> 60% AI 15 Min 12 hours 3 days P 5 min Humidity RH Unoccupied 12 DI COV 12 hours 3 days M N/A Override Hours Refrigerator 10 DI COV 12 hours 3 days C N/A Alarm min Damper 15 AO 12 hours 3 days N/A Position Minutes Heating coil 15 Valve AO 12 hours 3 days N/A Minutes Position 4-Pipe Fan Coil Trending and Alarms Testing Alarm Alarm Point Type Trend Trend Interval Type Range Delay Duration Duration Space 15 ±5°F 10 AI 12 hours 3 days P Temperature Minutes from SP min SA 15 ±5°F 10 AI 12 3 days P Temperature Minutes from SP min Pre-Filter 1 AI None None None M > SP Status hour 30 Water Sensor DI COV 12 hours 3 days M N/A Min Cooling Coil 15 Valve AO 12 3 days N/A Minutes Position Heating coil 15 Valve AO 12 hours 3 days N/A Minutes Position Status 30 Fan Coil DO COV 12 hours 3 days M <> min ON/OFF Command
Humidity AI 15 Min 12 hours 3 days P > 60% RH 5 min Unoccupied Override DI COV 12 hours 3 days M N/A 12 Hours Refrigerator Alarm DI COV 12 hours 3 days C N/A 10 min Damper Position AO 15 Minutes 12 hours 3 days N/A Heating coil Valve Position AO 15 Minutes 12 hours 3 days N/A 4-Pipe Fan Coil Trending and Alarms Point Type Interval Trend Duration Testing Trend Duration Type Alarm Range Alarm Delay Space Temperature AI 15 Minutes 12 hours 3 days P ±5°F from SP 10 min SA Temperature AI 15 Minutes 12 3 days P ±5°F from SP 10 min Pre-Filter Status AI None None None M > SP 1 hour Water Sensor DI COV 12 hours 3 days M N/A 30 Min Cooling Coil Valve Position AO 15 Minutes 12 3 days N/A Heating coil Valve Position AO 15 Minutes 12 hours 3 days N/A Fan Coil ON/OFF DO COV 12 hours 3 days M Status <> Command 30 min
019100.docx