Table . Eligible space heating scenarios – Scenario Decommissioning requirements Product to be Historical Product installed schedule category Number number number 10A 10A(i) Hard-wired electric room heater used as the main form Air to air heat 10A of heating the premises. pump (other than a ducted 10A(ii) Room air to air heat pump or other room heater 10A air to air heat pump) 10A(iii) Plug in electric heater used as the main form of heating 10A the premises, or wood fired room heater used as the main form of heating: an entire Class 1a, 4, 5, 6, 7b or 8 Building an entire dwelling within a Class 1b or 2 Building a room within a Class 3 or 9 Building as per the BCA” 10A(iv) Refrigerative air conditioner (non-ducted) that is not 10A located in if in residential premises, a bedroom, or otherwise, a room with an area less than 20m2 and a hard-wired electric room heater used as the main form of heating the premises 10A(v) Refrigerative air conditioner (non-ducted) that is not 10A located in if in residential premises, a bedroom, or otherwise, a room with an area less than 20m2 and a plug in electric room heater used as the main form of heating the premises 10A(vi) Refrigerative room air conditioner that is not located in 10A if in residential premises, a bedroom, or otherwise, a room with an area less than 20m2 and a gas or LPG room heater Specified Minimum Energy Efficiency The product installed must meet the relevant additional requirements listed in Table 10.2. Table . Additional requirements for space heating equipment to be installed – Product Requirement type Efficiency requirement category number 10A Minimum performance Product achieves: requirement a minimum RTHC of 2 kW at the H1 temperature condition a minimum ACOP of 4.2, if RTHC is 3 kW or less 4, in any other case
Table . – Eligible space heating scenarios Product category number Scenario Number Decommissioning requirements Product to be installed Historical schedule number 10A 10A(i) Hard-wired electric room heater used as the main form of heating the premises. Air to air heat pump (other than a ducted air to air heat pump) 10A 10A(ii) Room air to air heat pump or other room heater 10A 10A(iii) Plug in electric heater used as the main form of heating the premises, or wood fired room heater used as the main form of heating: an entire Class 1a, 4, 5, 6, 7b or 8 Building an entire dwelling within a Class 1b or 2 Building a room within a Class 3 or 9 Building as per the BCA” 10A 10A(iv) Refrigerative air conditioner (non-ducted) that is not located in if in residential premises, a bedroom, or otherwise, a room with an area less than 20m2 and a hard-wired electric room heater used as the main form of heating the premises 10A 10A(v) Refrigerative air conditioner (non-ducted) that is not located in if in residential premises, a bedroom, or otherwise, a room with an area less than 20m2 and a plug in electric room heater used as the main form of heating the premises 10A 10A(vi) Refrigerative room air conditioner that is not located in if in residential premises, a bedroom, or otherwise, a room with an area less than 20m2 and a gas or LPG room heater 10A Specified Minimum Energy Efficiency The product installed must meet the relevant additional requirements listed in Table 10.2. Table . – Additional requirements for space heating equipment to be installed Product category number Requirement type Efficiency requirement 10A Minimum performance requirement Product achieves: a minimum RTHC of 2 kW at the H1 temperature condition a minimum ACOP of 4.2, if RTHC is 3 kW or less 4, in any other case
Victorian-Energy-Upgrades-Specifications-Version-1.0.docx