Area/Location Maximum Lux Average Lux Recommended Remarks Open Yard 3 2 50 The lux at every corner Walk-way 7 4 50 poor. Immediate attention is Walk-way in front 21 15.4 50 this regard is solicited. All of high mast conventional tube-light fit- Generator Shed 23 11.5 100 tings are to be replaced by Heater Shed 26 16 50 T-5 fittings with electronic Walk-way in front 24 19.6 50 Ballast. Around 1/3 of of Heater/Testing halogen lights at high Area around G.U. 18 14.8 50 non-functional, which are to Along Boundary 8 4.29 50 Be replaced immediately. wall Extra lights are to be providd COD Pump Area 20 11 100 Along the boundary wall for security reason. Booster Pump 3 2 100 Disposal 18 15.66 100 Pump House Walk-way in front 33 26.2 50 of pump house Office Verandah 72 56.5 100 Office Room 172 80.16 200 Workers’ room 90 59.5 200 Energy Savings : Total conventional tube-lights of (36 + 12) watts are to be replaced by T-5 fittings (of 29 watts). There are total 77 nos of such fittings. Annual savings = (48 -29) watts x 77 nos x 12 hours/day x 365 days/year= 6407.94 KWHr, @ Rs.4.55/KWHr = Rs.29,156.00 Investment : 77 fittings x Rs.422.00 (cost of T5) = Rs.32,494.00. Simple pay-back period = 13 months. 40 watts Light Emmitting Diode (LED) fixtures can also be tested in place of 160 watt mercury vapour lamp, but no specific recommendation is meted out in this sphere (the concerned manufacturers should be consulted) GENERAL OBSERVATIONS OF THE AUDIT Oil Collecting Station is a very compact and continuous type of operation, receiving crude oil mix from 47 well exploration stations.
Area/Location Maximum Lux Average Lux Recommended Remarks Open Yard 3 2 50 The lux at every corner Walk-way 7 4 50 poor. Immediate attention is Walk-way in front of high mast 21 15.4 50 this regard is solicited. All conventional tube-light fit- Generator Shed 23 11.5 100 tings are to be replaced by Heater Shed 26 16 50 T-5 fittings with electronic Walk-way in front of Heater/Testing 24 19.6 50 Ballast. Around 1/3 of halogen lights at high Area around G.U. 18 14.8 50 non-functional, which are to Along Boundary wall 8 4.29 50 Be replaced immediately. Extra lights are to be providd COD Pump Area 20 11 100 Along the boundary wall for security reason. Booster Pump 3 2 100 Disposal Pump House 18 15.66 100 Walk-way in front of pump house 33 26.2 50 Office Verandah 72 56.5 100 Office Room 172 80.16 200 Workers’ room 90 59.5 200 Energy Savings : Total conventional tube-lights of (36 + 12) watts are to be replaced by T-5 fittings (of 29 watts). There are total 77 nos of such fittings. Annual savings = (48 -29) watts x 77 nos x 12 hours/day x 365 days/year= 6407.94 KWHr, @ Rs.4.55/KWHr = Rs.29,156.00 Investment : 77 fittings x Rs.422.00 (cost of T5) = Rs.32,494.00. Simple pay-back period = 13 months. 40 watts Light Emmitting Diode (LED) fixtures can also be tested in place of 160 watt mercury vapour lamp, but no specific recommendation is meted out in this sphere (the concerned manufacturers should be consulted) GENERAL OBSERVATIONS OF THE AUDIT Oil Collecting Station is a very compact and continuous type of operation, receiving crude oil mix from 47 well exploration stations.
Energy%20Audit%20Report-%20Makum%20OCS.docx