Rule .05(12)(b) Table 1. Density Factors (D) in square feet Agitated Flat Diving Entry Area Water in Water in Area (per for all Shallow Deep each other area or area or diving devices Shallow Deep board) including water or water (not slides Wading including area the Diving Area) Pools with minimal deck area 15 square 20 square 300 150 feet per feet per square square user user feet per feet per diving device board Pools with deck area at least equal to the water surface area 12 square 15 300 150 feet per square square square user feet per feet per feet per user diving device board Pool with deck area at least 10 square 12 square 300 150 twice the water surface area feet per feet per square square user user feet per feet per diving device board (c) The theoretical peak occupancy calculations shall be calculated by adding the sums of the applicable figures from Table 1. (d) A spa or hot water venue density factor shall not exceed one bather per ten square feet of surface area. (e) A waterslide landing pool may use the manufacturer established capacity if (13) Wading Pool Depth. Wading pools constructed after adoption of this chapter shall be separate and physically set apart from beginning or shallow water areas of swimming pools by at least fifteen feet of deck. Where a wading pool is adjacent to
Rule .05(12)(b) Table 1. Density Factors (D) in square feet Agitated Water in Shallow area or Shallow water or Wading area Flat Water in Deep area or Deep water (not including the Diving Area) Diving Area (per each diving board) Entry Area for all other devices including slides Pools with minimal deck area 15 square feet per user 20 square feet per user 300 square feet per diving board 150 square feet per device Pools with deck area at least equal to the water surface area 12 square feet per user 15 square feet per user 300 square feet per diving board 150 square feet per device Pool with deck area at least twice the water surface area 10 square feet per user 12 square feet per user 300 square feet per diving board 150 square feet per device (c) The theoretical peak occupancy calculations shall be calculated by adding the sums of the applicable figures from Table 1. (d) A spa or hot water venue density factor shall not exceed one bather per ten square feet of surface area. (e) A waterslide landing pool may use the manufacturer established capacity if (13) Wading Pool Depth. Wading pools constructed after adoption of this chapter shall be separate and physically set apart from beginning or shallow water areas of swimming pools by at least fifteen feet of deck. Where a wading pool is adjacent to
Chapter-511-3-5-Camden-2-6-2018.docx