52 CONSTRUCTION 5 4 3 2 1 Conductor: Cu – 2 1 Insulation: XLPE 2 Core: EPDM 3 Armour: steel galvanised wires, Al wires 4 Jacket: PVC 5 SPECIFICATION Type Standard XLPE/SWA/PVC IEC 60502 XLPE/SWA/PVC BS 5467 VDE 0276-603 XP 44 JUS N.C5.230 Nominal voltage 0,6/1 kV Test voltage 3500 V Minimum temperature during installation -5 °C Operating temperature -30 °C – +90 °C Maximum operating temperature +90 °C circuit temperature +250 °C/5s Colour of insulation HD 308. S2 test EN 50265-2-1 IEC 60332-1 Minimum bending radius 15 x Ø cable Coat colour Black APPLICATION For power distribution in urban networks and places where mechanical strains may be expected. Laying directly into ground, vertical mine shafts, and power plants. TECHNICAL DATA Drum No. of Maximal Current Current Overall Net size Conductor Copper conductors resistance carrying carrying diameter weight and cross of conductor capacities capacities weight (approx) sectional area at 20 °C in air in ground mm2 Ω/km A A mm kg/km kg/km m No 1 x 50 RM 0,387 169 195 19,1 480 788 1000 14 1 x 70 RM 0,268 213 238 21,1 672 1032 1000 14 1 x 95 RM 0,193 264 286 23,4 912 1300 1000 16 1 x 120 RM 0,153 307 325 26,3 1152 1657 1000 16 1 x 150 RM 0,124 352 365 28,3 1440 1960 1000 18 1 x 185 RM 0,0991 406 413 30,8 1776 2375 500 14 1 x 240 RM 0,0754 483 479 34,1 2304 3005 500 16 1 x 300 RM 0,0601 557 541 37,0 2880 3650 500 16 1 x 400 RM 0,047 646 614 42,0 3840 4720 500 18 Drum No. of Maximal Current Current Overall Net size Conductor Copper conductors resistance carrying carrying diameter weight and cross shape of conductor capacities capacities weight (approx) sectional area at 20 °C in air in ground
52 CONSTRUCTION 5 4 3 2 1 1 Conductor: Cu – 2 2 Insulation: XLPE 3 Core: EPDM 4 Armour: steel galvanised wires, Al wires 5 Jacket: PVC SPECIFICATION Type Standard XLPE/SWA/PVC IEC 60502 XLPE/SWA/PVC BS 5467 VDE 0276-603 XP 44 JUS N.C5.230 Nominal voltage 0,6/1 kV Test voltage 3500 V Minimum temperature during installation -5 °C Operating temperature -30 °C – +90 °C Maximum operating temperature +90 °C circuit temperature +250 °C/5s Colour of insulation HD 308. S2 test EN 50265-2-1 IEC 60332-1 Minimum bending radius 15 x Ø cable Coat colour Black APPLICATION For power distribution in urban networks and places where mechanical strains may be expected. Laying directly into ground, vertical mine shafts, and power plants. TECHNICAL DATA No. of conductors and cross sectional area Conductor Maximal resistance of conductor at 20 °C Current carrying capacities in air Current carrying capacities in ground Overall diameter (approx) Copper weight Net weight Drum size mm2 Ω/km A A mm kg/km kg/km m No 1 x 50 RM 0,387 169 195 19,1 480 788 1000 14 1 x 70 RM 0,268 213 238 21,1 672 1032 1000 14 1 x 95 RM 0,193 264 286 23,4 912 1300 1000 16 1 x 120 RM 0,153 307 325 26,3 1152 1657 1000 16 1 x 150 RM 0,124 352 365 28,3 1440 1960 1000 18 1 x 185 RM 0,0991 406 413 30,8 1776 2375 500 14 1 x 240 RM 0,0754 483 479 34,1 2304 3005 500 16 1 x 300 RM 0,0601 557 541 37,0 2880 3650 500 16 1 x 400 RM 0,047 646 614 42,0 3840 4720 500 18 No. of conductors and cross sectional area Conductor shape Maximal resistance of conductor at 20 °C Current carrying capacities in air Current carrying capacities in ground Overall diameter (approx) Copper weight Net weight Drum size
Catalogue-2014.docx