SECTION 27 10 00 STRUCTURED CABLING BASED ON DFD MASTER COMMUNICATION SPEC DATED 11/07/16 Notes to A/E: This section has been written to cover most (but not all) conditions that you will encounter. Depending on the requirements of your specific project, you may have to add material, delete items, or modify what is currently written. It is recommended that you examine the Communications Structured Cabling System Standards & Design Guidelines document available on the DFD web site. Edit all areas as applicable to meet the requirements of the project. Common options or features recognized by the DFD, or items where A/E input is needed are enclosed in [brackets] and/or <less-greater brackets>. Delete product types (Part 2) and related installation (Part 3) instructions that are not applicable to the project. Editing instructions are included throughout the document (italic text; red if viewed/printed in color). These instructions should be hidden or deleted for printing. Text can be hidden by modifying the MS-WORD to as part of the Font Style “A/E Instructions” use “Hidden Text” type. To display Instructions formatted as File Options “Hidden Text”, configure MS-Word /Display to Text on Screen. “Show” Hidden The document is structured to automatically update the Table of Contents when printed or in response to on TOC opens menu) in MS-Word. an “Update Field” command (right mouse click Confirm that TOC has updated and is accurate of prior to printing. TOC entries are Hyperlinks and can be used to navigate the document. Revision History: of Facilities Development / Master Specifications/Design Guidelines / Division 27 See “Division Communications / Revision – History”. GENERAL This section describes the products and execution requirements relating to furnishing and installation of Communications Cabling and Termination Components and related sub-systems as part of a Structured Cabling System for the project. The specified cabling may and support “voice”, “data”, audiovisual networked security applications as noted. Work may also include removal and recycling of unused, undocumented and otherwise "abandoned" cables. Refer to project drawings and Part 3 of this Section under "Salvage Materials". Included are the following topics:
SECTION 27 10 00 STRUCTURED CABLING BASED ON DFD MASTER COMMUNICATION SPEC DATED 11/07/16 Notes to A/E: This section has been written to cover most (but not all) conditions that you will encounter. Depending on the requirements of your specific project, you may have to add material, delete items, or modify what is currently written. It is recommended that you examine the Communications Structured Cabling System Standards & Design Guidelines document available on the DFD web site. Edit all areas as applicable to meet the requirements of the project. Common options or features recognized by the DFD, or items where A/E input is needed are enclosed in [brackets] and/or <less-greater brackets>. Delete product types (Part 2) and related installation (Part 3) instructions that are not applicable to the project. Editing instructions are included throughout the document (italic text; red if viewed/printed in color). These instructions should be hidden or deleted for printing. Text can be hidden by modifying the MS-WORD Style “A/E Instructions” to use “Hidden Text” as part of the Font type. To display Instructions formatted as “Hidden Text”, configure MS-Word File Options /Display to “Show” Hidden Text on Screen. The document is structured to automatically update the Table of Contents when printed or in response to an “Update Field” command (right mouse click on TOC opens menu) in MS-Word. Confirm that TOC has updated and is accurate of prior to printing. TOC entries are Hyperlinks and can be used to navigate the document. Revision History: See “Division of Facilities Development / Master Specifications/Design Guidelines / Division 27 – Communications / Revision History”. GENERAL This section describes the products and execution requirements relating to furnishing and installation of Communications Cabling and Termination Components and related sub-systems as part of a Structured Cabling System for the project. The specified cabling may support “voice”, “data”, audiovisual and networked security applications as noted. Work may also include removal and recycling of unused, undocumented and otherwise "abandoned" cables. Refer to project drawings and Part 3 of this Section under "Salvage Materials". Included are the following topics:
27%2010%2000.docx