650 650 0.39 (at 600 wide) (at 600 high) Hardwood or non-combustible setting blocks will be used to establish the correct edge cover. Non-insulating glasses: 7 mm thick Pyroshield or other CERTIFIRE approved glass subject to the conditions of the glass certificate. Intumescent Bead Dimensions Bead Fixings Max. Height Max. Width Max. Max. System Density (mm) (mm) Dia. Area (m2) 30 mm high by 25 mm Sealmaster wide splayed including Hardwood 60 mm long No.6 650 650 Fireglaze 60 2 a 5 x 5 mm bolection min screws at max – N/A 0.39 (at 600 wide) (at 600 high) mm Palusol liner (23 mm +/-1 mm edge 640 kg/m3 150 mm centres cover) 9. Intumescent Seals CERTIFIRE certificated intumescent seals are required to be fitted to these doors as below. For door assemblies/doorsets to BS476: Part 22 classified as FD60 – Mann McGowan Pyrostrip Intumescent Position Required Intumescent Protection Doorset Configuration 2No. 15 mm wide by 4 mm thick fitted – Flamebreak 660 Head centrally 10 mm apart Single-Acting, Single-Leaf Latched / Unlatched (max. 2388 mm high or 1183 mm 2No. 15 mm wide by 4 mm thick fitted – Vertical wide 2823 m2 max. area) – centrally 10 mm apart 1No. 30 mm wide by 4 mm thick fitted – Head centrally Flamebreak 660 2No. 15 mm wide by 4 mm thick fitted – Single-Acting, Double-Leaf Hanging centrally 10 mm apart Latched / Unlatched Square meeting edges 2No. 15 mm wide by 4 mm in primary (max. 2155 mm high or 935 mm Meeting edges wide 2.02 m2 max. area) leaf only - fitted centrally 8mm apart – 2No. 15 mm wide by 4 mm thick fitted – Flamebreak FF660 Head centrally 10 mm apart Single-Acting, Single-Leaf Latched / Unlatched (max. 2096 mm high or 933 mm 2No. 15 mm wide by 4 mm thick fitted – Vertical wide 1.94 m2 max. area) – centrally 10 mm apart Pyroplex 8700 Rigid Box Intumescent Seals
650 (at 600 wide) 650 (at 600 high) 0.39 Hardwood or non-combustible setting blocks will be used to establish the correct edge cover. Non-insulating glasses: 7 mm thick Pyroshield or other CERTIFIRE approved glass subject to the conditions of the glass certificate. Intumescent System Bead Dimensions Bead Density Fixings Max. Height (mm) Max. Width (mm) Max. Dia. Max. Area (m2) Sealmaster Fireglaze 60 – 2 mm Palusol liner 30 mm high by 25 mm wide splayed including a 5 x 5 mm bolection (23 mm +/-1 mm edge cover) Hardwood min 640 kg/m3 60 mm long No.6 screws at max 150 mm centres 650 (at 600 wide) 650 (at 600 high) N/A 0.39 9. Intumescent Seals CERTIFIRE certificated intumescent seals are required to be fitted to these doors as below. For door assemblies/doorsets to BS476: Part 22 – classified as FD60 Mann McGowan Pyrostrip Intumescent Doorset Configuration Position Required Intumescent Protection Flamebreak 660 Single-Acting, Single-Leaf Latched / Unlatched (max. 2388 mm high or 1183 mm wide – 2823 m2 max. area) Head 2No. 15 mm wide by 4 mm thick – fitted centrally 10 mm apart Vertical 2No. 15 mm wide by 4 mm thick – fitted centrally 10 mm apart Flamebreak 660 Single-Acting, Double-Leaf Latched / Unlatched Square meeting edges (max. 2155 mm high or 935 mm wide – 2.02 m2 max. area) Head 1No. 30 mm wide by 4 mm thick – fitted centrally Hanging 2No. 15 mm wide by 4 mm thick – fitted centrally 10 mm apart Meeting edges 2No. 15 mm wide by 4 mm in primary leaf only - fitted centrally 8mm apart Flamebreak FF660 Single-Acting, Single-Leaf Latched / Unlatched (max. 2096 mm high or 933 mm wide – 1.94 m2 max. area) Head 2No. 15 mm wide by 4 mm thick – fitted centrally 10 mm apart Vertical 2No. 15 mm wide by 4 mm thick – fitted centrally 10 mm apart Pyroplex 8700 Rigid Box Intumescent Seals
CF575%20Phillips%20Joinery.docx