APPENDIX 2 PRIMARY SIDE UTILITY METER SPECIFICATIONS Type of Metric Make/ Database Recording Protocol Division of UBCO meter Output interval & responsibility coordination duration Electrical KW, N/A BMS 15 minute BACnet Division 26 IT and KWh, Archiver Ongoing Modbus Facilities KVA TCP/IP Management MWh’s, N/A BMS 15 minute BACnet Division 20 IT and District Energy L/h, °C Archiver Ongoing MS/TP to install & Division Facilities supply Modbus 26 wiring Management and TCP/IP return gateway Gas Standard N/A BMS 15 minute Pulse Division 20 Facilities Cubic Archiver Ongoing output to install & Division Management Meters Electrical 26 networking (SCM) meter Water Cubic N/A BMS 15 minute Pulse Division 20 Facilities Meters Archiver Ongoing output to install & Division Management (M^3) Electrical 26 networking meter SECONDARY SIDE BMS METER SPECIFICATIONS System Metric Make/ Database Recording Protocol Division UBC Type Output Model interval & coordination Units duration Electrical KWh’s N/A BMS 15 minute Bacnet Division 26 Facilities Archiver 2 Year UDP/IP Management Gas SCM N/A BMS 15 minute Bacnet Division 20 Facilities Archiver 2 Year UDP/IP Management Thermal MWh’s, L/S N/A BMS 15 minute Bacnet Division 20 Facilities Energy °C supply Archiver 2 Year UDP/IP Management and return Water Cubic N/A BMS 15 minute Bacnet Division 20 Facilities Meters (M^3) Archiver 2 Year UDP/IP Management 2 Secondary Side BMS Meter Specifications ***END OF SECTION***
APPENDIX 2 PRIMARY SIDE UTILITY METER SPECIFICATIONS Type of meter Metric Output Make/ Database Recording interval & duration Protocol Division of responsibility UBCO coordination Electrical KW, KWh, KVA N/A BMS Archiver 15 minute Ongoing BACnet Modbus TCP/IP Division 26 IT and Facilities Management District Energy MWh’s, L/h, °C supply and return N/A BMS Archiver 15 minute Ongoing BACnet MS/TP to Modbus TCP/IP gateway Division 20 install & Division 26 wiring IT and Facilities Management Gas Standard Cubic Meters (SCM) N/A BMS Archiver 15 minute Ongoing Pulse output to Electrical meter Division 20 install & Division 26 networking Facilities Management Water Cubic Meters (M^3) N/A BMS Archiver 15 minute Ongoing Pulse output to Electrical meter Division 20 install & Division 26 networking Facilities Management SECONDARY SIDE BMS METER SPECIFICATIONS System Type Metric Output Units Make/ Model Database Recording interval & duration Protocol Division UBC coordination Electrical KWh’s N/A BMS Archiver 15 minute 2 Year Bacnet UDP/IP Division 26 Facilities Management Gas SCM N/A BMS Archiver 15 minute 2 Year Bacnet UDP/IP Division 20 Facilities Management Thermal Energy MWh’s, L/S °C supply and return N/A BMS Archiver 15 minute 2 Year Bacnet UDP/IP Division 20 Facilities Management Water Cubic Meters (M^3) N/A BMS Archiver 15 minute 2 Year Bacnet UDP/IP Division 20 Facilities Management 2 Secondary Side BMS Meter Specifications ***END OF SECTION***
019200-2018_Monitoring_Based_Commissioning_UBCO.docx