10 Introduce a system of ensuring the commencement preparedness’ at the beginning of each batch of production of each product by including appropriate endorsement by shift in charge in BMR of each batch. This shall necessarily cover relevant safety precautions like PPE, Training, Pep Talks, raw material labeling, equipment readiness etc.. P. Fire Safety Replace the existing plastic pipes with electrically conductive pipes for 1. transferring of chemicals from reactors to centrifuges etc. Extend the vents of centrifuges, reactor condensers, tray driers extended to 3 outside the building as they were found terminated inside (vents are inside in PB-III) Provide earthling to GLRs by using tantalum plugs and furnish the design data 4 of the same. Maintain the record for the periodical measurement for earthing and bonding 10 continuity Provide a Nitrogen generation plant in the factory arrange for Vacuum breaking 11 with Nitrogen, Nitrogen blanketing centrifuges, filters and storage tanks etc Provide flash back arresters to the vents of condensers, centrifuges, storage 13 tanks, charging tanks, Dump tanks etc Ensure the wheels of the trolleys , ladders etc are of conductive and anti friction 17 type Provide fire/smoke detection arrangements at all strategic locations and connect 20 them with alarm systems. Identify all process in total range of products mentioned in CFO where in 21 serious explosion and flash fire hazards are present and propose them only in a segregated buildings The equipment having serious fire hazard like reactors, centrifuges etc shall be 22 isolated from rest of the work place. Provide electrical interlocking to the dampers in ventilation with smoke/ heat 23 detection system 31 Provide roof mounted hydrant rings over the equipment with flammable materials or DCP flooding systems if water is not recommended and connect them to fire/ heat detection systems in order to get automatically pressed into service in case of a fire. (Provide water sprinkling system to reactors in PB-II and PB-III, and also to the remaining two bays in the ware house) 34 The fire fighting systems in the factory are not in proportion to the fire load potential in the factory thereby the factory is not self sufficient. Get the fire safety audit done through an expert third party and submit the compliance report Q. Storage and Handling Provide properly anchored & independently (without resting on the tanks) 3 supported access and working platforms to PPFRP and HDPE storage tanks (non-metallic material)
10 Introduce a system of ensuring the commencement preparedness’ at the beginning of each batch of production of each product by including appropriate endorsement by shift in charge in BMR of each batch. This shall necessarily cover relevant safety precautions like PPE, Training, Pep Talks, raw material labeling, equipment readiness etc.. P. Fire Safety 1. Replace the existing plastic pipes with electrically conductive pipes for transferring of chemicals from reactors to centrifuges etc. 3 Extend the vents of centrifuges, reactor condensers, tray driers extended to outside the building as they were found terminated inside (vents are inside in PB-III) 4 Provide earthling to GLRs by using tantalum plugs and furnish the design data of the same. 10 Maintain the record for the periodical measurement for earthing and bonding continuity 11 Provide a Nitrogen generation plant in the factory arrange for Vacuum breaking with Nitrogen, Nitrogen blanketing centrifuges, filters and storage tanks etc 13 Provide flash back arresters to the vents of condensers, centrifuges, storage tanks, charging tanks, Dump tanks etc 17 Ensure the wheels of the trolleys , ladders etc are of conductive and anti friction type 20 Provide fire/smoke detection arrangements at all strategic locations and connect them with alarm systems. 21 Identify all process in total range of products mentioned in CFO where in serious explosion and flash fire hazards are present and propose them only in a segregated buildings 22 The equipment having serious fire hazard like reactors, centrifuges etc shall be isolated from rest of the work place. 23 Provide electrical interlocking to the dampers in ventilation with smoke/ heat detection system 31 Provide roof mounted hydrant rings over the equipment with flammable materials or DCP flooding systems if water is not recommended and connect them to fire/ heat detection systems in order to get automatically pressed into service in case of a fire. (Provide water sprinkling system to reactors in PB-II and PB-III, and also to the remaining two bays in the ware house) 34 The fire fighting systems in the factory are not in proportion to the fire load potential in the factory thereby the factory is not self sufficient. Get the fire safety audit done through an expert third party and submit the compliance report Q. Storage and Handling 3 Provide properly anchored & independently (without resting on the tanks) supported access and working platforms to PPFRP and HDPE storage tanks (non-metallic material)
Vasant%20Chemicals.docx