sample is clear and bright with no visible water. High Point Vents (Section 6-12.2) Inspect high point vents. If fuel OM OM OM leaks are observed they should be repaired as soon as possible. High Weekly Vents Ensure that quick-disconnect dust caps are in place and that high point vent valves are locked. Sight Flow Indicators (Section 6-12.3) Verify there are no leaks around OM OM OM pipe connection fittings and glass Sight Flow Daily or at each Indicators seals. Also check glass for use indications of cracks. ELECTRONIC RELEASE DETECTION MONITORING Rope Sensor Systems (Section 6-13.1.1) Ensure the monitoring OM OM OM associated with the rope sensor(s) Daily is powered on and no alarms are Rope Sensor present. System Test rope sensor system and SM SM SM Annually ensure it is functional. Point Sensor - Dry (Section 6-13.1.2) Ensure the monitoring OM OM OM associated with the point Daily sensor(s) is powered on and no alarms are present. Point Sensor - Dry Ensure monitoring space is clear OM OM OM Monthly and free of debris and liquid. Test sensor and ensure it is SM SM SM Annually functional. Visual Monitoring (Section 6-14.1)
sample is clear and bright with no visible water. High Point Vents (Section 6-12.2) High Vents Inspect high point vents. If fuel leaks are observed they should be repaired as soon as possible. Ensure that quick-disconnect dust caps are in place and that high point vent valves are locked. Weekly OM OM OM Sight Flow Indicators (Section 6-12.3) Sight Flow Indicators Verify there are no leaks around pipe connection fittings and glass seals. Also check glass for indications of cracks. Daily or at each use OM OM OM ELECTRONIC RELEASE DETECTION MONITORING Rope Sensor Systems (Section 6-13.1.1) Rope Sensor System Ensure the monitoring associated with the rope sensor(s) is powered on and no alarms are present. Daily OM OM OM Test rope sensor system and ensure it is functional. Annually SM SM SM Point Sensor - Dry (Section 6-13.1.2) Point Sensor - Dry Ensure the monitoring associated with the point sensor(s) is powered on and no alarms are present. Daily OM OM OM Ensure monitoring space is clear and free of debris and liquid. Monthly OM OM OM Test sensor and ensure it is functional. Annually SM SM SM Visual Monitoring (Section 6-14.1)
ufc_3_460_03_appendix_c.docx