Table 336: Shaded Pole to PSC Deemed Savings Measure Wbase Wee LF DCEvap DG COP Demand Energy (Shaded (PSC) per Impact Impact Pole) case (kW) (kWh) Temp Cooler: Shaded Pole 50 22 0.9 100% 0.98 2.5 0.0355 311 to PSC: 1-14 Watt Cooler: Shaded Pole 93 48 0.9 100% 0.98 2.5 0.0574 503 to PSC: 16-23 Watt Cooler: Shaded Pole 142 90 0.9 100% 0.98 2.5 0.0660 578 to PSC: 1/20 HP (37 Watt) Freezer: Shaded 50 22 0.9 94.4% 0.98 1.3 0.0425 373 Pole to PSC: 1-14 Watt Freezer: Shaded 93 48 0.9 94.4% 0.98 1.3 0.0687 602 Pole to PSC: 16-23 Watt Freezer: Shaded 142 90 0.9 94.4% 0.98 1.3 0.0790 692 Pole to PSC: 1/20 HP (37 Watt) Table 337: PSC to ECM Deemed Savings Measure Wbase Wee LF DCEvap DG COP Demand Energy (PSC) (ECM) per Impact Impact case (kW) (kWh) Temp Cooler: PSC to ECM: 22 14 0.9 100% 0.98 2.5 0.0105 92 1-14 Watt Cooler: PSC to ECM: 48 30 0.9 100% 0.98 2.5 0.0228 200 16-23 Watt Cooler: PSC to ECM: 90 56 0.9 100% 0.98 2.5 0.0433 380 1/20 HP (37 Watt) Freezer: PSC to 22 14 0.9 94.4% 0.98 1.3 0.0126 110 ECM: 1-14 Watt Freezer: PSC to 48 30 0.9 94.4% 0.98 1.3 0.0273 239 ECM: 16-23 Watt Freezer: PSC to 90 56 0.9 94.4% 0.98 1.3 0.0518 454 ECM: 1/20 HP (37 Watt)
Table 336: Shaded Pole to PSC Deemed Savings Measure Wbase (Shaded Pole) Wee (PSC) LF DCEvap DG COP per case Temp Demand Impact (kW) Energy Impact (kWh) Cooler: Shaded Pole to PSC: 1-14 Watt 50 22 0.9 100% 0.98 2.5 0.0355 311 Cooler: Shaded Pole to PSC: 16-23 Watt 93 48 0.9 100% 0.98 2.5 0.0574 503 Cooler: Shaded Pole to PSC: 1/20 HP (37 Watt) 142 90 0.9 100% 0.98 2.5 0.0660 578 Freezer: Shaded Pole to PSC: 1-14 Watt 50 22 0.9 94.4% 0.98 1.3 0.0425 373 Freezer: Shaded Pole to PSC: 16-23 Watt 93 48 0.9 94.4% 0.98 1.3 0.0687 602 Freezer: Shaded Pole to PSC: 1/20 HP (37 Watt) 142 90 0.9 94.4% 0.98 1.3 0.0790 692 Table 337: PSC to ECM Deemed Savings Measure Wbase (PSC) Wee (ECM) LF DCEvap DG COP per case Temp Demand Impact (kW) Energy Impact (kWh) Cooler: PSC to ECM: 1-14 Watt 22 14 0.9 100% 0.98 2.5 0.0105 92 Cooler: PSC to ECM: 16-23 Watt 48 30 0.9 100% 0.98 2.5 0.0228 200 Cooler: PSC to ECM: 1/20 HP (37 Watt) 90 56 0.9 100% 0.98 2.5 0.0433 380 Freezer: PSC to ECM: 1-14 Watt 22 14 0.9 94.4% 0.98 1.3 0.0126 110 Freezer: PSC to ECM: 16-23 Watt 48 30 0.9 94.4% 0.98 1.3 0.0273 239 Freezer: PSC to ECM: 1/20 HP (37 Watt) 90 56 0.9 94.4% 0.98 1.3 0.0518 454
Proposed_2011_TRM_Update.docx