TABLE 1.2 Facilities Maintenance Section (FMS) VENTILATION Date Location/Equipment Flow Rate Results Comments Average Water Treatment Plant/ Shop 129 fpm Adequate Ventilation Smoke Test-Good 6/4/13 #83/ Flouride Feeder #1 6/4/13 Water Treatment Plant/ Shop N/A N/A Not at time of inspection “ON” #83/ Flouride Feeder #2 6/4/13 Water Treatment Plant/ Shop N/A Inadequate Ventilation Smoke Test-Negligible #83/ Soda Ash Note: Machine is working; however, ventilation is not operable during the time of inspection. 6/4/13 Water Treatment Plant/ Shop 173 fpm Adequate Ventilation Smoke Test-Good #83/ Chemistry Water Lab 6/4/13 Water Treatment Plant/ Shop 104 fpm Adequate Ventilation Smoke Test-Good #83/ Operator control room Manufacturer: Hamilton 6/6/13 Roads and Grounds/ Shop #71/ 1700 fpm Adequate Ventilation Smoke Test-Good Vehicle Exhaust #1 6/6/13 Roads and Grounds/ Shop #71/ 1583 fpm Adequate Ventilation Smoke Test-Good Vehicle Exhaust #2 2.2 Attachment (4)
TABLE 1.2 Facilities Maintenance Section (FMS) VENTILATION Date Location/Equipment Flow Rate Average Results Comments 6/4/13 Water Treatment Plant/ Shop #83/ Flouride Feeder #1 129 fpm Adequate Ventilation Smoke Test-Good 6/4/13 Water Treatment Plant/ Shop #83/ Flouride Feeder #2 N/A N/A Not “ON” at time of inspection 6/4/13 Water Treatment Plant/ Shop #83/ Soda Ash N/A Inadequate Ventilation Smoke Test-Negligible Note: Machine is working; however, ventilation is not operable during the time of inspection. 6/4/13 Water Treatment Plant/ Shop #83/ Chemistry Water Lab 173 fpm Adequate Ventilation Smoke Test-Good 6/4/13 Water Treatment Plant/ Shop #83/ Operator control room 104 fpm Adequate Ventilation Smoke Test-Good Manufacturer: Hamilton 6/6/13 Roads and Grounds/ Shop #71/ Vehicle Exhaust #1 1700 fpm Adequate Ventilation Smoke Test-Good 6/6/13 Roads and Grounds/ Shop #71/ Vehicle Exhaust #2 1583 fpm Adequate Ventilation Smoke Test-Good 2.2 Attachment (4)
2014%20FMS%20PERIODIC%20INDUSTRIAL%20HYGIENE%20SURVEY.docx