C2.1 Control Unit or Transponder Tests Control Unit/Transponder Field Location: Control Unit/Transponder Identification: Yes No N/A Power visual indicator operates. A ‘on’ B Common visual trouble signal operates. Common audible trouble signal operates. C Trouble signal silence switch operates. D E Main Power supply failure trouble signal operates. Ground fault tested on positive and negative initiates trouble signal. F Alert signal operates. G H Alarm signal operates. I Automatic transfer from alert signal to alarm signal operates. Time: Manual transfer from alert signal to alarm signal. J Automatic transfer from to alarm signal cancel (acknowledge) operates on a K two stage system. L signal silence inhibit function operates. Alarm signal manual silence operates. M N Alarm signal silence visual indication operates Alarm signal and visible signal devices, when silenced, automatically reinitiate O upon subsequent alarm. In same zone In other zone/circuit P Alarm signal silence automatic cut-out timer. Time: Audible and visual alert signals and alarm signals programmed and operate per Q design and specification, or documentation as detailed in Appendix E, Description of Fire Alarm System for Inspection and Test Procedures. Input circuit alarm and supervisory operation, including audible and visual R indication operates. S Input circuit supervision fault causes a trouble indication. T Output circuit alarm indicators operate. U Output circuit supervision fault causes a trouble indication. V Visual indicator test (lamp test) operates. Coded signal sequences operate not less than the required number of times and W the correct alarm signal operates thereafter. X Coded signal sequences are not interrupted by subsequent alarms. Y Ancillary device by-pass results in trouble signal. circuit to output circuit operation, including ancillary device circuits for correct program operation, as per design and specification, or documentation as detailed Z in Appendix E, Description of Fire Alarm System for Inspection and Test Procedures. AA Fire alarm reset function operates. BB Main power to emergency power supply transfer operates. Smoke detector alarm verification (status change confirmation) verified. [Refer to CC Subsection 6.7.4.3, Smoke Detector Alarm Verification (Status Change Confirmation)]. Yes No N/A Recommended Additional Testing (not mandated by the Standard): Alarm, trouble, & supervisory relays function correctly. Control panel bonded to ground. Is an AC disconnecting switch installed? YES NO (ULC CAN4-S524 restricts this, but some AHJs will accept it. A answer here must be in the “YES” “Remarks” section of this report.)
C2.1 Control Unit or Transponder Tests Control Unit/Transponder Field Location: Control Unit/Transponder Identification: Yes No N/A A Power ‘on’ visual indicator operates. B Common visual trouble signal operates. C Common audible trouble signal operates. D Trouble signal silence switch operates. E Main Power supply failure trouble signal operates. F Ground fault tested on positive and negative initiates trouble signal. G Alert signal operates. H Alarm signal operates. I Automatic transfer from alert signal to alarm signal operates. Time: J Manual transfer from alert signal to alarm signal. K Automatic transfer from to alarm signal cancel (acknowledge) operates on a two stage system. L signal silence inhibit function operates. M Alarm signal manual silence operates. N Alarm signal silence visual indication operates O Alarm signal and visible signal devices, when silenced, automatically reinitiate upon subsequent alarm. In same zone In other zone/circuit P Alarm signal silence automatic cut-out timer. Time: Q Audible and visual alert signals and alarm signals programmed and operate per design and specification, or documentation as detailed in Appendix E, Description of Fire Alarm System for Inspection and Test Procedures. R Input circuit alarm and supervisory operation, including audible and visual indication operates. S Input circuit supervision fault causes a trouble indication. T Output circuit alarm indicators operate. U Output circuit supervision fault causes a trouble indication. V Visual indicator test (lamp test) operates. W Coded signal sequences operate not less than the required number of times and the correct alarm signal operates thereafter. X Coded signal sequences are not interrupted by subsequent alarms. Y Ancillary device by-pass results in trouble signal. Z circuit to output circuit operation, including ancillary device circuits for correct program operation, as per design and specification, or documentation as detailed in Appendix E, Description of Fire Alarm System for Inspection and Test Procedures. AA Fire alarm reset function operates. BB Main power to emergency power supply transfer operates. CC Smoke detector alarm verification (status change confirmation) verified. [Refer to Subsection 6.7.4.3, Smoke Detector Alarm Verification (Status Change Confirmation)]. Recommended Additional Testing (not mandated by the Standard): Yes No N/A Alarm, trouble, & supervisory relays function correctly. Control panel bonded to ground. Is an AC disconnecting switch installed? YES NO (ULC CAN4-S524 restricts this, but some AHJs will accept it. A “YES” answer here must be in the “Remarks” section of this report.)
BuildingAnnualTestReport.docx