First stage membrane 170-370 lb/in.2 60-90°F 600 lb/in.2, Design vessels array 2 gauge Inlet 113°F Infoa 100-325 lb/in.2 Set Valuesc gauge Brine 15 lb/in.2 gauge Permeate 15-30 gal/min Brine 60-95 gal/min Permeate First stage RO 170-370 lb/in.2 60-90°F 370 lb/in.2 SS Design booster pumps gauge gauge, 120°F, Infoa 200 gal/min 75–200 gal/min Set Valuesc Second RO feed tank 0 lb/in.2 gauge 60-90°F 0 lb/in.2 gauge, 304 SS Design 120°F Infoa Set Valuesc Second stage RO feed 400-520 lb/in.2 600 lb/in.2 SS Design pump gauge gauge, 120°F Infoa Set Valuesc 290 gal/min Operating Proceduree Second stage RO skid 100-450 lb/in.2 64-90°F 600 lb/in.2, Design Inlet 113°F, Infoa 70 gal/min 100-400 lb/in.2 Set Valuesc Brine 50-80 lb/in.2 Permeate 15 gal/min Brine 135-150 gal/min Permeate Polishers and Effluent pH Adjustment Tank Polisher column 70 lb/in.2 gauge 152 gal/min Design Inlet Infoa 25-50 lb/in.2 Set Valuesc gauge Outlet 20-100 gal/min Resin traps 20-45 lb/in.2 Set Valuesc gauge Effluent pH 0 lb/in.2 gauge 50-120°F 0 lb/in.2 gauge, 304 SS with CS Design adjustment tank 120°F saddle Infoa Set Valuesc Effluent pH 70 90 lb/in.2 50-120°F 175 gal/min Design – adjustment tank gauge Infoa pumps 40-150 gal/min Operating Procedured Set Valuesc
First stage membrane vessels array 2 170-370 lb/in.2 gauge Inlet 100-325 lb/in.2 gauge Brine 15 lb/in.2 gauge Permeate 15-30 gal/min Brine 60-95 gal/min Permeate 60-90°F 600 lb/in.2, 113°F Design Infoa Set Valuesc First stage RO booster pumps 170-370 lb/in.2 gauge 75–200 gal/min 60-90°F 370 lb/in.2 gauge, 120°F, 200 gal/min SS Design Infoa Set Valuesc Second RO feed tank 0 lb/in.2 gauge 60-90°F 0 lb/in.2 gauge, 120°F 304 SS Design Infoa Set Valuesc Second stage RO feed pump 400-520 lb/in.2 gauge gal/min 600 lb/in.2 gauge, 120°F SS Design Infoa Set Valuesc Operating Proceduree Second stage RO skid 100-450 lb/in.2 Inlet 100-400 lb/in.2 Brine 50-80 lb/in.2 Permeate 15 gal/min Brine 135-150 gal/min Permeate 64-90°F 600 lb/in.2, 113°F, 70 gal/min Design Infoa Set Valuesc Polishers and Effluent pH Adjustment Tank Polisher column 70 lb/in.2 gauge Inlet 25-50 lb/in.2 gauge Outlet 20-100 gal/min 152 gal/min Design Infoa Set Valuesc Resin traps 20-45 lb/in.2 gauge Set Valuesc Effluent pH adjustment tank 0 lb/in.2 gauge 50-120°F 0 lb/in.2 gauge, 120°F 304 SS with CS saddle Design Infoa Set Valuesc Effluent pH adjustment tank pumps 70 – 90 lb/in.2 gauge 40-150 gal/min 50-120°F 175 gal/min Design Infoa Operating Procedured Set Valuesc 290
314321_-_DRAFT_RPP-PLAN-61349_Draft.docx