Activity is not part of upgrades refurbishment that is As determined by Table 34.12 required to comply with Part J6 of the Building Code as amended from time to time Additional variables for determining GHG reduction Table . Annual operating hours and illumination power density (IPD) at sites required to comply with Part J6 of the Building – Code Annual operating (per IPD Type of space year) Auditorium, church and public hall 2000 10 Board room and conference room 3000 10 Carpark—entry zone 7000 25 (first 20 m of travel) Carpark—general 7000 6 (undercover) Common rooms, spaces and corridors in a Class 2 building 7000 8 Control room, switch room and the like in a 2 building As determined by Table 34.8 9 Corridors As determined by Table 34.8 8 Courtroom 2000 12 Dormitory of a Class 3 building used for sleeping only 3000 6 Dormitory of a Class 3 building used for sleeping and study 3000 9 lobby from outside the building As determined by Table 34.8 15 Health care children’s ward and examination room 6000 10 – Health care patient ward 6000 7 – Health-care—all patient care areas including corridors where cyanosis 6000 13 lamps are used Kitchen and food preparation area As determined by 34.8 8 Laboratory—artificially lit to an ambient level of 400 lx or more 3000 12 Library—stack and shelving area 3000 12 Library reading room and general areas 3000 10 – Lounge area for communal use in a Class 3 building or Class 9c aged 7000 10 care building Maintained emergency lighting 8500 1 Museum and gallery—circulation, cleaning and service lighting 2000 8 Office artificially lit to an ambient level of 200 lx or more 3000 9 – Office artificially lit to an ambient level of less than 200 lx 3000 7 – Plant room As determined by 34.8 5 A for the serving and consumption of food or drinks to the public 5000 18 that fall under Division H - Accommodation and food services as
Activity is not part of upgrades refurbishment that is required to comply with Part J6 of the Building Code as amended from time to time As determined by Table 34.12 Additional variables for determining GHG reduction Table . – Annual operating hours and illumination power density (IPD) at sites required to comply with Part J6 of the Building Code Type of space Annual operating (per year) IPD Auditorium, church and public hall 2000 10 Board room and conference room 3000 10 Carpark—entry zone (first 20 m of travel) 7000 25 Carpark—general (undercover) 7000 6 Common rooms, spaces and corridors in a Class 2 building 7000 8 Control room, switch room and the like in a 2 building As determined by Table 34.8 9 Corridors As determined by Table 34.8 8 Courtroom 2000 12 Dormitory of a Class 3 building used for sleeping only 3000 6 Dormitory of a Class 3 building used for sleeping and study 3000 9 lobby from outside the building As determined by Table 34.8 15 Health care – children’s ward and examination room 6000 10 Health care – patient ward 6000 7 Health-care—all patient care areas including corridors where cyanosis lamps are used 6000 13 Kitchen and food preparation area As determined by 34.8 8 Laboratory—artificially lit to an ambient level of 400 lx or more 3000 12 Library—stack and shelving area 3000 12 Library – reading room and general areas 3000 10 Lounge area for communal use in a Class 3 building or Class 9c aged care building 7000 10 Maintained emergency lighting 8500 1 Museum and gallery—circulation, cleaning and service lighting 2000 8 Office – artificially lit to an ambient level of 200 lx or more 3000 9 Office – artificially lit to an ambient level of less than 200 lx 3000 7 Plant room As determined by 34.8 5 A for the serving and consumption of food or drinks to the public that fall under Division H - Accommodation and food services as 5000 18
Victorian-Energy-Upgrades-Specifications-Version-1.0.docx