6. Identify instrumentation required for each test. 7. Identify who will provide instrumentation for each test. 8. Operational Description. This shall include, for example, the design criteria, design intent, code requirements, specifics of the equipment to be provided, sequences of operation, operating priorities, protocols, etc. 1.10 SCHEDULE 1.10.1 Commissioning Schedule. Integrate functional performance testing and commissioning requirements into the Contract Schedule. Commissioning scheduling is the responsibility of the Design Builder. 1. Prior to the beginning of Start-up or functional performance testing activities, update the schedule of commissioning activities monthly. 2. Two weeks prior to the beginning of Start-up or functional performance testing activities, provide a detailed two week Look Ahead schedule. Thereafter, update the two week Look Ahead schedule weekly for the duration of commissioning for that construction phase. The two week Look Ahead schedule shall identify the date, time, beginning location, Design Builder personnel required, and anticipated duration for each Start-up or test activity. 1.10.2 Commissioning of systems shall proceed per the criteria established in the specific sections that follow, with activities to be performed on a timely bases. Commissioning of systems may proceed prior to final completion of systems, The Test Engineer must be available to respond promptly to avoid delay to the Contract Schedule or Contract Time. 1.10.3 Problems observed be addressed immediately, in terms of notification to responsible parties, and actions to correct deficiencies. 1.11 COORDINATION WITH UNIVERSITY'S REPRESENTATIVE’S WITNESS 1.11.1 The University's Representative will witness all Start-up and test activities specified. The University's Representative will designate witnesses and alternates for each activity. 1.11.2 Notify the University's Representative in writing of the date, time, location, and anticipated duration of Start-up and test activities as required in "Schedule" above. 1.11.3 Provide written timely notice to University's Representative of any changes in date, time, location, anticipated duration of Start-up and test activities. For the purpose of this paragraph, written notice shall be received by University's Representative a minimum of 72 hours in advance to be considered timely notice. 1.11.4 Design Builder shall reimburse the University's Representative for actual costs incurred by the University as the result of failure to provide timely notice per preceding paragraph of changes in date, time, location, anticipated duration of Start-up and test activities.
6. Identify instrumentation required for each test. 7. Identify who will provide instrumentation for each test. 8. Operational Description. This shall include, for example, the design criteria, design intent, code requirements, specifics of the equipment to be provided, sequences of operation, operating priorities, protocols, etc. 1.10 SCHEDULE 1.10.1 Commissioning Schedule. Integrate functional performance testing and commissioning requirements into the Contract Schedule. Commissioning scheduling is the responsibility of the Design Builder. 1. Prior to the beginning of Start-up or functional performance testing activities, update the schedule of commissioning activities monthly. 2. Two weeks prior to the beginning of Start-up or functional performance testing activities, provide a detailed two week Look Ahead schedule. Thereafter, update the two week Look Ahead schedule weekly for the duration of commissioning for that construction phase. The two week Look Ahead schedule shall identify the date, time, beginning location, Design Builder personnel required, and anticipated duration for each Start-up or test activity. 1.10.2 Commissioning of systems shall proceed per the criteria established in the specific sections that follow, with activities to be performed on a timely bases. Commissioning of systems may proceed prior to final completion of systems, The Test Engineer must be available to respond promptly to avoid delay to the Contract Schedule or Contract Time. 1.10.3 Problems observed be addressed immediately, in terms of notification to responsible parties, and actions to correct deficiencies. 1.11 COORDINATION WITH UNIVERSITY'S REPRESENTATIVE’S WITNESS 1.11.1 The University's Representative will witness all Start-up and test activities specified. The University's Representative will designate witnesses and alternates for each activity. 1.11.2 Notify the University's Representative in writing of the date, time, location, and anticipated duration of Start-up and test activities as required in "Schedule" above. 1.11.3 Provide written timely notice to University's Representative of any changes in date, time, location, anticipated duration of Start-up and test activities. For the purpose of this paragraph, written notice shall be received by University's Representative a minimum of 72 hours in advance to be considered timely notice. 1.11.4 Design Builder shall reimburse the University's Representative for actual costs incurred by the University as the result of failure to provide timely notice per preceding paragraph of changes in date, time, location, anticipated duration of Start-up and test activities.
db_specifications.docx