2.2 IDENTIFICATION PRODUCTS A. Comply with TIA/EIA-606-A and UL 969 for labeling materials, including label stocks, and inks used by label printers. B. Comply with requirements in Section 260553 "Identification for Electrical Systems." 2.3 SOURCE QUALITY CONTROL Factory test UTP cables according to TIA/EIA-568-C.2. Factory test multimode optical fiber cables according to TIA/EIA-526-14-A and TIA/EIA-568- C.3. C. Provide test and inspection reports. PART 3 - 3.1 FIELD QUALITY CONTROL A. Perform tests and inspections. Visually inspect UTP and optical fiber cable jacket materials for NRTL certification markings. Inspect cabling connections for compliance with TIA/EIA-568-C.1. Visually confirm Category 6a, marking of patch cables. Visually confirm Fiber patch coble marking. Visually inspect cable placement, and patch cords, and labeling of all components. B. Use copper patch cord lock-in devices to prevent the disconnection of critical equipment connections. END OF SECTION 271619
2.2 IDENTIFICATION PRODUCTS A. Comply with TIA/EIA-606-A and UL 969 for labeling materials, including label stocks, and inks used by label printers. B. Comply with requirements in Section 260553 "Identification for Electrical Systems." 2.3 SOURCE QUALITY CONTROL Factory test UTP cables according to TIA/EIA-568-C.2. Factory test multimode optical fiber cables according to TIA/EIA-526-14-A and TIA/EIA-568- C.3. C. Provide test and inspection reports. PART 3 - 3.1 FIELD QUALITY CONTROL A. Perform tests and inspections. Visually inspect UTP and optical fiber cable jacket materials for NRTL certification markings. Inspect cabling connections for compliance with TIA/EIA-568-C.1. Visually confirm Category 6a, marking of patch cables. Visually confirm Fiber patch coble marking. Visually inspect cable placement, and patch cords, and labeling of all components. B. Use copper patch cord lock-in devices to prevent the disconnection of critical equipment connections. END OF SECTION 271619
27-00-00-master-spec-division-27.docx