The total combined length of exhaust and intake vents cannot exceed 85 combined feet for venting or 200 combined 2” feet for combustion air must be supplied when drawing air from the mechanical room. Avoid the 3” venting. Adequate room contaminates listed in the installation manual. (Refer to appliance installation manual venting section for additional venting requirements.) The heater shall be in compliance with the NOx emissions limit set forth in SCAQMD Rule 1146.2. The heater shall be factory assembled, test-fired for correct BTU input, and adjusted for proper combustion parameters. Complete operating and installation instructions shall be furnished with every heater as packaged by the manufacturer for shipping. The surfaces of these products contacted by consumable water contain less than 0.25% lead by weight, as required by the Safe Drinking Water Act, Section 1417. The appliance shall operate at high elevations without additional parts. However, adjustments to the combustion system may be required at any elevation. See installation manual for combustion system setting details. Maximum unit dimensions shall be length inches, width inches and height inches. Maximum unit weight shall be pounds. NOTE: Due to variations in CSD-1 requirements from state to state, please consult with the factory for all controls required in your jurisdiction. NOTE: Westinghouse reserves the right to make product changes or updates without notice and will not be held liable for typographical errors in literature.
The total combined length of exhaust and intake vents cannot exceed 85 combined feet for 2” venting or 200 combined feet for 3” venting. Adequate combustion air must be supplied when drawing air from the mechanical room. Avoid the room contaminates listed in the installation manual. (Refer to appliance installation manual venting section for additional venting requirements.) The heater shall be in compliance with the NOx emissions limit set forth in SCAQMD Rule 1146.2. The heater shall be factory assembled, test-fired for correct BTU input, and adjusted for proper combustion parameters. Complete operating and installation instructions shall be furnished with every heater as packaged by the manufacturer for shipping. The surfaces of these products contacted by consumable water contain less than 0.25% lead by weight, as required by the Safe Drinking Water Act, Section 1417. The appliance shall operate at high elevations without additional parts. However, adjustments to the combustion system may be required at any elevation. See installation manual for combustion system setting details. Maximum unit dimensions shall be length inches, width inches and height inches. Maximum unit weight shall be pounds. NOTE: Due to variations in CSD-1 requirements from state to state, please consult with the factory for all controls required in your jurisdiction. NOTE: Westinghouse reserves the right to make product changes or updates without notice and will not be held liable for typographical errors in literature.
whl-028.docx