Pipe penetration where there is no steel sleeve or cast in place fire stopping device/sleeve, provide steel angles fastened to floor surrounding the penetration or group of 2”x 2” x 1/8” galvanized penetrations to prevent water from getting to penetration. Provide urethane caulk between angles and floor and fasten angles to floor minimum on center. Seal corners water tight with urethane 8” caulk. Floors subject to water intrusion or rooms housing electrical equipment include the following locations: Food Service/Kitchen Areas Walk In Coolers/Freezers Laundries Restrooms Locker/Shower Rooms Janitor Rooms w/ Sinks Wet Laboratories Mechanical/Plumbing Equipment Rooms Swimming Pool Rooms/Pool Equipment Rooms Chemical/Hazardous Waste Storage Maintenance/Industrial Shops Vehicle Storage and Parking Ramps Greenhouses Data/Telecommunications Rooms Electrical Equipment Rooms Edit the above list for each project. Add other locations where appropriate. Consultant shall coordinate details on drawings with the above sleeve specification. Provide waterproof caulk sealant top coating on fire stopping system (or other approved means to protect the fire stopping system from water) in areas subject to wash down such as Food Service and Dish Washing Areas. AGENCY TRAINING All training provided for agency shall comply with the format, general content requirements and submission guidelines specified under Section 01 91 01 or 01 91 02. END OF SECTION
Pipe penetration where there is no steel sleeve or cast in place fire stopping device/sleeve, provide 2”x 2” x 1/8” galvanized steel angles fastened to floor surrounding the penetration or group of penetrations to prevent water from getting to penetration. Provide urethane caulk between angles and floor and fasten angles to floor minimum 8” on center. Seal corners water tight with urethane caulk. Floors subject to water intrusion or rooms housing electrical equipment include the following locations: Food Service/Kitchen Areas Walk In Coolers/Freezers Laundries Restrooms Locker/Shower Rooms Janitor Rooms w/ Sinks Wet Laboratories Mechanical/Plumbing Equipment Rooms Swimming Pool Rooms/Pool Equipment Rooms Chemical/Hazardous Waste Storage Maintenance/Industrial Shops Vehicle Storage and Parking Ramps Greenhouses Data/Telecommunications Rooms Electrical Equipment Rooms Edit the above list for each project. Add other locations where appropriate. Consultant shall coordinate details on drawings with the above sleeve specification. Provide waterproof caulk sealant top coating on fire stopping system (or other approved means to protect the fire stopping system from water) in areas subject to wash down such as Food Service and Dish Washing Areas. AGENCY TRAINING All training provided for agency shall comply with the format, general content requirements and submission guidelines specified under Section 01 91 01 or 01 91 02. END OF SECTION
21%2005%2000.docx