G59 Substation Name/Number SAP Reference Date Generation Operation Mode LTP / STP Network EPN / SPN / LPN HV / LV Reference Test Voltage Export MPAN Value:_____________ Wind / Biomass / / Biogas / Waste Incineration / PV / CHP Generation Type Other (Please specify): _____________________________ Owner/Company Details Commissioning Company Details Name Name Address Address (Location of generating plant) Post Code Post Code Telephone number Telephone number Reference number Reference number Generating Plant Details Manufacturer / Supplier Number & size of machines Supply voltage Machine voltage Diagrams of interlocks, synchronising & neutral earthing Drg.No. Power factor correction equipment connected to machine µF/kVAr factor correction equipment connected to installation µF/kVAr Installation Inspection Neutral earthing satisfactory at all voltage levels () HV Installation Synchronising / interlocking arrangements satisfactory () Earthing of all equipment satisfactory. () LV Installation Main switch to generator LOCKABLE in OFF position ONLY () Warning labels fitted at mains position () Relevant supply agreement signed by customer () All Installations Copy of test results sent to/retained by the customer ()
G59 Substation Name/Number SAP Reference Date Generation Operation Mode LTP / STP Network EPN / SPN / LPN Reference Test Voltage HV / LV Value:_____________ Export MPAN Generation Type Wind / Biomass / / Biogas / Waste Incineration / PV / CHP Other (Please specify): _____________________________ Owner/Company Details Commissioning Company Details Name Name Address (Location of generating plant) Address Post Code Post Code Telephone number Telephone number Reference number Reference number Generating Plant Details Manufacturer / Supplier Number & size of machines Supply voltage Machine voltage Diagrams of interlocks, synchronising & neutral earthing Drg.No. Power factor correction equipment connected to machine µF/kVAr factor correction equipment connected to installation µF/kVAr Installation Inspection HV Installation Neutral earthing satisfactory at all voltage levels () Synchronising / interlocking arrangements satisfactory () LV Installation Earthing of all equipment satisfactory. () Main switch to generator LOCKABLE in OFF position ONLY () Warning labels fitted at mains position () All Installations Relevant supply agreement signed by customer () Copy of test results sent to/retained by the customer ()
ECP+11-0315+G59+Test+Form.docx