CE6 1000+ Substation Name Substation Number Voltage Switchgear Switchboard Number Manufacturer Schneider Serial Number Type CE6 Protection CTs CT Ratio Relay Serial Number Protection Settings (specified by planner/designer) Overcurrent Settings Earth Fault Settings Setting Current Setting Current Curve Curve Time Multiplier Time Multiplier Highset Setting Current Highset Setting Current Highset Time Highset Time SEF Setting Current SEF Time Preliminary Checks () Visual inspection satisfactory (no visible signs of damage etc) satisfactory SF6 gas pressure satisfactory Functional/Interlock Checks () Open and close circuit-breaker switches cannot be operated when service selected Circuit-breaker cannot be operated when selected Open and close earth switches Test access cannot be opened when circuit-breaker in On and Off position Test access can be opened when earth switch closed Circuit-breaker cannot be operated when test access open
CE6 1000+ Substation Name Substation Number Voltage Switchgear Switchboard Number Manufacturer Schneider Serial Number Type CE6 Protection CTs CT Ratio Relay Serial Number Protection Settings (specified by planner/designer) Overcurrent Settings Earth Fault Settings Setting Current Setting Current Curve Curve Time Multiplier Time Multiplier Highset Setting Current Highset Setting Current Highset Time Highset Time SEF Setting Current SEF Time Preliminary Checks () Visual inspection satisfactory (no visible signs of damage etc) satisfactory SF6 gas pressure satisfactory Functional/Interlock Checks () Open and close circuit-breaker switches cannot be operated when service selected Circuit-breaker cannot be operated when selected Open and close earth switches Test access cannot be opened when circuit-breaker in On and Off position Test access can be opened when earth switch closed Circuit-breaker cannot be operated when test access open
ECP+11-0512j+Schneider+CE6+with+Sepam+1000%2B+Relay+Test+Form.docx