Lubrication devices and grease fittings. Copper, brass, aluminum, stainless steel and bronze surfaces. Valve stems and rotating shafts. Pressure gauges and thermometers. Glass. Nameplates. Control and instrument panels shall be cleaned, damaged surfaces repaired, and shall be touched-up with matching paint obtained from panel manufacturer. Pumps, motors, steel and cast-iron bases, and coupling guards shall be cleaned, and shall be touched-up with the same paint type and color as utilized by the pump manufacturer. Temporary Facilities: Apply paint to surfaces that do not have existing finish coats. This may include painting exposed metals where hangers were removed or where equipment was moved or removed. Paint shall withstand the following temperatures without peeling or discoloration: Condensate and Feedwater: 38 degrees C (100 degrees F) on insulation jacket surface and 121 degrees C (250 degrees F) on metal pipe surface. Steam: 52 degrees C (125 degrees F) on insulation jacket surface and 190 degrees C (374 degrees F) on metal pipe surface. Final result shall be smooth, even-colored, even-textured factory finish on all items. Completely repaint the entire piece of equipment if necessary to achieve this. Lead based paints are prohibited. IDENTIFICATION SIGNS Provide laminated plastic signs, with engraved lettering not less than 5 mm (3/16 inch) high, designating functions, for all equipment, switches, motor controllers, relays, meters, control devices, including automatic control valves. Nomenclature and identification symbols shall correspond to that used in maintenance manual, and in diagrams specified elsewhere. Attach by chain, adhesive, or screws. Factory Built Equipment: Metal plate, securely attached, with name and address of manufacturer, serial number, model number, size, performance. Pipe Identification: Refer to Section 09 91 00, PAINTING.
Lubrication devices and grease fittings. Copper, brass, aluminum, stainless steel and bronze surfaces. Valve stems and rotating shafts. Pressure gauges and thermometers. Glass. Nameplates. Control and instrument panels shall be cleaned, damaged surfaces repaired, and shall be touched-up with matching paint obtained from panel manufacturer. Pumps, motors, steel and cast-iron bases, and coupling guards shall be cleaned, and shall be touched-up with the same paint type and color as utilized by the pump manufacturer. Temporary Facilities: Apply paint to surfaces that do not have existing finish coats. This may include painting exposed metals where hangers were removed or where equipment was moved or removed. Paint shall withstand the following temperatures without peeling or discoloration: Condensate and Feedwater: 38 degrees C (100 degrees F) on insulation jacket surface and 121 degrees C (250 degrees F) on metal pipe surface. Steam: 52 degrees C (125 degrees F) on insulation jacket surface and 190 degrees C (374 degrees F) on metal pipe surface. Final result shall be smooth, even-colored, even-textured factory finish on all items. Completely repaint the entire piece of equipment if necessary to achieve this. Lead based paints are prohibited. IDENTIFICATION SIGNS Provide laminated plastic signs, with engraved lettering not less than 5 mm (3/16 inch) high, designating functions, for all equipment, switches, motor controllers, relays, meters, control devices, including automatic control valves. Nomenclature and identification symbols shall correspond to that used in maintenance manual, and in diagrams specified elsewhere. Attach by chain, adhesive, or screws. Factory Built Equipment: Metal plate, securely attached, with name and address of manufacturer, serial number, model number, size, performance. Pipe Identification: Refer to Section 09 91 00, PAINTING.
VA%2023%2005%2011.docx