Provide supply Bathroom/Shower/ air with fans 20C and electric Laundry*(greater None Unit Heaters duct heaters. than 4 fixtures not 68 F Provide counting lavatories) exhaust fans Provide 7.2 C Storage None Unit heaters adequate 45 F ventilation 20C Provide ceiling DFAC (Dining Area) None Unit Heaters fans 68 F Provide 20C DFAC (Kitchen) None Unit Heaters adequate 68 F ventilation 25.6C 20C Comm rooms and Split pack heat pump Comm Maint units 78 F 68 F Medical Treatment 25.6C 20C Split pack heat pump Rooms and inpatient units 78 F 68 F rooms 25.6C 20C Classrooms (not pack heat pump training buildings) units 78 F 68 F 20C Gymnasium None Wood Heaters 68 F Provide POL Storage None none adequate ventilation Provide 7.2 C Arms Storage None Unit heater adequate 45 F ventilation Provide 12.7 C Vehicle Maintenance None Unit heaters adequate 55 F ventilation Enclosed Power Provide manually Plant Provide 12.8C adjusted recirculation None adequate (Office space to be air from radiator 55 F ventilation. provided with split exhaust. pack heat pump unit) 20C Provide ceiling Guard House None Wood Heaters fans 68 F 20C Provide ceiling Guard Tower None Wood Heaters fans 68 F Provide 12.7 C Well House None Unit heaters adequate 55 F ventilation
Bathroom/Shower/ Laundry*(greater than 4 fixtures not counting lavatories) None 20C 68 F Unit Heaters Provide supply air with fans and electric duct heaters. Provide exhaust fans Storage None 7.2 C 45 F Unit heaters Provide adequate ventilation DFAC (Dining Area) None 20C 68 F Unit Heaters Provide ceiling fans DFAC (Kitchen) None 20C 68 F Unit Heaters Provide adequate ventilation Comm rooms and Comm Maint 25.6C 78 F 20C 68 F Split pack heat pump units Medical Treatment Rooms and inpatient rooms 25.6C 78 F 20C 68 F Split pack heat pump units Classrooms (not training buildings) 25.6C 78 F 20C 68 F pack heat pump units Gymnasium None 20C 68 F Wood Heaters POL Storage None none Provide adequate ventilation Arms Storage None 7.2 C 45 F Unit heater Provide adequate ventilation Vehicle Maintenance None 12.7 C 55 F Unit heaters Provide adequate ventilation Enclosed Power Plant (Office space to be provided with split pack heat pump unit) None 12.8C 55 F Provide manually adjusted recirculation air from radiator exhaust. Provide adequate ventilation. Guard House None 20C 68 F Wood Heaters Provide ceiling fans Guard Tower None 20C 68 F Wood Heaters Provide ceiling fans Well House None 12.7 C 55 F Unit heaters Provide adequate ventilation
01%2010%2015%20Technical%20Requirements%208Oct12.docx