25 Nickel, mg / dm3 < 0,01 26 Anionic Surface Active Agents, 0,012 0,05 мг/дм3 — 27 Fluoride mg / dm3 0,17 0,19 — 28 Oil, mg / dm3 <0,01 0,04 — 29 Sodium, mg / dm3 16,17 23,95 — Silicon, mg / dm3 30 0,1 6,09 — 31 Cobalt mg / dm3 <0,05 32 Selenium mg / dm3 <0,0005 0,0095 — 33 Antimony, mg / dm3 <0,0005 0,0006 — 34 Strontium, mg / dm3 <0,01 0,21 — 35 Microbial number, CFU / cm3 33 - 1500 36 Collihages, BDO / dm3 0 - 2600 37 Phytoplankton, cl / cm3 - 135000 Index Coliforms, colony forming units(КУО)/ dm3 38 1500 - more 110000 39 Temperature, 1 - 25 оС 40 Total alkalinity mg. eq / dm3 3,1 6,0 — 41 BOD5, mgО2/dm3 2,24 6,96 — 42 Dissolved oxygen mgO2 / dm3 2,16 14,42 — 43 Permanganate oxidation, mgO2 / dm3 7,84 17,20 — 3.2 Review of Vinnytsia supply system are two complexes of treatment facilities on the territory of the water pumping station, which were put into operation in different years. The complex of buildings of station №2, capacity of 100 thousand m3 / day, which was put into operation stage-wise in 1969 and in 1979. Complex of facilities of station capacity 107 thousand m3 / day, which was put №3, into operation in 1990. The total design capacity of the water treatment plant is 207 thousand m3 / day. The detailed technological scheme of water pumping stations 2, 3 is shown in Figure 1.
25 Nickel, mg / dm3 < 0,01 26 Anionic Surface Active Agents, мг/дм3 0,012 — 0,05 27 Fluoride mg / dm3 0,17 — 0,19 28 Oil, mg / dm3 <0,01 — 0,04 29 Sodium, mg / dm3 16,17 — 23,95 30 Silicon, mg / dm3 0,1 — 6,09 31 Cobalt mg / dm3 <0,05 32 Selenium mg / dm3 <0,0005 — 0,0095 33 Antimony, mg / dm3 <0,0005 — 0,0006 34 Strontium, mg / dm3 <0,01 — 0,21 35 Microbial number, CFU / cm3 33 - 1500 36 Collihages, BDO / dm3 0 - 2600 37 Phytoplankton, cl / cm3 - 135000 38 Index Coliforms, colony forming units(КУО)/ dm3 1500 - more 110000 39 Temperature, оС 1 - 25 40 Total alkalinity mg. eq / dm3 3,1 — 6,0 41 BOD5, mgО2/dm3 2,24 — 6,96 42 Dissolved oxygen mgO2 / dm3 2,16 — 14,42 43 Permanganate oxidation, mgO2 / dm3 7,84 — 17,20 3.2 Review of Vinnytsia supply system are two complexes of treatment facilities on the territory of the water pumping station, which were put into operation in different years. The complex of buildings of station №2, capacity of 100 thousand m3 / day, which was put into operation stage-wise in 1969 and in 1979. Complex of facilities of station №3, capacity 107 thousand m3 / day, which was put into operation in 1990. The total design capacity of the water treatment plant is 207 thousand m3 / day. The detailed technological scheme of water pumping stations 2, 3 is shown in Figure 1.
Terms_%20of_%20Reference_VIN-CQ-02.docx