If equipped with lubricating oil charge, old oil, and fill with new to full mark on sight indicator (also fill bulb). Refer to for inspection and SM SM SM maintenance requirements of As required electric motors. Vertical Inline Pumps (Section 3-8.1.2) Check for proper operations while SM SM SM pump is in use. Check suction and discharge pressure gauges for abnormal readings. Check for unusual noise, vibration, overheating of bearings. Quarterly Tighten or replace loose, missing or damaged nuts, bolts, or screws. Inspect suction and discharge isolation dampeners for misalignment and wear. Vertical Inline Inspect mechanical if possible, for proper operating temperature, drips, leaks and dirt. alignment, clearances, and SM SM SM rotation of shaft and coupler Annually (requires removal of coupler shroud or cover). Lubricate pump bearings. to for inspection and SM SM SM As required maintenance requirements of electric motors. Vertical Turbine/Submerged Turbine (Section 3-8.1.3) Check for proper operations while SM SM SM Quarterly pump is in use. Check discharge Vertical pressure gauge for abnormal readings.
If equipped with lubricating oil charge, old oil, and fill with new to full mark on sight indicator (also fill bulb). Refer to for inspection and maintenance requirements of electric motors. As required SM SM SM Vertical Inline Pumps (Section 3-8.1.2) Vertical Inline Check for proper operations while pump is in use. Check suction and discharge pressure gauges for abnormal readings. Check for unusual noise, vibration, overheating of bearings. Tighten or replace loose, missing or damaged nuts, bolts, or screws. Inspect suction and discharge isolation dampeners for misalignment and wear. Inspect mechanical if possible, for proper operating temperature, drips, leaks and dirt. Quarterly SM SM SM alignment, clearances, and rotation of shaft and coupler (requires removal of coupler shroud or cover). Lubricate pump bearings. Annually SM SM SM to for inspection and maintenance requirements of electric motors. As required SM SM SM Vertical Turbine/Submerged Turbine (Section 3-8.1.3) Vertical Check for proper operations while pump is in use. Check discharge pressure gauge for abnormal readings. Quarterly SM SM SM
ufc_3_460_03_appendix_c.docx