1) Complete electrical ratings, including primary and secondary voltage, decibel rating, temperature rise, nominal impedance, voltage regulation, and no load and full load losses. 2) Nameplate data. 3) Elementary and interconnection wiring diagrams. 4) Technical data for each component. 5) Dimensioned exterior views of the substations. 6) Dimensioned section views of the substations. 7) Floor plan of the substations. 8) Foundation plan for the substations. 9) Provisions and required locations for external conduit and wiring entrances. 10) Approximate design weights. SPEC WRITER NOTE: Include the following paragraph for projects in seismic areas of moderate-high, high and very high seismicities as listed in Table 4 of VA Handbook H-18-8, Seismic Design Requirements. //c. Certification from the manufacturer that the substations have been seismically tested to International Building Code requirements. Certification shall be based upon simulated seismic forces on a shake table or by analytical methods, but not by experience data or other methods.// 2. Manuals: a. Submit, simultaneously with the shop drawings, complete maintenance and operating manuals, including technical data sheets, wiring diagrams, and information for ordering replacement parts. 1) Include three-line diagrams showing device terminal numbers. 2) Include schematic signal and control diagrams, with all terminals identified, matching terminal identification in the substation. 3) Include information for testing, repair, troubleshooting, assembly, and disassembly. b. If changes have been made to the maintenance and operating manuals originally submitted, submit updated maintenance and operating manuals two weeks prior to the final inspection. 3. Test Reports:
1) Complete electrical ratings, including primary and secondary voltage, decibel rating, temperature rise, nominal impedance, voltage regulation, and no load and full load losses. 2) Nameplate data. 3) Elementary and interconnection wiring diagrams. 4) Technical data for each component. 5) Dimensioned exterior views of the substations. 6) Dimensioned section views of the substations. 7) Floor plan of the substations. 8) Foundation plan for the substations. 9) Provisions and required locations for external conduit and wiring entrances. 10) Approximate design weights. SPEC WRITER NOTE: Include the following paragraph for projects in seismic areas of moderate-high, high and very high seismicities as listed in Table 4 of VA Handbook H-18-8, Seismic Design Requirements. //c. Certification from the manufacturer that the substations have been seismically tested to International Building Code requirements. Certification shall be based upon simulated seismic forces on a shake table or by analytical methods, but not by experience data or other methods.// 2. Manuals: a. Submit, simultaneously with the shop drawings, complete maintenance and operating manuals, including technical data sheets, wiring diagrams, and information for ordering replacement parts. 1) Include three-line diagrams showing device terminal numbers. 2) Include schematic signal and control diagrams, with all terminals identified, matching terminal identification in the substation. 3) Include information for testing, repair, troubleshooting, assembly, and disassembly. b. If changes have been made to the maintenance and operating manuals originally submitted, submit updated maintenance and operating manuals two weeks prior to the final inspection. 3. Test Reports:
261116.docx