SECTION 26 05 33 RACEWAY AND BOXES FOR ELECTRICAL SYSTEMS BASED ON DFD MASTER ELECTRICAL SPEC DATED 01/22/18 This section has been written to cover most (but not all) situations that you will encounter. Depending on the requirements of your specific project, you may have to add material, delete items, or modify what is currently written. The Division of Facilities Development expects changes and comments from you. Generally, all systems are required to be in conduit or surface raceway. This section includes language relevant to multiple divisions of work (26, 27 and 28) and may be referenced in specification sections for those divisions of work. Coordinate content with those sections and, where applicable, the designers responsible for those sections. PART 1 - GENERAL SCOPE This section describes the products and execution requirements relating to furnishing and installing raceways and boxes and related systems as part of a raceway system for electrical, communications, and other low-voltage systems for the project. Included are the following topics: PART 1 - GENERAL Scope Related Work References Submittals PART 2 - PRODUCTS General Rigid Metal Conduit (RMC) and Fittings PVC Coated Rigid Metal Conduit Intermediate Metal Conduit (IMC) and Fittings Electrical Metallic Tubing (EMT) and Fittings Flexible Metal Conduit (FMC) and Fittings Liquidtight Flexible Metal Conduit (LFMC) and Fittings Electrical Nonmetallic Tubing (ENT) and Fittings Rigid Polyvinyl Chloride Conduit (PVC) and Fittings Fiberglass Resin Conduit (RTRC) and Fittings High Density Polyethylene Conduit (HDPE) and Fittings Conduit Supports Surface Metal Raceway Surface Nonmetal Raceway Multi-Outlet Assembly Auxiliary Gutters (Wireways) Conduit Water Sealant Pull and Junction Boxes In Grade Handholes and Boxes Outlet Boxes Outlet Box Extenders Floor Boxes Poke-Through Assemblies Boxes for Audio-Video Equipment Boxes for Fire Alarm Audio-Visual Notification Appliances PART 3 - EXECUTION Conduit Sizing, Arrangement, and Support Conduit Installation Conduit Installation Schedule PVC Coated Rigid Metal Conduit Installation High Density Polyethylene Conduit (HDPE) Installation Surface Metal Raceway and Multi-Outlet Assembly Installation Nonmetallic Surface Raceway Installation Auxiliary Gutters (Wireways) Installation Coordination of Box Locations Pull and Junction Box Installation
SECTION 26 05 33 RACEWAY AND BOXES FOR ELECTRICAL SYSTEMS BASED ON DFD MASTER ELECTRICAL SPEC DATED 01/22/18 This section has been written to cover most (but not all) situations that you will encounter. Depending on the requirements of your specific project, you may have to add material, delete items, or modify what is currently written. The Division of Facilities Development expects changes and comments from you. Generally, all systems are required to be in conduit or surface raceway. This section includes language relevant to multiple divisions of work (26, 27 and 28) and may be referenced in specification sections for those divisions of work. Coordinate content with those sections and, where applicable, the designers responsible for those sections. PART 1 - GENERAL SCOPE This section describes the products and execution requirements relating to furnishing and installing raceways and boxes and related systems as part of a raceway system for electrical, communications, and other low-voltage systems for the project. Included are the following topics: PART 1 - GENERAL Scope Related Work References Submittals PART 2 - PRODUCTS General Rigid Metal Conduit (RMC) and Fittings PVC Coated Rigid Metal Conduit Intermediate Metal Conduit (IMC) and Fittings Electrical Metallic Tubing (EMT) and Fittings Flexible Metal Conduit (FMC) and Fittings Liquidtight Flexible Metal Conduit (LFMC) and Fittings Electrical Nonmetallic Tubing (ENT) and Fittings Rigid Polyvinyl Chloride Conduit (PVC) and Fittings Fiberglass Resin Conduit (RTRC) and Fittings High Density Polyethylene Conduit (HDPE) and Fittings Conduit Supports Surface Metal Raceway Surface Nonmetal Raceway Multi-Outlet Assembly Auxiliary Gutters (Wireways) Conduit Water Sealant Pull and Junction Boxes In Grade Handholes and Boxes Outlet Boxes Outlet Box Extenders Floor Boxes Poke-Through Assemblies Boxes for Audio-Video Equipment Boxes for Fire Alarm Audio-Visual Notification Appliances PART 3 - EXECUTION Conduit Sizing, Arrangement, and Support Conduit Installation Conduit Installation Schedule PVC Coated Rigid Metal Conduit Installation High Density Polyethylene Conduit (HDPE) Installation Surface Metal Raceway and Multi-Outlet Assembly Installation Nonmetallic Surface Raceway Installation Auxiliary Gutters (Wireways) Installation Coordination of Box Locations Pull and Junction Box Installation
26%2005%2033.docx