Belews Creek 1 Gm Badin-Tuckertown Woodleaf-Godbey Existing Operating Loading 100 kV Line Garden Procedure [2029] (93.3 %) (Yadkin Facility) 500 kV Line Accelerated 4 Years (Godbey) Oconee 1 Gm 1.08 miles 477 ACSR Lawsons Fork-Pinewood Lawsons Fork- Reconductor Loading B/W 100 kV Line 1 West Spartanburg [2030] (91.1 %) (Pinewood) W/B 100 kV Line 1 Accelerated 4 Years (Pinewood) $125,000 TABLE N DUKE ENERGY CAROLINAS SUMMARY OF POTENTIAL RELIABILITY ISSUES 2024 SHOULDER - WS2 Potential Potential Element Contingency Solution Issue ($2013) Belews Creek 1 Gm High Rock-Tuckertown Woodleaf-Godbey Existing Operating Loading 100 kV Line Garden Procedure [2024] (102.5 %) (Yadkin Facility) 500 kV Line Accelerated 2 Years (Godbey)
Badin-Tuckertown 100 kV Line (Yadkin Facility) Belews Creek 1 Gm Woodleaf-Godbey Garden 500 kV Line (Godbey) Loading (93.3 %) Existing Operating Procedure [2029] Accelerated 4 Years Lawsons Fork-Pinewood B/W 100 kV Line 1 (Pinewood) Oconee 1 Gm Lawsons Fork- West Spartanburg W/B 100 kV Line 1 (Pinewood) Loading (91.1 %) 1.08 miles 477 ACSR Reconductor [2030] Accelerated 4 Years $125,000 TABLE N DUKE ENERGY CAROLINAS SUMMARY OF POTENTIAL RELIABILITY ISSUES 2024 SHOULDER - WS2 Element Contingency Potential Issue Potential Solution ($2013) High Rock-Tuckertown 100 kV Line (Yadkin Facility) Belews Creek 1 Gm Woodleaf-Godbey Garden 500 kV Line (Godbey) Loading (102.5 %) Existing Operating Procedure [2024] Accelerated 2 Years
2013_Carolinas_Wind_Study_Report_FINAL_redacted.docx