Do not install equipment foundations, equipment or piping until coordination/shop drawings have been approved. In addition, for HVAC systems, provide details of the following: Mechanical equipment rooms. Hangers, inserts, supports, and bracing. Pipe sleeves. Duct or equipment penetrations of floors, walls, ceilings, or roofs. Manufacturer's Literature and Data: Include full item description and optional features and accessories. Include dimensions, weights, materials, applications, standard compliance, model numbers, size, and capacity. Submit under the pertinent section rather than under this section. Submit belt drive with the driven equipment. Submit selection data for specific drives when requested by the COR. Submit electric motor data and variable speed drive data with the driven equipment. Equipment and materials identification. Fire-stopping materials. Hangers, inserts, supports and bracing. Provide complete stress analysis for variable spring and constant support hangers. For boiler plants, refer to Section 23 21 11, BOILER PLANT PIPING SYSTEMS, for additional requirements. Wall, floor, and ceiling plates. Rigging Plan: Provide documentation of the capacity and weight of the rigging and equipment intended to be used. The rigging plan shall include the path of travel of the load, the staging area and intended access, and qualifications of the operator and signal person. Maintenance Data and Operating Instructions: Maintenance and operating manuals in accordance with Section 01 00 00, GENERAL REQUIREMENTS, paragraph, INSTRUCTIONS, for systems and equipment. Complete operating and maintenance manuals including wiring diagrams, technical data sheets, information for ordering replacement and troubleshooting guide: Include complete list indicating all components of the systems. Include complete diagrams of the internal wiring for each item of equipment.
Do not install equipment foundations, equipment or piping until coordination/shop drawings have been approved. In addition, for HVAC systems, provide details of the following: Mechanical equipment rooms. Hangers, inserts, supports, and bracing. Pipe sleeves. Duct or equipment penetrations of floors, walls, ceilings, or roofs. Manufacturer's Literature and Data: Include full item description and optional features and accessories. Include dimensions, weights, materials, applications, standard compliance, model numbers, size, and capacity. Submit under the pertinent section rather than under this section. Submit belt drive with the driven equipment. Submit selection data for specific drives when requested by the COR. Submit electric motor data and variable speed drive data with the driven equipment. Equipment and materials identification. Fire-stopping materials. Hangers, inserts, supports and bracing. Provide complete stress analysis for variable spring and constant support hangers. For boiler plants, refer to Section 23 21 11, BOILER PLANT PIPING SYSTEMS, for additional requirements. Wall, floor, and ceiling plates. Rigging Plan: Provide documentation of the capacity and weight of the rigging and equipment intended to be used. The rigging plan shall include the path of travel of the load, the staging area and intended access, and qualifications of the operator and signal person. Maintenance Data and Operating Instructions: Maintenance and operating manuals in accordance with Section 01 00 00, GENERAL REQUIREMENTS, paragraph, INSTRUCTIONS, for systems and equipment. Complete operating and maintenance manuals including wiring diagrams, technical data sheets, information for ordering replacement and troubleshooting guide: Include complete list indicating all components of the systems. Include complete diagrams of the internal wiring for each item of equipment.
VA%2023%2005%2010.docx