The cabinet is heavy. Removing the cabinet from its carton requires a minimum of two people. If installing optional EBP(S), make sure to install the EBP(S) directly below the UPS so that all wiring between the cabinets is installed behind the front covers and inaccessible to users. Mounting are required for each individual cabinet NOTE (1)To install the rail kit Assemble the left and right rails to the rear rails as shown in Figure1.Do not tighten the screws. Adjust each rail size for the depth of your rack. Figure 1 Securing the Rails Select the proper size in the rack for positioning the UPS (see Figure 2). The rail occupies four positions on the front and rear of the rack. Tighten four M5 Umbrella Nuts in the side of rail assembly (see Figure 1). Fix one rail assembly to the front of the rack with one M5×12 pan-head screw and one M5 cage nut. Using two M5 cage nuts and two M5×12 pan-head screws, to fix the rail assembly to the rear of the rack. Figure 2 Fixing the Rails Repeat Steps 3 and 4 for the other rail assembly. Tighten the four butterfly nuts in the middle of each rail assembly. If installing optional cabinets, repeat Step 1 through Step 6 for each rail kit. Place the UPS on a flat, stable surface with the front of the cabinet facing to you. Align the mounting brackets with the screw holes on each side of the UPS and fix with the supplied M4×8 flat-head screws(see Figure 3) Figure 3 Installing the Mounting Brackets If installing optional cabinets, repeat Step 8 and 9 for each cabinet. Slide the UPS and any other optional cabinets into the rack. Secure the of the UPS to the rack using one M5×12 pan-head screws and one M5 cage nuts on each side(see Figure 4).Install the bottom screw on each side through the bottom hole of mounting bracket and the bottom hole of the rail. Repeat for any optional cabinets. Figure 4 Securing the Front of the Cabinet Continue to the following section, “Rackmount Wiring Installation. (2)Rackmount Wiring Installation Installing the UPS, including connecting the UPS internal batteries Connecting any Optional EBP(S)
The cabinet is heavy. Removing the cabinet from its carton requires a minimum of two people. If installing optional EBP(S), make sure to install the EBP(S) directly below the UPS so that all wiring between the cabinets is installed behind the front covers and inaccessible to users. NOTE Mounting are required for each individual cabinet (1)To install the rail kit Assemble the left and right rails to the rear rails as shown in Figure1.Do not tighten the screws. Adjust each rail size for the depth of your rack. Figure 1 Securing the Rails Select the proper size in the rack for positioning the UPS (see Figure 2). The rail occupies four positions on the front and rear of the rack. Tighten four M5 Umbrella Nuts in the side of rail assembly (see Figure 1). Fix one rail assembly to the front of the rack with one M5×12 pan-head screw and one M5 cage nut. Using two M5 cage nuts and two M5×12 pan-head screws, to fix the rail assembly to the rear of the rack. Figure 2 Fixing the Rails Repeat Steps 3 and 4 for the other rail assembly. Tighten the four butterfly nuts in the middle of each rail assembly. If installing optional cabinets, repeat Step 1 through Step 6 for each rail kit. Place the UPS on a flat, stable surface with the front of the cabinet facing to you. Align the mounting brackets with the screw holes on each side of the UPS and fix with the supplied M4×8 flat-head screws(see Figure 3) Figure 3 Installing the Mounting Brackets If installing optional cabinets, repeat Step 8 and 9 for each cabinet. Slide the UPS and any other optional cabinets into the rack. Secure the of the UPS to the rack using one M5×12 pan-head screws and one M5 cage nuts on each side(see Figure 4).Install the bottom screw on each side through the bottom hole of mounting bracket and the bottom hole of the rail. Repeat for any optional cabinets. Figure 4 Securing the Front of the Cabinet Continue to the following section, “Rackmount Wiring Installation. (2)Rackmount Wiring Installation Installing the UPS, including connecting the UPS internal batteries Connecting any Optional EBP(S)
UDC9100_RT%20PF1.0%20(RTIII)%20(IEC)%201-3.docx