WY18Z-073LLT Steam Turbine 105.5 MVA, 11.5 KV , 50 Hz Ansaldo Ansaldo, Italy Generator (Air cooled, Static Excitation) STG Transformer 110 MVA (235/11.5KV) BHEL BHEL, India Oil Filled Balance of Plant Cummins India ( Engine model VTA 28-G. Generator : Black start DG 500 KVA ~ 2 Nos Ltd Stamford, model HC54402) With Redundant Filters & Pressure Fuel Gas System Max operating flow 1.46 MMSCMD Multitex Regulators as well as Orifice Flow meter, Pressure Reduction 27/19 barg Concrete Structure 20000m3/h flow , 7 nos twin Cells Paharpur Cooling Cooling Tower Induced Draft Counter flow Tower, Calcutta Paharur model no 83462-4.0-108 Circulating Cooling 3 Nos, Vertical Mixed Flow, 8872 Mather and Platt Model No 36 VMF4 Water Pumps M3/H (I) Limited Aux. Cooling Water Mather and Platt 3 Nos, Vertical Mixed Flow, 890 M3/H Model No 12 VMF Pumps (I) Limited DM Plant 2 X 60 m3/h Ion Exchange 1) Hydrant Pumps (2 Nos Motor driven and 1 Nos Diesel Engine 1) Split casing Horizontal Pumps driven) 1) Mather &Platt (I) Ltd. 2) Auto/remote & Manual Operation. Plant Fire Fighting 2) Spray System(1 Nos Motor driven System and 1 Nos Diesel Engine driven) 2) Notifier by 3) Addressable Type Honeywell 3) Deluge System 4) Plant Fire Alarm System Control Systems Symphony Enterprise Management and Control System, GT & ST control INFI-NET Uni-direction, High ABB MESA ABB system Sped Data Network, 10 to 2 MHz, Communication Protocol INIIT 12 Invensys HRSG & BOP Control Processor : CP60 Invensys Foxboro on XP Model Fox View V99.201 Control system Platform
Steam Turbine Generator 105.5 MVA, 11.5 KV , 50 Hz Ansaldo Ansaldo, Italy WY18Z-073LLT (Air cooled, Static Excitation) STG Transformer 110 MVA (235/11.5KV) BHEL BHEL, India Oil Filled Balance of Plant Black start DG 500 KVA ~ 2 Nos Cummins India Ltd ( Engine model VTA 28-G. Generator : Stamford, model HC54402) Fuel Gas System Max operating flow 1.46 MMSCMD Multitex With Redundant Filters & Pressure Regulators as well as Orifice Flow meter, Pressure Reduction 27/19 barg Cooling Tower 20000m3/h flow , 7 nos twin Cells Induced Draft Counter flow Paharpur Cooling Tower, Calcutta Concrete Structure Paharur model no 83462-4.0-108 Circulating Cooling Water Pumps 3 Nos, Vertical Mixed Flow, 8872 M3/H Mather and Platt (I) Limited Model No 36 VMF4 Aux. Cooling Water Pumps 3 Nos, Vertical Mixed Flow, 890 M3/H Mather and Platt (I) Limited Model No 12 VMF DM Plant 2 X 60 m3/h Ion Exchange Plant Fire Fighting System 1) Hydrant Pumps (2 Nos Motor driven and 1 Nos Diesel Engine driven) 2) Spray System(1 Nos Motor driven and 1 Nos Diesel Engine driven) 3) Deluge System 4) Plant Fire Alarm System 1) Mather &Platt (I) Ltd. 2) Notifier by Honeywell 1) Split casing Horizontal Pumps 2) Auto/remote & Manual Operation. 3) Addressable Type Control Systems GT & ST control system ABB MESA ABB Symphony Enterprise Management and Control System, INFI-NET Uni-direction, High Sped Data Network, 10 to 2 MHz, Communication Protocol INIIT 12 HRSG & BOP Control system Control Processor : CP60 Invensys Invensys Foxboro on XP Platform Model Fox View V99.201
220mwcc50hz.docx