Sl Equipment Total capacity Energy Used Energy requirement 01 Indirect Heater (6 Separate for HP Natural gas is used to 2,700 cum/day nos) Dry & wet, LP maintain the to wet 0 Emulsion Treater (3 2730 KL/day Natural gas is used nos) continuously to maintain the flame in the thermo-chemical process 0 Electro-static 2000 KL/ day Electricity supply is Load is fluctuating, power Treater (1 no) required to maintain drawn varies from 2.734.8 the voltage potential KW for the electro-static process 0 Crude Oil Delivery 1-3 : 40 KL/hr Mechanical power to Pump (6 nos) : 100 KL/hr run the pump is met by 5-6 : 60 KL/hr gas engine 0 Formation Water 100 cum/hr by 3 Ph electric Electric drawn by Pump (4 nos) motors of capacity 30 each motor = 22 KW, total Note : 2 pumps at a KW each power = 44 KW time 0 Booster Pump ( 5 75 cum/hr run by 3 Ph Electric power drawn by nos), 1 pump electric motors of each motor 11.54 continuously + 1 capacity 15 KW pump occasionally Circulating Pump ( 3 23 cum/hr Pump run by 3 Ph Electric power drawn = nos), one runs electric of 7.5 KW 4.5 KW intermittently (run hr- 5 hrs/day) Cooling Tower ( 50 cum/hr Pump power = 3.75 Available with 250 KVA set 2nos), one with KW only, runs for 15 hrs a day each Gas generator Fan = 3.75 KW, with electric drawn = Run by electric 4.88 KW
Sl Equipment Total capacity Energy Used Energy requirement 01 Indirect Heater (6 nos) Separate for HP Dry & wet, LP wet Natural gas is used to maintain the to 2,700 cum/day 0 Emulsion Treater (3 nos) 2730 KL/day Natural gas is used continuously to maintain the flame in the thermo-chemical process 0 Electro-static Treater (1 no) 2000 KL/ day Electricity supply is required to maintain the voltage potential for the electro-static process Load is fluctuating, power drawn varies from 2.734.8 KW 0 Crude Oil Delivery Pump (6 nos) 1-3 : 40 KL/hr : 100 KL/hr 5-6 : 60 KL/hr Mechanical power to run the pump is met by gas engine 0 Formation Water Pump (4 nos) Note : 2 pumps at a time 100 cum/hr by 3 Ph electric motors of capacity 30 KW each Electric drawn by each motor = 22 KW, total power = 44 KW 0 Booster Pump ( 5 nos), 1 pump continuously + 1 pump occasionally 75 cum/hr run by 3 Ph electric motors of capacity 15 KW Electric power drawn by each motor 11.54 Circulating Pump ( 3 nos), one runs intermittently 23 cum/hr Pump run by 3 Ph electric of 7.5 KW (run hr- 5 hrs/day) Electric power drawn = 4.5 KW Cooling Tower ( 2nos), one with each Gas generator 50 cum/hr Pump power = 3.75 KW Fan = 3.75 KW, Run by electric Available with 250 KVA set only, runs for 15 hrs a day with electric drawn = 4.88 KW
Energy%20Audit%20Report-%20Makum%20OCS.docx