Conformed drawings developed by the Contractor shall be issued as the next sequential revision from previous releases. The revision block shall state "For Record Purposes". All clouds, revision diamonds, and other interim control markings shall be removed. All information listed as "later" or "hold" shall be completed. The conformed drawings shall be clear and readable in both full size and B size reduction. Contractor shall provide new versions of Subcontractor drawings if the Owner judges originals to be too damaged, deteriorated, or illegible. All Subcontractors' drawings shall be conformed to reflect actual installed configuration. These Subcontractor drawings shall be in sufficient detail to indicate the kind, size, arrangement, weight of each component, and operation of component materials and devices, the external connections, anchorages, and supports required; the dimensions needed for installation, and correlation with other materials and equipment. Final Subcontractor's drawings shall be bound in the equipment operation and maintenance manuals. One electronic copy for each drawing shall be supplied in AutoCAD format in a version acceptable to PacifiCorp. Drawing Information: All AutoCAD and drawing requirements are per Specification DCAP876. This specification includes, but is not limited to, information on the following: [PacifiCorp] Title Block Information. /Borders are provided and required. Drawing numbers shall conform to the existing specific plant numbering guidelines. If there are no existing guidelines that apply, PacifiCorp will supply new numbers that can be used. Indexes, lists, data sheets, and schedules per Specification DCAP876, or other if approved. Drawing revisions. Lists All lists, including but not limited to drawing lists, instrument lists, equipment lists, circuit lists, raceway lists, conduit lists, piping and accessories lists, bills of materials, etc. shall be furnished in an Excel compatible file format per Specification DCAP876, or other as may be approved by Owner. Instrumentation Lists and Data Sheets: All instruments shall be given a "Tag Number" composed of two to four alpha characters and a three digit numeric reference per the Instrumentation Society of American standards and existing specific plant procedures.
Conformed drawings developed by the Contractor shall be issued as the next sequential revision from previous releases. The revision block shall state "For Record Purposes". All clouds, revision diamonds, and other interim control markings shall be removed. All information listed as "later" or "hold" shall be completed. The conformed drawings shall be clear and readable in both full size and B size reduction. Contractor shall provide new versions of Subcontractor drawings if the Owner judges originals to be too damaged, deteriorated, or illegible. All Subcontractors' drawings shall be conformed to reflect actual installed configuration. These Subcontractor drawings shall be in sufficient detail to indicate the kind, size, arrangement, weight of each component, and operation of component materials and devices, the external connections, anchorages, and supports required; the dimensions needed for installation, and correlation with other materials and equipment. Final Subcontractor's drawings shall be bound in the equipment operation and maintenance manuals. One electronic copy for each drawing shall be supplied in AutoCAD format in a version acceptable to PacifiCorp. Drawing Information: All AutoCAD and drawing requirements are per Specification DCAP876. This specification includes, but is not limited to, information on the following: [PacifiCorp] Title Block Information. /Borders are provided and required. Drawing numbers shall conform to the existing specific plant numbering guidelines. If there are no existing guidelines that apply, PacifiCorp will supply new numbers that can be used. Indexes, lists, data sheets, and schedules per Specification DCAP876, or other if approved. Drawing revisions. Lists All lists, including but not limited to drawing lists, instrument lists, equipment lists, circuit lists, raceway lists, conduit lists, piping and accessories lists, bills of materials, etc. shall be furnished in an Excel compatible file format per Specification DCAP876, or other as may be approved by Owner. Instrumentation Lists and Data Sheets: All instruments shall be given a "Tag Number" composed of two to four alpha characters and a three digit numeric reference per the Instrumentation Society of American standards and existing specific plant procedures.
2013S_RFP_EPCAgreementandAppendices_A-R_andSchedule1.DOCX