5. For Items C1 through C4 above, Contractor shall provide the following listed materials when necessary and indicated under type of inspection above: a. Refractory Patch and Coat Material b. Gasket - low-water cutoff c. Automatic Feed d. Hand Hole e. Man Hole f. Asbestos Rope g. Hand Valve Packing h. Lubricant - oil and grease i. Oil Burner Nozzles j. Electrodes k. Filters - oil and air l. Belts m. Clean up material n. Contact Cleaner D. PUMPS 1. Annual Inspection a. Lubricate pump bearings per manufacturer's recommendations. b. Lubricate motor bearings per manufacturer's recommendations. c. Tighten all nuts and bolts. Check motor mounts and vibration pads (adjust as required). d. Visually check pump alignment and coupling. e. Check motor operating conditions. f. Inspect electrical connections and contactors. g. Check and clean strainers, and check hand valves. h. Inspect mechanical seals. Replace as required or inspect pump packing and adjust as needed. i. Verify gauges for accuracy. j. Clean external surfaces as required. 2. Semi-Annual Inspection a. Lubricate pump bearings per manufacturer's recommendations. b. Lubricate motor bearings per manufacturer's recommendations. c. Check suction and discharge pressures. d. Check packing or mechanical seal. 3. For Items D1 and D2 above, Contractor shall provide the following listed materials when necessary and indicated under type of inspection above: a. Belts b. Motor Mounts c. Vibration Pads d. Seals e. Packing f. Lubricant - oil and grease g. Contact Cleaner h. Clean up materials E. CONDENSING UNITS 1. Air Cooled, Start-Up Inspection
5. For Items C1 through C4 above, Contractor shall provide the following listed materials when necessary and indicated under type of inspection above: a. Refractory Patch and Coat Material b. Gasket - low-water cutoff c. Automatic Feed d. Hand Hole e. Man Hole f. Asbestos Rope g. Hand Valve Packing h. Lubricant - oil and grease i. Oil Burner Nozzles j. Electrodes k. Filters - oil and air l. Belts m. Clean up material n. Contact Cleaner D. PUMPS 1. Annual Inspection a. Lubricate pump bearings per manufacturer's recommendations. b. Lubricate motor bearings per manufacturer's recommendations. c. Tighten all nuts and bolts. Check motor mounts and vibration pads (adjust as required). d. Visually check pump alignment and coupling. e. Check motor operating conditions. f. Inspect electrical connections and contactors. g. Check and clean strainers, and check hand valves. h. Inspect mechanical seals. Replace as required or inspect pump packing and adjust as needed. i. Verify gauges for accuracy. j. Clean external surfaces as required. 2. Semi-Annual Inspection a. Lubricate pump bearings per manufacturer's recommendations. b. Lubricate motor bearings per manufacturer's recommendations. c. Check suction and discharge pressures. d. Check packing or mechanical seal. 3. For Items D1 and D2 above, Contractor shall provide the following listed materials when necessary and indicated under type of inspection above: a. Belts b. Motor Mounts c. Vibration Pads d. Seals e. Packing f. Lubricant - oil and grease g. Contact Cleaner h. Clean up materials E. CONDENSING UNITS 1. Air Cooled, Start-Up Inspection
358685330.docx