16 Whether method of Cables laid inside the Electrical room is acceptable 17 Total Electrical Load of the Air conditioning Floor load Light & power load 18 Whether electrical load balancing is acceptable (give details of wise load ) 19 Other special observations, if any record the results of particular inspections applied separately 6.Assessment of Transformer No. Capacity of P-P P-N Phase Total Neutral Whether Remarks Voltage Voltage Current electrical of of each on of each each load & its of & its machine if any 1. Rating loaded or Not 2. make and 3. type extant thereof in % R Y B R Y B R Y B KW A 7. Assessment of Elevator P-P P-N Phase Total Parameters of the motors Voltage Voltage electrical on of . load of i each & & of its its (KW) of if any or 1. Not Rating R Y B R Y B R Y B KW A 3.type
16 Whether method of Cables laid inside the Electrical room is acceptable 17 Total Electrical Load of the Floor Air conditioning load Light & power load 18 Whether electrical load balancing is acceptable (give details of wise load ) 19 Other special observations, if any record the results of particular inspections applied separately 6.Assessment of Transformer No. of Capacity of each 1. Rating 2. make 3. type P-P Voltage of each P-N Voltage each Phase Total electrical load Neutral & its & its of Whether loaded and extant thereof in % Remarks of machine or Not on if any R Y B R Y B R Y B KW A 7. Assessment of Elevator of . each 1. Rating 3.type P-P Voltage P-N Voltage Phase Total electrical load Parameters of the motors & its & its of of or Not on i if any (KW) of R Y B R Y B R Y B KW A Current
C007481187204EED561F69BE269B761F.DOCX