operator Master Master certificate vault meter vault or contains contains standing standing water water will be from from required to Does leaking unknown Does demonstrate water origin*. (see that system the photo #) operator has achieved (see photo the The master exist appropriate exist #) meter vault at in in level of the any any certification. The connection master to Alternatively, the meter vault at the system the [wholesaler] pits? could employ pits? water connection system to Yes Yes a certified the contained contract standing [wholesaler] No No operator; water water system caused If so, by contained unknown If what will be standing source(s). so, is the required to water caused water what show the by could leaking create a is the of contractual water potential system the agreement backflow components of and the in problem the vault. if the contract This water the system operator’s loses could create a certification potential pressure and level. the backflow water is Information problem siphoned if on certified the back system into the Wyoming loses main. Since contract pressure and the operators the [consecutive] water is may be found siphoned is responsible at the for back the into the following main. maintenance The website: . of components the master must meter be repaired to connection, the halt the leakage. [consecutive] must identify the source of the standing water. If the source of the water is leakage from water system
operator certificate or will be required to demonstrate that the operator has achieved the appropriate level of certification. Alternatively, the system could employ a certified contract operator; will be required to show the contractual agreement and the contract operator’s certification level. Information on certified Wyoming contract operators may be found at the following website: . Does exist in any pits? Yes No If so, what is the of the Master meter vault contains standing water from leaking water system (see photo #) The master meter vault at the connection to the [wholesaler] water system contained standing water caused by leaking water system components in the vault. This water could create a potential backflow problem if the system loses pressure and the water is siphoned back into the main. The components must be repaired to halt the leakage. Does exist in any pits? Yes No If so, what is the of the Master vault contains standing water from unknown origin*. (see photo #) The master meter vault at the connection to the [wholesaler] water system contained standing water caused by unknown source(s). water could create a potential backflow problem if the system loses pressure and the water is siphoned back into the main. Since the [consecutive] is responsible for the maintenance of the master meter connection, the [consecutive] must identify the source of the standing water. If the source of the water is leakage from water system
ss_wyoming_form.docx