Power capacity: 20 Ampere, single phase, 120 VAC continuous duty. Wire gauge: #12 AWG, solid copper, connected to room’s internal AC Power Panel, or as directed by COR. Number of AC power outlets: Minimum 4 receptacles. Enclosure: Fully self-contained, metal 102 mm (4 inch) x 102 mm (4 inches) x 64 mm (2-1/2 inches) with cover Connection: Minimum 25.4 mm (1 inch) conduit connected to room’s AC Panel, or as directed by COR Number of boxes: One. Compliance: NRTL (i.e. UL); NPFA - 70 (NEC). AC Outlet Strips: Power Capacity: 15 Ampere, single phase, 120 VAC continuous duty. Wire Gauge: Minimum #12 AWG, solid copper. Number of AC Power Outlets: Minimum 10 grounded. “U” Enclosure: Fully self-contained; typically metal. Connecting Wire: Minimum 2 m (6 feet) long, with three prong self-grounding AC plug connected to cabinet’s internal AC box. “Quad” Number of Strips: 2. Certification: NRTL (i.e. UL). AC Power Line Surge Protector and Filter Construction: Input Voltage Range: 120 VAC + 15 percent at 50/60 Hz, single phase. Power Service Capacity: 20 AMP, 120 VAC. Voltage Output Regulation: +5.0 percent, instantaneous of input. Circuit Breaker: 15 AMP; may be self-contained. AC Outlets: Minimum four duplex grounded NEMA 5-20R. Response Time: 5.0 nanosecond. Suppression: Isolate and filter any noise, surge spikes Surge: Minimum 20,000 AMP. Noise: Common: -40 dB. Differential: -45 dB. Clamping Voltage: Minimum 300 V. Enclosure: One; self-contained.
Power capacity: 20 Ampere, single phase, 120 VAC continuous duty. Wire gauge: #12 AWG, solid copper, connected to room’s internal AC Power Panel, or as directed by COR. Number of AC power outlets: Minimum 4 receptacles. Enclosure: Fully self-contained, metal 102 mm (4 inch) x 102 mm (4 inches) x 64 mm (2-1/2 inches) with cover Connection: Minimum 25.4 mm (1 inch) conduit connected to room’s AC Panel, or as directed by COR Number of boxes: One. Compliance: NRTL (i.e. UL); NPFA - 70 (NEC). AC Outlet Strips: Power Capacity: 15 Ampere, single phase, 120 VAC continuous duty. Wire Gauge: Minimum #12 AWG, solid copper. Number of AC Power Outlets: Minimum 10 “U” grounded. Enclosure: Fully self-contained; typically metal. Connecting Wire: Minimum 2 m (6 feet) long, with three prong self-grounding AC plug connected to cabinet’s internal AC “Quad” box. Number of Strips: 2. Certification: NRTL (i.e. UL). AC Power Line Surge Protector and Filter Construction: Input Voltage Range: 120 VAC + 15 percent at 50/60 Hz, single phase. Power Service Capacity: 20 AMP, 120 VAC. Voltage Output Regulation: +5.0 percent, instantaneous of input. Circuit Breaker: 15 AMP; may be self-contained. AC Outlets: Minimum four duplex grounded NEMA 5-20R. Response Time: 5.0 nanosecond. Suppression: Isolate and filter any noise, surge spikes Surge: Minimum 20,000 AMP. Noise: Common: -40 dB. Differential: -45 dB. Clamping Voltage: Minimum 300 V. Enclosure: One; self-contained.
VA271100.docx