2 Overvoltage Category (III*) (P) 6.2.4 Construction Assumed Voltage Drop for Package Plant (V) (P) 3 6.2.4.1 General Supply Restrictions (P) 4 Material(s) of Construction (Including 3 Details of Any Protective Coatings) (P/S) Lightning and Surge Protection 6 Requirements (P) Type of Assembly Construction () (P/S) 4 a Cubicle/multi-cubicle 5.0 PERFORMANCE SPECIFICATION b Box/multi-box 6 Degree of Ingress 3 Minimum Design Life Protection (IP Code) (P/S) (20 years*) (P) 7 Size/Weight Restrictions (P) 6.0 DESIGN SPECIFICATION 6.1 General 6.2.4.5 Mounting Arrangements 6.1.1 General and Safety Requirements 1 Mounting Arrangements () (P/S) Skid/frame mounted 3 Method of Fault Protection Wall mounted (ADS*) (P/S) Other (specify) 6.1.6 O & M Manuals 6.2.5 Earthing and Bonding 1 Reference for O & M Manual Specification 4 Separate Earth Bars/ ([P) Studs Required (Y/N) (P) 6.2.6 Cabling and Wiring 6.2 The Assembly 6.2.6.1 General 6.2.1 General Ratio of CSAs of Neutral 2 Form of Internal Separation (P/S) 3 and Line Conductors Form 2 assemblies (2a or (100 %*) (P) 2b) Form 4 assemblies (4a or 6.2.7 Requirements for Specific Components 4b) 6.2.7.1 Indicating Lamps 5 Control Circuit Test Facilities () (S) Internal push-button 2 Lamp Colours/Meanings (P) Test position on switching Available/auto-available white and isolation device Supply on 7 Diversity factor (S) Running 6.2.2 Electrical Components Stopped Emergency stop 4 Component (P) Details (S) Dangerous condition red Normal condition Alarm yellow/ amber Tripped/fault yellow/
2 Overvoltage Category (III*) (P) 3 Assumed Voltage Drop for Package Plant (V) (P) 4 Supply Restrictions (P) 6 Lightning and Surge Protection Requirements (P) 5.0 PERFORMANCE SPECIFICATION 3 Minimum Design Life (20 years*) (P) 6.0 DESIGN SPECIFICATION 6.1 General 6.1.1 General and Safety Requirements 3 Method of Fault Protection (ADS*) (P/S) 6.1.6 O & M Manuals 1 Reference for O & M Manual Specification ([P) 6.2 The Assembly 6.2.1 General 2 Form of Internal Separation (P/S) Form 2 assemblies (2a or 2b) Form 4 assemblies (4a or 4b) 5 Control Circuit Test Facilities () (S) Internal push-button Test position on switching and isolation device 7 Diversity factor (S) 6.2.2 Electrical Components 4 Component (P) Details (S) 6.2.4 Construction 6.2.4.1 General 3 Material(s) of Construction (Including Details of Any Protective Coatings) (P/S) 4 Type of Assembly Construction () (P/S) a Cubicle/multi-cubicle b Box/multi-box 6 Degree of Ingress Protection (IP Code) (P/S) 7 Size/Weight Restrictions (P) 6.2.4.5 Mounting Arrangements 1 Mounting Arrangements () (P/S) Skid/frame mounted Wall mounted Other (specify) 6.2.5 Earthing and Bonding 4 Separate Earth Bars/ Studs Required (Y/N) (P) 6.2.6 Cabling and Wiring 6.2.6.1 General 3 Ratio of CSAs of Neutral and Line Conductors (100 %*) (P) 6.2.7 Requirements for Specific Components 6.2.7.1 Indicating Lamps 2 Lamp Colours/Meanings (P) Available/auto-available white Supply on Running Stopped Emergency stop Dangerous condition red Normal condition Alarm yellow/ amber Tripped/fault yellow/
304i5datasheets.docx