distribution to 128 indoor units. Remote data query in 1-day units Power File saving in Microsoft Excel format. Distribution Each Group Each Group Power distribution data storage for one System year MIM-B16 or MIM-B16N required for power use measurements Full indoor unit control with simple contact (Emergency/Lock) External Contact State output (Operation/Error) for Each Each Interface synchronous control Channel Channel 10 digital outputs (2 reserved) / 8 digital inputs (2 reserved) Control & monitoring zone edition Wireless/wired remote control restriction Smart Central Each Group Each Group Management Temperature limit setting Operation mode restriction User can edit control logic with arithmetic/conditional operators and parameters. User editable Efficient energy saving realization for Each Group Each Group control logic various operation conditions. EHP/ERV/AHU parameters + AND/OR + Arithmetic equation Function Important data is stored in SD memory Data backup/ card Each Group Each Group useful history Record the operation history and management history Specify unoccupied room settings for applicable indoor units Unoccupied Mode Room Control Each Group - Configuration Fan speed Set temperature Operation ON/OFF Mode: Heat, cool, cool storage, hot water Operation pattern: standard, rotation, efficiency DVM Chiller Enable/disable Water Law Each Group Each Group Control Enable/disable quiet mode Forced fan mode Demand/maximum current control (50~100% of design current)
Power Distribution System distribution to 128 indoor units. Remote data query in 1-day units File saving in Microsoft Excel format. Power distribution data storage for one year MIM-B16 or MIM-B16N required for power use measurements Each Group Each Group External Contact Interface Full indoor unit control with simple contact (Emergency/Lock) State output (Operation/Error) for synchronous control 10 digital outputs (2 reserved) / 8 digital inputs (2 reserved) Each Channel Each Channel Smart Central Management Control & monitoring zone edition Wireless/wired remote control restriction Temperature limit setting Operation mode restriction Each Group Each Group User editable control logic User can edit control logic with arithmetic/conditional operators and parameters. Efficient energy saving realization for various operation conditions. EHP/ERV/AHU parameters + AND/OR + Arithmetic equation Function Each Group Each Group Data backup/ useful history management Important data is stored in SD memory card Record the operation history and history Each Group Each Group Unoccupied Room Control Configuration Specify unoccupied room settings for applicable indoor units Mode Fan speed Set temperature Each Group - DVM Chiller Control Operation ON/OFF Mode: Heat, cool, cool storage, hot water Operation pattern: standard, rotation, efficiency Enable/disable Water Law Enable/disable quiet mode Forced fan mode Demand/maximum current control (50~100% of design current) Each Group Each Group
DVM%20S%20Water%201%20Phase%20Guide%20Spec_DVM%20S%20Water%201%20Phase%20Guide%20Spec.docx