Reaction cylinders 0-43 gal/min < 43.3 gal/min Teflon-coated Design aluminum Infoa Set Valuesc Hydrogen peroxide 40–90 gal/min 160°F 175 gal/min CS with ester Design combined decomposers lining Infoa 85 lb/in.2 Outlet 150 lb/in.2 Set Valuesc 100 lb/in.2 Inlet gauge 180°F pH Adjustment Tank pH adjustment tank 0 lb/in.2 gauge 90–140°F 0 lb/in.2 gauge, 304/304L SS Design 200°F Infoa Set Valuesc pH adjustment tank 100-120 gal/min 90–140°F 150 lb/in.2, Operating pumps 110-120 lb/in.2 140°F Proceduree gauge Set Valuesc Degasification Column Degasification inlet 86–140°F 316L SS Training cooler manuald Degasification vessel 86°F 175 gal/min, FRP ±12 in. H2O at 100°F Degasification 30 50 lb/in.2 86°F 175 gal/min, 316 SS Design – transfer pumps gauge 45 lb/in.2 Infoa Operating Proceduree Reverse Osmosis System First RO feed tank 0 lb/in.2 gauge 50-90°F 0 lb/in.2 gauge, 304 SS Design 120°F Infoa Set Valuesc First stage RO feed 250 300 50-90°F 600 lb/in.2 SS Design – pumps lb/in.2 gauge gauge, 120°F Infoa Set Valuesc 290 gal/min Operating Proceduree First stage membrane 100-270 lb/in.2 60-90°F 600 lb/in.2, Design vessels array 1 gauge Inlet 113°F Infoa 30-120 lb/in.2 Set Valuesc gauge Brine Operating Proceduree <10 lb/in.2 gauge Permeate 70-120 gal/min Brine 60-90 gal/min Permeate
Reaction cylinders 0-43 gal/min < 43.3 gal/min Teflon-coated aluminum Design Infoa Set Valuesc Hydrogen peroxide decomposers 40–90 gal/min 85 lb/in.2 Outlet 100 lb/in.2 Inlet 160°F 175 gal/min combined 150 lb/in.2 gauge 180°F CS with ester lining Design Infoa Set Valuesc pH Adjustment Tank pH adjustment tank 0 lb/in.2 gauge 90–140°F 0 lb/in.2 gauge, 200°F 304/304L SS Design Infoa Set Valuesc pH adjustment tank pumps 100-120 gal/min 110-120 lb/in.2 gauge 90–140°F 150 lb/in.2, 140°F Operating Proceduree Set Valuesc Degasification Column Degasification inlet cooler 86–140°F 316L SS Training manuald Degasification vessel 86°F 175 gal/min, ±12 in. H2O at 100°F FRP Degasification transfer pumps 30 – 50 lb/in.2 gauge 86°F 175 gal/min, 45 lb/in.2 316 SS Design Infoa Operating Proceduree Reverse Osmosis System First RO feed tank 0 lb/in.2 gauge 50-90°F 0 lb/in.2 gauge, 120°F 304 SS Design Infoa Set Valuesc First stage RO feed pumps 250 – 300 lb/in.2 gauge gal/min 50-90°F 600 lb/in.2 gauge, 120°F SS Design Infoa Set Valuesc Operating Proceduree First stage membrane vessels array 1 100-270 lb/in.2 gauge Inlet 30-120 lb/in.2 gauge Brine <10 lb/in.2 gauge Permeate 70-120 gal/min Brine 60-90 gal/min Permeate 60-90°F 600 lb/in.2, 113°F Design Infoa Set Valuesc Operating Proceduree 290
314321_-_DRAFT_RPP-PLAN-61349_Draft.docx