Installation and Relocation RFP RFP Attachment A – Requirements Response Template Termination hardware shall be provided for each pair/strand provided in the cable plant. Each pair/strand shall be terminated on each end on the appropriate hardware as outlined in the following sub-section. Fully Meets Partially Meets Meets w/Customization Does Not Meet Description: Twisted-Pair Cable Termination Each pair on each end of each intra-building backbone cable shall be terminated on 110AA2-100-FT or 110AA2-300- FT terminal blocks mounted on the plywood backboard provided and mounted in each FD. 110-C5 clips shall be installed on each five pairs in the cable once terminated on the 110 terminal blocks. Fully Meets Partially Meets Meets w/Customization Does Not Meet Description: Optical Cable Termination Each strand on each end of each intra-building backbone cable shall be terminated using a connector compatible with previously installed connectors. These connectors shall be housed in an appropriately sized optical fiber distribution center that will be mounted on an equipment rack. The optical fiber distribution center will be mounted using ‘external star’ star washers on every mounting screw. Sufficient connector panels in a twelve port configuration will be provided. Blank plates shall occupy any vacant connector panel spaces. Fully Meets Partially Meets Meets w/Customization Does Not Meet Description: Capitol Complex Cabling Each building on the Capitol Grounds shall be provided with a 100Ω, shielded, flooded, 24 AWG , twisted-pair, PE89 outside plant cable sized in accordance with the building’s internal pair requirements. In addition, each building on this project may be provided with optical fiber cables. Where cost effective, ‘Composite’ or cables may be allowed on each individual projects. ‘hybrid’ Fully Meets Partially Meets Meets w/Customization Does Not Meet Description: Inter-Building Optical Fiber Cable All optical fiber cable used for outside plant on a project shall be dielectric cable (no metallic components whatsoever). Each cable shall be rated as OFNR and shall be a loose tube construction flooded to prevent the intrusion of water into the cable assembly. Meets Partially Meets Meets w/Customization Does Not Meet Description: Multimode Optical Cable This shall be manufactured to provide transmission, bandwidth and performance in accordance with ANSI/TIA/EIA-568-B.1 and B.3. Each strand of multimode cable shall be 50/125µm, loose tube and rated to provide as a minimum the following parameters:
Installation and Relocation RFP RFP – Attachment A Requirements Response Template Termination hardware shall be provided for each pair/strand provided in the cable plant. Each pair/strand shall be terminated on each end on the appropriate hardware as outlined in the following sub-section. Fully Meets Partially Meets Meets w/Customization Does Not Meet Description: Twisted-Pair Cable Termination Each pair on each end of each intra-building backbone cable shall be terminated on 110AA2-100-FT or 110AA2-300- FT terminal blocks mounted on the plywood backboard provided and mounted in each FD. 110-C5 clips shall be installed on each five pairs in the cable once terminated on the 110 terminal blocks. Fully Meets Partially Meets Meets w/Customization Does Not Meet Description: Optical Cable Termination Each strand on each end of each intra-building backbone cable shall be terminated using a connector compatible with previously installed connectors. These connectors shall be housed in an appropriately sized optical fiber distribution center that will be mounted on an equipment rack. The optical fiber distribution center will be mounted using ‘external star’ star washers on every mounting screw. Sufficient connector panels in a twelve port configuration will be provided. Blank plates shall occupy any vacant connector panel spaces. Fully Meets Partially Meets Meets w/Customization Does Not Meet Description: Capitol Complex Cabling Each building on the Capitol Grounds shall be provided with a 100Ω, shielded, flooded, 24 AWG , twisted-pair, PE89 outside plant cable sized in accordance with the building’s internal pair requirements. In addition, each building on this project may be provided with optical fiber cables. Where cost effective, ‘Composite’ or ‘hybrid’ cables may be allowed on each individual projects. Fully Meets Partially Meets Meets w/Customization Does Not Meet Description: Inter-Building Optical Fiber Cable All optical fiber cable used for outside plant on a project shall be dielectric cable (no metallic components whatsoever). Each cable shall be rated as OFNR and shall be a loose tube construction flooded to prevent the intrusion of water into the cable assembly. Meets Partially Meets Meets w/Customization Does Not Meet Description: Multimode Optical Cable This shall be manufactured to provide transmission, bandwidth and performance in accordance with ANSI/TIA/EIA-568-B.1 and B.3. Each strand of multimode cable shall be 50/125µm, loose tube and rated to provide as a minimum the following parameters:
Solicitation0900000228AttachmentA.docx