POTENTIAL SPILL PREDICTION Potential oil locations and a description of existing measures for the avoidance and/or containment of the release of oils from the facility are presented in this section. Specific facility recommendations for improved containment measures are presented in Section 10.0. Potential Total Volume Potential Type Secondary Area/Source Spill Volume Flow Direction* (Gal.)/Source of Failure Containment (gal.) TRANSFORMERS #1 Transformer failure 255 255 On concrete pad, west ELS Building None Mineral Oil toward City Ave. Spill during oil transfer 25 by PECO** #2 Transformer failure 460 460 Onto concrete pad and Mandeville Hall None Mineral Oil ground. Spill during oil transfer 46 Owned by PECO** #3 Transformer failure 255 255 Onto concrete pad and Ashwood Hall None Mineral Oil ground. Spill during oil transfer 25 Owned by PECO** Transformer failure 210 #4 210 Onto concrete pad and None Moore Hall Mineral Oil ground. Spill during oil transfer 21 Transformer failure 319 #5 319 Onto concrete pad and None Quad T.H. Mineral Oil ground. Spill during oil transfer 31 #6 Transformer failure 150 150 On concrete pad, east Boiler Room #134 None Mineral Oil toward retaining wall. Spill during oil transfer 15 Power Plant #7 Transformer failure 150 150 On concrete pad, east Boiler Room #131 None Mineral Oil toward retaining wall. Spill during oil transfer 15 Power Plant Transformer failure 201 #8 201 Onto concrete pad and None Gest Lawn Mineral Oil ground. Spill during oil transfer 20 Transformer failure 237 #9 237 Onto concrete pad and None Post Hall 1 Mineral Oil ground. Spill during oil transfer 23 Transformer failure 237 #10 237 Onto concrete pad and None Post Hall 2 Mineral Oil ground. Spill during oil transfer 23 Transformer failure 264 #11 264 On concrete pad, east None Xavier Hall Mineral Oil toward Lapsley Lane. Spill during oil transfer 26
POTENTIAL SPILL PREDICTION Potential oil locations and a description of existing measures for the avoidance and/or containment of the release of oils from the facility are presented in this section. Specific facility recommendations for improved containment measures are presented in Section 10.0. Area/Source Total Volume (Gal.)/Source Potential Type of Failure Potential Spill Volume (gal.) Flow Direction* Secondary Containment TRANSFORMERS #1 ELS Building by PECO** 255 Mineral Oil Transformer failure 255 On concrete pad, west toward City Ave. None Spill during oil transfer 25 #2 Mandeville Hall Owned by PECO** 460 Mineral Oil Transformer failure 460 Onto concrete pad and ground. None Spill during oil transfer 46 #3 Ashwood Hall Owned by PECO** 255 Mineral Oil Transformer failure 255 Onto concrete pad and ground. None Spill during oil transfer 25 #4 Moore Hall 210 Mineral Oil Transformer failure 210 Onto concrete pad and ground. None Spill during oil transfer 21 #5 Quad T.H. 319 Mineral Oil Transformer failure 319 Onto concrete pad and ground. None Spill during oil transfer 31 #6 Boiler Room #134 Power Plant 150 Mineral Oil Transformer failure 150 On concrete pad, east toward retaining wall. None Spill during oil transfer 15 #7 Boiler Room #131 Power Plant 150 Mineral Oil Transformer failure 150 On concrete pad, east toward retaining wall. None Spill during oil transfer 15 #8 Gest Lawn 201 Mineral Oil Transformer failure 201 Onto concrete pad and ground. None Spill during oil transfer 20 #9 Post Hall 1 237 Mineral Oil Transformer failure 237 Onto concrete pad and ground. None Spill during oil transfer 23 #10 Post Hall 2 237 Mineral Oil Transformer failure 237 Onto concrete pad and ground. None Spill during oil transfer 23 #11 Xavier Hall 264 Mineral Oil Transformer failure 264 On concrete pad, east toward Lapsley Lane. None Spill during oil transfer 26
SPCC%202006%20FINALa%202010%20rev616.docx