Division 23 specification sections and submit the test reports and records to the COR. Should evidence of malfunction in any tested system, or piece of equipment or component part thereof, occur during or as a result of tests, make proper corrections, repairs or replacements, and repeat tests at no additional cost or time to the Government. When completion of certain work or system occurs at a time when final control settings and adjustments cannot be properly made to make performance tests, then conduct such performance tests and finalize control settings for heating systems and for cooling systems respectively during first actual seasonal use of respective systems following completion of work. Rescheduling of these tests shall be requested in writing to COR for approval. No adjustments maybe made during the acceptance inspection. All adjustments shall have been made by this point. //Perform tests as required for commissioning provisions in accordance with Section 23 08 00, COMMISSIONING OF HVAC SYSTEMS and Section 01 91 00, GENERAL COMMISSIONING REQUIREMENTS.// DEMONSTRATIONS AND TESTS, TEMPORARY BOILER PLANT EQUIPMENT Test prior to placing in service. Demonstrate to COR the proper operation of all equipment, instruments, operating and safety controls, and devices. Demonstrate to COR the proper operation of burners. Emissions within limits specified for new boilers on this project. Stable at all operating points with no pulsations. No impingement on the Morrison tube or furnace walls, or water tubes. Smooth flame light off, with no delays, puffs or flashbacks. Turndown capability as specified. Develop full steam output capacity required. New boilers installed in temporary location: Perform all tests required by boiler specification. Perform complete retest after boiler is placed in its permanent location. //COMMISSIONING Provide commissioning documentation in accordance with the requirements of Section 23 08 00, COMMISSIONING OF HVAC SYSTEMS.
Division 23 specification sections and submit the test reports and records to the COR. Should evidence of malfunction in any tested system, or piece of equipment or component part thereof, occur during or as a result of tests, make proper corrections, repairs or replacements, and repeat tests at no additional cost or time to the Government. When completion of certain work or system occurs at a time when final control settings and adjustments cannot be properly made to make performance tests, then conduct such performance tests and finalize control settings for heating systems and for cooling systems respectively during first actual seasonal use of respective systems following completion of work. Rescheduling of these tests shall be requested in writing to COR for approval. No adjustments maybe made during the acceptance inspection. All adjustments shall have been made by this point. //Perform tests as required for commissioning provisions in accordance with Section 23 08 00, COMMISSIONING OF HVAC SYSTEMS and Section 01 91 00, GENERAL COMMISSIONING REQUIREMENTS.// DEMONSTRATIONS AND TESTS, TEMPORARY BOILER PLANT EQUIPMENT Test prior to placing in service. Demonstrate to COR the proper operation of all equipment, instruments, operating and safety controls, and devices. Demonstrate to COR the proper operation of burners. Emissions within limits specified for new boilers on this project. Stable at all operating points with no pulsations. No impingement on the Morrison tube or furnace walls, or water tubes. Smooth flame light off, with no delays, puffs or flashbacks. Turndown capability as specified. Develop full steam output capacity required. New boilers installed in temporary location: Perform all tests required by boiler specification. Perform complete retest after boiler is placed in its permanent location. //COMMISSIONING Provide commissioning documentation in accordance with the requirements of Section 23 08 00, COMMISSIONING OF HVAC SYSTEMS.
VA%2023%2005%2010.docx