manufacturers specification, however no less than annual inspection. Part 10—STANDBY POWER SUPPLY SYSTEM Standby power supply system E3.4, Clause 6 of Every six months Specification G3.8 test to ensure auxiliary power is operable. As per manufacturers recommendations or alternatively for diesel engines where the manufacturers recommendations are not available - test as prescribed in AS 1851 2012 – based on proving electrical load in lieu of flow/pressure for pump sets. Part 11—BUILDING CLEARANCE AND FIRE APPLIANCES Open space around large C2.3 to C2.4 Annual inspection to isolated buildings ensure that unobstructed access to buildings and firefighting facilities are maintained Vehicular access around large C2.3 to C2.4 Annual inspection to isolated buildings ensure clearance is maintained Part 12—MECHANICAL VENTILATION AND HOT, WARM AND COOLING WATER SYSTEMS Mechanical ventilation E2.2, F4.5, F4.11 AS 3666.2 -2011 systems incorporating cooling tower systems (other than a system serving only a single sole-occupancy unit in a Class 2 or 3 building or a Class 4 part of a building) Mechanical ventilation F2.7 AS 3666.2 -2011 systems incorporating hot and warm water systems (other than a system serving only a single sole-occupancy unit in a Class 2 or 3 building or a Class 4 part of a building)
manufacturers specification, however no less than annual inspection. Part 10—STANDBY POWER SUPPLY SYSTEM Standby power supply system E3.4, Clause 6 of Specification G3.8 Every six months test to ensure auxiliary power is operable. As per manufacturers recommendations or alternatively for diesel engines where the manufacturers recommendations are not available - test as prescribed in AS 1851 – 2012 based on proving electrical load in lieu of flow/pressure for pump sets. Part 11—BUILDING CLEARANCE AND FIRE APPLIANCES Open space around large isolated buildings C2.3 to C2.4 Annual inspection to ensure that unobstructed access to buildings and firefighting facilities are maintained Vehicular access around large isolated buildings C2.3 to C2.4 Annual inspection to ensure clearance is maintained Part 12—MECHANICAL VENTILATION AND HOT, WARM AND COOLING WATER SYSTEMS Mechanical ventilation systems incorporating cooling tower systems (other than a system serving only a single sole-occupancy unit in a Class 2 or 3 building or a Class 4 part of a building) E2.2, F4.5, F4.11 AS 3666.2 -2011 Mechanical ventilation systems incorporating hot and warm water systems (other than a system serving only a single sole-occupancy unit in a Class 2 or 3 building or a Class 4 part of a building) F2.7 AS 3666.2 -2011
2018-ESM-schedule.docx