New coal-fired 30 CO 400 ppm by ≥ boiler volume on a dry corrected to 3% O2 New boiler 10 and < 30 PM 0.42 lb per MMBtu ≥ of heat input New coal-fired 10 and < 30 Hg 0.0000048 lb per ≥ boiler MMBtu of heat input New coal-fired 10 and < 30 CO 400 ppm by ≥ boiler volume on a dry basis corrected to 3% O2 New biomass-fired 30 PM 0.03 lb per MMBtu ≥ boiler of heat input New biomass-fired 10 and < 30 PM 0.07 lb per MMBtu ≥ boiler of heat input New oil-fired boiler 30 PM 0.03 lb per MMBtu ≥ of heat input New boiler 10 and < 30 PM 0.03 lb per MMBtu ≥ of heat input Existing coal-fired 10 Hg 0.0000048 lb per ≥ boiler MMBtu of heat input Existing coal-fired 10 CO 400 ppm by ≥ boiler volume on a dry basis corrected to 3% O2 Work/Management Practices 3. Work practice/management practices for specific boiler subcategories. Boiler Subcategory Work/Management Practice Existing or new coal (units with heat input Follow manufacturer’s recommended capacity of 10 MMBtu/hr or greater) procedures for start-up/shutdown Existing or new coal (units with a heat Tune up of boiler biennially input capacity of less than 10 MMBtu/hr) Existing or new biomass or oil unit Tune up of boiler biennially Existing coal, biomass, or oil with a Must conduct the one-time energy heat input capacity of 10 MMBtu/hr or assessment. greater) General compliance requirements (§63.11205): Any affected source must be operated and maintained, including associated air pollution
New coal-fired boiler ≥ 30 CO 400 ppm by volume on a dry corrected to 3% O2 New boiler ≥ 10 and < 30 PM 0.42 lb per MMBtu of heat input New coal-fired boiler ≥ 10 and < 30 Hg 0.0000048 lb per MMBtu of heat input New coal-fired boiler ≥ 10 and < 30 CO 400 ppm by volume on a dry basis corrected to 3% O2 New biomass-fired boiler ≥ 30 PM 0.03 lb per MMBtu of heat input New biomass-fired boiler ≥ 10 and < 30 PM 0.07 lb per MMBtu of heat input New oil-fired boiler ≥ 30 PM 0.03 lb per MMBtu of heat input New boiler ≥ 10 and < 30 PM 0.03 lb per MMBtu of heat input Existing coal-fired boiler ≥ 10 Hg 0.0000048 lb per MMBtu of heat input Existing coal-fired boiler ≥ 10 CO 400 ppm by volume on a dry basis corrected to 3% O2 Work/Management Practices 3. Work practice/management practices for specific boiler subcategories. Boiler Subcategory Work/Management Practice Existing or new coal (units with heat input capacity of 10 MMBtu/hr or greater) Follow manufacturer’s recommended procedures for start-up/shutdown Existing or new coal (units with a heat input capacity of less than 10 MMBtu/hr) Tune up of boiler biennially Existing or new biomass or oil unit Tune up of boiler biennially Existing coal, biomass, or oil with a heat input capacity of 10 MMBtu/hr or greater) Must conduct the one-time energy assessment. General compliance requirements (§63.11205): Any affected source must be operated and maintained, including associated air pollution
Boiler%20rule%20summary.docx