Installing PEMS Up to 50% less cost to install and maintain than CEMS and reduces the hardware and consumables (pumps, analyzers and calibration gases) needed for operation. Chilled Filter Filter the Chilled Water system on campus to clean heat transfer surfaces for System (in energy savings , reduce corrosion rates to maintain longer equipment and prevent progress) harmful clogging and bacterial growth for a healthier environment. New Lights CRC Replaced all HID lights in gym with LED lighting. New Lights Replaced over 1,000 HID fixtures with long life T5 high output lamps. Garages Duke Energy We received a total of over $160,000 of rebates for various projects in FY16. UC is Rebates Duke's largest recipient of rebate funds and UC has done more projects than any of Duke's other customers. Vontz Lab air flow controls upgrade to allow reduced outdoor air into the building for conditioning during unoccupied hours. ECUP air Ike Ratliff, Replacing inefficient Gardner Denver Air Compressors with a single variable speed compressors Bundy, Maury unit. This will be the main compressor and will reduce energy consumption. Replacement DuPont Old Chem lighting Replace MH lighting with LED throughout building. 461 bulbs. retrofit Utility tunnel Installed occupancy sensors on utility tunnel lighting that had been on 24/7. lighting VPC Boiler Replaced burners on two boilers with high efficiency burners. Outside lighting Replaced incandescent outside lighting fixtures with LED in various locations (Langsam plaza, Fishwick). Control valves Replaced all HW/ CHW control valves at Procter hall. They were all leaking through. replacement Demand limiting programming at the air handler level to reduce energy consumption when needed for peak shaving. Scioto - Dorm Messer, GBBN, Replace shell, HVAC, and lighting. CMTA
Installing PEMS Up to 50% less cost to install and maintain than CEMS and reduces the hardware and consumables (pumps, analyzers and calibration gases) needed for operation. Chilled Filter System (in progress) Filter the Chilled Water system on campus to clean heat transfer surfaces for energy savings , reduce corrosion rates to maintain longer equipment and prevent harmful clogging and bacterial growth for a healthier environment. New Lights CRC Replaced all HID lights in gym with LED lighting. New Lights Garages Replaced over 1,000 HID fixtures with long life T5 high output lamps. Duke Energy Rebates We received a total of over $160,000 of rebates for various projects in FY16. UC is Duke's largest recipient of rebate funds and UC has done more projects than any of Duke's other customers. Vontz Lab air flow controls upgrade to allow reduced outdoor air into the building for conditioning during unoccupied hours. ECUP air compressors Replacement Ike Ratliff, Bundy, Maury DuPont Replacing inefficient Gardner Denver Air Compressors with a single variable speed unit. This will be the main compressor and will reduce energy consumption. Old Chem lighting retrofit Replace MH lighting with LED throughout building. 461 bulbs. Utility tunnel lighting Installed occupancy sensors on utility tunnel lighting that had been on 24/7. VPC Boiler Replaced burners on two boilers with high efficiency burners. Outside lighting Replaced incandescent outside lighting fixtures with LED in various locations (Langsam plaza, Fishwick). Control valves replacement Replaced all HW/ CHW control valves at Procter hall. They were all leaking through. Demand limiting programming at the air handler level to reduce energy consumption when needed for peak shaving. Scioto - Dorm Messer, GBBN, CMTA Replace shell, HVAC, and lighting.
UC2016TFEfficiencyReporting.docx