Analysis Table: Requirement R1 Applicable Entities and Facilities Covered Elsewhere WECC Standard NERC Standards Narrative VAR-002-WECC-2 VAR-001-4.2 The Applicable Entities of the WECC Standard are addressed Applicability Applicability in VAR-001-4.2 and 4.1 Generator Operators 4.1 Transmission Operators 4.2 Transmission Operators 4.2 Generator Operators Whereas VAR-002-WECC-2 that operate synchronous within the Western specifically identifies condensers Interconnection (for the generators and synchronous WECC Variance) condensers as the applicable 4.3 This VAR-002-WECC-2 facilities, these specific assets Standard only applies to VAR-002-4.1 need not be called out. synchronous generators and Applicability Rather, by setting the voltage synchronous condensers that 4.1 Generator Operator schedule as a results-oriented are connected to the Bulk goal, the Transmission Electric System. 4.2 Generator Owner Operator can allow for an array of assets to deploy without confining the resources to a specific list. Analysis Table: Requirement R1 AVR in Service and Controlling – Covered Elsewhere VAR-002-WECC-2 VAR-002-4 VAR-001-4.1 Narrative Generator Operator Generator Operator Transmission Operator and Transmission Operator
Analysis Table: Requirement R1 Applicable Entities and Facilities Covered Elsewhere WECC Standard NERC Standards Narrative VAR-002-WECC-2 Applicability 4.1 Generator Operators 4.2 Transmission Operators that operate synchronous condensers 4.3 This VAR-002-WECC-2 Standard only applies to synchronous generators and synchronous condensers that are connected to the Bulk Electric System. VAR-001-4.2 Applicability 4.1 Transmission Operators 4.2 Generator Operators within the Western Interconnection (for the WECC Variance) VAR-002-4.1 Applicability 4.1 Generator Operator 4.2 Generator Owner The Applicable Entities of the WECC Standard are addressed in VAR-001-4.2 and Whereas VAR-002-WECC-2 specifically identifies generators and synchronous condensers as the applicable facilities, these specific assets need not be called out. Rather, by setting the voltage schedule as a results-oriented goal, the Transmission Operator can allow for an array of assets to deploy without confining the resources to a specific list. Analysis Table: Requirement R1 AVR in Service and Controlling – Covered Elsewhere VAR-002-WECC-2 VAR-002-4 VAR-001-4.1 Narrative Generator Operator and Transmission Operator Generator Operator Transmission Operator
WECC-0127%20VAR-002-WECC-2%20Request%20to%20Retire%20-%20Attachment%20G%20Technical%20Justification.docx