New Old Motor Old Motor New Motor New Motor vibration Couple De-Couple Without Point Description Couple reading condition Condition cover - condition Condition 14.03.2013 20.02.2013 21.02.2013 04.03.2013 09.03.2013 02.03.2013 Motor OutBoard 1.7 4.59 3.112 1.833 5.187 1.408 Horizontal Motor OutBoard 0.5 0.503 0.175 0.106 0.26 0.444 Horiz Peakvue Outboard 2.3 13.21 10.46 12.54 5.733 11.22 Vertical Motor Outboard 0.9 1.445 1.518 1.001 0.704 0.879 Axial Motor Inboard 1.06 2.05 1.278 0.938 2.948 0.96 Horizontal Motor Inboard 0.3 0.811 0.277 0.127 0.139 0.292 Horiz Peakvue Motor Inboard 1.7 5.283 4.287 4.981 3.144 4.221 Vertical Motor Inboard 0.9 1.209 1.045 1.228 1.128 1.229 Axial Pump Inboard 1 1.216 - - - 1.309 Horizontal Pump Inboard 1.8 2.465 - - - 2.654 Vertical Pump Inboard 2.5 1.046 - - - 1.291 Axial
Point Description Old Motor Couple condition 20.02.2013 Old Motor De-Couple Condition 21.02.2013 New Motor Condition 02.03.2013 New Motor Without cover - 04.03.2013 New Couple condition 09.03.2013 vibration reading 14.03.2013 Motor OutBoard Horizontal 4.59 3.112 1.833 5.187 1.408 1.7 Motor OutBoard Horiz Peakvue 0.503 0.175 0.106 0.26 0.444 0.5 Outboard Vertical 13.21 10.46 12.54 5.733 11.22 2.3 Motor Outboard Axial 1.445 1.518 1.001 0.704 0.879 0.9 Motor Inboard Horizontal 2.05 1.278 0.938 2.948 0.96 1.06 Motor Inboard Horiz Peakvue 0.811 0.277 0.127 0.139 0.292 0.3 Motor Inboard Vertical 5.283 4.287 4.981 3.144 4.221 1.7 Motor Inboard Axial 1.209 1.045 1.228 1.128 1.229 0.9 Pump Inboard Horizontal 1.216 - - - 1.309 1 Pump Inboard Vertical 2.465 - - - 2.654 1.8 Pump Inboard Axial 1.046 - - - 1.291 2.5
Vertical_Motor_Vibration_behaviour.docx