional requirements apply— (a) there must be at least one pipe fitting no less than 64mm, 3 thread/25mm 50mm nominal bore British Standard Pipe (BSP) round male coupling; (b) all pipe work and valving between the water supply and the water supply outlet must be no less than 50mm nominal bore; (c) if the water supply is less than 20m from the building, each outlet must face away from the building to allow access during emergencies. (8) This regulation does not apply if— (a) the bushfire attack level of the allotment is determined as LOW or 12·5 in accordance with Clause 2.2 or Appendix B (as the case requires) of AS 3959 Construction of buildings in bushfire-prone areas, as incorporated for the time being by the BCA; and (b) there is a fire hydrant connected to a reticulated water supply within 120m of the rear of the building. Reg. 809 809 Access for emergency vehicles inserted by S.R. No. (1) This regulation applies if— 105/2009 reg. 6, (a) construction of a Class 1a building is revoked by proposed on the same allotment as a Class 1a S.R. No. 105/2009 building that was destroyed in bushfires reg. 10, new between 1 January 2009 and 31 March 2009 reg. 809 inserted by (inclusive); and S.R. No. 82/2010 reg. 5.
be protected from the effects of radiant heat and flame. (7) If the static water supply is above ground, the following additional requirements apply— r. 808 (a) there must be at least one pipe fitting no less than 64mm, 3 thread/25mm 50mm nominal bore British Standard Pipe (BSP) round male coupling; (b) all pipe work and valving between the water supply and the water supply outlet must be no less than 50mm nominal bore; (c) if the water supply is less than 20m from the building, each outlet must face away from the building to allow access during emergencies. (8) This regulation does not apply if— (a) the bushfire attack level of the allotment is determined as LOW or 12·5 in accordance with Clause 2.2 or Appendix B (as the case requires) of AS 3959 Construction of buildings in bushfire-prone areas, as incorporated for the time being by the BCA; and (b) there is a fire hydrant connected to a reticulated water supply within 120m of the rear of the building. Reg. 809 inserted by S.R. No. 105/2009 reg. 6, revoked by S.R. No. 105/2009 reg. 10, new reg. 809 inserted by S.R. No. 82/2010 reg. 5. 809 Access for emergency vehicles r. 809 (1) This regulation applies if— (a) construction of a Class 1a building is proposed on the same allotment as a Class 1a building that was destroyed in bushfires between 1 January 2009 and 31 March 2009 (inclusive); and
06-68sr026.docx