Instant start and rapid start ballasts (not classified as sign 0.993 0.38 0.25 ballasts) that are designed to operate 8-foot high output lamps Programmed start ballasts (not classified as sign ballasts) 0.973 0.70 0.37 that are designed to operate 8-foot high output lamps Sign ballasts that operate 8-foot high output lamps 0.993 0.47 0.25 Instant start and rapid start residential ballasts that operate: 0.993 0.41 0.25 4-foot medium bipin lamps 2-foot U-shaped lamps 8-foot slimline lamps Programmed start residential ballasts that are designed to 0.973 0.71 0.37 operate: 4-foot medium bipin lamps 2-foot U-shaped lamps Canada Table 32. Minimum efficacy of fluorescent lamps as per CAN/CSA-C819-11. Medium bi-pin base, U-shaped, High output, rapid-start, recessed Slimline, instant-start, rapid-start double contact single-pin Length (mm) 1200 560–635 2400 2400 Nominal wattage (W) > 35 ≤ 35 > 35 ≤ 35 > 100 ≤ 100 > 65 ≤ 65 Average CRI 69 45 69 45 69 45 69 45 Rated luminous 75 75 68 64 80 80 80 80 efficacy (lm/W) Table 33. Minimum efficiency requirements for ballasts in Canada. Minimum Ballast Application for Operation of Ballast Input Voltage (V) Total Nominal Lamp Wattage (W) Efficacy Factor (BEF) 120 40 2.29 One F40T12 lamp 277 40 2.29 Also for use on 40W/48T10/RS lamps 347 40 2.22 120 34 2.61 One F34T12 lamp 277 34 2.61 347 34 2.53 120 80 1.17 Two F40T12 lamps 277 80 1.17 Also for use on 40W/48T10/RS lamps 347 80 1.12 120 68 1.35 Two F34T12 lamps 277 68 1.35 347 68 1.29 120 150 0.63 Two F96T12(IS) lamps 277 150 0.63 Also for use on 60W/96T12/IS lamps 347 150 0.62 Two F96T12(ES) lamps 120 120 0.77
Instant start and rapid start ballasts (not classified as sign ballasts) that are designed to operate 8-foot high output lamps 0.993 0.38 0.25 Programmed start ballasts (not classified as sign ballasts) that are designed to operate 8-foot high output lamps 0.973 0.70 0.37 Sign ballasts that operate 8-foot high output lamps 0.993 0.47 0.25 Instant start and rapid start residential ballasts that operate: 4-foot medium bipin lamps 2-foot U-shaped lamps 8-foot slimline lamps 0.993 0.41 0.25 Programmed start residential ballasts that are designed to operate: 4-foot medium bipin lamps 2-foot U-shaped lamps 0.973 0.71 0.37 Canada Table 32. Minimum efficacy of fluorescent lamps as per CAN/CSA-C819-11. Medium bi-pin base, rapid-start U-shaped, High output, rapid-start, recessed double contact Slimline, instant-start, single-pin Length (mm) 1200 560–635 2400 2400 Nominal wattage (W) > 35 ≤ 35 > 35 ≤ 35 > 100 ≤ 100 > 65 ≤ 65 Average CRI 69 45 69 45 69 45 69 45 Rated luminous efficacy (lm/W) 75 75 68 64 80 80 80 80 Table 33. Minimum efficiency requirements for ballasts in Canada. Application for Operation of Ballast Input Voltage (V) Total Nominal Lamp Wattage (W) Minimum Ballast Efficacy Factor (BEF) One F40T12 lamp Also for use on 40W/48T10/RS lamps 120 40 2.29 277 40 2.29 347 40 2.22 One F34T12 lamp 120 34 2.61 277 34 2.61 347 34 2.53 Two F40T12 lamps Also for use on 40W/48T10/RS lamps 120 80 1.17 277 80 1.17 347 80 1.12 Two F34T12 lamps 120 68 1.35 277 68 1.35 347 68 1.29 Two F96T12(IS) lamps Also for use on 60W/96T12/IS lamps 120 150 0.63 277 150 0.63 347 150 0.62 Two F96T12(ES) lamps 120 120 0.77
280715_Commercial_lighting_Product_Profile_0_0.docx