b. Horizontal Cable Manage-ment (1) Combination TIA/EIA minimum Category 5E, 19” rack width, Organizers in one RU (1.75”) multiples to suite system de-sign, front and rear cable rout-ing rings required, six MIN. (2) Cable Bars Required - 19” rack width rear or front (a) Flat type cabinet or rack mount-able, contains cable tie bars and/or wire saddles. Required - 19” rack width rear (1” X 4” MIN) or front (1 ½” X 3” MIN) cabinet or rack (b) Duct type mount-able; alternate 2” X 4” MIN rear and 3” X 3” front MIN ducts are allowed, each duct in multiple of 1.0 RU (1.75”) height. ALLOWED TO SUPPLEMENT CONDUIT RUNS – DO NOT USE FOR EMERGENCY/ LIFE & PUBLIC SAFETY/ (3) Cable Hangers CRITICAL SERVICE COMMUNICATION CABLES – THESE ARE REQURED TO BE IN CONDUIT. WHEN APPROVED - in open cable runs, 3” X 2.5” 2.5” MIN, wall or ceiling mountable, allows (a) Wall Mountable cables to be installed and re-moved from hanger, black color metal or high impact plastic construction MIN required. WHEN APPROVED - in open cable runs shall be compliment TO AC-CESS Type 66, 110 0R 110A (b) Bar Type block cable loops; screw mountable required. Required - above and or inside 19” cabinet panels where wire looms are not provided, (c) Rack Mountable allows quick cable attachment or removal, screw mountable. WHEN APPROVED - shall nominally be 12 in. (305 mm) wide, rung spacing of 9” (225 mm) (4) Cable Ladder and be certified / listed for service. NRTL labeled for support of minimum Category 5E cabling, designed to prevent degradation (5) Cable Support of cable per-formance and pin - points that could damage cable. c. Vertical or Horizontal Cable Management Required - 4” MIN length, black in color, (1) Cable Ties ultraviolet resis-tant. (2) Cable Tie Mounting De-vices Required - square style 0.5” X 0.5” MIN, allows two MAX cable ties to be attached in (a) Adhesive Backed either direction, attaches directly to metal or slick surfaces, re-quires additional screw
b. Horizontal Cable Manage-ment (1) Combination Organizers TIA/EIA minimum Category 5E, 19” rack width, in one RU (1.75”) multiples to suite system de-sign, front and rear cable rout-ing rings required, six MIN. (2) Cable Bars (a) Flat type Required - 19” rack width rear or front cabinet or rack mount-able, contains cable tie bars and/or wire saddles. (b) Duct type Required - 19” rack width rear (1” X 4” MIN) or front (1 ½” X 3” MIN) cabinet or rack mount-able; alternate 2” X 4” MIN rear and 3” X 3” front MIN ducts are allowed, each duct in multiple of 1.0 RU (1.75”) height. (3) Cable Hangers ALLOWED TO SUPPLEMENT CONDUIT RUNS – DO NOT USE FOR EMERGENCY/ LIFE & PUBLIC SAFETY/ CRITICAL SERVICE COMMUNICATION CABLES – THESE ARE REQURED TO BE IN CONDUIT. (a) Wall Mountable WHEN APPROVED - in open cable runs, 3” X 2.5” 2.5” MIN, wall or ceiling mountable, allows cables to be installed and re-moved from hanger, black color metal or high impact plastic construction MIN required. (b) Bar Type WHEN APPROVED - in open cable runs shall be compliment TO AC-CESS Type 66, 110 0R 110A block cable loops; screw mountable required. (c) Rack Mountable Required - above and or inside 19” cabinet panels where wire looms are not provided, allows quick cable attachment or removal, screw mountable. (4) Cable Ladder WHEN APPROVED - shall nominally be 12 in. (305 mm) wide, rung spacing of 9” (225 mm) and be certified / listed for service. (5) Cable Support NRTL labeled for support of minimum Category 5E cabling, designed to prevent degradation of cable per-formance and pin - points that could damage cable. c. Vertical or Horizontal Cable Management (1) Cable Ties Required - 4” MIN length, black in color, ultraviolet resis-tant. (2) Cable Tie Mounting De-vices (a) Adhesive Backed Required - square style 0.5” X 0.5” MIN, allows two MAX cable ties to be attached in either direction, attaches directly to metal or slick surfaces, re-quires additional screw
275319.docx