Tables Table 4below sets out the minimum clearances that apply for the Shared User's Equipment relevant to this section of the Code. Table 4 - Asset Clearances on Pole from Shared User’s Equipment to Distribution Company’s Assets Item of Electricity Distribution System Insulated LV Wiring (including LV Bare LV insulated Earth & 6.6, 11, Mains & ABC 66 kV Shared User's LV Supervisory 22 kV Services FSD FOLCB Mains O/H Equipment services) O/H O/H O/H O/H Circuit & UG Circuits Circuits Circuit Circuit Cable dressed on the pole RF Antenna is (a) below 100 380 1000 1000 1000 600 2400 3900 (Excluding Macrocells) RF Not Not Not Not Not Not Not (b) Antenna is 100 Allowed Allowed Allowed Allowed Allowed Allowed Allowed Above
Tables Table 4below sets out the minimum clearances that apply for the Shared User's Equipment relevant to this section of the Code. Table 4 - Asset Clearances on Pole from Shared User’s Equipment to Distribution Company’s Assets Shared User's Equipment Item of Electricity Distribution System Insulated LV Wiring (including insulated LV services) & UG Cable dressed on the pole Earth & Supervisory O/H Circuits LV Bare Mains & Services O/H Circuit FSD FOLCB LV ABC Mains O/H Circuit 6.6, 11, 22 kV O/H Circuits 66 kV O/H Circuit (a) RF Antenna is below (Excluding Macrocells) 100 380 1000 1000 1000 600 2400 3900 (b) RF Antenna is Above 100 Not Allowed Not Allowed Not Allowed Not Allowed Not Allowed Not Allowed Not Allowed
VESI_Shared_Use_of_Poles_Code-For_Industry_Review.docx