Locations only) 38-60 degrees C Flexible 38 (1.5) 38 (1.5) 50 (2.0) 50 (2.0) (100-140 degrees F) Elastomeric Cellular (Domestic Hot Water Thermal (Above Supply and Return) ground piping only) 38-60 degrees C Cellular 38 (1.5) 38 (1.5) 50 (2.0) 50 (2.0) (100-140 degrees F) Thermal (Domestic Hot Water Supply and Return) 4-15 degrees C Rigid Cellular 25 (1.0) 25(1.0) 25 (1.0) 25 (1.0) (40-60 degrees F) Phenolic Foam (Above ground (//Ice water piping only) piping// (exterior locations only) 4-15 degrees C 25 (1.0) 25(1.0) 25 (1.0) 25 (1.0) (40-60 degrees F) Closed-Cell (//Ice water Rigid(Exterior piping// Locations only) (4-15 degrees C Flexible 25 (1.0) 25(1.0) 25 (1.0) 25 (1.0) (40-60 degrees F) Elastomeric Cellular (//Ice Thermal (Above piping//) ground piping only) 4-15 degrees C Cellular Glass 38 (1.5) 38 (1.5) 38 (1.5) 38 (1.5) (40-60 degrees F) Thermal (//Ice water piping// E N D
Locations only) 38-60 degrees C (100-140 degrees F) (Domestic Hot Water Supply and Return) Flexible Elastomeric Cellular Thermal (Above ground piping only) 38 (1.5) 38 (1.5) 50 (2.0) 50 (2.0) 38-60 degrees C (100-140 degrees F) (Domestic Hot Water Supply and Return) Cellular Thermal 38 (1.5) 38 (1.5) 50 (2.0) 50 (2.0) 4-15 degrees C (40-60 degrees F) (//Ice water piping// Rigid Cellular Phenolic Foam (Above ground piping only) (exterior locations only) 25 (1.0) 25(1.0) 25 (1.0) 25 (1.0) 4-15 degrees C (40-60 degrees F) (//Ice water piping// Closed-Cell Rigid(Exterior Locations only) 25 (1.0) 25(1.0) 25 (1.0) 25 (1.0) (4-15 degrees C (40-60 degrees F) (//Ice piping//) Flexible Elastomeric Cellular Thermal (Above ground piping only) 25 (1.0) 25(1.0) 25 (1.0) 25 (1.0) 4-15 degrees C (40-60 degrees F) (//Ice water piping// Cellular Glass Thermal 38 (1.5) 38 (1.5) 38 (1.5) 38 (1.5) E N D
VA220711.docx