Maintain constant ambient room temperature for 48 before, during and after installation or until cured. Minimum temperature of 10°C (50°F) and maximum temperature of 30°C (85°F). Do not apply Product while ambient and substrate temperatures are rising. Erect suitable barriers and post legible signs at points of entry to prevent traffic and trades from entering the work area during application and curing period of the floor. Ensure adequate ventilation and air flow. WARRANTY Submit Warranty information in accordance with Section [01 77 00 Closeout Procedures] – [________]. Submit Applicator’s written warranty, signed and issued in the name of Owner warranting the Work of this Section against defects in materials and workmanship for a period of one (1) year from the date of Substantial Performance of the Work. Products MANUFACTURER Basis-of-Design Manufacturer: Sika Canada Inc. 601 Delmar Avenue, Pointe-Claire, Quebec, H9R 4A9 Phone (514) 697-2610, Fax (514) 697-3087 . Substitutions: Consultant may consider additional manufacturers having similar Products to Basis-of-Design Manufacturer listed above during the construction period, provided they meet the performance and aesthetic requirements established by the named Products. Submit requests for substitution in accordance with [Section 01 25 00 Substitution – Procedures] [________] before starting any Work of this Section: SYSTEM Resinous Flooring System: trowel applied and sealed decorative epoxy floor, composed of multi-coloured quartz aggregates finished with transparent top coats and as follows: Compressive Strength: 47.8 MPa (6,931 psi) at 28 days in accordance with ASTM C579. Flexural Strength: 11.1 MPa (1,610 psi) at 28 days in accordance with ASTM C580. Hardness: 85 Shore D at 7 days in accordance with ASTM D2240. VOC Content: 25 g/L in accordance with ASTM D2369. ≤ Pull-off Strength: > 4.9 MPa (>710 psi) with substrate failure in accordance with ASTM
Maintain constant ambient room temperature for 48 before, during and after installation or until cured. Minimum temperature of 10°C (50°F) and maximum temperature of 30°C (85°F). Do not apply Product while ambient and substrate temperatures are rising. Erect suitable barriers and post legible signs at points of entry to prevent traffic and trades from entering the work area during application and curing period of the floor. Ensure adequate ventilation and air flow. WARRANTY Submit Warranty information in accordance with Section [01 77 00 – Closeout Procedures] [________]. Submit Applicator’s written warranty, signed and issued in the name of Owner warranting the Work of this Section against defects in materials and workmanship for a period of one (1) year from the date of Substantial Performance of the Work. Products MANUFACTURER Basis-of-Design Manufacturer: Sika Canada Inc. 601 Delmar Avenue, Pointe-Claire, Quebec, H9R 4A9 Phone (514) 697-2610, Fax (514) 697-3087 . Substitutions: Consultant may consider additional manufacturers having similar Products to Basis-of-Design Manufacturer listed above during the construction period, provided they meet the performance and aesthetic requirements established by the named Products. Submit requests for substitution in accordance with [Section 01 25 00 – Substitution Procedures] [________] before starting any Work of this Section: SYSTEM Resinous Flooring System: trowel applied and sealed decorative epoxy floor, composed of multi-coloured quartz aggregates finished with transparent top coats and as follows: Compressive Strength: 47.8 MPa (6,931 psi) at 28 days in accordance with ASTM C579. Flexural Strength: 11.1 MPa (1,610 psi) at 28 days in accordance with ASTM C580. Hardness: 85 Shore D at 7 days in accordance with ASTM D2240. VOC Content: ≤ 25 g/L in accordance with ASTM D2369. Pull-off Strength: > 4.9 MPa (>710 psi) with substrate failure in accordance with ASTM
Spec%20Sikafloor%20Quartzite%20Trowel%20System%203-6mm%20Canada_05_2013v1.docx