Chiller 1 DO COV 12 Hours 3 days N/A Enable Chiller 1 Iso-Valve DO COV 12 Hours 3 days N/A Command Chiller 2 DO COV 12 3 days N/A Enable Chiller 2 Iso-Valve DO COV 12 Hours 3 days N/A Command Refrigerant Exhaust Fan DO COV 12 Hours 3 days N/A Start / Stop Condenser Water System Trending and Alarms Testing Alarm Alarm Alarm Point Type Trend Interval Type Range Delay Duration Duration Chiller 1 15 Condenser AI 12 Hours 3 days N/A Minutes Entering Temp Chiller 1 15 Condenser AI 12 3 days N/A Minutes Leaving Temp Chiller 2 15 Condenser AI 12 Hours 3 days N/A Minutes Entering Temp Chiller 2 15 Condenser AI 12 Hours 3 days N/A Minutes Leaving Temp Cooling Tower 15 AI 12 Hours 3 days N/A 1 Supply Temp Minutes Cooling Tower 15 AI 12 3 days N/A 1 Return Temp Minutes Cooling Tower 15 10 AI 12 Hours 3 days P < 45 oF 1 Basin Temp Minutes Min Cooling Tower 15 AI 12 3 days N/A 2 Supply Temp Minutes Cooling Tower 15 AI 12 3 days N/A 2 Return Temp Minutes Cooling Tower 15 10 AI 12 3 days P < 45 oF 2 Basin Temp Minutes Min Condenser 15 Water Supply AI 12 Hours 3 days N/A Minutes Temp
Chiller 1 Enable DO COV 12 Hours 3 days N/A Chiller 1 Iso-Valve Command DO COV 12 Hours 3 days N/A Chiller 2 Enable DO COV 12 3 days N/A Chiller 2 Iso-Valve Command DO COV 12 Hours 3 days N/A Refrigerant Exhaust Fan Start / Stop DO COV 12 Hours 3 days N/A Condenser Water System Trending and Alarms Point Type Interval Duration Testing Trend Duration Alarm Type Alarm Range Alarm Delay Chiller 1 Condenser Entering Temp AI 15 Minutes 12 Hours 3 days N/A Chiller 1 Condenser Leaving Temp AI 15 Minutes 12 3 days N/A Chiller 2 Condenser Entering Temp AI 15 Minutes 12 Hours 3 days N/A Chiller 2 Condenser Leaving Temp AI 15 Minutes 12 Hours 3 days N/A Cooling Tower 1 Supply Temp AI 15 Minutes 12 Hours 3 days N/A Cooling Tower 1 Return Temp AI 15 Minutes 12 3 days N/A Cooling Tower 1 Basin Temp AI 15 Minutes 12 Hours 3 days P < 45 oF 10 Min Cooling Tower 2 Supply Temp AI 15 Minutes 12 3 days N/A Cooling Tower 2 Return Temp AI 15 Minutes 12 3 days N/A Cooling Tower 2 Basin Temp AI 15 Minutes 12 3 days P < 45 oF 10 Min Condenser Water Supply Temp AI 15 Minutes 12 Hours 3 days N/A
019100.docx