Inspect wheels (if equipped) for SM SM SM warping, cracking, and uneven wear. Quarterly Inspect exposed piping and components for corrosion. Refer to for inspection and SM SM SM maintenance requirements of As required fueling nozzle. Mobile Pantographs (Section 4-7.1.2) entire pantograph under OM OM OM static pump head pressure and check for leaks, ease of Monthly movement, and damaged grounding or bonding wire. Inspect exposed piping and SM SM SM components for corrosion. Lubricate wheels. Quarterly Mobile Pantographs Inspect wheels for warping, cracking and uneven wear. Refer to for inspection and SM SM SM maintenance requirements of pantograph hydrant adapters. As required Refer to for inspection and maintenance requirements of fueling nozzles. HYDRANT ADAPTERS AND NOZZLES Hydrant Adapters (Section 4-7.3) Inspect hydrant adapter for proper SM SM SM operation, damage, and wear. Hydrant Quarterly Adapters Test operation of dry break system. Fueling Nozzles (Section 4-7.4)
Inspect wheels (if equipped) for warping, cracking, and uneven wear. Inspect exposed piping and components for corrosion. Quarterly SM SM SM Refer to for inspection and maintenance requirements of fueling nozzle. As required SM SM SM Mobile Pantographs (Section 4-7.1.2) Mobile Pantographs entire pantograph under static pump head pressure and check for leaks, ease of movement, and damaged grounding or bonding wire. Monthly OM OM OM Inspect exposed piping and components for corrosion. Lubricate wheels. Inspect wheels for warping, cracking and uneven wear. Quarterly SM SM SM Refer to for inspection and maintenance requirements of pantograph hydrant adapters. Refer to for inspection and maintenance requirements of fueling nozzles. As required SM SM SM HYDRANT ADAPTERS AND NOZZLES Hydrant Adapters (Section 4-7.3) Hydrant Adapters Inspect hydrant adapter for proper operation, damage, and wear. Test operation of dry break system. Quarterly SM SM SM Fueling Nozzles (Section 4-7.4)
ufc_3_460_03_appendix_c.docx