Cooling Tower 1 Fan Start / DO COV 12 Hours 3 days N/A Stop Cooling Tower 2 Fan Start / DO COV 12 Hours 3 days N/A Stop Condenser Water Pump 1 DO COV 12 3 days N/A Start / Stop Condenser Water Pump 2 DO COV 12 Hours 3 days N/A Start / Stop Steam Boiler System Trending and Alarms Testing Trend Alarm Alarm Point Type Trend Interval Type Range Delay Duration Duration Boiler 1 15 ±5% 10 Steam AI 12 Hours 3 days P Minutes from SP Min Pressure Boiler 1 15 Steam AI 12 Hours 3 days N/A Minutes Temperature Boiler 1 Fire 15 AI 12 Hours 3 days N/A Signal Minutes Boiler 2 15 ±5% 10 Steam AI 12 Hours 3 days P Minutes from SP Min Pressure Boiler 2 15 Steam AI 12 Hours 3 days N/A Minutes Temperature Boiler 2 Fire 15 AI 12 Hours 3 days N/A Signal Minutes System Steam 15 ±5% 10 AI 12 Hours 3 days P Pressure Minutes from SP Min Boiler 1 DI COV 12 3 days N/A Enable Status Boiler 1 10 DI COV 12 Hours 3 days P <> Status min Command Boiler 1 DI COV 12 Hours 3 days C True 1 Min Alarm
Cooling Tower 1 Fan Start / Stop DO COV 12 Hours 3 days N/A Cooling Tower 2 Fan Start / Stop DO COV 12 Hours 3 days N/A Condenser Water Pump 1 Start / Stop DO COV 12 3 days N/A Condenser Water Pump 2 Start / Stop DO COV 12 Hours 3 days N/A Steam Boiler System Trending and Alarms Point Type Trend Interval Duration Testing Trend Duration Alarm Type Alarm Range Delay Boiler 1 Steam Pressure AI 15 Minutes 12 Hours 3 days P ±5% from SP 10 Min Boiler 1 Steam Temperature AI 15 Minutes 12 Hours 3 days N/A Boiler 1 Fire Signal AI 15 Minutes 12 Hours 3 days N/A Boiler 2 Steam Pressure AI 15 Minutes 12 Hours 3 days P ±5% from SP 10 Min Boiler 2 Steam Temperature AI 15 Minutes 12 Hours 3 days N/A Boiler 2 Fire Signal AI 15 Minutes 12 Hours 3 days N/A System Steam Pressure AI 15 Minutes 12 Hours 3 days P ±5% from SP 10 Min Boiler 1 Enable DI COV 12 3 days N/A Boiler 1 Status DI COV 12 Hours 3 days P Status <> Command 10 min Boiler 1 Alarm DI COV 12 Hours 3 days C True 1 Min
019100.docx