2.9 Ideally light fittings should be positioned to allow easy access for lamp changing. This is not always possible. However, with the present long life span of lamps (particularly discharge lamps) it would be advantageous to plan ahead and budget for a complete periodic lamp change, carried out professionally, without health and safety risks. 3. Emergency Lighting There is currently no statutory requirement for churches to provide emergency lighting. It is however, the duty of the PCC to carry out a risk assessment, as required under the Health and Safety Regulations. NB: This is not the case for church halls that are available for public hire. 3.1 If the assessment results in a decision to provide emergency lighting, it should be installed in accordance with BS5266. 3.2 An emergency lighting log book, with the record of regular testing must be kept up to date. Without regular testing and maintenance, emergency lighting will soon become ineffective. 3.3 The emergency light fittings should be non-maintained units (i.e. to activate only on power failure). For aesthetic reasons it would be preferable to incorporate the emergency unit within a general lighting fitting if possible. 3.4 If infrequent provision only, is required, illuminated exit signs and emergency lighting can be provided by portable in’ units, with the provision of a discreet socket and bracket in the appropriate positions. When ‘plug not in use the emergency lighting units could be kept energised, adjacent to the electricity mains supply position. This would also help to ensure that the lighting units are in working order prior to use. 4. External Floodlighting There are many things to consider before deciding to floodlight the exterior of the church: 4.1 Light pollution, particularly in rural churches.
2.9 Ideally light fittings should be positioned to allow easy access for lamp changing. This is not always possible. However, with the present long life span of lamps (particularly discharge lamps) it would be advantageous to plan ahead and budget for a complete periodic lamp change, carried out professionally, without health and safety risks. 3. Emergency Lighting There is currently no statutory requirement for churches to provide emergency lighting. It is however, the duty of the PCC to carry out a risk assessment, as required under the Health and Safety Regulations. NB: This is not the case for church halls that are available for public hire. 3.1 If the assessment results in a decision to provide emergency lighting, it should be installed in accordance with BS5266. 3.2 An emergency lighting log book, with the record of regular testing must be kept up to date. Without regular testing and maintenance, emergency lighting will soon become ineffective. 3.3 The emergency light fittings should be non-maintained units (i.e. to activate only on power failure). For aesthetic reasons it would be preferable to incorporate the emergency unit within a general lighting fitting if possible. 3.4 If infrequent provision only, is required, illuminated exit signs and emergency lighting can be provided by portable ‘plug in’ units, with the provision of a discreet socket and bracket in the appropriate positions. When not in use the emergency lighting units could be kept energised, adjacent to the electricity mains supply position. This would also help to ensure that the lighting units are in working order prior to use. 4. External Floodlighting There are many things to consider before deciding to floodlight the exterior of the church: 4.1 Light pollution, particularly in rural churches.
Electrical_Wiring_in_Churches.docx