Quarterly Check for particulate accumulation on intake filters and clean or replace if accumulation results in pressure drop of airflow outside of established operating limits. Check air filter and housing for integrity and correct, as needed. Semi- Annual 1. Check control system and devices for evidence of improper operation and adjust, repair or replace components, as needed. 2. Check p-trap and prime, as needed, to ensure proper operation. 3. Check fan belt tension, check for belt wear and proper alignment and replace, as needed, to ensure proper operation. 4. Check for proper operation of cooling or heating coil and clean, restore or replace, as needed. 5. Check the coils for any blockage, debries, or holes and clean, as needed. If unit is direct drive check for any loose item that might cause the unit any problems. 7. Check and clean coils, if present. C. Gas Unit Heater Check unit to make sure it is clean from dust, paper, debris, and clean, as needed. Check heat exchanger for any defects or cracks. Check pilot light to insure proper operation. Fire up unit and check the flame for proper flame burn. Cycle the unit through the thermostat making sure the unit comes on and goes off at the set temperature. Make sure the flue is clear of all obstructions and debris. Set thermostat at desired temperature. D. Air Conditioner Split System Clean or replace filter. Check electrical cord for damage. Clean the evaporator and condenser coils. Re-establish power to unit and check for proper operation.
Quarterly Check for particulate accumulation on intake filters and clean or replace if accumulation results in pressure drop of airflow outside of established operating limits. Check air filter and housing for integrity and correct, as needed. Semi- Annual 1. Check control system and devices for evidence of improper operation and adjust, repair or replace components, as needed. 2. Check p-trap and prime, as needed, to ensure proper operation. 3. Check fan belt tension, check for belt wear and proper alignment and replace, as needed, to ensure proper operation. 4. Check for proper operation of cooling or heating coil and clean, restore or replace, as needed. 5. Check the coils for any blockage, debries, or holes and clean, as needed. If unit is direct drive check for any loose item that might cause the unit any problems. 7. Check and clean coils, if present. C. Gas Unit Heater Check unit to make sure it is clean from dust, paper, debris, and clean, as needed. Check heat exchanger for any defects or cracks. Check pilot light to insure proper operation. Fire up unit and check the flame for proper flame burn. Cycle the unit through the thermostat making sure the unit comes on and goes off at the set temperature. Make sure the flue is clear of all obstructions and debris. Set thermostat at desired temperature. D. Air Conditioner Split System Clean or replace filter. Check electrical cord for damage. Clean the evaporator and condenser coils. Re-establish power to unit and check for proper operation.
358685330.docx