been configured for discharge air temperature control. Range of temperature setting: Cool/Dry mode: 46°F - 64°F Heat mode: 64°F - 86°F Fan Speed Models with 3 air flow speed settings: High Each Group Each Group Setting /Mid/Low Air flow 2-step direction Air Flow Direct setting at a specific angle. Each Each Group Direction Setting Air flow operation varies depending on the model. Remote control with the public IP address Web Server Each Group Each Group No management software required – Function management Wireless/wired remote controller Accessible level restriction setting / Dynamic user Specify the scope of control and Each Group Each security monitoring unit on a per-user Management 3 accessible levels: Admin/Manager/User When an error is currently occurring in the system(s), the afflicted unit and the error Error Each Group Each Group code are displayed Error notification via email Up to 256 schedule settings Schedule Each Group Each Group Operation Weekly and schedule setting Power distribution to 256 indoor units. Remote data query in 1-day units Power File saving in Microsoft Excel format. Distribution Each Group Each Group distribution data storage for one year System MIM-B16 or MIM-B16N required for power use measurements Full indoor unit control with simple contact (Emergency/Lock) External Contact State output (Operation/Error) for Each Each Interface synchronous control Channel Channel 10 digital outputs (2 reserved) / 8 digital inputs (2 reserved) Control & monitoring zone edition Wireless/wired remote control restriction Smart Central Each Group Each Group Management Temperature limit setting Operation mode restriction
been configured for discharge air temperature control. Range of temperature setting: Cool/Dry mode: 46°F - 64°F Heat mode: 64°F - 86°F Fan Speed Setting Models with 3 air flow speed settings: High /Mid/Low Each Group Each Group Air Flow Direction Setting Air flow 2-step direction Direct setting at a specific angle. Air flow operation varies depending on the model. Each Each Group Web Server Function Remote control with the public IP address No management software required – management Each Group Each Group Accessible level / Dynamic user security Management Wireless/wired remote controller restriction setting Specify the scope of control and monitoring unit on a per-user 3 accessible levels: Admin/Manager/User Each Group Each Error When an error is currently occurring in the system(s), the afflicted unit and the error code are displayed Error notification via email Each Group Each Group Schedule Operation Up to 256 schedule settings Weekly and schedule setting Each Group Each Group Power Distribution System Power distribution to 256 indoor units. Remote data query in 1-day units File saving in Microsoft Excel format. distribution data storage for one year MIM-B16 or MIM-B16N required for power use measurements Each Group Each Group External Contact Interface Full indoor unit control with simple contact (Emergency/Lock) State output (Operation/Error) for synchronous control 10 digital outputs (2 reserved) / 8 digital inputs (2 reserved) Each Channel Each Channel Smart Central Management Control & monitoring zone edition Wireless/wired remote control restriction Temperature limit setting Operation mode restriction Each Group Each Group
DVM%20S%20Water%201%20Phase%20Guide%20Spec_DVM%20S%20Water%201%20Phase%20Guide%20Spec.docx