E.B.7 The Generator Owner The Generator Owner did The Generator Owner The Generator did not provide all of not provide all of the data did not provide all of Owner did not the data required in required in E.B.7, on any the data required in provide all of the E.B.7, on any one two occasions. E.B.7, on any three data required in occasion. occasions. E.B.7, on any four or more occasions. The following table replaces the MOD-026 Attachment 1, Excitation Control System or Plant Volt/Var Model Verification Periodicity table in its entirety, and is only applicable to the Western Interconnection. MOD-026 Attachment 1 This Table is Applicable Only to the Western Interconnection. Row Excitation Control System or Plant Volt/Var Function Model Verification Periodicity Number Verification Condition Required Action Establishing the initial verification date Transmit the verified model, documentation and data for an applicable unit. to the Transmission Planner on or before the Effective Date. (Requirement R2) Row 4 applies when calculating generation fleet compliance during the five-year implementation period. See Section E.A.5 of this variance for Effective Dates. 2 Subsequent verification for an applicable Transmit the verified model, documentation and data unit. to the Transmission Planner on or before the five-year anniversary of the last transmittal, per Note 1 at the end (Requirement R2) of this table. 3 Initial verification for a new applicable Transmit the verified model, documentation and data unit or for an existing applicable unit to the Transmission Planner within 365 calendar days with new excitation control system or after the commissioning date. plant volt/var control function equipment installed. (Requirement R2)
E.B.7 The Generator Owner did not provide all of the data required in E.B.7, on any one occasion. The Generator Owner did not provide all of the data required in E.B.7, on any two occasions. The Generator Owner did not provide all of the data required in E.B.7, on any three occasions. The Generator Owner did not provide all of the data required in E.B.7, on any four or more occasions. The following table replaces the MOD-026 Attachment 1, Excitation Control System or Plant Volt/Var Model Verification Periodicity table in its entirety, and is only applicable to the Western Interconnection. Row Number MOD-026 Attachment 1 This Table is Applicable Only to the Western Interconnection. Excitation Control System or Plant Volt/Var Function Model Verification Periodicity Verification Condition Required Action Establishing the initial verification date for an applicable unit. (Requirement R2) Transmit the verified model, documentation and data to the Transmission Planner on or before the Effective Date. Row 4 applies when calculating generation fleet compliance during the five-year implementation period. See Section E.A.5 of this variance for Effective Dates. 2 Subsequent verification for an applicable unit. (Requirement R2) Transmit the verified model, documentation and data to the Transmission Planner on or before the five-year anniversary of the last transmittal, per Note 1 at the end of this table. 3 Initial verification for a new applicable unit or for an existing applicable unit with new excitation control system or plant volt/var control function equipment installed. (Requirement R2) Transmit the verified model, documentation and data to the Transmission Planner within 365 calendar days after the commissioning date.
WECC-0101%20MOD-26%20for%20Reballot%20-%20Variance%20Only%20-%20From%20Tech%20Writer.docx