1. CSA C22.2-182.1: Industrial Type Special Use Attachment Plugs, Receptacles and Connectors 2. CSA C22.1 Canadian Electrical Code Part I (CEC) E. Intertek Semko F. National Fire Protection Association (NFPA) 1. NFPA 70 National Electrical Code (NEC) 1.03 SUBMITTALS A. Comply with Section 01 33 00 Submittal Procedures. – B. Product Data: 1. literature and product specifications Submit manufacturer’s descriptive for each product. 2. product drawings. Manufacturer’s 1.04 QUALITY ASSURANCE A. Manufacturer Qualifications: Products shall be free of defects in material and workmanship. Furnished products shall be listed or classified by third party agencies suitable for the intended purpose. WARRANTY Product is warranted free of defects in material and workmanship. Product is warranted to perform the intended function within design limits. PART 2 PRODUCTS – 2.01 GENERAL A. These devices shall be UL Listed, CSA, and Certified for circuit interrupting at full Intertek SEMKO rated current. B. Devices shall be rated 16A at 415 VAC maximum. Devices shall be rated 20, 30, 60, 100 amperes at 600 VAC, and 250 VDC maximum. Devices shall be rated 32, 63, 125 amperes at 415 VAC maximum. C. These devices shall have the following catalog numbering scheme: 1. ABB_P_WPlugs 2. ABB_C_W Connectors 3. ABB_R_WReceptacles 4. ABB_B_WInlets D. These devices shall provide internal environmental seals for marine and extreme wet applications. E. These devices shall be used with hard service cord or junior hard service cord in accordance to the NEC table 400.4. 2.02 MANUFACTURERS
1. CSA C22.2-182.1: Industrial Type Special Use Attachment Plugs, Receptacles and Connectors 2. CSA C22.1 Canadian Electrical Code Part I (CEC) E. Intertek Semko F. National Fire Protection Association (NFPA) 1. NFPA 70 National Electrical Code (NEC) 1.03 SUBMITTALS A. Comply with Section 01 33 00 – Submittal Procedures. B. Product Data: 1. Submit manufacturer’s descriptive literature and product specifications for each product. 2. Manufacturer’s product drawings. 1.04 QUALITY ASSURANCE A. Manufacturer Qualifications: Products shall be free of defects in material and workmanship. Furnished products shall be listed or classified by third party agencies suitable for the intended purpose. WARRANTY Product is warranted free of defects in material and workmanship. Product is warranted to perform the intended function within design limits. PART 2 – PRODUCTS 2.01 GENERAL A. These devices shall be UL Listed, CSA, and Intertek SEMKO Certified for circuit interrupting at full rated current. B. Devices shall be rated 16A at 415 VAC maximum. Devices shall be rated 20, 30, 60, 100 amperes at 600 VAC, and 250 VDC maximum. Devices shall be rated 32, 63, 125 amperes at 415 VAC maximum. C. These devices shall have the following catalog numbering scheme: 1. ABB_P_WPlugs 2. ABB_C_W Connectors 3. ABB_R_WReceptacles 4. ABB_B_WInlets D. These devices shall provide internal environmental seals for marine and extreme wet applications. E. These devices shall be used with hard service cord or junior hard service cord in accordance to the NEC table 400.4. 2.02 MANUFACTURERS
26_27_26.17.docx