Water cooled 500 to 699 9.1 10.0 0.171 7 Water cooled 700 to 999 9.3 10.2 0.171 8 cooled 1000 to 1499 9.3 10.2 0.171 9 Water cooled 9.8 10.7 0.171 10 ≥1500 control air conditioner default factors —Close Default factor for a control air conditioner model that appears in the GEMS Register Item Net sensible Default factors cooling capacity (kW) Baseline High Capacity factor sensible efficiency energy threshold efficiency ratio 1 Less than 19.05 3.3 3.6 0.65 kW 2 From 19.05 kW to 3.2 3.5 0.65 less than 39.5 kW 3 From 39.5 kW to 3.3 3.6 0.65 less than 70.0 kW 4 Greater than or 3.3 3.6 0.65 equal to 70.0 kW display cabinet default factors —Refrigerated Default factor for a refrigerated display cabinet that appears in the GEMS Register Item Cabinet type M-package Default factor: temperature class Baseline efficiency (kWh/day/m2) 1 RS 1—Unlit shelves All 8.37 2 RS 1—Lit shelves All 10.66 3 RS 2—Unlit shelves All 8.49
7 Water cooled 500 to 699 9.1 10.0 0.171 8 Water cooled 700 to 999 9.3 10.2 0.171 9 cooled 1000 to 1499 9.3 10.2 0.171 10 Water cooled ≥1500 9.8 10.7 0.171 —Close control air conditioner default factors Default factor for a control air conditioner model that appears in the GEMS Register Item Net sensible cooling capacity (kW) Default factors Baseline sensible energy efficiency ratio High efficiency threshold Capacity factor 1 Less than 19.05 kW 3.3 3.6 0.65 2 From 19.05 kW to less than 39.5 kW 3.2 3.5 0.65 3 From 39.5 kW to less than 70.0 kW 3.3 3.6 0.65 4 Greater than or equal to 70.0 kW 3.3 3.6 0.65 —Refrigerated display cabinet default factors Default factor for a refrigerated display cabinet that appears in the GEMS Register Item Cabinet type M-package temperature class Default factor: Baseline efficiency (kWh/day/m2) 1 RS 1—Unlit shelves All 8.37 2 RS 1—Lit shelves All 10.66 3 RS 2—Unlit shelves All 8.49
commercial-appliances-determination.docx