months. item 1, 2 or 3 (12 calendar month requirement) but did so in more than 13 calendar months but less than or equal to 14 calendar months. Each Transmission Owner shall provide its The Transmission The Transmission The Transmission The Transmission MOD-025-2 R3. Transmission Planner with verification of the Owner verified and Owner verified and Owner verified and Owner verified Reactive Power capability of its applicable recorded the Reactive recorded the recorded the Reactive and recorded the Facilities as follows: Power capability of its Reactive Power Power capability of Reactive Power [Please see the applicable capability of an applicable capability of its standard for more information] synchronous its applicable synchronous applicable condenser, but synchronous condenser unit, but synchronous submitted the data to condenser, but submitted the data to its condenser, but its Transmission submitted the Transmission submitted the data to Planner more than 90 data to its Planner more than 150 its Transmission calendar days, but Transmission calendar days, but Planner more than 180 within 120 calendar Planner more than within 180 calendar calendar days of the days, of the date the 120 calendar days, days, of the date the date the data is data is recorded for a but within 150 data is recorded for a recorded for a staged staged test calendar days, of the staged test or the date test or the date or the date the data is date the data is the data is selected for the data is selected for selected for recorded for a verification using verification using verification staged historical operational historical operational using historical test or the date the data. data. operational data is OR OR data. selected for The Transmission The Transmission OR verification using Owner verified the Owner failed to The Transmission historical Reactive Power verify the Reactive Owner verified the operational capability, per Power capability, per Reactive Power data. Attachment 1 Attachment 1 of an capability, per OR and submitted the data applicable Attachment 1 and The Transmission but was synchronous submitted the data but Owner verified the missing 67 to 99 condenser unit. was missing 1 to up to Reactive Power percent of the OR and including 33 capability, per data. The Transmission percent of the data. Attachment 1 OR Owner performed
months. item 1, 2 or 3 (12 calendar month requirement) but did so in more than 13 calendar months but less than or equal to 14 calendar months. MOD-025-2 R3. Each Transmission Owner shall provide its Transmission Planner with verification of the Reactive Power capability of its applicable Facilities as follows: [Please see the standard for more information] The Transmission Owner verified and recorded the Reactive Power capability of its applicable synchronous condenser, but submitted the data to its Transmission Planner more than 90 calendar days, but within 120 calendar days, of the date the data is recorded for a staged test or the date the data is selected for verification using historical operational data. OR The Transmission Owner verified the Reactive Power capability, per Attachment 1 and submitted the data but was missing 1 to up to and including 33 percent of the data. The Transmission Owner verified and recorded the Reactive Power capability of its applicable synchronous condenser, but submitted the data to its Transmission Planner more than 120 calendar days, but within 150 calendar days, of the date the data is recorded for a staged test or the date the data is selected for verification using historical operational data. OR The Transmission Owner verified the Reactive Power capability, per Attachment 1 The Transmission Owner verified and recorded the Reactive Power capability of an applicable synchronous condenser unit, but submitted the data to its Transmission Planner more than 150 calendar days, but within 180 calendar days, of the date the data is recorded for a staged test or the date the data is selected for verification using historical operational data. OR The Transmission Owner verified the Reactive Power capability, per Attachment 1 and submitted the data but was missing 67 to 99 percent of the data. OR The Transmission Owner verified and recorded the Reactive Power capability of its applicable synchronous condenser, but submitted the data to its Transmission Planner more than 180 calendar days of the date the data is recorded for a staged test or the date the data is selected for verification using historical operational data. OR The Transmission Owner failed to verify the Reactive Power capability, per Attachment 1 of an applicable synchronous condenser unit. OR The Transmission Owner performed
VSL_Matrix_Complete_2016_01_01.docx