Assessment Changing Places Facility Performance Specification The following table outlines the Changing Places Performance Specifications and provides a comment as to whether the current design complies. Accessible Feature Design Performance Requirements Comments / Recommendation Complies Ceiling height The minimum ceiling height of the facility is to be determined by the design Dimension key items at next stage of documentation. To be confirmed of the ceiling hoist specified for the facility. OR Complies Ceiling height The facility must achieve the following as a minimum requirement, with Ceiling hoist dimensioned at xxxxmm from FFL to underside of track. To be confirmed regard to the ceiling installation and track system: or OR A minimum height of 2400mm clear unobstructed vertical height above Dimension distance from FFL to underside of track at next stage of Complies the finished floor level (AFFL) to the underside of any ceiling hoist track, documentation. ceiling hoist component or other fixture and fittings. Ceiling hoist Provide a powered room coverage hoist system that is permanently being Full coverage gantry indicated on drawings. To be confirmed charged. OR OR This is also called XY system or gantry, including 2 parallel fixed rails and a Full coverage gantry not indicated on drawings. Review hoist system Complies perpendicular moving traverse rail. and provide details at next stage of documentation. This must provide coverage over the entire room for greatest flexibility when the facility. Ensure full coverage of the bathroom, including toilet and change table, is provided. Ceiling hoist system equivalent to: Details have been provided for the track system. To be confirmed 1. Rail system with a safe working load (SWL) of 180kg minimum. Or OR 2. Two fixed parallel rails. Details have not been provided for the track system. Provide details at Complies 3. One moving traverse rail. (May require piggyback support rail.) next stage of documentation. 4. Includes wall or ceiling mounted charger. 5. Standard GPO required to be provided by builder at ceiling level. Ceiling hoist Hoist system equivalent to: Hoist complies as specified. To be confirmed 1. hoist OR OR 2. Lifting height up to a min 210cm Details have not been provided for the system. Provide details at Complies 3. Min load 180kg next stage of documentation. 4. Hoist Case Flame Retardant ABS
Assessment Changing Places Facility Performance Specification The following table outlines the Changing Places Performance Specifications and provides a comment as to whether the current design complies. Accessible Feature Design Performance Requirements Comments / Recommendation Complies Ceiling height The minimum ceiling height of the facility is to be determined by the design of the ceiling hoist specified for the facility. Dimension key items at next stage of documentation. To be confirmed OR Complies Ceiling height The facility must achieve the following as a minimum requirement, with regard to the ceiling installation and track system: A minimum height of 2400mm clear unobstructed vertical height above the finished floor level (AFFL) to the underside of any ceiling hoist track, ceiling hoist component or other fixture and fittings. Ceiling hoist dimensioned at xxxxmm from FFL to underside of track. or Dimension distance from FFL to underside of track at next stage of documentation. To be confirmed OR Complies Ceiling hoist Provide a powered room coverage hoist system that is permanently being charged. This is also called XY system or gantry, including 2 parallel fixed rails and a perpendicular moving traverse rail. This must provide coverage over the entire room for greatest flexibility when the facility. Ensure full coverage of the bathroom, including toilet and change table, is provided. Full coverage gantry indicated on drawings. OR Full coverage gantry not indicated on drawings. Review hoist system and provide details at next stage of documentation. To be confirmed OR Complies Ceiling hoist system equivalent to: 1. Rail system with a safe working load (SWL) of 180kg minimum. 2. Two fixed parallel rails. 3. One moving traverse rail. (May require piggyback support rail.) 4. Includes wall or ceiling mounted charger. 5. Standard GPO required to be provided by builder at ceiling level. Details have been provided for the track system. Or Details have not been provided for the track system. Provide details at next stage of documentation. To be confirmed OR Complies Ceiling hoist Hoist system equivalent to: 1. hoist 2. Lifting height up to a min 210cm 3. Min load 180kg 4. Hoist Case Flame Retardant ABS Hoist complies as specified. OR Details have not been provided for the system. Provide details at next stage of documentation. To be confirmed OR Complies
Schematic-Design-Review-Guidlines.docx