AHU CFM OA-Max YES NO YES NO YES NO – 􀂉 􀂉 􀂉 􀂉 􀂉 􀂉 AHU CFM RA-Min YES NO YES NO YES NO – 􀂉 􀂉 􀂉 􀂉 􀂉 􀂉 AHU CFM RA-Max YES NO YES NO YES NO – 􀂉 􀂉 􀂉 􀂉 􀂉 􀂉 AHU GPM Coil YES NO YES NO YES NO – 􀂉 􀂉 􀂉 􀂉 􀂉 􀂉 AHU GPM Coil YES NO YES NO YES NO – 􀂉 􀂉 􀂉 􀂉 􀂉 􀂉 Fan CFM YES NO YES NO YES NO – 􀂉 􀂉 􀂉 􀂉 􀂉 􀂉 Fan - ESP YES NO YES NO YES NO 􀂉 􀂉 􀂉 􀂉 􀂉 􀂉 Grille CFM YES NO YES NO YES NO – 􀂉 􀂉 􀂉 􀂉 􀂉 􀂉 Grille CFM YES NO YES NO YES NO – 􀂉 􀂉 􀂉 􀂉 􀂉 􀂉 Offset – YES NO YES NO YES NO 􀂉 􀂉 􀂉 􀂉 􀂉 􀂉 Pump GPM YES NO YES NO YES NO – 􀂉 􀂉 􀂉 􀂉 􀂉 􀂉 Pump GPM YES NO YES NO YES NO – 􀂉 􀂉 􀂉 􀂉 􀂉 􀂉 VAV CFM Min YES NO YES NO YES NO – 􀂉 􀂉 􀂉 􀂉 􀂉 􀂉 VAV CFM Max YES NO YES NO YES NO – 􀂉 􀂉 􀂉 􀂉 􀂉 􀂉 Edit and expand Table to match sampling methodology and project Design. Triple duty valves for pumps operated by VFD are 100% open? YES NO Diffusers and grilles with adjustable throw patterns adjusted to match contract documents? YES NO Final ductwork control static pressure setpoint recorded? YES NO Final hydronic control differential pressure setpoint recorded? YES NO VAV box recorded YES NO “k” factors Pump impeller required trimming completed YES NO Conclusion Acceptable Criteria: All points listed are within listed tolerances of design and original recordings and were recorded in accordance with TAB plan and/or NEBB standards. Comments: Observations: Final Status: Accepted Not Accepted Relevant Trend Data Static Pressure Setpoint (VFD fans ONLY), Hydronic Loop Differential Setpoint (VFD pumps ONLY). Witnesses Name Signature
AHU – CFM OA-Max 􀂉 YES 􀂉 NO 􀂉 YES 􀂉 NO 􀂉 YES 􀂉 NO AHU – CFM RA-Min 􀂉 YES 􀂉 NO 􀂉 YES 􀂉 NO 􀂉 YES 􀂉 NO AHU – CFM RA-Max 􀂉 YES 􀂉 NO 􀂉 YES 􀂉 NO 􀂉 YES 􀂉 NO AHU – GPM Coil 􀂉 YES 􀂉 NO 􀂉 YES 􀂉 NO 􀂉 YES 􀂉 NO AHU – GPM Coil 􀂉 YES 􀂉 NO 􀂉 YES 􀂉 NO 􀂉 YES 􀂉 NO Fan – CFM 􀂉 YES 􀂉 NO 􀂉 YES 􀂉 NO 􀂉 YES 􀂉 NO Fan - ESP 􀂉 YES 􀂉 NO 􀂉 YES 􀂉 NO 􀂉 YES 􀂉 NO Grille – CFM 􀂉 YES 􀂉 NO 􀂉 YES 􀂉 NO 􀂉 YES 􀂉 NO Grille – CFM 􀂉 YES 􀂉 NO 􀂉 YES 􀂉 NO 􀂉 YES 􀂉 NO Offset – 􀂉 YES 􀂉 NO 􀂉 YES 􀂉 NO 􀂉 YES 􀂉 NO Pump – GPM 􀂉 YES 􀂉 NO 􀂉 YES 􀂉 NO 􀂉 YES 􀂉 NO Pump – GPM 􀂉 YES 􀂉 NO 􀂉 YES 􀂉 NO 􀂉 YES 􀂉 NO VAV – CFM Min 􀂉 YES 􀂉 NO 􀂉 YES 􀂉 NO 􀂉 YES 􀂉 NO VAV – CFM Max 􀂉 YES 􀂉 NO 􀂉 YES 􀂉 NO 􀂉 YES 􀂉 NO Edit and expand Table to match sampling methodology and project Design. Triple duty valves for pumps operated by VFD are 100% open? YES NO Diffusers and grilles with adjustable throw patterns adjusted to match contract documents? YES NO Final ductwork control static pressure setpoint recorded? YES NO Final hydronic control differential pressure setpoint recorded? YES NO VAV box “k” factors recorded YES NO Pump impeller required trimming completed YES NO Conclusion Acceptable Criteria: All points listed are within listed tolerances of design and original recordings and were recorded in accordance with TAB plan and/or NEBB standards. Comments: Observations: Final Status: Accepted Not Accepted Relevant Trend Data Static Pressure Setpoint (VFD fans ONLY), Hydronic Loop Differential Setpoint (VFD pumps ONLY). Witnesses Name Signature
23%2008%2000.docx