15 Assess completed Table 1 Yes / No No action If Yes, connect equipment against requirements of G5/4 If No, take background Sect 6.3.2 harmonic measurements Have the requirements been from the point of met? connection and then go to Q20 UKPN Response G5/4 Stage 2 Assessment Q Requirement Response Customer Action UKPN Action 16 Provide maximum individual n/a Enter emission No action harmonic current emissions values into Table 1, for EVCP column 2 below 17 Take background harmonic n/a No action Take background measurements from the point measurements of connection 18 Are background levels of Yes / No No action If go to Q9 Yes, harmonic distortion <75% of If No, go to Q20 the individual harmonic order planning levels in G5/4 Table 3? 19 Assess completed Table 1 Yes / No No action If connect equipment Yes, against requirements of G5/4 If No, go to Q20 Sect 7.4.2. Are the requirements met? 20 Predict system distortion due Yes / No No action If Yes, connect equipment to connection of EVCP in If No, go to Q21 accordance with G5/4 Sect 7.3. Are the requirements met? 21 Is connection at LV? Yes / No No action If Yes, no connection possible without mitigation If No, advise customer to perform G5/4 Stage 3 assessment Signed on behalf of Signed on behalf of customer UK Power Networks Print name Print name Date Date Table 1
15 Assess completed Table 1 against requirements of G5/4 Sect 6.3.2 Have the requirements been met? UKPN Response Yes / No No action If Yes, connect equipment If No, take background harmonic measurements from the point of connection and then go to Q20 G5/4 Stage 2 Assessment Q Requirement Response Customer Action UKPN Action 16 Provide maximum individual harmonic current emissions for EVCP n/a Enter emission values into Table 1, column 2 below No action 17 Take background harmonic measurements from the point of connection n/a No action Take background measurements 18 Are background levels of harmonic distortion <75% of the individual harmonic order planning levels in G5/4 Table 3? Yes / No No action If Yes, go to Q9 If No, go to Q20 19 Assess completed Table 1 against requirements of G5/4 Sect 7.4.2. Are the requirements met? Yes / No No action If Yes, connect equipment If No, go to Q20 20 Predict system distortion due to connection of EVCP in accordance with G5/4 Sect 7.3. Are the requirements met? Yes / No No action If Yes, connect equipment If No, go to Q21 21 Is connection at LV? Yes / No No action If Yes, no connection possible without mitigation If No, advise customer to perform G5/4 Stage 3 assessment Signed on behalf of customer Signed on behalf of UK Power Networks Print name Print name Date Date Table 1
EDS+08-5050B+Electric+Vehicle+Charging+Point+Data+Collection+Form.docx