EXECUTIVE SUMMARY Major Recommendations and Savings potentials : and Medium Terms : Recommendations Savings per Annum Investment (Rs.) Pay back period KWHr Rs. Balancing single phase 1393 6,338.00 Nil Immediate loads in three phases equally Controlling of make-up 5,831 26,531.00 Nil Immediate water line in cooling tower Connecting capacitor 23,460 1,06,743.00 5,475.00 ½ month across Chiller compressor Replacing FTL by T-5 11,820 53,781.00 1,02,546.00 1 yr 11 months fittings in rooms/chambers Replacing FTL by CFL 5,518.8 25,111.00 15,120.00 7.5 months fittings in corridor Replacing HPSV trial by T-5 8,094.24 36,829.00 68,400.00 1 yr 10 months based fittings in compound 1.2 Long Term: No recommendation
EXECUTIVE SUMMARY Major Recommendations and Savings potentials : and Medium Terms : Recommendations Savings per Annum Investment (Rs.) Pay back period KWHr Rs. Balancing single phase loads in three phases equally 1393 6,338.00 Nil Immediate Controlling of make-up water line in cooling tower 5,831 26,531.00 Nil Immediate Connecting capacitor across Chiller compressor 23,460 1,06,743.00 5,475.00 ½ month Replacing FTL by T-5 fittings in rooms/chambers 11,820 53,781.00 1,02,546.00 1 yr 11 months Replacing FTL by CFL fittings in corridor 5,518.8 25,111.00 15,120.00 7.5 months Replacing HPSV by T-5 based fittings in compound 8,094.24 36,829.00 68,400.00 1 yr 10 months 1.2 Long Term: No recommendation trial
Energy%20Audit%20Report%20-%20OIL%20MTDC.docx