(LPR, PC, HWH, HWHR, GH and GHR) 39-99 degrees C 38 38 (1.5) ---- ---- (100-211 degrees F) (1.5) Closed-Cell (LPR, PC, HWH, HWHR, Rigid GH and GHR) (Exterior Locations only) 38-94 degrees C Flexible 38 38 (1.5) ---- ---- (100-200 degrees F) Elastomeric (1.5) Cellular (LPR, PC, HWH, HWHR, Thermal (Above GH and GHR) ground piping only) 4-16 degrees C Rigid Cellular 38 38 (1.5) 38 (1.5) 38 (1.5) Phenolic Foam (1.5) (40-60 degrees F) (CH, CHR, GC, GCR and RS for DX refrigeration) 4-16 degrees C Cellular 50 50 (2.0) 75 (3.0) 75 (3.0) Glass (2.0) (40-60 degrees F) (CH and CHR within chiller room and pipe chase and underground) 4-16 degrees C Cellular 38 38 (1.5) 38 (1.5) 38 (1.5) Glass (1.5) (40-60 degrees F) (CH, CHR, GC, GCR and RS for DX refrigeration) 4-16 degrees C 38 38 (1.5) 50 (2.0) 50 (2.0) (1.5) (40-60 degrees F) Closed-Cell Rigid (CH, CHR, GC and GCR (where underground) 4-16 degrees C 38 38 (1.5) 38 (1.5) 38 (1.5) (1.5) (40-60 degrees F) Closed-Cell (CH, CHR, GC, GCR Rigid (Exterior and RS for DX Locations refrigeration) only) (40-60 degrees F) Flexible 38 38 (1.5) 38 (1.5) 38 (1.5) Elastomeric (1.5) (CH, CHR, GC, GCR Cellular
(LPR, PC, HWH, HWHR, GH and GHR) 39-99 degrees C (100-211 degrees F) (LPR, PC, HWH, HWHR, GH and GHR) Closed-Cell Rigid (Exterior Locations only) 38 (1.5) 38 (1.5) ---- ---- 38-94 degrees C (100-200 degrees F) (LPR, PC, HWH, HWHR, GH and GHR) Flexible Elastomeric Cellular Thermal (Above ground piping only) 38 (1.5) 38 (1.5) ---- ---- 4-16 degrees C (40-60 degrees F) (CH, CHR, GC, GCR and RS for DX refrigeration) Rigid Cellular Phenolic Foam 38 (1.5) 38 (1.5) 38 (1.5) 38 (1.5) 4-16 degrees C (40-60 degrees F) (CH and CHR within chiller room and pipe chase and underground) Cellular Glass 50 (2.0) 50 (2.0) 75 (3.0) 75 (3.0) 4-16 degrees C (40-60 degrees F) (CH, CHR, GC, GCR and RS for DX refrigeration) Cellular Glass 38 (1.5) 38 (1.5) 38 (1.5) 38 (1.5) 4-16 degrees C (40-60 degrees F) (CH, CHR, GC and GCR (where underground) Closed-Cell Rigid 38 (1.5) 38 (1.5) 50 (2.0) 50 (2.0) 4-16 degrees C (40-60 degrees F) (CH, CHR, GC, GCR and RS for DX refrigeration) Closed-Cell Rigid (Exterior Locations only) 38 (1.5) 38 (1.5) 38 (1.5) 38 (1.5) (40-60 degrees F) (CH, CHR, GC, GCR Flexible Elastomeric Cellular 38 (1.5) 38 (1.5) 38 (1.5) 38 (1.5)
230711.docx