All other component blast 790 785 Y Adequate Capture gates CLOSED during Powermatic 15” measurement Planer All other component blast 262 785 N Adequate Capture gates OPEN during measurements EXHAUST VENTILATION EVALUATION SUMMARY MCCS 17 December 2014 COMMAND: DATE: BUILDING/LOCATION: 3167, Wood Shop TYPE: Stationary Woodworking Equipment Facilities Maintenance SHOP: Measured Required Meets Volumetric Volumetric Equipment Required Smoke Test Comments Flow Rate Flow Rate Standard? (cfm) (cfm) All other component blast 110 100 Y Adequate Capture gates CLOSED during Dewalt measurement Compound All other component blast Mitre Saw 28 100 N Adequate Capture gates OPEN during measurements Note: fpm=feet per minute
Powermatic 15” Planer 790 785 Y Adequate Capture All other component blast gates CLOSED during measurement 262 785 N Adequate Capture All other component blast gates OPEN during measurements EXHAUST VENTILATION EVALUATION SUMMARY COMMAND: MCCS BUILDING/LOCATION: 3167, Wood Shop SHOP: Facilities Maintenance DATE: 17 December 2014 TYPE: Stationary Woodworking Equipment Equipment Measured Volumetric Flow Rate (cfm) Required Volumetric Flow Rate (cfm) Meets Required Standard? Smoke Test Comments Dewalt Compound Mitre Saw 110 100 Y Adequate Capture All other component blast gates CLOSED during measurement 28 100 N Adequate Capture All other component blast gates OPEN during measurements Note: fpm=feet per minute
2015%20MCCS%20Periodic%20Industrial%20Hygiene%20Survey%20Report.docx