Districts, Loading 21.2-C, 43.1, 43.2, 49.4-C, Appendix A Note: The Index entries immediately before and after High “District, are provided to show where this new entry belongs in the Index. Index, Page 17 Index Topic Rule . Height of Guy Figure 86 (Appendix G) High Fire-Threat District 18-A, 21.2-D, 37, 80.1-A, 80.1-B High Voltage Signs (See Marking) Note: The Index entries immediately before and after Fire-Threat “High District” are provided to show where this new entry belongs in the Index” General Order 95, Rule 35, Table 1, Case 14 and Reference (hhh) Adopted Rule in Final Form Table 1 Wire or Conductor Concerned A B C D E F G Span Wires Communication Trolley Supply Supply Supply Supply (Other than Conductors Contact, Conductors Conductors Conductors Conductors Case Nature of Trolley (Including Feeder of 0 - 750 and and and No. Clearance Span Open Wire, and Volts and Supply Supply Supply Wires) Cables and Span Supply Cables, Cables, Cables, Overhead Service Drops), Cables 750 - 22,500 22.5 - 300 300 - 550 Guys and Supply Service 0 - 5,000 Treated as Volts kV kV Messengers Drops of Volts in Rule 57.8 (mm) 0 - 750 Volts
Districts, Loading 21.2-C, 43.1, 43.2, 49.4-C, Appendix A Note: The Index entries immediately before and after “District, High are provided to show where this new entry belongs in the Index. Index, Page 17 Index Topic Rule . Height of Guy Figure 86 (Appendix G) High Fire-Threat District 18-A, 21.2-D, 37, 80.1-A, 80.1-B High Voltage Signs (See Marking) Note: The Index entries immediately before and after “High Fire-Threat District” are provided to show where this new entry belongs in the Index” General Order 95, Rule 35, Table 1, Case 14 and Reference (hhh) Adopted Rule in Final Form Case No. Nature of Clearance Table 1 Wire or Conductor Concerned A Span Wires (Other than Trolley Span Wires) Overhead Guys and Messengers B Communication Conductors (Including Open Wire, Cables and Service Drops), Supply Service Drops of 0 - 750 Volts C Trolley Contact, Feeder and Span 0 - 5,000 Volts D Supply Conductors of 0 - 750 Volts and Supply Cables Treated as in Rule 57.8 E Supply Conductors and Supply Cables, 750 - 22,500 Volts F Supply Conductors and Supply Cables, 22.5 - 300 kV G Supply Conductors and Supply Cables, 300 - 550 kV (mm)
200976667.docx