transmission shall be programmable based on armed state of the controller. These custom points shall include: Area Keyswitch arming/disarming • Tour Point • Garage Delay • Entry/ Exit Route • False Alarm Prevention point • Entry/ Exit Route w/False Alarm Prevention • Work Late Button • Activity Monitor (input point used with Activity- Based Arming / Alarm on No Activity area • programming) Command Point (input programmed to carry out specific system, door or area commands • upon activation of the point). Each controller shall support up to 128 outputs. An output shall be configured to be activated • based upon the following criteria: System wide events • Area events • Specific door events • Specific input point events • Pressing a function key on an LCD keypad • System type events activate a pre-programmed output based upon any one of the following • actions occurring across all areas, points or doors within the controller’s system configuration: RS485 communications failure • A/C failure Ground • • Partially on No phone line detected • • Report delay Fully on • • Time lost off • • Time changed In • • Program edit Siren on • • Program error Digital trouble • • Fuse failure Was in alarm • • Application module trouble Point bypassed • • Duress PIN Fire • • Door locked out Hold-up • • Forced entry Auxiliary alert • • Door held open Supervisory • • Door tamper Vault • • Door open Burglary • • Door secure Trouble • • Door sensor trouble Low/No battery • • Area type events activate a pre-programmed output based upon any one of the following • actions occurring within a defined area: Alarm • Was in Sonalert tones on stay) • • Sonalert (no exit tones on fire • • stay)
transmission shall be programmable based on armed state of the controller. These custom points shall include: • Area Keyswitch arming/disarming • Tour Point • Garage Delay • Entry/ Exit Route • False Alarm Prevention point • Entry/ Exit Route w/False Alarm Prevention • Work Late Button • Activity Monitor (input point used with Activity- Based Arming / Alarm on No Activity area programming) • Command Point (input programmed to carry out specific system, door or area commands upon activation of the point). • Each controller shall support up to 128 outputs. An output shall be configured to be activated based upon the following criteria: • System wide events • Area events • Specific door events • Specific input point events • Pressing a function key on an LCD keypad • System type events activate a pre-programmed output based upon any one of the following actions occurring across all areas, points or doors within the controller’s system configuration: • RS485 communications failure • Ground • Partially on • Fully on • off • In • Siren on • Digital trouble • Was in alarm • Point bypassed • Fire • Hold-up • Auxiliary alert • Supervisory • Vault • Burglary • Trouble • Low/No battery • A/C failure • No phone line detected • Report delay • Time lost • Time changed • Program edit • Program error • Fuse failure • Application module trouble • Duress PIN • Door locked out • Forced entry • Door held open • Door tamper • Door open • Door secure • Door sensor trouble • Area type events activate a pre-programmed output based upon any one of the following actions occurring within a defined area: • Alarm • Was in • fire • Sonalert tones on stay) • Sonalert (no exit tones on stay)
Verex%20AE%20Guide%20Specification%20V4%2091.docx