R250 R250 18 R290 R250 R250 22 R290 R250 R290 R250 R290 28 R250 R290 35 R290 R250 R290 42 R290 R250 R290 54 R290 Table 1: Suitable Copper Pipes The manufacturer, V.S.H. FITTINGS B.V. carries the following Certification: Manufactured in accordance with ISO 9001:2015 - 'Quality Management Systems’. Print & Identification XPress Stainless Steel GAS Pipe is marked as follows: SudoXPress stainless DN [dimension x wall thickness] Stainless steel/Edelstahl–Sanitary/Sanitär–GAS 1.4401/AISI316 EN10312 DVGW GW541 Reg.nr. [DVGW registration number] SVGW ÖVGW W1.397 WRAS VA1.22/20294 VA1.12/18769 SINTEF PZH SITAC 0168/04 ATEC 14/15-2097 CSTBat 116-2097 LPCB VdS G4080037 [operational pressure LPCB/VdS] bar <FM> [operational pressure FM] psi C(UL)US LISTED 4NB1 [operational pressure UL/cUL] psi KK NDE ATG 3057 [batch number or production date], [supplier code] [model designation, repeated every 60 cm] XPress Stainless Steel GAS fittings are marked as follows: Yellow marking, GAS, GT5/PN5, 316L, XPress, Dimension, DVGW XPress Stainless Steel GAS fittings have the following packaging labels: Dimension, Description, EAN No., Art. No., Approvals, Quantity Type R…..G, KE KELIT COPPERFIX Pipe is marked as follows: TX88 BS EN 1057 [Hardness H/HH] [Dimensions: 18x0.8] [TYPE X] [Production date] XPress Copper GAS fittings are marked as follows: Yellow marking, GAS, GT1/PN5, RYW, Dimension, DVGW, Gastec Qa XPress Copper GAS fittings have the following packaging labels: Type Dimension, Description, EAN no., Art. no., Approvals, Quantity G…..,
18 R250 R250 R290 22 R250 R250 R290 28 R250 R290 R250 R290 35 R250 R290 R290 42 R250 R290 R290 54 R250 R290 R290 Table 1: Suitable Copper Pipes The manufacturer, V.S.H. FITTINGS B.V. carries the following Certification: Manufactured in accordance with ISO 9001:2015 - 'Quality Management Systems’. Print & Identification XPress Stainless Steel GAS Pipe is marked as follows: SudoXPress stainless DN [dimension x wall thickness] Stainless steel/Edelstahl–Sanitary/Sanitär–GAS 1.4401/AISI316 EN10312 DVGW GW541 Reg.nr. [DVGW registration number] SVGW ÖVGW W1.397 WRAS VA1.22/20294 VA1.12/18769 SINTEF PZH SITAC 0168/04 ATEC 14/15-2097 CSTBat 116-2097 LPCB VdS G4080037 [operational pressure LPCB/VdS] bar <FM> [operational pressure FM] psi C(UL)US LISTED 4NB1 [operational pressure UL/cUL] psi KK NDE ATG 3057 [batch number or production date], [supplier code] [model designation, repeated every 60 cm] XPress Stainless Steel GAS fittings are marked as follows: Yellow marking, GAS, GT5/PN5, 316L, XPress, Dimension, DVGW XPress Stainless Steel GAS fittings have the following packaging labels: Type R…..G, Dimension, Description, EAN No., Art. No., Approvals, Quantity KE KELIT COPPERFIX Pipe is marked as follows: TX88 BS EN 1057 [Hardness H/HH] [Dimensions: 18x0.8] [TYPE X] [Production date] XPress Copper GAS fittings are marked as follows: Yellow marking, GAS, GT1/PN5, RYW, Dimension, DVGW, Gastec Qa XPress Copper GAS fittings have the following packaging labels: Type G….., Dimension, Description, EAN no., Art. no., Approvals, Quantity
VSH-XPress-GAS-Australasia-Technical-Specification-Rev1-12-03-18.docx