FLEXIBLE SHEATHED POWER CABLES Power cables 450/750 V 70 3 2 1 CONSTRUCTION Conductor: Cu – class 5 1 Insulation: PVC type TI2 2 Jacket: PVC type TM2 3 SPECIFICATION Type Standard FROR CEI 20-20; CEI 20-22; CEI 20-37; CEI 20-52 Nominal voltage 450/750 V Test voltage 2500 V Minimum temperature during installation -5 °C Operating temperature -30 °C – +70 °C Maximum operating temperature +70 °C circuit temperature +160 °C/5s Colour of insulation HD 308. S2 test EN 50265-2-1 IEC 60332-1 Minimum bending radius 4 x Ø cable Coat colour Gray RAL 7035 APPLICATION A cable for permanent installation and for portable devices, mostly for temporary installation at trade shows and public events. TECHNICAL DATA No. of Maximal Current Current Overall size Copper conductors resistance carrying carrying diameter and of conductor capacities capacities in (approx) sectional area at 20 °C in air ground mm2 Ω/km A A mm kg/km kg/km m No 2 x 1,5 13,3 17 19,5 8,1 29 98 100 coil 2 x 2,5 7,98 22,5 26 9,9 48 150 100 coil 2x4 4,95 30 35 10,5 77 190 100 coil 2x6 3,3 40 46 12,5 115 260 100 coil 2 x 10 1,91 52 63 16,9 192 470 500 9 2 x 16 1,21 69 85 19,5 307 630 500 9 2 x 25 0,78 90 112 23,1 480 940 500 10 3 x 1,5 13,3 17 19,5 8,5 43 116 100 coil 3 x 2,5 7,98 22 26 10,4 72 179 100 coil 3x4 4,95 30 35 11,7 115 240 100 coil 3x6 3,3 40 46 13,4 173 330 100 coil 3 x 10 1,91 46 57 17,9 288 580 500 9 3 x 16 1,21 62 76 20,7 460 820 500 10 3 x 25 0,78 80 96 24,5 720 1175 500 10 Maximal of resistance of conductor at 20 °C
FLEXIBLE SHEATHED POWER CABLES Power cables 450/750 V 70 3 2 1 CONSTRUCTION 1 Conductor: Cu – class 5 2 Insulation: PVC type TI2 3 Jacket: PVC type TM2 SPECIFICATION Type Standard FROR CEI 20-20; CEI 20-22; CEI 20-37; CEI 20-52 Nominal voltage 450/750 V Test voltage 2500 V Minimum temperature during installation -5 °C Operating temperature -30 °C – +70 °C Maximum operating temperature +70 °C circuit temperature +160 °C/5s Colour of insulation HD 308. S2 test EN 50265-2-1 IEC 60332-1 Minimum bending radius 4 x Ø cable Coat colour Gray RAL 7035 APPLICATION A cable for permanent installation and for portable devices, mostly for temporary installation at trade shows and public events. TECHNICAL DATA No. of conductors and sectional area Maximal resistance of conductor at 20 °C Current carrying capacities in air Current carrying capacities in ground Overall diameter (approx) Copper size mm2 Ω/km A A mm kg/km kg/km m No 2 x 1,5 13,3 17 19,5 8,1 29 98 100 coil 2 x 2,5 7,98 22,5 26 9,9 48 150 100 coil 2x4 4,95 30 35 10,5 77 190 100 coil 2x6 3,3 40 46 12,5 115 260 100 coil 2 x 10 1,91 52 63 16,9 192 470 500 9 2 x 16 1,21 69 85 19,5 307 630 500 9 2 x 25 0,78 90 112 23,1 480 940 500 10 3 x 1,5 13,3 17 19,5 8,5 43 116 100 coil 3 x 2,5 7,98 22 26 10,4 72 179 100 coil 3x4 4,95 30 35 11,7 115 240 100 coil 3x6 3,3 40 46 13,4 173 330 100 coil 3 x 10 1,91 46 57 17,9 288 580 500 9 3 x 16 1,21 62 76 20,7 460 820 500 10 3 x 25 0,78 80 96 24,5 720 1175 500 10 of Maximal resistance of conductor at 20 °C
Catalogue-2014.docx