Generator Operator has notified the Transmission a different control Operator of one of the following: mode as instructed by the That the generator is being operated in start-up, Transmission shutdown, or testing mode pursuant to a Real-time Operator, and communication or a procedure that was previously failed to provide provided to the Transmission Operator; or That the the required generator is not being operated in automatic notifications to voltage control mode or in the control mode that Transmission was instructed by the Transmission Operator for a Operator as reason other than start-up, shutdown, or testing. identified in Requirement R1. The Generator The Generator N/A N/A VAR-002-4 R2. Unless exempted by the Transmission Operator, each Operator did not Operator did not Generator Operator shall maintain the generator have a conversion maintain the voltage voltage or Reactive Power schedule (within each methodology when or Reactive Power generating provided by the Facility’s capabilities) it monitors voltage schedule as Transmission Operator, or otherwise shall meet the at a location instructed by the conditions of notification for deviations from the different from the Transmission voltage or Reactive Power schedule provided by the schedule provided Operator and did Transmission Operator. by the not make the Transmission necessary Operator. notifications required by the Transmission Operator. OR The Generator Operator did not have an operating AVR, and the responsible entity did not use an alternative method for controlling voltage. OR The Generator
Generator Operator has notified the Transmission Operator of one of the following: That the generator is being operated in start-up, shutdown, or testing mode pursuant to a Real-time communication or a procedure that was previously provided to the Transmission Operator; or That the generator is not being operated in automatic voltage control mode or in the control mode that was instructed by the Transmission Operator for a reason other than start-up, shutdown, or testing. a different control mode as instructed by the Transmission Operator, and failed to provide the required notifications to Transmission Operator as identified in Requirement R1. VAR-002-4 R2. Unless exempted by the Transmission Operator, each Generator Operator shall maintain the generator voltage or Reactive Power schedule (within each generating Facility’s capabilities) provided by the Transmission Operator, or otherwise shall meet the conditions of notification for deviations from the voltage or Reactive Power schedule provided by the Transmission Operator. N/A N/A The Generator Operator did not have a conversion methodology when it monitors voltage at a location different from the schedule provided by the Transmission Operator. The Generator Operator did not maintain the voltage or Reactive Power schedule as instructed by the Transmission Operator and did not make the necessary notifications required by the Transmission Operator. OR The Generator Operator did not have an operating AVR, and the responsible entity did not use an alternative method for controlling voltage. OR The Generator
VSL_Matrix_Complete_2016_01_01.docx