UIP completion file checklist Example Northern Gas Networks 300101010 reference UIP reference TEST101 Plot address Average Company Ltd, 1 Main Road, Harrogate, HG1 1AA Job type New connection POC grids 447261, 411683 Asset(s) length(s) - 90mm MDPE LP Main (72M) X 63mm MDPE LP Service (6M) Abandoned and newly laid (with clear differentiation between main(s) and service(s)) Valve card(s) and valve 1 SIV - Valve card included Valve Number 1576 Donkin – – numbers 0.25 turns clockwise Test certificates Test Duration 00:25 - 350MBAR (Main) and 00:05 100MBAR (service) Tested / Commissioned by Jane Doe of UIP Corporate MPRN(s) 9353134701 DR8? DR8 Error Policy Document Included Asset found to not be – material on maps. Ductile Iron (not steel) and main found 5m closer to kerb RO/NRO/G17 RO Included Variations Minor variation in regards to the length of the main, 5 extra meters of main laid on site. Caused due to parent main not being in location as per maps (please see DR8) Pipe orientation(s) Horizontal below / Horizontal below Method(s) laid Open cut / Open cut Joint type(s) Electrofusion / Electrofusion ASLAID Included 1:1250 scale – Connection type(s) Encirclement Tee and reducer (connection depth 0.7) / HVTT (Connection Point depth 0.7) Pressure(s) LP Number of plots 1 Asset material MDPE Depth(s) Encirclement tee and reducer (connection point depth 0.7m) / HVTT (connection point depth 0.7m) Main asset depth – 0.7m / service asset depth 0.8m Property Types (D/I/C) Commercial
UIP completion file checklist Example Northern Gas Networks reference 300101010 UIP reference TEST101 Plot address Average Company Ltd, 1 Main Road, Harrogate, HG1 1AA Job type New connection POC grids 447261, 411683 Asset(s) length(s) - Abandoned and newly laid (with clear differentiation between main(s) and service(s)) 90mm MDPE LP Main (72M) X 63mm MDPE LP Service (6M) Valve card(s) and valve numbers 1 SIV - Valve card included – Valve Number 1576 – Donkin 0.25 turns clockwise Test certificates Test Duration 00:25 - 350MBAR (Main) and 00:05 100MBAR (service) Tested / Commissioned by Jane Doe of UIP Corporate MPRN(s) 9353134701 DR8? DR8 Error Policy Document Included – Asset found to not be material on maps. Ductile Iron (not steel) and main found 5m closer to kerb RO/NRO/G17 RO Included Variations Minor variation in regards to the length of the main, 5 extra meters of main laid on site. Caused due to parent main not being in location as per maps (please see DR8) Pipe orientation(s) Horizontal below / Horizontal below Method(s) laid Open cut / Open cut Joint type(s) Electrofusion / Electrofusion ASLAID Included – 1:1250 scale Connection type(s) Encirclement Tee and reducer (connection depth 0.7) / HVTT (Connection Point depth 0.7) Pressure(s) LP Number of plots 1 Asset material MDPE Depth(s) Encirclement tee and reducer (connection point depth 0.7m) / HVTT (connection point depth 0.7m) – Main asset depth 0.7m / service asset depth 0.8m Property Types (D/I/C) Commercial
UIP-completion-file-checklist.docx