The controller display have a high-contrast 3.5-inch (8.9 cm) screen with a resolution of 320x240 at 65,536 colors. The LCD brightness shall be a minimum of 200 lumens. Ethernet Jack The controller shall have a 100 Base-TX Ethernet jack. The jack shall accept RJ45 connectors. The jack shall be compliant with CAT5, CAT5e, and CAT6 Ethernet cable. The jack shall be RoHS compliant. The jack shall meet or exceed IEEE 802.3 standards. The jack shall have indicator LEDs. Power Specifications The controller shall come standard with a 120 VAC transformer, which has apparent power of 40 VA. The controller shall not exceed 30 VAC RMS output on the two-wire. The controller shall be able to support up to a 1.45 amp output current. Surge Protection The controller have 3 levels of surge protection built into the controller including a replaceable and fusible surge protection PC board. The controller shall have a minimum of a 1 picosecond surge response time. Environmental Specifications The controller be able to operate in environments ranging from 32°F to 140°F (0°C to 60°C) ambient temperatures. Controller Enclosures Enclosure Options Pedestal The pre-assembled enclosure shall be 17.38″ W x 36.25″ H x 12.63″ D (44 cm W x 92 cm H x 32 cm D). The pedestal enclosure be a NEMA type 3R rainproof enclosure manufactured entirely of 16-gauge 304-grade stainless steel. The main housing shall be louvered for cross flow ventilation. Filter screens shall cover all louvers
The controller display have a high-contrast 3.5-inch (8.9 cm) screen with a resolution of 320x240 at 65,536 colors. The LCD brightness shall be a minimum of 200 lumens. Ethernet Jack The controller shall have a 100 Base-TX Ethernet jack. The jack shall accept RJ45 connectors. The jack shall be compliant with CAT5, CAT5e, and CAT6 Ethernet cable. The jack shall be RoHS compliant. The jack shall meet or exceed IEEE 802.3 standards. The jack shall have indicator LEDs. Power Specifications The controller shall come standard with a 120 VAC transformer, which has apparent power of 40 VA. The controller shall not exceed 30 VAC RMS output on the two-wire. The controller shall be able to support up to a 1.45 amp output current. Surge Protection The controller have 3 levels of surge protection built into the controller including a replaceable and fusible surge protection PC board. The controller shall have a minimum of a 1 picosecond surge response time. Environmental Specifications The controller be able to operate in environments ranging from 32°F to 140°F (0°C to 60°C) ambient temperatures. Controller Enclosures Enclosure Options Pedestal The pre-assembled enclosure shall be 17.38″ W x 36.25″ H x 12.63″ D (44 cm W x 92 cm H x 32 cm D). The pedestal enclosure be a NEMA type 3R rainproof enclosure manufactured entirely of 16-gauge 304-grade stainless steel. The main housing shall be louvered for cross flow ventilation. Filter screens shall cover all louvers
BL-3200_V12_nonproprietary_spec.docx