the values of the fixtures that discharge to the receptor, but not less than the value given for drainage fixture unit drainage fixture unit the indirect waste receptor in Table 709.1 or 709.2. 709.4.1 Clear-water waste receptors. Where waste receptors such as floor drains, floor sinks and hub drains receive only clear-water waste from display cases, refrigerated display cases, ice bins, coolers and freezers, such receptors shall have a value of one-half. drainage fixture unit
the drainage fixture unit values of the fixtures that discharge to the receptor, but not less than the drainage fixture unit value given for the indirect waste receptor in Table 709.1 or 709.2. 709.4.1 Clear-water waste receptors. Where waste receptors such as floor drains, floor sinks and hub drains receive only clear-water waste from display cases, refrigerated display cases, ice bins, coolers and freezers, such receptors shall have a drainage fixture unit value of one-half.
709-ICC_PLUMBING_CODE_FIXTURE_UNITS.docx