Conduct operational check of card SM SM SM and key lock system and ensure Card and Annually Key Locks that all features provided with the installed system are operational. Lightning Protection Systems (Section 9-4) Inspect air terminals to make sure SM SM SM they are securely attached to the roof of the building, canopy, or the of equipment. Check all Lightning connections between the air Protection Annually terminals and the grounding loop Systems or grounding rods. Repair damaged or loose connections and perform continuity check after repairs. Ground Verification System (Section 9-5) Conduct an operational check of SM SM SM the ground verification system and ensure that all features provided Ground with the installed system are Verification Quarterly operational. Inspect the plug for System corrosion, weakness, or loose nuts and replace if heavily dented or deformed. Electronic Overfill Protection Systems (Section 9-6) Conduct operational check of SM SM SM Electronic overfill prevention system and Overfill ensure that all features provided Quarterly Protection with the installed system are Systems operational. ALTERNATE POL FACILITIES Liquefied Petroleum Tanks (Section 10-1.1) Inspect fuel tank for leaks. If a OM OM OM leak is occurring, the odorizing Liquefied agent of the gas should be Petroleum Monthly Tanks detectable. Use a soap and water solution to spray on areas suspected of leaks. Systems that
Card and Key Locks Conduct operational check of card and key lock system and ensure that all features provided with the installed system are operational. Annually SM SM SM Lightning Protection Systems (Section 9-4) Lightning Protection Systems Inspect air terminals to make sure they are securely attached to the roof of the building, canopy, or the of equipment. Check all connections between the air terminals and the grounding loop or grounding rods. Repair damaged or loose connections and perform continuity check after repairs. Annually SM SM SM Ground Verification System (Section 9-5) Ground Verification System Conduct an operational check of the ground verification system and ensure that all features provided with the installed system are operational. Inspect the plug for corrosion, weakness, or loose nuts and replace if heavily dented or deformed. Quarterly SM SM SM Electronic Overfill Protection Systems (Section 9-6) Electronic Overfill Protection Systems Conduct operational check of overfill prevention system and ensure that all features provided with the installed system are operational. Quarterly SM SM SM ALTERNATE POL FACILITIES Liquefied Petroleum Tanks (Section 10-1.1) Liquefied Petroleum Tanks Inspect fuel tank for leaks. If a leak is occurring, the odorizing agent of the gas should be detectable. Use a soap and water solution to spray on areas suspected of leaks. Systems that Monthly OM OM OM
ufc_3_460_03_appendix_c.docx