Fire Resistance Rating: indicated in Contract Documents for doors. Spreader Bar: Removable, at sill. Frame Anchorage Devices: To securely fasten to wall construction without distortion or stress. In accordance with fire resistance rating indicated in Contract Documents. Door Systems: Integrated Door Assemblies shall meet or exceed ANSI/BHMA A156.32 Standard for Integrated Opening Assemblies. Doors shall conform to ANSI/SDI A250.8, Grade 1 for Steel Doors. Door assemblies shall include door body with factory installed latching/locking devices and will include: An integrated continuous with hidden fasteners on the door edge. An adjustable leading edge with hidden lock mounting fasteners and integral, recessed smoke seal. Doors shall be constructed with a U-shaped, 16 gauge reinforcement channel top and bottom and will include metal internal reinforcements for closers and magnetic holder/releases. Door assemblies shall be tested and listed for use without the need for overlapping astragals. Thickness: 1-3/4 inches. Faces: 18 gauge cold rolled steel, with no seams or spot welds. Core: Honeycomb. Core: Steel stiffened. Core: Polystyrene. Core: Lead Configurations: Elevator smoke assembly, single. Elevator smoke assembly, pair. Elevator lobby assembly, single. Elevator lobby assembly, pair. Cross corridor fire doors, single. Cross corridor fire doors, pair. Stairwell doors, single. Stairwell doors, pair. of assembly, single. of assembly, pair. Surgical suites, single. Surgical suites, pair. Electric Doors: Remotely controlled. Operation: Fail safe. Operation: Fail secure. Operation: Electric unlatching in conjunction with motor operator by others. FINISHES The designations used in schedules and elsewhere to indicate hardware finishes are those listed in ANSI/BHMA A156.18 or traditional U.S. finishes shown by certain manufacturers for their products. Provide quality of finish, including thickness of plating or coating (if any), composition, hardness, and other qualities complying with manufacturer's standards, but in no case less than specified by referenced standards for the applicable units of hardware. Frames: Factory prime painted for field-applied finish.
Fire Resistance Rating: indicated in Contract Documents for doors. Spreader Bar: Removable, at sill. Frame Anchorage Devices: To securely fasten to wall construction without distortion or stress. In accordance with fire resistance rating indicated in Contract Documents. Door Systems: Integrated Door Assemblies shall meet or exceed ANSI/BHMA A156.32 Standard for Integrated Opening Assemblies. Doors shall conform to ANSI/SDI A250.8, Grade 1 for Steel Doors. Door assemblies shall include door body with factory installed latching/locking devices and will include: An integrated continuous with hidden fasteners on the door edge. An adjustable leading edge with hidden lock mounting fasteners and integral, recessed smoke seal. Doors shall be constructed with a U-shaped, 16 gauge reinforcement channel top and bottom and will include metal internal reinforcements for closers and magnetic holder/releases. Door assemblies shall be tested and listed for use without the need for overlapping astragals. Thickness: 1-3/4 inches. Faces: 18 gauge cold rolled steel, with no seams or spot welds. Core: Honeycomb. Core: Steel stiffened. Core: Polystyrene. Core: Lead Configurations: Elevator smoke assembly, single. Elevator smoke assembly, pair. Elevator lobby assembly, single. Elevator lobby assembly, pair. Cross corridor fire doors, single. Cross corridor fire doors, pair. Stairwell doors, single. Stairwell doors, pair. of assembly, single. of assembly, pair. Surgical suites, single. Surgical suites, pair. Electric Doors: Remotely controlled. Operation: Fail safe. Operation: Fail secure. Operation: Electric unlatching in conjunction with motor operator by others. FINISHES The designations used in schedules and elsewhere to indicate hardware finishes are those listed in ANSI/BHMA A156.18 or traditional U.S. finishes shown by certain manufacturers for their products. Provide quality of finish, including thickness of plating or coating (if any), composition, hardness, and other qualities complying with manufacturer's standards, but in no case less than specified by referenced standards for the applicable units of hardware. Frames: Factory prime painted for field-applied finish.
SECTION-081700-Synterga-Door-Specification.docx