Check it has not been discharged or the tag tampered with. Further Info: Fire Hose Reels SWP: Work Equipment and Fire Safety Competency Responsible Person and Competent Person Requirement: RP Condition Inspection – Requirement: CP Testing and inspection (Service / Maintenance) – RP Layperson – Qualification CP Member of Institute of fire engineers with British – Requirement: Standard 5306 RP Monthly – Frequency: CP 12 Monthly – RP Monthly – Best Practice: CP 12 Monthly – Information Exchange RP Quarterly – Upload Frequency: CP 12 Monthly – Further Info: A fire hose is a high-pressure hose used to carry water or other fire retardant (such as foam) to a fire to extinguish it. Fire Doors including automatic hold open – SWP: Work Equipment, Fire Safety and Fire door guidance Competency Responsible Person and Competent Person Requirement: Inspection RP Condition – Requirement: CP Testing and inspection (Service / Maintenance) – Qualification RP Layperson – Requirement: CP Member of Institute of fire engineers – RP Weekly (If not included in Fire Risk Assessment) – Frequency: CP 6 Monthly – RP Weekly – Best Practice: CP 6 Monthly – Information Exchange RP Quarterly – Upload Frequency: CP 6 Monthly – Further Info: The weekly visual inspection should be carried out by the RP, only where the Fire Risk Assessment has identified scheduled inspections of fire doors at periodic intervals and is included in the action plan may the weekly RP inspection be not applicable. The condition check should include; door operation, seals, 3mm gap between frame and door, function test of automatic held open doors.
Further Info: Check it has not been discharged or the tag tampered with. Fire Hose Reels SWP: Work Equipment and Fire Safety Competency Requirement: Responsible Person and Competent Person Inspection Requirement: RP – Condition CP – Testing and inspection (Service / Maintenance) Qualification Requirement: RP – Layperson CP – Member of Institute of fire engineers with British Standard 5306 Frequency: RP – Monthly CP – 12 Monthly Best Practice: RP – Monthly CP – 12 Monthly Information Exchange Upload Frequency: RP – Quarterly CP – 12 Monthly Further Info: A fire hose is a high-pressure hose used to carry water or other fire retardant (such as foam) to a fire to extinguish it. Fire Doors – including automatic hold open SWP: Work Equipment, Fire Safety and Fire door guidance Competency Requirement: Responsible Person and Competent Person Inspection Requirement: RP – Condition CP – Testing and inspection (Service / Maintenance) Qualification Requirement: RP – Layperson CP – Member of Institute of fire engineers Frequency: RP – Weekly (If not included in Fire Risk Assessment) CP – 6 Monthly Best Practice: RP – Weekly CP – 6 Monthly Information Exchange Upload Frequency: RP – Quarterly CP – 6 Monthly Further Info: The weekly visual inspection should be carried out by the RP, only where the Fire Risk Assessment has identified scheduled inspections of fire doors at periodic intervals and is included in the action plan may the weekly RP inspection be not applicable. The condition check should include; door operation, seals, 3mm gap between frame and door, function test of automatic held open doors.
swp%20property%20management%20and%20compliance%20v5%2000%2024-08-2012.docx