CHAPTER 29 PLUMBING SYSTEMS [P] Table 2902.1 MINIUMUM NUMBER OF REQUIRED PLUMBING FIXTURESa (See Sections 2902.1.1 and 2902.2) Water Closetsf (Urinals See Section 419.2 of Drinking the International Fountainsg (See Plumbing Code) Lavatories Section 410.1 of Bathtubs/ the International Male Female Male Female No. Classification Occupancy Description Showers Plumbing Code Other Theaters and other buildings for the 1 service A-1d 1 per 125 1 per 65 60 1 per 200 1 per 500 — performing arts and sinke motion pictures Nightclubs, bars, taverns, halls 1 service 1 per 40 1 per 40 1 per 75 1 per 500 — and buildings for sink similar purposes A-2d Restaurants, 1 service banquet halls and 1 per 75 1 per 75 1 per 200 1 per 500 — sink food courts Auditoriums without permanent seating, art galleries, exhibition halls, 1 service 1 per 125 1 per 65 60 1 per 200 1 per 500 — museums, lecture sink halls, libraries, arcades and gymnasiums A-3d 1 Assembly Passenger 1 service terminals and 1 per 500 1 per 500 1 per 750 1 per 1,000 — sink transport facilitiesf Places of worship 1 service and other religious 1 per 150 1 per 75 1 per 200 1 per 1,000 — sink services 1 per 75 for 1 per 40 35 the first for the first Coliseums, arenas, 1,500 and 1 1,520 and 1 skating rinks, pools per 120 for per 60 for 1 per 1 service A-4 and tennis courts for 1 per 150 1 per 1,000 — the the 200 sink indoor sporting remainder remainder events and activities exceeding exceeding 1,500 1,520 1 per 75 for 1 per 40 35 Stadiums, the first for the first amusement 1,500 and 1 1,520 and 1 bleachers and per 120 for per 60 for 1 per 1 service A-5 1 per 150 1 per 1,000 — grandstands for the the 200 sink outdoor sporting remainder remainder events and activities exceeding exceeding 1,500 1,520 (continued) [P] Table 2902.1 continued – MINIUMUM NUMBER OF REQUIRED PLUMBING FIXTURESa
CHAPTER 29 PLUMBING SYSTEMS [P] Table 2902.1 MINIUMUM NUMBER OF REQUIRED PLUMBING FIXTURESa (See Sections 2902.1.1 and 2902.2) No. Classification Occupancy Description Water Closetsf (Urinals See Section 419.2 of the International Plumbing Code) Lavatories Bathtubs/ Showers Drinking Fountainsg (See Section 410.1 of the International Plumbing Code Other Male Female Male Female 1 Assembly A-1d Theaters and other buildings for the performing arts and motion pictures 1 per 125 1 per 65 60 1 per 200 — 1 per 500 1 service sinke A-2d Nightclubs, bars, taverns, halls and buildings for similar purposes 1 per 40 1 per 40 1 per 75 — 1 per 500 1 service sink Restaurants, banquet halls and food courts 1 per 75 1 per 75 1 per 200 — 1 per 500 1 service sink A-3d Auditoriums without permanent seating, art galleries, exhibition halls, museums, lecture halls, libraries, arcades and gymnasiums 1 per 125 1 per 65 60 1 per 200 — 1 per 500 1 service sink Passenger terminals and transport facilitiesf 1 per 500 1 per 500 1 per 750 — 1 per 1,000 1 service sink Places of worship and other religious services 1 per 150 1 per 75 1 per 200 — 1 per 1,000 1 service sink A-4 Coliseums, arenas, skating rinks, pools and tennis courts for indoor sporting events and activities 1 per 75 for the first 1,500 and 1 per 120 for the remainder exceeding 1,500 1 per 40 35 for the first 1,520 and 1 per 60 for the remainder exceeding 1,520 1 per 200 1 per 150 — 1 per 1,000 1 service sink A-5 Stadiums, amusement bleachers and grandstands for outdoor sporting events and activities 1 per 75 for the first 1,500 and 1 per 120 for the remainder exceeding 1,500 1 per 40 35 for the first 1,520 and 1 per 60 for the remainder exceeding 1,520 1 per 200 1 per 150 — 1 per 1,000 1 service sink (continued) [P] Table 2902.1 – continued MINIUMUM NUMBER OF REQUIRED PLUMBING FIXTURESa
2015%20IBC%20Running%20Doc%20with%20Proposed%20Amendments.docx