LOW VOLTAGE POWER CABLES cables 0,6/1 kV 79 CONSTRUCTION 4 3 2 1 Conductor: Cu – class 1 and 2 1 Insulation: PVC 2 Core: EPDM 3 Jacket: PVC 4 SPECIFICATION Type Standard EYY HD 603 S1.Part 3A (DIN VDE 0276 Teil 603) PP 00 JUS N.C5.220 PVC/PVC IEC 60502 PVC/PVC BS 6346 Nominal voltage 0,6/1 kV Test voltage 4000 V Minimum temperature during installation -5 °C Operating temperature -30 °C – +70 °C Maximum operating temperature +70 °C Short circuit temperature +160 °C/5s Colour of insulation HD 308. S2 test EN 50265-2-1 IEC 60332-1 Minimum bending radius 12 x Ø cable Coat colour Black APPLICATION A power cable suitable for laying in air, soil, water, concrete, in enclosed locations, cable ducts, power plants, industrial applications, city power grids - where mechanical damages are not expected, and cables are not exposed to excessive pulling forces. TECHNICAL DATA Drum No. of Maximal Current Current Overall Net size Conductor Copper conductors resistance carrying carrying diameter weight and cross shape of conductor capacities capacities weight (approx) sectional area at 20 °C in air in ground mm2 Ω/km A A mm kg/km kg/km m No 1 x 1,5 RE 12,1 27 41 6,4 14 48 1000 6 1 x 2,5 RE 7,41 35 55 6,8 24 60 1000 6 1x4 RE 4,41 47 71 7,5 38 85 1000 7 1x6 RE 3,08 59 90 8,0 58 111 1000 7 1 x 10 RM 1,83 64 83 9,3 96 164 1000 7 1 x 16 RM 1,15 84 107 10,3 154 228 1000 8 1 x 25 RM 0,727 114 138 12,1 240 336 1000 9 1 x 35 RM 0,524 139 164 13,2 336 445 1000 10 1 x 50 RM 0,387 169 195 15,0 480 598 1000 10 1 x 70 RM 0,268 213 238 16,8 672 796 1000 1 81
LOW VOLTAGE POWER CABLES cables 0,6/1 kV 79 CONSTRUCTION 4 3 2 1 1 Conductor: Cu – class 1 and 2 2 Insulation: PVC 3 Core: EPDM 4 Jacket: PVC SPECIFICATION Type Standard EYY HD 603 S1.Part 3A (DIN VDE 0276 Teil 603) PP 00 JUS N.C5.220 PVC/PVC IEC 60502 PVC/PVC BS 6346 Nominal voltage 0,6/1 kV Test voltage 4000 V Minimum temperature during installation -5 °C Operating temperature -30 °C – +70 °C Maximum operating temperature +70 °C Short circuit temperature +160 °C/5s Colour of insulation HD 308. S2 test EN 50265-2-1 IEC 60332-1 Minimum bending radius 12 x Ø cable Coat colour Black APPLICATION A power cable suitable for laying in air, soil, water, concrete, in enclosed locations, cable ducts, power plants, industrial applications, city power grids - where mechanical damages are not expected, and cables are not exposed to excessive pulling forces. TECHNICAL DATA No. of conductors and cross sectional area Conductor shape Maximal resistance of conductor at 20 °C Current carrying capacities in air Current carrying capacities in ground Overall diameter (approx) Copper weight Net weight Drum size mm2 Ω/km A A mm kg/km kg/km m No 1 x 1,5 RE 12,1 27 41 6,4 14 48 1000 6 1 x 2,5 RE 7,41 35 55 6,8 24 60 1000 6 1x4 RE 4,41 47 71 7,5 38 85 1000 7 1x6 RE 3,08 59 90 8,0 58 111 1000 7 1 x 10 RM 1,83 64 83 9,3 96 164 1000 7 1 x 16 RM 1,15 84 107 10,3 154 228 1000 8 1 x 25 RM 0,727 114 138 12,1 240 336 1000 9 1 x 35 RM 0,524 139 164 13,2 336 445 1000 10 1 x 50 RM 0,387 169 195 15,0 480 598 1000 10 1 x 70 RM 0,268 213 238 16,8 672 796 1000 1 81
Catalogue-2014.docx