Steam Station #2 1/3 AO 15 Min 12 Hours 3 days N/A Control Valve Position Steam Station #2 2/3 AO 15 Min 12 Hours 3 days N/A Control Valve Position Steam Station Bypass Valve AO 15 Min 12 Hours 3 days N/A Position HW Pump 1 DO COV 12 Hours 3 days N/A Start/Stop HW Pump 2 DO COV 12 Hours 3 days N/A Start/Stop HWR #1 Valve DO COV 12 Hours 3 days N/A HWR #2 Valve DO COV 12 3 days N/A Chilled Water System Trending and Alarms Testing Trend Alarm Alarm Alarm Point Type Trend Trend Interval Type Range Delay Duration Duration Chiller 1 15 Entering AI 12 Hours 3 days N/A Minutes Temperature Chiller 1 15 ±5°F 10 Leaving AI 12 Hours 3 days P Minutes from SP Min Temperature Chiller 1 15 AI 12 Hours 3 days N/A Flow Minutes Chiller 1 15 AI 12 Hours 3 days N/A Percent Load Minutes Chiller 1 KW 15 AI 12 Hours 3 days N/A Consumption Minutes Chiller 1 15 AI 12 Hours 3 days N/A Tonnage Minutes Chiller 2 15 Entering AI 12 Hours 3 days N/A Minutes Temperature Chiller 2 15 ±5°F 10 Leaving AI 12 Hours 3 days P Minutes from SP Min Temperature Chiller 2 15 AI 12 Hours 3 days N/A Flow Minutes
Steam Station #2 1/3 Control Valve Position AO 15 Min 12 Hours 3 days N/A Steam Station #2 2/3 Control Valve Position AO 15 Min 12 Hours 3 days N/A Steam Station Bypass Valve Position AO 15 Min 12 Hours 3 days N/A HW Pump 1 Start/Stop DO COV 12 Hours 3 days N/A HW Pump 2 Start/Stop DO COV 12 Hours 3 days N/A HWR #1 Valve DO COV 12 Hours 3 days N/A HWR #2 Valve DO COV 12 3 days N/A Chilled Water System Trending and Alarms Point Type Trend Interval Trend Duration Testing Trend Duration Alarm Type Alarm Range Alarm Delay Chiller 1 Entering Temperature AI 15 Minutes 12 Hours 3 days N/A Chiller 1 Leaving Temperature AI 15 Minutes 12 Hours 3 days P ±5°F from SP 10 Min Chiller 1 Flow AI 15 Minutes 12 Hours 3 days N/A Chiller 1 Percent Load AI 15 Minutes 12 Hours 3 days N/A Chiller 1 KW Consumption AI 15 Minutes 12 Hours 3 days N/A Chiller 1 Tonnage AI 15 Minutes 12 Hours 3 days N/A Chiller 2 Entering Temperature AI 15 Minutes 12 Hours 3 days N/A Chiller 2 Leaving Temperature AI 15 Minutes 12 Hours 3 days P ±5°F from SP 10 Min Chiller 2 Flow AI 15 Minutes 12 Hours 3 days N/A
019100.docx