the containment area, leaking valves, fittings, or components. Leaking valves, fittings or components must be repaired immediately or immediately removed from service and isolated to prevent further discharge. Any irregularities, (e.g., missing valve handles, bolts, nuts, screens) will be assessed for priority and repaired as soon as possible or as required depending on the nature of the defect (See for an example of the STI SP001 Standard Monthly Inspection Checklist). Annual External Inspection OM OM OM (Identified as P in Table 8-2): A more detailed examination of the tank and appurtenances must be Annually performed annually. (See for an example of the STI SP001 Standard Annual Inspection Checklist). Formal External Inspection SM SM SM (Identified as E in Table 8-2): A formal external inspection as defined in STI SP001 Standard for the Inspection of Aboveground Storage Tanks must be conducted by certified STI SP001 inspector. As established Formal Internal Inspection by SCP based on (Identified as I in 8-2): A tank size and formal internal inspection as category listed in defined in STI SP001 Standard for Tables 8-1 and the Inspection of Aboveground 8-2 Storage Tanks must be performed by a certified STI SP001 inspector. Leak Test (Identified as L in Table 8-2): A leak test as defined in STI SP001 Standard for the Inspection of Aboveground Storage Tanks must be performed in accordance with STI SP001 Standard for the
the containment area, leaking valves, fittings, or components. Leaking valves, fittings or components must be repaired immediately or immediately removed from service and isolated to prevent further discharge. Any irregularities, (e.g., missing valve handles, bolts, nuts, screens) will be assessed for priority and repaired as soon as possible or as required depending on the nature of the defect (See for an example of the STI SP001 Standard Monthly Inspection Checklist). Annual External Inspection (Identified as P in Table 8-2): A more detailed examination of the tank and appurtenances must be performed annually. (See for an example of the STI SP001 Standard Annual Inspection Checklist). Annually OM OM OM Formal External Inspection (Identified as E in Table 8-2): A formal external inspection as defined in STI SP001 Standard for the Inspection of Aboveground Storage Tanks must be conducted by certified STI SP001 inspector. Formal Internal Inspection (Identified as I in 8-2): A formal internal inspection as defined in STI SP001 Standard for the Inspection of Aboveground Storage Tanks must be performed by a certified STI SP001 inspector. Leak Test (Identified as L in Table 8-2): A leak test as defined in STI SP001 Standard for the Inspection of Aboveground Storage Tanks must be performed in accordance with STI SP001 Standard for the As established by SCP based on tank size and category listed in Tables 8-1 and 8-2 SM SM SM
ufc_3_460_03_appendix_c.docx