Issue 5 Security Rating 3, is not considered to be adequate. 2.9.6 The of the critical area must be made secure up to the floor construction above. The internal ceiling construction need only be designed to achieve containment requirements. Lighting and power 2.10.1 Standard (general purpose) light fittings and electrical outlet sockets are adequate light fittings to be positioned to avoid all shadows over any working surfaces whether from high level fittings or persons standing in front of working surfaces benches and light fitting positions to be such that need for task lighting is avoided adequate numbers (as discussed and agreed with Project Sponsor Group) of electrical and data points to be provided, both under and over bench, to avoid excessive trailing of leads and use of multi adapters. Additional requirements for CL3 laboratories: 2.10.2 Standard (general purpose) fittings and electrical outlet sockets are adequate - light fittings to be suspended or surface mounted with minimal ingress into ceiling and visible seal (recessed fittings not acceptable). 2.10.3 Non-maintained emergency lighting to be provided in all CL3 areas adequate to enable staff to make work safe under power loss conditions. Additional requirements for CL3 laboratories subject to ATCSA controls: 2.10.4 Any utility (electricity, telecommunication, alarm monitoring etc.) essential for the safety and security of the critical area must be secured in appropriate housings with access covers meeting LPS 1175: Issue 5, Security Rating 4. Miscellaneous 2.11.1 No requirement for emergency drench shower unless significant volumes of hazardous
Issue 5 Security Rating 3, is not considered to be adequate. 2.9.6 The of the critical area must be made secure up to the floor construction above. The internal ceiling construction need only be designed to achieve containment requirements. Lighting and power 2.10.1 Standard (general purpose) light fittings and electrical outlet sockets are adequate light fittings to be positioned to avoid all shadows over any working surfaces whether from high level fittings or persons standing in front of working surfaces benches and light fitting positions to be such that need for task lighting is avoided adequate numbers (as discussed and agreed with Project Sponsor Group) of electrical and data points to be provided, both under and over bench, to avoid excessive trailing of leads and use of multi adapters. Additional requirements for CL3 laboratories: 2.10.2 Standard (general purpose) fittings and electrical outlet sockets are adequate - light fittings to be suspended or surface mounted with minimal ingress into ceiling and visible seal (recessed fittings not acceptable). 2.10.3 Non-maintained emergency lighting to be provided in all CL3 areas adequate to enable staff to make work safe under power loss conditions. Additional requirements for CL3 laboratories subject to ATCSA controls: 2.10.4 Any utility (electricity, telecommunication, alarm monitoring etc.) essential for the safety and security of the critical area must be secured in appropriate housings with access covers meeting LPS 1175: Issue 5, Security Rating 4. Miscellaneous 2.11.1 No requirement for emergency drench shower unless significant volumes of hazardous
Safety_Office_Requirement_-_LM_update09Oct14.docx