(vi) Chapter 505.4.1, Single-Wall Heat Exchangers. (vii) Chapter 507.1, Dielectric Insulator. (viii) Chapter 507.4, Ground Support. (ix) Chapter 507.5, Drainage Pans. (x) Chapter 507.24, Installation Instructions. (5) Chapter 6, Water Supply and Distribution a. The board does not adopt Chapter 612.0, Residential Fire Sprinkler Systems. (6) Chapter 7, Sanitary Drainage a. The board amends Chapter 705.5.2, Solvent Cement Joints, as follows: Solvent cement joints for PVC pipe and fittings shall be clean from dirt and moisture. Pipe shall be cut square and pipe shall be deburred. Where surfaces to be joined are cleaned and free of dirt, moisture, oil and other foreign material, apply primer in accordance with ASTM F656. b. The board does not adopt Chapter 713.5, Permits. c. The board does not adopt Table 721.1. (7) Chapter 9, Vents a. The board adopts Chapter 906.0, Vent Terminations, with the following amendments: (i) 906.1, Roof Terminations. Each vent pipe or stack shall extend through its flashing and shall terminate vertically not less than two (2) feet above the roof nor less than one (1) foot from any vertical surface. (ii) 906.3, Use of Roof. Vent pipes shall be extended separately or combined, of full required size, not less than two (2) feet above the roof or fire wall. Flagpoling of vents shall be prohibited except where the roof is used for purposes other than weather protection. Vents within ten (10) feet (3,048 mm) of any part of the roof that is used for such other purposes shall extend not less than seven (7) feet (2,134 mm) above such roof and shall be securely stayed.
(vi) Chapter 505.4.1, Single-Wall Heat Exchangers. (vii) Chapter 507.1, Dielectric Insulator. (viii) Chapter 507.4, Ground Support. (ix) Chapter 507.5, Drainage Pans. (x) Chapter 507.24, Installation Instructions. (5) Chapter 6, Water Supply and Distribution a. The board does not adopt Chapter 612.0, Residential Fire Sprinkler Systems. (6) Chapter 7, Sanitary Drainage a. The board amends Chapter 705.5.2, Solvent Cement Joints, as follows: Solvent cement joints for PVC pipe and fittings shall be clean from dirt and moisture. Pipe shall be cut square and pipe shall be deburred. Where surfaces to be joined are cleaned and free of dirt, moisture, oil and other foreign material, apply primer in accordance with ASTM F656. b. The board does not adopt Chapter 713.5, Permits. c. The board does not adopt Table 721.1. (7) Chapter 9, Vents a. The board adopts Chapter 906.0, Vent Terminations, with the following amendments: (i) 906.1, Roof Terminations. Each vent pipe or stack shall extend through its flashing and shall terminate vertically not less than two (2) feet above the roof nor less than one (1) foot from any vertical surface. (ii) 906.3, Use of Roof. Vent pipes shall be extended separately or combined, of full required size, not less than two (2) feet above the roof or fire wall. Flagpoling of vents shall be prohibited except where the roof is used for purposes other than weather protection. Vents within ten (10) feet (3,048 mm) of any part of the roof that is used for such other purposes shall extend not less than seven (7) feet (2,134 mm) above such roof and shall be securely stayed.
395c-all-2016.docx