The NAME of demanded GOODS Unit of Item Description Quantity Standard Measure Odorant tank Horizontal ТУ Pressure - 1,6 MPa 1 1 ea Material --- 09Г2С К60 ПБ 03-576-03 Capacity - V=2.5 m³; Ø1400 mm Gas condensate receiver (Drainage) tank V = 5 m³; m = 4,2t; P = ------ 5.5 Mpa ЕСКП 5,5 ТУ 2 1 ea Material - or 09Г2С 08Х18Н10Т ПБ 03-576-03----------------- Underground, at a depth of 1,8 meters from ground level For Condensate capacity ЕП 3-1400 Pipe GOST 8732-78 (V = 3m3; P=0,07 MPa; D = 1400 mm L = 2796 3 mm) 8 ea Angle GOST 17375-2001 Underground, at a depth of 1,8 meters from Reducer GOST ground level Gas separator СЦВ-8-1220/8,8 ea Dx = 1220mm; H = 2900mm; 4 2 ТУ3683-001-93823823 Working Pressure =2,5 7,5 MPa; – Q = 12,6 mln 36,1 mln m³/ day; – weight 3000 kg – Filter separator Dn 150, Pn 5.5 MPa GOST 52630-12 ФС-150, ea 5 1 Material - 09Г2С
The NAME of demanded GOODS Item Description Unit of Measure Quantity Standard 1 Odorant tank Horizontal Pressure - 1,6 MPa Material --- 09Г2С К60 Capacity - V=2.5 m³; Ø1400 mm ea 1 ТУ ПБ 03-576-03 2 Gas condensate receiver (Drainage) tank V = 5 m³; m = 4,2t; P = 5.5 Mpa ЕСКП 5,5 Material - 09Г2С or 08Х18Н10Т Underground, at a depth of 1,8 meters from ground level ea 1 ------ ТУ ПБ 03-576-03----------------- 3 Condensate capacity ЕП 3-1400 (V = 3m3; P=0,07 MPa; D = 1400 mm L = 2796 mm) Underground, at a depth of 1,8 meters from ground level ea 8 For Pipe GOST 8732-78 Angle GOST 17375-2001 Reducer GOST 4 Gas separator СЦВ-8-1220/8,8 Dx = 1220mm; H = 2900mm; Working Pressure =2,5 – 7,5 MPa; Q = 12,6 mln – 36,1 mln m³/ day; weight – 3000 kg ea 2 ТУ3683-001-93823823 5 Filter separator ФС-150, Dn 150, Pn 5.5 MPa Material - 09Г2С ea 1 GOST 52630-12
02.08.2018-22009-18%20requirement%20for%20separator%20and%20tanks.docx