reduced pressure backflow preventer at each connection to the existing potable water system. Water, where available, shall be provided at no cost to the Contractor. Pressure, flow rate and volume of water shall be provided at conditions that will not disrupt the operations of the existing system, provide any facilities required to make the water source characteristics suitable for Contractor's intended use(s) without adversely impacting the existing system. 2. Maintain connections, pipe, fittings and fixtures and conserve wateruse so none is wasted. Failure to stop leakage or other wastes, or causing unacceptable adverse impacts on the existing system, will be cause for immediate revocation (at RE/COR's discretion) of use of water from the Cemetery's system and will require or result in the Contractor connection(s) being immediately shut-off. G. Fuel: The Government will furnish the Natural and/or LP gas required for: burner cleaning; normal initial burner setup and performing the specified burner tests through the applicable installed conveyance system. Fuel required for prolonged burner setup, adjustments, or modifications due to improper design or operation of burner, or control devices shall be furnished by the Contractor at Contractor's expense. SPEC WRITER NOTES: 1. Review this article with the Project Manager and determine the details of where and how the work by others is to be accomplished and coordinated. 2. Modify this Article as required so it is coordinated with drawings and specifications to result in a fully functional Telephone system, once all of the work by the Contractor and others is completed. 1.21 NEW TELEPHONE EQUIPMENT A. The contractor shall coordinate with the work of installation of telephone equipment by others. This work shall be completed before the building is turned over to VA. SPEC WRITER NOTES: 1. Delete TESTS when not applicable to project. Check with Team Mechanical and Electrical Engineers, coordinate and modify this Article accordingly. 1.22 TESTS A. Pretest mechanical and electrical equipment and systems and make corrections required for proper operation of such systems before
reduced pressure backflow preventer at each connection to the existing potable water system. Water, where available, shall be provided at no cost to the Contractor. Pressure, flow rate and volume of water shall be provided at conditions that will not disrupt the operations of the existing system, provide any facilities required to make the water source characteristics suitable for Contractor's intended use(s) without adversely impacting the existing system. 2. Maintain connections, pipe, fittings and fixtures and conserve wateruse so none is wasted. Failure to stop leakage or other wastes, or causing unacceptable adverse impacts on the existing system, will be cause for immediate revocation (at RE/COR's discretion) of use of water from the Cemetery's system and will require or result in the Contractor connection(s) being immediately shut-off. G. Fuel: The Government will furnish the Natural and/or LP gas required for: burner cleaning; normal initial burner setup and performing the specified burner tests through the applicable installed conveyance system. Fuel required for prolonged burner setup, adjustments, or modifications due to improper design or operation of burner, or control devices shall be furnished by the Contractor at Contractor's expense. SPEC WRITER NOTES: 1. Review this article with the Project Manager and determine the details of where and how the work by others is to be accomplished and coordinated. 2. Modify this Article as required so it is coordinated with drawings and specifications to result in a fully functional Telephone system, once all of the work by the Contractor and others is completed. 1.21 NEW TELEPHONE EQUIPMENT A. The contractor shall coordinate with the work of installation of telephone equipment by others. This work shall be completed before the building is turned over to VA. SPEC WRITER NOTES: 1. Delete TESTS when not applicable to project. Check with Team Mechanical and Electrical Engineers, coordinate and modify this Article accordingly. 1.22 TESTS A. Pretest mechanical and electrical equipment and systems and make corrections required for proper operation of such systems before
010001GenReqMajor.docx