Replace belt as recommended by manufacturer. Inspect pump body. Ensure pump Dispenser body is clean and free of fuel. Pumps Inspect air eliminator. Ensure air eliminator is clean and free of fuel and that the vent tube is not obstructed. EFSO SYSTEMS EFSO Systems (Section 7-16) Check the operation of the EFSO SM SM SM system by activating the fueling system and then pressing each of the EFSO buttons. Ensure that Quarterly each button disables power to all EFSO of the dispensers and fuel pumps Systems installed at the service station. Refer to for inspection and SM SM SM maintenance requirements of As required EFSO pushbutton signs. RECOVERY Stage I Vapor Recovery (Section 7-17) Inspect vapor recovery hoses for OM OM OM Daily or before gouges, cuts or outside wear that each use may result in vapor leaks Stage I Inspect caps and camlock fittings SM SM SM Vapor Quarterly for tightness and leaks. Recovery Refer to for inspection and SM SM SM maintenance requirements of As required Stage I vapor recovery piping. Vapor Burners (Section 7-17.3) Inspect vapor burners to ensure SM SM SM that the pilot flame system is Vapor Quarterly Burners operating properly. Fans, duct work, and dampeners must also be inspected to ensure proper air
Dispenser Pumps Replace belt as recommended by manufacturer. Inspect pump body. Ensure pump body is clean and free of fuel. Inspect air eliminator. Ensure air eliminator is clean and free of fuel and that the vent tube is not obstructed. EFSO SYSTEMS EFSO Systems (Section 7-16) EFSO Systems Check the operation of the EFSO system by activating the fueling system and then pressing each of the EFSO buttons. Ensure that each button disables power to all of the dispensers and fuel pumps installed at the service station. Quarterly SM SM SM Refer to for inspection and maintenance requirements of EFSO pushbutton signs. As required SM SM SM RECOVERY Stage I Vapor Recovery (Section 7-17) Stage I Vapor Recovery Inspect vapor recovery hoses for gouges, cuts or outside wear that may result in vapor leaks Daily or before each use OM OM OM Inspect caps and camlock fittings for tightness and leaks. Quarterly SM SM SM Refer to for inspection and maintenance requirements of Stage I vapor recovery piping. As required SM SM SM Vapor Burners (Section 7-17.3) Vapor Burners Inspect vapor burners to ensure that the pilot flame system is operating properly. Fans, duct work, and dampeners must also be inspected to ensure proper air Quarterly SM SM SM
ufc_3_460_03_appendix_c.docx