3. Boxes shall have adjustable covers. 4. Coverplates shall be removable and the proper depth for and coordinated with the floor coverings and finishes. D. Service fittings: 1. Shall be the low compact type, satinfinished aluminum. 2. Power outlets shall have receptacles as indicated and as specified in Section 26 27 26, WIRING DEVICES. 3. Telecommunications outlets shall have dimensions which are approximately the same as the power outlets. Data, telephone and other telecommunications jacks shall be as required by the applicable specifications. 4. Include mounting, hinged cover, and trim to support and provide access to connector, jack, or receptacle devices mounted flush with floor within insert. SPEC WRITER NOTE: Delete between // // if not applicable to project. Also delete any other item or paragraph not applicable to the section and renumber the paragraphs. PART 3 EXECUTION 3.1 INSTALLATION A. Installation shall be in accordance with the NEC, manufacturers recommendations, and as shown on the drawings. B. Connect the raceways, boxes, and fittings so they are mechanically firm, electrically continuous, and watertight. C. Align, level, and make the raceways parallel to or at right angles with the building walls. D. Level raceways with floor slab, including height adjustments for floor finishes. E. Raceways shall be free from burrs, sharp edges, dents and other defects. F. Cap or plug unused openings with standard fittings. G. Fasten the junction boxes firmly in place to prevent their movement during pouring of the slabs. H. Raceway systems be supported at not more than 1500 mm (five feet) on centers. I. Specific methods of installing the raceways shall be demonstrated to and approved by the //Resident Engineer// //COTR// prior to performing the installation.
3. Boxes shall have adjustable covers. 4. Coverplates shall be removable and the proper depth for and coordinated with the floor coverings and finishes. D. Service fittings: 1. Shall be the low compact type, satinfinished aluminum. 2. Power outlets shall have receptacles as indicated and as specified in Section 26 27 26, WIRING DEVICES. 3. Telecommunications outlets shall have dimensions which are approximately the same as the power outlets. Data, telephone and other telecommunications jacks shall be as required by the applicable specifications. 4. Include mounting, hinged cover, and trim to support and provide access to connector, jack, or receptacle devices mounted flush with floor within insert. SPEC WRITER NOTE: Delete between // // if not applicable to project. Also delete any other item or paragraph not applicable to the section and renumber the paragraphs. PART 3 EXECUTION 3.1 INSTALLATION A. Installation shall be in accordance with the NEC, manufacturers recommendations, and as shown on the drawings. B. Connect the raceways, boxes, and fittings so they are mechanically firm, electrically continuous, and watertight. C. Align, level, and make the raceways parallel to or at right angles with the building walls. D. Level raceways with floor slab, including height adjustments for floor finishes. E. Raceways shall be free from burrs, sharp edges, dents and other defects. F. Cap or plug unused openings with standard fittings. G. Fasten the junction boxes firmly in place to prevent their movement during pouring of the slabs. H. Raceway systems be supported at not more than 1500 mm (five feet) on centers. I. Specific methods of installing the raceways shall be demonstrated to and approved by the //Resident Engineer// //COTR// prior to performing the installation.
VA%2026%2005%2039.docx