Boiler commissioning procedure and maintenance 1. Fill in commissioning procedure” , pay an attention on your personal data and the „Boiler boiler specification. 2. Check the chimney draft, it must be around 15-20 In case of to large chimney draft, draft regulator should be used. If the chimney draft is to little it is necessary to rebuild the chimney or to install supporting fan ( chimney exhaust fan). 3. Check the section( hydraulic diameter of chimney cannot be smaller than the diameter of boiler flue ), chimney tightness and the connection of a chimney with a boiler flue. Connecting flue pipe with chimney should go up with at least 5º angle to lower pressure loss. Boiler should be connected with chimney with shortest possible section but with required minimal distance to boiler-room’s wall. 4. Ensure water to the boiler and then check tightness of hydraulic connections and the boiler body. In installation with forced flow of water; system need to be adjusted in case of lack of power – need to be assured minimal theoretical power collection from boiler under gravitation: 200 18 kw - 4 kw Orlan /Orligno 200 25 kW 5 kw – Orlan/Orligno 200 40 kw 8 kw – Orlan /Orligno 200 60 kw 15 kw – Orlan/Orligno 200 80 kw 25 kw – Orlan 96 kw 32 kW – Orlan 130 kw - 50 kW 5. Control correctness of electrical connections accordingly to the point “Electrical connections” 6. CONTROL THE CORRECT AIR SETTINGS: 6a). Control primary air settings: - unscrew the nut from the primary air baffle - set up the primary air baffle - screw in the nut holding the primary air baffle. Orlan/Orligno 200 18 kw 9 mm Orlan /Orligno 200 25 kW 9 mm 200 40 kw 16 mm Orlan /Orligno 200 60 kw 9 mm Orlan/Orligno 200 80 kw 9 mm Orlan 96 kw 22 mm Orlan 130 kw 22 mm
Boiler commissioning procedure and maintenance 1. Fill in „Boiler commissioning procedure” , pay an attention on your personal data and the boiler specification. 2. Check the chimney draft, it must be around 15-20 In case of to large chimney draft, draft regulator should be used. If the chimney draft is to little it is necessary to rebuild the chimney or to install supporting fan ( chimney exhaust fan). 3. Check the section( hydraulic diameter of chimney cannot be smaller than the diameter of boiler flue ), chimney tightness and the connection of a chimney with a boiler flue. Connecting flue pipe with chimney should go up with at least 5º angle to lower pressure loss. Boiler should be connected with chimney with shortest possible section but with required minimal distance to boiler-room’s wall. 4. Ensure water to the boiler and then check tightness of hydraulic connections and the boiler body. In installation with forced flow of water; system need to be adjusted in case of lack of power – need to be assured minimal theoretical power collection from boiler under gravitation: 200 18 kw - 4 kw Orlan /Orligno 200 25 kW – 5 kw Orlan/Orligno 200 40 kw – 8 kw Orlan /Orligno 200 60 kw – 15 kw Orlan/Orligno 200 80 kw – 25 kw Orlan 96 kw – 32 kW Orlan 130 kw - 50 kW 5. Control correctness of electrical connections accordingly to the point “Electrical connections” 6. CONTROL THE CORRECT AIR SETTINGS: 6a). Control primary air settings: - unscrew the nut from the primary air baffle - set up the primary air baffle - screw in the nut holding the primary air baffle. Orlan/Orligno 200 18 kw 9 mm Orlan /Orligno 200 25 kW 9 mm 200 40 kw 16 mm Orlan /Orligno 200 60 kw 9 mm Orlan/Orligno 200 80 kw 9 mm Orlan 96 kw 22 mm Orlan 130 kw 22 mm
Boiler%20Commissioning%20Angus%20Super.docx