The connector must protect the fuse from water or weather damage. Contact between the fuse and fuse holder must be spring loaded. Fuses must: 1. Be standard, midget, ferrule type 2. Have a nontime-delay feature 3. Be 13/32 by 1-1/2 inches Fuse ratings for luminaires are shown in the following table: Fuse Current Rating Requirements Circuit voltage Fuse voltage rating Soffit and roadway luminaires 120 V(ac) 250 V(ac) 5 A 240 V(ac) 250 V(ac) 5 A 480 V(ac) 500-600 V(ac) 5 A Fuse ratings for transformers are shown in the following table: Fuse Current Rating Requirements Circuit voltage Fuse voltage Fuse current rating for rating Single phase (two wires) Transformers (primary side) 1 kVA 2 kVA 3 kVA 120 V(ac) 250 V(ac) 10 A 20 A 30 A 240 V(ac) 250 V(ac) 6 A 10 A 20 A 480 V(ac) 500-600 V(ac) 3 A 6 A 10 A Replace section 86-1.02P(1) with: 10-19-18 86-1.02P(1) General The enclosures must be NEMA 3R and include a dead front panel and a hasp with a hole for a padlock. Except for a service equipment enclosure, an enclosure must: 1. Be manufactured from steel and either galvanized, cadmium plated, or powder coated 2. Mount to a standard, pole, post, or sign structural frame 3. Provide a minimum space of 2-1/2 inches between the internal components and the enclosure's sides The enclosure's machine screws and bolts must not protrude outside the cabinet wall. The fasteners on the exterior of an enclosure must be vandal resistant and not be removable. The exterior screws, nuts, bolts, and washers must be stainless steel. Add between 6th and 7th paragraphs of section 86-1.02P(2): 10-19-18 Service equipment enclosure must have the meter view windows located on the front side of the enclosure for Types III-AF, BF, CF and DF. Service equipment enclosure must have the view windows located on the back side of the enclosure for Types III-AR, BR, CR and DR.
The connector must protect the fuse from water or weather damage. Contact between the fuse and fuse holder must be spring loaded. Fuses must: 1. Be standard, midget, ferrule type 2. Have a nontime-delay feature 3. Be 13/32 by 1-1/2 inches Fuse ratings for luminaires are shown in the following table: Fuse Current Rating Requirements Circuit voltage Fuse voltage rating Soffit and roadway luminaires 120 V(ac) 250 V(ac) 5 A 240 V(ac) 250 V(ac) 5 A 480 V(ac) 500-600 V(ac) 5 A Fuse ratings for transformers are shown in the following table: Fuse Current Rating Requirements Circuit voltage Fuse voltage rating Fuse current rating for Single phase (two wires) Transformers (primary side) 1 kVA 2 kVA 3 kVA 120 V(ac) 250 V(ac) 10 A 20 A 30 A 240 V(ac) 250 V(ac) 6 A 10 A 20 A 480 V(ac) 500-600 V(ac) 3 A 6 A 10 A Replace section 86-1.02P(1) with: 10-19-18 86-1.02P(1) General The enclosures must be NEMA 3R and include a dead front panel and a hasp with a hole for a padlock. Except for a service equipment enclosure, an enclosure must: 1. Be manufactured from steel and either galvanized, cadmium plated, or powder coated 2. Mount to a standard, pole, post, or sign structural frame 3. Provide a minimum space of 2-1/2 inches between the internal components and the enclosure's sides The enclosure's machine screws and bolts must not protrude outside the cabinet wall. The fasteners on the exterior of an enclosure must be vandal resistant and not be removable. The exterior screws, nuts, bolts, and washers must be stainless steel. Add between 6th and 7th paragraphs of section 86-1.02P(2): 10-19-18 Service equipment enclosure must have the meter view windows located on the front side of the enclosure for Types III-AF, BF, CF and DF. Service equipment enclosure must have the view windows located on the back side of the enclosure for Types III-AR, BR, CR and DR.
RSS_A10-19-18__2018.docx