-0.2Hz 4 75% +10% 20 minutes (Step) -0.5Hz 5 75% +25% 20 minutes (ramp of 1Hz/sec) +0.5Hz 6 75% -25% 10 minutes (ramp of 1Hz/sec) +0.5Hz 7 75% -25% 10 minutes (ramp of 2Hz/sec) -0.2Hz 8 90% +10% 20 minutes (Step) -0.5Hz 9 90% +10% 10 minutes (ramp of 1Hz/sec) -0.5Hz 10 90% +10% 10 minutes (ramp of 2Hz/sec) -0.2Hz 11 92% +8% 20 minutes (Step) -0.2Hz 12 95% +5% 20 minutes (Step) +0.5Hz 13 100% -25% 10 minutes (ramp of 1Hz/sec) +0.5Hz 14 100% -25% 10 minutes (ramp of 2Hz/sec) All of the following trends and screenshots must be recorded by the Unit during the test. Failure to provide any of these trends will result in test cancellation. No. Signal Name Sample Rate Source Active Power at Connection Point Unit to specify, or as 1 Unit to specify (MW) agreed with TSO Reactive Power at Connection Unit to specify, or as 2 Unit to specify Point (Mvar) agreed with TSO Unit to specify, 100ms or as 3 Active at Generator (MW) Unit to specify agreed with TSO Reactive Power at Generator Unit to specify, 100ms or as 4 Unit to specify (Mvar) agreed with TSO Generator Circuit Breaker position 5 Unit to specify, Unit to specify (Open / Closed) Unit to specify, or as 6 Generator Voltage (kV) Unit to specify agreed with TSO Unit to specify, 100ms or as 7 Turbine Speed (RPM) Unit to specify agreed with TSO Unit to specify, or as 8 Shaft Vibration (µmp-p) Unit to specify agreed with TSO Unit to specify, or as 9 Blade Path Temperature (°C) Unit to specify agreed with TSO
4 75% -0.2Hz (Step) +10% 20 minutes 5 75% -0.5Hz (ramp of 1Hz/sec) +25% 20 minutes 6 75% +0.5Hz (ramp of 1Hz/sec) -25% 10 minutes 7 75% +0.5Hz (ramp of 2Hz/sec) -25% 10 minutes 8 90% -0.2Hz (Step) +10% 20 minutes 9 90% -0.5Hz (ramp of 1Hz/sec) +10% 10 minutes 10 90% -0.5Hz (ramp of 2Hz/sec) +10% 10 minutes 11 92% -0.2Hz (Step) +8% 20 minutes 12 95% -0.2Hz (Step) +5% 20 minutes 13 100% +0.5Hz (ramp of 1Hz/sec) -25% 10 minutes 14 100% +0.5Hz (ramp of 2Hz/sec) -25% 10 minutes All of the following trends and screenshots must be recorded by the Unit during the test. Failure to provide any of these trends will result in test cancellation. No. Signal Name Sample Rate Source 1 Active Power at Connection Point (MW) Unit to specify, or as agreed with TSO Unit to specify 2 Reactive Power at Connection Point (Mvar) Unit to specify, or as agreed with TSO Unit to specify 3 Active at Generator (MW) Unit to specify, 100ms or as agreed with TSO Unit to specify 4 Reactive Power at Generator (Mvar) Unit to specify, 100ms or as agreed with TSO Unit to specify 5 Generator Circuit Breaker position (Open / Closed) Unit to specify, Unit to specify 6 Generator Voltage (kV) Unit to specify, or as agreed with TSO Unit to specify 7 Turbine Speed (RPM) Unit to specify, 100ms or as agreed with TSO Unit to specify 8 Shaft Vibration (µmp-p) Unit to specify, or as agreed with TSO Unit to specify 9 Blade Path Temperature (°C) Unit to specify, or as agreed with TSO Unit to specify
Test_46_48_Operating-Reserves-Final.docx