ENTER x1 To confirm setting CANCEL x3 To return to initial screen Functions This is only done once relevant to the functional setting required. x4 Function Configuration ↓ x1, x1 Derived E/F → ↓ ENTER x1, x1, ENTER x1 To Enable the Derived E/F (Earth fault) ↓ x1, x1, x1, To Disable the Measured E/F ↓ ↑ ENTER x1 To confirm setting CANCEL x3 To return to initial start-up screen Step 2 Overcurrent – Ensure that the cancel button has been pressed three times to start from first initial start-up screen. x5 Current Protection ↓ x2, x2 51-1 Element → ↓ ENTER x1, x1,ENTER x1 To enable the overcurrent element ↓ x1, ENTER x1 51-1 Setting ↓ To increase/decrease value. Set to 0.4In ↑/↓ ENTER x1 To confirm settings x1 51-1 Curve Characteristic ↓ x1 To increase/decrease Set to IEC-NI ↑/↓ ENTER x1 To confirm setting x1 51-1 Time Multiplier ↓ ENTER x1 To increase/decrease value. Set to 1.5 ↑/↓ ENTER x1 To confirm setting CANCEL x4, To return to initial screen Output Configuration ↓x8 ENTER x1 51-1 →x2, ↓x5, To move cursor to Binary Output B03 →x2 To enable/disable Binary Output B03 ↑/↓ x1 To move cursor to Binary Output B04 → To enable/disable Binary Output B04 ↑/↓ x1 To confirm Binary Outputs CANCEL x4 To return to initial start-up screen
ENTER x1 To confirm setting CANCEL x3 To return to initial screen Functions This is only done once relevant to the functional setting required. ↓ x4 Function Configuration → x1, ↓ x1 Derived E/F ENTER x1, ↓ x1, ENTER x1 To Enable the Derived E/F (Earth fault) ↓ x1, x1, ↑ x1, To Disable the Measured E/F ENTER x1 To confirm setting CANCEL x3 To return to initial start-up screen Step 2 – Overcurrent Ensure that the cancel button has been pressed three times to start from first initial start-up screen. ↓ x5 Current Protection → x2, ↓ x2 51-1 Element ENTER x1, ↓ x1,ENTER x1 To enable the overcurrent element ↓ x1, ENTER x1 51-1 Setting ↑/↓ To increase/decrease value. Set to 0.4In ENTER x1 To confirm settings ↓ x1 51-1 Curve Characteristic x1 ↑/↓ To increase/decrease Set to IEC-NI ENTER x1 To confirm setting ↓ x1 51-1 Time Multiplier ENTER x1 ↑/↓ To increase/decrease value. Set to 1.5 ENTER x1 To confirm setting CANCEL x4, ↓x8 To return to initial screen Output Configuration →x2, ↓x5, ENTER x1 51-1 →x2 To move cursor to Binary Output B03 ↑/↓ To enable/disable Binary Output B03 → x1 ↑/↓ x1 To move cursor to Binary Output B04 To enable/disable Binary Output B04 To confirm Binary Outputs CANCEL x4 To return to initial start-up screen
ECP+11-0512h+Lucy+VCE6a+with+Argus+7SR11+Relay+Test+Form.docx