Inspect valve exterior for corrosion and tightness of bolts. Repaint and retighten as required Globe Valves (Section 6-6.2.7) Open and close valve to check for SM SM SM ease of operation. Adjust packing per manufacturer’s specifications as needed. Globe Valves Quarterly Inspect valve exterior for corrosion and tightness of bolts. Repaint/tighten as required Valves (Section 6-6.2.8) Use external test lever to make Quarterly SM SM SM sure the valve is not sticking if equipped. If a check valve is suspected of not checking and cannot be serviced in place, it Check must be removed from the piping Valves system and serviced in a shop. Inspect valve exterior for corrosion and tightness of bolts. Repaint and retighten as required. Line Blanks, Ring Spacers, and Spectacle Blinds (Section 6-6.2.9) Inspect exposed side of spectacle SM SM SM blinds. The exposed side must be Line Blanks, kept clean and free of corrosion. Ring Spacers, Spectacle blinds should be Quarterly and inspected to ensure they are Spectacle installed with the correct Blinds orientation for the desired flow or no-flow condition. Manual Gear Operators (Section 6-6.2.10) Manual Valve SM SM SM Lubricate gear driven operators Gear Quarterly and check for smooth operation Operators
Inspect valve exterior for corrosion and tightness of bolts. Repaint and retighten as required Globe Valves (Section 6-6.2.7) Globe Valves Open and close valve to check for ease of operation. Adjust packing per manufacturer’s specifications as needed. Inspect valve exterior for corrosion and tightness of bolts. Repaint/tighten as required Quarterly SM SM SM Valves (Section 6-6.2.8) Check Valves Use external test lever to make sure the valve is not sticking if equipped. If a check valve is suspected of not checking and cannot be serviced in place, it must be removed from the piping system and serviced in a shop. Inspect valve exterior for corrosion and tightness of bolts. Repaint and retighten as required. Quarterly SM SM SM Line Blanks, Ring Spacers, and Spectacle Blinds (Section 6-6.2.9) Line Blanks, Ring Spacers, and Spectacle Blinds Inspect exposed side of spectacle blinds. The exposed side must be kept clean and free of corrosion. Spectacle blinds should be inspected to ensure they are installed with the correct orientation for the desired flow or no-flow condition. Quarterly SM SM SM Manual Gear Operators (Section 6-6.2.10) Manual Valve Gear Operators Lubricate gear driven operators and check for smooth operation Quarterly SM SM SM
ufc_3_460_03_appendix_c.docx