Diagrams shall have their terminals identified to facilitate installation, operation and maintenance. Provide a listing of recommended replacement for keeping in stock supply, including sources of supply, for equipment. Include in the listing belts for equipment: Belt manufacturer, model number, size and style, and distinguished whether of multiple belt sets. Boiler Plant Maintenance Data and Operating Instructions: Provide //4// // // bound copies or 2 electronic versions on CD //DVD//. Deliver to COR not less than 30 days prior to completion of a phase or final inspection. Include all new and temporary equipment and all elements of each assembly. Data sheet on each device listing model, size, capacity, pressure, speed, horsepower, pump impeller size, other data. Manufacturer’s installation, maintenance, repair, and operation instructions for each device. Include assembly drawings and parts lists. Include operating precautions and reasons for precautions. Lubrication instructions including type and quantity of lubricant. Schematic diagrams and wiring diagrams of all control systems corrected to include all field modifications. Description of boiler firing and operating sequence including description of relay and interlock positions at each part of the sequence. Set points of all interlock devices. Trouble-shooting for control systems. of the combustion control system. procedures. system programming information for parameters, such as set points, that do not require services of an experienced technician. written instructions that are specific for the system installed on testing all safety devices. The instructions should be in the same format and in compliance and equivalent to the VHA Boiler Plant Safety Devices Testing Manual for each test. All safety devices listed in the manual shall be tested and documentation provided certifying completion. Provide copies of approved HVAC equipment submittals to the TAB //and Commissioning// Subcontractor.
Diagrams shall have their terminals identified to facilitate installation, operation and maintenance. Provide a listing of recommended replacement for keeping in stock supply, including sources of supply, for equipment. Include in the listing belts for equipment: Belt manufacturer, model number, size and style, and distinguished whether of multiple belt sets. Boiler Plant Maintenance Data and Operating Instructions: Provide //4// // // bound copies or 2 electronic versions on CD //DVD//. Deliver to COR not less than 30 days prior to completion of a phase or final inspection. Include all new and temporary equipment and all elements of each assembly. Data sheet on each device listing model, size, capacity, pressure, speed, horsepower, pump impeller size, other data. Manufacturer’s installation, maintenance, repair, and operation instructions for each device. Include assembly drawings and parts lists. Include operating precautions and reasons for precautions. Lubrication instructions including type and quantity of lubricant. Schematic diagrams and wiring diagrams of all control systems corrected to include all field modifications. Description of boiler firing and operating sequence including description of relay and interlock positions at each part of the sequence. Set points of all interlock devices. Trouble-shooting for control systems. of the combustion control system. procedures. system programming information for parameters, such as set points, that do not require services of an experienced technician. written instructions that are specific for the system installed on testing all safety devices. The instructions should be in the same format and in compliance and equivalent to the VHA Boiler Plant Safety Devices Testing Manual for each test. All safety devices listed in the manual shall be tested and documentation provided certifying completion. Provide copies of approved HVAC equipment submittals to the TAB //and Commissioning// Subcontractor.
VA%2023%2005%2010.docx