Inspect and maintain canopies in SM SM SM accordance with UFC 3-110-04 Canopies As required Roofing Maintenance and Repair. Emergency Eyewash/Showers (Section 11-3) Test operation of the emergency SM SM SM eyewash/shower by pushing on the activation handles. Ensure the is not brown in color, due to rust in the piping or dirt seeping in from a hole in the buried piping. For systems with tempered water, ensure that the water that is being supplied by the emergency eyewash/shower is between 60 and 100 degrees F (16 and 39 degrees C). For systems with a Weekly horn and strobe light, ensure that the horn and strobe light activate when the activation lever on the emergency eyewash/shower is pushed. For systems that interface with Installation or fire emergency systems, pre-coordinate before Emergency Eyewash/ testing. At some Installations Showers emergency eyewashes and showers act as EFSOs and are tied into the fire alarm systems. Inspect portable/packaged safety SM SM SM showers and eyewash stations for proper operation. fluid levels. Where tap water is used, fluid must be replaced monthly. Less frequent intervals of fluid change, as recommended by the manufacturer, are acceptable Monthly where a solution or water additive is used. Ensure packaged eyewash supplies are within the listed expiration date. Tags or labels must be attached to the unit or adjacent to it, indicating the fluid change schedule.
Canopies Inspect and maintain canopies in accordance with UFC 3-110-04 Roofing Maintenance and Repair. As required SM SM SM Emergency Eyewash/Showers (Section 11-3) Emergency Eyewash/ Showers Test operation of the emergency eyewash/shower by pushing on the activation handles. Ensure the is not brown in color, due to rust in the piping or dirt seeping in from a hole in the buried piping. For systems with tempered water, ensure that the water that is being supplied by the emergency eyewash/shower is between 60 and 100 degrees F (16 and 39 degrees C). For systems with a horn and strobe light, ensure that the horn and strobe light activate when the activation lever on the emergency eyewash/shower is pushed. For systems that interface with Installation or fire emergency systems, pre-coordinate before testing. At some Installations emergency eyewashes and showers act as EFSOs and are tied into the fire alarm systems. Weekly SM SM SM Inspect portable/packaged safety showers and eyewash stations for proper operation. fluid levels. Where tap water is used, fluid must be replaced monthly. Less frequent intervals of fluid change, as recommended by the manufacturer, are acceptable where a solution or water additive is used. Ensure packaged eyewash supplies are within the listed expiration date. Tags or labels must be attached to the unit or adjacent to it, indicating the fluid change schedule. Monthly SM SM SM
ufc_3_460_03_appendix_c.docx