If shutter is not correctly set then loosen the wing nut and set the shutter in right position: 6d) CHECK BEFORE FIRST LIGHTNING UP IF THERE’S FREE FLOW OF AIR FROM PRIMARY AIR CHANNELS AND SECONDARY AIR HOLES IN NOZZLE BY TURNING ON THE FAN ON THE CONTROLLER. 7. Check the number and positioning of U firebricks in the bottom chamber (they must be placed along the chamber under the nozzle openings as shown on 2nd photo): Orlan/Orligno 200 18 kw 2 pcs Orlan /Orligno 200 25 kW 2 pcs Orlan/Orligno 200 40 kw 2 pcs Orlan /Orligno 200 60 kw 3 pcs Orlan/Orligno 200 80 kw 4 pcs Orlan 96 kw 4 pcs Orlan 130 kw 4 pcs 8. Check all threaded parts (hinges, door handles) if they’re greased with any mechanical grease (should be greased once a 2-3 weeks): 8.Light the boiler according to the point from the manual. „Lighting” 9. In case if fumes get out of the boiler door it is necessary to put out the boiler and start the boiler door and the hinges regulation. Both upper and lower door are fastened with two hinges. When the hinges are regulated the door must be taken off with fast , energetic uplifting. Next start regulation of the hinges accordingly to attached file. Caution! After the boiler door regulation it can be necessary to use force while closing door , after correct rope placing ( after few closings of the boiler door) closing will be much easier. After season maintenance activities: –heating
If shutter is not correctly set then loosen the wing nut and set the shutter in right position: 6d) CHECK BEFORE FIRST LIGHTNING UP IF THERE’S FREE FLOW OF AIR FROM PRIMARY AIR CHANNELS AND SECONDARY AIR HOLES IN NOZZLE BY TURNING ON THE FAN ON THE CONTROLLER. 7. Check the number and positioning of U firebricks in the bottom chamber (they must be placed along the chamber under the nozzle openings as shown on 2nd photo): Orlan/Orligno 200 18 kw 2 pcs Orlan /Orligno 200 25 kW 2 pcs Orlan/Orligno 200 40 kw 2 pcs Orlan /Orligno 200 60 kw 3 pcs Orlan/Orligno 200 80 kw 4 pcs Orlan 96 kw 4 pcs Orlan 130 kw 4 pcs 8. Check all threaded parts (hinges, door handles) if they’re greased with any mechanical grease (should be greased once a 2-3 weeks): 8.Light the boiler according to the point „Lighting” from the manual. 9. In case if fumes get out of the boiler door it is necessary to put out the boiler and start the boiler door and the hinges regulation. Both upper and lower door are fastened with two hinges. When the hinges are regulated the door must be taken off with fast , energetic uplifting. Next start regulation of the hinges accordingly to attached file. Caution! After the boiler door regulation it can be necessary to use force while closing door , after correct rope placing ( after few closings of the boiler door) closing will be much easier. After –heating season maintenance activities:
Boiler%20Commissioning%20Angus%20Orligno%20200.docx