Designed in accordance with NFPA 230. Must be designed to meet local building, fire, and life-safety codes. The warehouse will have heated x and unheated space. (30’ 62’) One side of the warehouse shall be isolated and be serviced with heating, ventilation, and air conditioning (HVAC). Insulated exposed duct work with overhead diffusers. The HVAC shall be designed to provide controlled environment for storage of the LAWPS resin. Include electric lighting system and electric outlets (110 and 240). Lighting to provide required lumen for light industrial storage with 3 way switches at each entrance for each bay. Exterior automatic day/night lighting at each exterior man door. One 240 volt outlet in each bay and wall mounted duplex outlets every OC. 50’ The entire warehouse shall be insulated. Include non-slip surface treatments on floors subject to wetting, such as outdoor docks, to eliminate slips and falls to personnel Include signage (life safety, exit, emergency lighting, etc.). Incorporate energy efficiency designs (light colored roof, white painted interior metal roof decking, energy efficient fixtures, etc.). 4 each exterior concealed overhead coiling door by with 8’W 12’H bumper guards and weather seal. Bottom lock powered operation with manual override. One by interior powered roll up door with bumper guards into 8’W 12’H the heated space. 4 exterior and 3 interior man doors by Door frames minimum 14 3’ 7’. gauge metal frames, hardware to be latch sets with emergency crash bar on interior. by exterior concrete pad at each roll up door. by exterior 12’ 10’ 4’ 4’ concrete pad at each exterior man door. Provide a Radio Fire Alarm Reporter (RFAR) box to be connected to the site fire alarm system. Foundation design shall utilize LAWPS Geotechnical Report Concrete and rebar design and construction shall be in accordance with ACI 318-11 and ACI 301-10
Designed in accordance with NFPA 230. Must be designed to meet local building, fire, and life-safety codes. The warehouse will have heated (30’ x 62’) and unheated space. One side of the warehouse shall be isolated and be serviced with heating, ventilation, and air conditioning (HVAC). Insulated exposed duct work with overhead diffusers. The HVAC shall be designed to provide controlled environment for storage of the LAWPS resin. Include electric lighting system and electric outlets (110 and 240). Lighting to provide required lumen for light industrial storage with 3 way switches at each entrance for each bay. Exterior automatic day/night lighting at each exterior man door. One 240 volt outlet in each bay and wall mounted duplex outlets every 50’ OC. The entire warehouse shall be insulated. Include non-slip surface treatments on floors subject to wetting, such as outdoor docks, to eliminate slips and falls to personnel Include signage (life safety, exit, emergency lighting, etc.). Incorporate energy efficiency designs (light colored roof, white painted interior metal roof decking, energy efficient fixtures, etc.). 4 each exterior concealed overhead coiling door 8’W by 12’H with bumper guards and weather seal. Bottom lock powered operation with manual override. One 8’W by 12’H interior powered roll up door with bumper guards into the heated space. 4 exterior and 3 interior man doors 3’ by 7’. Door frames minimum 14 gauge metal frames, hardware to be latch sets with emergency crash bar on interior. 12’ by 10’ exterior concrete pad at each roll up door. 4’ by 4’ exterior concrete pad at each exterior man door. Provide a Radio Fire Alarm Reporter (RFAR) box to be connected to the site fire alarm system. Foundation design shall utilize LAWPS Geotechnical Report Concrete and rebar design and construction shall be in accordance with ACI 318-11 and ACI 301-10
01_50_00_LAWP_Site_Prep_Facilities_Aids_and_Temporary_Controls_Rev._01_(redline).docx