High No out-of-plane wall anchors exist nor does a load path exist to transfer diaphragm shear to connection: the classroom or offices walls. Entrance Anchorage of canopies is inadequate. canopies: Stairs: URM is unacceptable in the stairways. * G Gravity EQ Earthquake W Wind S - Snow – – – Comments: Table 5- 4 Photo No. Item Description No. Dry rot: Evidence of dry rot exists in the soffit at the northwest corner of the warehouse. Mildew: Evidence of mildew exists in the ceiling of the boiler room. Termite: Evidence of termite damage exists in the foundation next to the south stairway. Settlement: Approximately 1” of settlement was observed at the front entry. Corrosion: Corrosion was observed in rebar in the concrete column at the south end of the warehouse. Comments:
High connection: No out-of-plane wall anchors exist nor does a load path exist to transfer diaphragm shear to the classroom or offices walls. Entrance canopies: Anchorage of canopies is inadequate. Stairs: URM is unacceptable in the stairways. * G – Gravity EQ – Earthquake W – Wind S - Snow Comments: Table 5- 4 No. Item Description Photo No. Dry rot: Evidence of dry rot exists in the soffit at the northwest corner of the warehouse. Mildew: Evidence of mildew exists in the ceiling of the boiler room. Termite: Evidence of termite damage exists in the foundation next to the south stairway. Settlement: Approximately 1” of settlement was observed at the front entry. Corrosion: Corrosion was observed in rebar in the concrete column at the south end of the warehouse. Comments:
SER-T-Welfare-Facilities-US.docx