CONTINUATION PAGE PROJECT NAME: PROJECT #549-15-514 Building 60 Emergency Power Upgrade Dallas, VA Medical Center – 36C257-18-B-0826 SOLICITATION NUMBER: BID DUE DATE: FRIDAY, SEPTEMBER 28, 2018 @ 1:00 P.M. CST SUBMITTED: Date & Time Entered - 8/20/2018 from 11:13:28 AM to 11:29:24 AM; CDT; BY: TREVINO GROUP, INC., THE; QUESTIONS: #1 - #11 (within ‘vendor portal’): We request a 2nd site visit ASAP, thanks? ANSWER: To VISN 17 MATOC GROUP, a second and final ‘site visit’ has been scheduled by Dallas Engineering Service on FRIDAY, AUGUST 24, 2018 from 9:00 AM 10:30 AM. Any interested MATOC – Contractor will meet at the same location, of the first the Dallas VA ‘site visit’ at Resident Engineering Trailer #TT55; this (Friday) 8/24/2018 from 9 10:30 a.m. CDT. – (A second visit will be accommodated at 9am Friday August 24) Request extension to submission of questions based on question 1 additional site visit? ANSWER: The RFI cut-off will therefore be extended until FRIDAY, AUGUST 31, because of the implementation of the August 24th. 2018, 4:30 P.M., second ‘site visit’ on Confirm acceptable # of with multiple shut downs for new scope of work, per not on reference of not to “scope summary” front plan page, “shut down exceed 10 hours” But does not mention multiple shut downs acceptable. Assuming 2 to 3 shut downs for new scope All within 10-hour window? ANSWER: Facility will review MOP provided by Contractor and coordinate that will assure the fewest shutdowns are needed and provide the most efficient means of delivery of the SOW. No set number of outages can be provided. All outages required will be supported. It is expected that the Contractor will wish to minimize outages. Confirm intent of new connection after 1200amp circuit breaker removed at generator, what is acceptable new connection? -will j-box be installed for new connections -are we
CONTINUATION PAGE PROJECT NAME: PROJECT #549-15-514 Building 60 Emergency Power Upgrade – Dallas, VA Medical Center SOLICITATION NUMBER: 36C257-18-B-0826 BID DUE DATE: FRIDAY, SEPTEMBER 28, 2018 @ 1:00 P.M. CST SUBMITTED: Date & Time Entered - 8/20/2018 from 11:13:28 AM to 11:29:24 AM; CDT; BY: TREVINO GROUP, INC., THE; QUESTIONS: #1 - #11 (within ‘vendor portal’): We request a 2nd site visit ASAP, thanks? ANSWER: To VISN 17 MATOC GROUP, a second and final ‘site visit’ has been scheduled by Dallas Engineering Service on FRIDAY, AUGUST 24, 2018 from 9:00 AM – 10:30 AM. Any interested MATOC Contractor will meet at the same location, of the first ‘site visit’ at the Dallas VA Resident Engineering Trailer #TT55; this (Friday) 8/24/2018 from 9 – 10:30 a.m. CDT. (A second visit will be accommodated at 9am Friday August 24) Request extension to submission of questions based on question 1 additional site visit? ANSWER: The RFI cut-off will therefore be extended until FRIDAY, AUGUST 31, 2018, 4:30 P.M., because of the implementation of the second ‘site visit’ on August 24th. Confirm acceptable # of with multiple shut downs for new scope of work, per not on “scope summary” front plan page, reference of “shut down not to exceed 10 hours” But does not mention multiple shut downs acceptable. Assuming 2 to 3 shut downs for new scope All within 10-hour window? ANSWER: Facility will review MOP provided by Contractor and coordinate that will assure the fewest shutdowns are needed and provide the most efficient means of delivery of the SOW. No set number of outages can be provided. All outages required will be supported. It is expected that the Contractor will wish to minimize outages. Confirm intent of new connection after 1200amp circuit breaker removed at generator, what is acceptable new connection? -will j-box be installed for new connections -are we
36C25718B0826-A00001000_Amend_1.docx