External Static Pressure (“WC) Model Number Standard Acceptable Range AM007FNLDCH/AA 0.08” 0 0.16” – AM009FNLDCH/AA 0.08” 0 0.16” – AM012FNLDCH/AA 0.08” 0 0.16” – AM018FNLDCH/AA 0.08” 0 0.16” – AM024FNLDCH/AA 0.08” 0 0.16” – AM030FNLDCH/AA 0.12” 0 0.24” – AM036FNLDCH/AA 0.12” 0 0.24” – AM048FNLDCH/AA 0.12” 0 0.24” – fan speed shall be adjustable by optional remote controller or manufacturer provided service software according to external static pressure. indoor unit shall only serve areas in the same room (cannot serve areas in different fire envelopes). Filter: air shall be filtered by means of a standard factory installed return air filter on rear of unit. return connection through rear or bottom of unit with removal and replacement of return air conversion plate. Other filtration is field provided (recommended). Coil: indoor coil be of nonferrous construction with slit fins on copper tubing. tubing have inner grooves for high efficiency heat exchange. tube joints shall be brazed with phos-copper or silver alloy. coils shall be pressure tested at the factory. condensate pan and drain shall be provided under the coil. condensate be gravity drained from the fan coil. coil fins are coated with hydrophilic paint.
External Static Pressure (“WC) Model Number Standard Acceptable Range AM007FNLDCH/AA 0.08” 0 – 0.16” AM009FNLDCH/AA 0.08” 0 – 0.16” AM012FNLDCH/AA 0.08” 0 – 0.16” AM018FNLDCH/AA 0.08” 0 – 0.16” AM024FNLDCH/AA 0.08” 0 – 0.16” AM030FNLDCH/AA 0.12” 0 – 0.24” AM036FNLDCH/AA 0.12” 0 – 0.24” AM048FNLDCH/AA 0.12” 0 – 0.24” fan speed shall be adjustable by optional remote controller or manufacturer provided service software according to external static pressure. indoor unit shall only serve areas in the same room (cannot serve areas in different fire envelopes). Filter: air shall be filtered by means of a standard factory installed return air filter on rear of unit. return connection through rear or bottom of unit with removal and replacement of return air conversion plate. Other filtration is field provided (recommended). Coil: indoor coil be of nonferrous construction with slit fins on copper tubing. tubing have inner grooves for high efficiency heat exchange. tube joints shall be brazed with phos-copper or silver alloy. coils shall be pressure tested at the factory. condensate pan and drain shall be provided under the coil. condensate be gravity drained from the fan coil. coil fins are coated with hydrophilic paint.
DVM%20S%20Water%201%20Phase%20Guide%20Spec_DVM%20S%20Water%201%20Phase%20Guide%20Spec.docx