ITEM FURNISHED SET BY POWER CONTROL BY WIRING WIRING Equipment Motors MC MC EC UNL BSM Motor Control Centers EC EC EC UNL BSM Unit Mounted Motor Starters, Contactors, MC MC EC UNL BSM Disconnect Switches, Thermal Overloads And Heaters Loose Motor Starters, Contactors, EC EC EC UNL BSM Disconnect Switches, Thermal Overloads And Heaters Pushbutton Stations And Safety Stop EC EC NA UNL BSM Switches Air Handling Systems And – Hydronic Systems Variable Speed Drives And Associated UNL BSM EC EC UNL BSM Safety Disconnects (with appropriate fuses) Temporary Heating/Cooling And GC MC/EC EC MC/EC Connections Thermostats And Terminal Controls UNL BSM EC EC EC – Line Voltage Chillers and Boilers MC MC EC MC Computer Room Air Conditioning and MC MC EC MC Controls DX Split Systems Controls MC MC EC MC Room Controls Transformer Panels UNL BSM EC EC UNL BSM Thermostats And Terminal Unit Controls UNL BSM UNL BSM UNL BSM UNL BSM Low Voltage – Air Terminal Units And Hydronic Reheat MC MC NA NA Coils Air Terminal Units And Electric Reheat MC MC EC NA Coils Lab Room and Fume Hood Air Terminal MC MC NA UNL BSM Units Lab Fume Hood Monitors and/or UNL BSM NA NA UNL BSM Controllers Air Compressors and Air Dryers MC MC EC NA Pneumatic Control Air Mains MC MC NA NA Pneumatic Control Device Terminations NA NA NA Termination UNL BSM Building Automation System Control UNL BSM UNL BSM EC UNL BSM Panels Air Handling And Hydronic Systems UNL BSM UNL BSM NA UNL BSM Controls Air Handling Systems Pressure Sensors UNL BSM UNL BSM NA UNL BSM Automatic Control Damper Actuators UNL BSM UNL BSM NA UNL BSM Automatic Control Dampers AHU UNL BSM MC NA UNL BSM Economizer Air Handling Systems Air Flow Stations UNL BSM UNL BSM NA UNL BSM Smoke/Fire Dampers MC MC EC UNL BSM
ITEM FURNISHED BY SET BY POWER WIRING CONTROL WIRING Equipment Motors MC MC EC UNL BSM Motor Control Centers EC EC EC UNL BSM Unit Mounted Motor Starters, Contactors, Disconnect Switches, Thermal Overloads And Heaters MC MC EC UNL BSM Loose Motor Starters, Contactors, Disconnect Switches, Thermal Overloads And Heaters EC EC EC UNL BSM Pushbutton Stations And Safety Stop Switches – Air Handling Systems And Hydronic Systems EC EC NA UNL BSM Variable Speed Drives And Associated Safety Disconnects (with appropriate fuses) UNL BSM EC EC UNL BSM Temporary Heating/Cooling And Connections GC MC/EC EC MC/EC Thermostats And Terminal Controls – Line Voltage UNL BSM EC EC EC Chillers and Boilers MC MC EC MC Computer Room Air Conditioning and Controls MC MC EC MC DX Split Systems Controls MC MC EC MC Room Controls Transformer Panels UNL BSM EC EC UNL BSM Thermostats And Terminal Unit Controls – Low Voltage UNL BSM UNL BSM UNL BSM UNL BSM Air Terminal Units And Hydronic Reheat Coils MC MC NA NA Air Terminal Units And Electric Reheat Coils MC MC EC NA Lab Room and Fume Hood Air Terminal Units MC MC NA UNL BSM Lab Fume Hood Monitors and/or Controllers UNL BSM NA NA UNL BSM Air Compressors and Air Dryers MC MC EC NA Pneumatic Control Air Mains MC MC NA NA Pneumatic Control Device Terminations NA NA NA Termination UNL BSM Building Automation System Control Panels UNL BSM UNL BSM EC UNL BSM Air Handling And Hydronic Systems Controls UNL BSM UNL BSM NA UNL BSM Air Handling Systems Pressure Sensors UNL BSM UNL BSM NA UNL BSM Automatic Control Damper Actuators UNL BSM UNL BSM NA UNL BSM Automatic Control Dampers AHU Economizer UNL BSM MC NA UNL BSM Air Handling Systems Air Flow Stations UNL BSM UNL BSM NA UNL BSM Smoke/Fire Dampers MC MC EC UNL BSM
23%2005%2013%20-%20Electrical%20Requirements%20for%20Mechanical%20Equipment.docx