Location Details Material Details Results / Management Details Photographs Building 05 - Toilets/Locker Building ID: Material Type: Cement Based Status of ACM: REMOVED (DEMOLISHED) Elevation: Ground Floor Quantity: 15 - m2 Sample #: 34348 / 21511 / 21512 Position Wall Condition: - Sample Result: No Asbestos Detected Installed: Primary - Cleaners storeroom Friability: Risk Rating: Location: Secondary Surface Throughout - - Recommendation: Location: Treatment: Urgent Action Required? Non-masonry wall sections to all elevations. Includes wall below timber shelving to east elevation (Sample ID 34348: NAD - South elevation / Sample ID Comments: 21511: NAD - North elevation / Sample ID 21512: NAD - West elevation). No Location Details Material Details Results / Management Details Photographs Building 05 - Toilets/Locker Building ID: Material Type: Cement Based Status of ACM: REMOVED Rooms (DEMOLISHED) Elevation: Ground Floor Quantity: 3 - m2 Sample #: N10101-S11 Position Wall Condition: - Sample Result: No Asbestos Detected Installed: Primary - External Friability: Risk Rating: Location: Secondary Surrounding door to cleaners Surface - Recommendation: - storeroom Location: Treatment: Urgent Action Required? Comments: Wall sheeting surrounding door to cleaners room. Sampled during a previous assessment. No
Location Details Material Details Results / Management Details Photographs Building ID: Building 05 - Toilets/Locker (DEMOLISHED) Material Type: Cement Based Status of ACM: REMOVED Elevation: Ground Floor Quantity: 15 - m2 Sample #: 34348 / 21511 / 21512 Position Installed: Wall Condition: - Sample Result: No Asbestos Detected Primary Location: Cleaners storeroom Friability: - Risk Rating: Secondary Location: Throughout Surface Treatment: - Recommendation: - Comments: Non-masonry wall sections to all elevations. Includes wall below timber shelving to east elevation (Sample ID 34348: NAD - South elevation / Sample ID 21511: NAD - North elevation / Sample ID 21512: NAD - West elevation). Urgent Action Required? No Location Details Material Details Results / Management Details Photographs Building ID: Building 05 - Toilets/Locker Rooms (DEMOLISHED) Material Type: Cement Based Status of ACM: REMOVED Elevation: Ground Floor Quantity: 3 - m2 Sample #: N10101-S11 Position Installed: Wall Condition: - Sample Result: No Asbestos Detected Primary Location: External Friability: - Risk Rating: Secondary Location: Surrounding door to cleaners storeroom Surface Treatment: - Recommendation: - Comments: Wall sheeting surrounding door to cleaners room. Sampled during a previous assessment. Urgent Action Required? No
EEN10101%20-%2034-46%20Dalrymple%20Road%20Townsville%20_Garbutt_%20Asbestos%20Register%20Ver.docx