Breather membrane: As clause 785. 130 INTERNAL WALL By others GENERAL REQUIREMENTS/PREPARATORY WORK 210 DESIGN Complete the detailed design of the rainscreen cladding and associated features shown on the preliminary design drawings to meet the requirements of this specification. Co-ordinate detailed design with that for all related works. 215 DESIGN PROPOSALS The preliminary design drawings indicate design intent but do not preclude submission with tender of reasonable alternative proposals for consideration. 220 SPECIFICATION Comply with the latest edition of the Centre for Window and Cladding Technology (CWCT) ‘Standard for walls with ventilated rainscreen’ and ‘Standard for testing of ventilated rainscreen” unless specified otherwise in this section. Keep a copy of the CWCT ‘Standard for walls with ventilated rainscreen’ and ‘Standard for testing of ventilated rainscreen’ together with other CWCT publications invoked by these documents, at the design office, workshop and on site, readily accessible for reference at all times during the course of the works. 230 INFORMATION TO BE PROVIDED DURING DETAILED DESIGN Submit the following cladding particulars: A schedule of detailed drawings and dates for submission for comment. A schedule of loads that will be transmitted from the rainscreen cladding to the structure. Proposed fixing details and systems relevant to the structural design and construction with methods of adjustment and tolerances. A schedule of all fabrication tolerances/size tolerances. A detailed testing programme in compliance with the main contract master programme A detailed fabrication and installation programme in compliance with the main contract master programme. A quality plan in compliance with the CWCT ‘Guide to good practice for facades’, section 6. Proposals to support any outstanding applications for Building Regulation consents or relaxations. 232 QUALITY PLAN Requirement: Submit during detailed design. Content: In accordance with BS 5750, BS EN ISO 9001 and including the following: Name of the quality manager. Quality assessment procedures. Inspection procedures to be adopted in checking the work. Stages at which check lists will be used and samples of the lists.
Breather membrane: As clause 785. 130 INTERNAL WALL By others GENERAL REQUIREMENTS/PREPARATORY WORK 210 DESIGN Complete the detailed design of the rainscreen cladding and associated features shown on the preliminary design drawings to meet the requirements of this specification. Co-ordinate detailed design with that for all related works. 215 DESIGN PROPOSALS The preliminary design drawings indicate design intent but do not preclude submission with tender of reasonable alternative proposals for consideration. 220 SPECIFICATION Comply with the latest edition of the Centre for Window and Cladding Technology (CWCT) ‘Standard for walls with ventilated rainscreen’ and ‘Standard for testing of ventilated rainscreen” unless specified otherwise in this section. Keep a copy of the CWCT ‘Standard for walls with ventilated rainscreen’ and ‘Standard for testing of ventilated rainscreen’ together with other CWCT publications invoked by these documents, at the design office, workshop and on site, readily accessible for reference at all times during the course of the works. 230 INFORMATION TO BE PROVIDED DURING DETAILED DESIGN Submit the following cladding particulars: A schedule of detailed drawings and dates for submission for comment. A schedule of loads that will be transmitted from the rainscreen cladding to the structure. Proposed fixing details and systems relevant to the structural design and construction with methods of adjustment and tolerances. A schedule of all fabrication tolerances/size tolerances. A detailed testing programme in compliance with the main contract master programme A detailed fabrication and installation programme in compliance with the main contract master programme. A quality plan in compliance with the CWCT ‘Guide to good practice for facades’, section 6. Proposals to support any outstanding applications for Building Regulation consents or relaxations. 232 QUALITY PLAN Requirement: Submit during detailed design. Content: In accordance with BS 5750, BS EN ISO 9001 and including the following: Name of the quality manager. Quality assessment procedures. Inspection procedures to be adopted in checking the work. Stages at which check lists will be used and samples of the lists.
PSP-Matrix-2-Specification.docx