4.4 The database web interface should have a hierarchical display for Yes selection of the following: Site Site single line diagram Substation single line diagram PD trend for plant items monitored 5. Guarantee and Warranty Period 5.1 The test unit, sensors and accessories shall have a 12-month Yes standard hardware warranty. 5.2 The unit shall be provided with an optional extension to warranty on Yes request, in conjunction with an After-Sales Service Contract. 6. Training and Transfer of Technologies Requirements 6.1 Optional customer specific training available in use of the system. Yes 7. After-Sales Service Contract (Optional) 7.1 The supplier shall offer diagnostic advice based on monitoring data Yes access provided by the end user. 7.2 Technical support from HVPD engineers (via email/phone) Yes Yes 7.3 Emergency response by phone or email on any identified incidents (within 24 hours) 7.4 One site visit per annum to carry out diagnostic testing and location Yes (first visit recommended to be carried out three months after completion of the commissioning). 7.5 Periodic condition monitoring reports at regularity to be agreed Yes between client and supplier. Yes 7.6 The supplier shall provide support on-event where the system has remote connection or manual data transfer to the supplier. 7.7 Diagnostic recommendations from OLPD monitoring data and Yes maintenance intervention advice 7.8 Comparison and benchmarking of the OLPD activity in the assets Yes monitored across the network with existing asset knowledge. 7.9 Annual software upgrades of monitoring system and server/database Yes software. 8. Summary of Main Technical Parameters
4.4 The database web interface should have a hierarchical display for selection of the following: Site Site single line diagram Substation single line diagram PD trend for plant items monitored Yes 5. Guarantee and Warranty Period 5.1 The test unit, sensors and accessories shall have a 12-month standard hardware warranty. Yes 5.2 The unit shall be provided with an optional extension to warranty on request, in conjunction with an After-Sales Service Contract. Yes 6. Training and Transfer of Technologies Requirements 6.1 Optional customer specific training available in use of the system. Yes 7. After-Sales Service Contract (Optional) 7.1 The supplier shall offer diagnostic advice based on monitoring data access provided by the end user. Yes 7.2 Technical support from HVPD engineers (via email/phone) Yes 7.3 Emergency response by phone or email on any identified incidents (within 24 hours) Yes 7.4 One site visit per annum to carry out diagnostic testing and location (first visit recommended to be carried out three months after completion of the commissioning). Yes 7.5 Periodic condition monitoring reports at regularity to be agreed between client and supplier. Yes 7.6 The supplier shall provide support on-event where the system has remote connection or manual data transfer to the supplier. Yes 7.7 Diagnostic recommendations from OLPD monitoring data and maintenance intervention advice Yes 7.8 Comparison and benchmarking of the OLPD activity in the assets monitored across the network with existing asset knowledge. Yes 7.9 Annual software upgrades of monitoring system and server/database software. Yes 8. Summary of Main Technical Parameters
PR6100-SA003-2_HVPD_Kronos-Monitor_On-line_PD_Monitor_-_Unbranded_Specification.docx