Table V.I.2. - Boiler/Industrial Furnace Permit Conditions, Monitoring and Automatic Waste Feed Cutoff Systems [Use a table for each unit and fill in all columns with the appropriate information] Parameter Monitoring Monitoring Device Device Location Permit AWFCO Y/N2 Basis1 Operating Parameters Maximum Total Hazardous Waste Feed Rate [Volumetric Flow Meter3 or Feed System lb/hr Y [Additional hazardous waste feed limits shall be Mass Flow as applicable added as determined necessary based upon feed to the feed mechanism] mechanism and/or waste-specific needs] Maximum Total Pumpable Hazardous Waste Mass Volumetric Flow Meter3 or Feed System lb/hr Feed Rate [Not applicable for Tier I or Tier I Mass Flow Meter adjusted metals control limits] Minimum Primary Combustion Chamber Thermocouple [or other Primary °F Y Temperature device] Chamber Exit Minimum Secondary Combustion Chamber Thermocouple [or other Secondary °F Y Temperature device] Chamber Exit Maximum Secondary and/or Primary Combustion Thermocouple [or Secondary °F Y Chamber Temperature [Include if using Tier II, III device] Chamber Exit metals controls only] Maximum Flue Gas Temperature at PM Control Thermocouple [or other At entrance to °F Y Device Inlet [Tier II and Tier III Metals only as device] PM Control applicable] Device Maximum Combustion Gas Velocity Indicator [If Y condition is something other than "maximum combustion gas velocity", write specific name of condition] Atomization parameters [as necessary] Feed Rates: (Metals, Total Chlorine, and Ash) Volumetric Flow Meter3 or Mass Flow Meter Feed Limits Specified in Table N N Systems ____ [Maximum Constituent Feed Rates] Secondary Combustion Zone Pressure [or e.g., in. H2O [Yes, if neg. method for fugitives monitoring] pressure is used
Table V.I.2. - Boiler/Industrial Furnace Permit Conditions, Monitoring and Automatic Waste Feed Cutoff Systems [Use a table for each unit and fill in all columns with the appropriate information] Parameter Monitoring Basis1 Monitoring Device Device Location Permit AWFCO Y/N2 Operating Parameters Maximum Total Hazardous Waste Feed Rate [Additional hazardous waste feed limits shall be added as determined necessary based upon feed mechanism and/or waste-specific needs] [Volumetric Flow Meter3 or Mass Flow as applicable to the feed mechanism] Feed System lb/hr Y Maximum Total Pumpable Hazardous Waste Mass Feed Rate [Not applicable for Tier I or Tier I adjusted metals control limits] Volumetric Flow Meter3 or Mass Flow Meter Feed System lb/hr Minimum Primary Combustion Chamber Temperature Thermocouple [or other device] Primary Chamber Exit °F Y Minimum Secondary Combustion Chamber Temperature Thermocouple [or other device] Secondary Chamber Exit °F Y Maximum Secondary and/or Primary Combustion Chamber Temperature [Include if using Tier II, III metals controls only] Thermocouple [or device] Secondary Chamber Exit °F Y Maximum Flue Gas Temperature at PM Control Device Inlet [Tier II and Tier III Metals only as applicable] Thermocouple [or other device] At entrance to PM Control Device °F Y Maximum Combustion Gas Velocity Indicator [If condition is something other than "maximum combustion gas velocity", write specific name of condition] Y Atomization parameters [as necessary] Feed Rates: (Metals, Total Chlorine, and Ash) Volumetric Flow Meter3 or Mass Flow Meter Feed Systems Limits Specified in Table ____ [Maximum Constituent Feed Rates] N N Secondary Combustion Zone Pressure [or method for fugitives monitoring] e.g., in. H2O [Yes, if neg. pressure is used
RCRA%20Part%20B%20Application.docx