ECC Olympian Model D125P1 1563 KVA / 125kw South side of the Gym FACILITY GENERATOR GENERATOR LOCATION PCC Onan/Cummins 350 DFCC - Engine Model East side outside of NTA855-G3 fence FMWCC Onan 400 kw Loading Dock Detroit Diesel/750RXC6DT2 75 kw Unit 11 – JCC Admin - Outside camp fence 99AOO782-S 75 kva SNCC (2) Caterpillar 3412, 755 HP 520kw Behind housing Unit #1 HDSP Central Onan Model DGBB - 4485365 (3) Detroit Diesel Spectrum/1750 DS4, 1750 kw Central Plant Detroit Diesel Spectrum/1750 D Sec, 1750 kw Central SDCC Olympian Model: D200 kw Diesel Near Tower 4 Kohler Model 200REOZDC 2000kw Diesel Building TLVCC Operates off the two Kohler generators from SDCC SDCC Proposals must include a detailed description of services to be provided for Section 3.1.1, and Section 3.1.2: The "Manufacture Recommendation" (what the manufactures would like to see performed to optimize the generator reliability); The "Manufacture Required" (the minimum that is required to ensure any type of reliability) services for each generator; and If the listed in are not included in Section 3.2, Minimum Requirements, either the "Manufacture Recommendation" or "Manufacture Required," they must be quoted individually. MINIMUM REQUIREMENTS The following requirements will need to be provided annually for preventative maintenance: Level I Service to be performed once a year (January or February.) Inspect/adjust/clean as needed all hoses, belts, battery cables, governor linkage, wiring, supports, verify grounding, exhaust system, fuel lines, fuel tank, fuel level, transfer pump and/or day tank for proper operations; Adjust injectors; Inspect air filters; Inspect all hoses, belts, battery cables and fuel line;
ECC Olympian Model D125P1 1563 KVA / 125kw South side of the Gym FACILITY GENERATOR GENERATOR LOCATION PCC Onan/Cummins 350 DFCC - Engine Model NTA855-G3 East side outside of fence FMWCC Onan 400 kw Loading Dock Detroit Diesel/750RXC6DT2 – 75 kw Unit 11 JCC 99AOO782-S 75 kva Admin - Outside camp fence SNCC (2) Caterpillar 3412, 755 HP 520kw Behind housing Unit #1 HDSP Onan Model DGBB - 4485365 Central (3) Detroit Diesel Spectrum/1750 DS4, 1750 kw Central Plant Detroit Diesel Spectrum/1750 D Sec, 1750 kw Central SDCC Olympian Model: D200 kw Diesel Near Tower 4 Kohler Model 200REOZDC 2000kw Diesel Building TLVCC Operates off the two Kohler generators from SDCC SDCC Proposals must include a detailed description of services to be provided for Section 3.1.1, and Section 3.1.2: The "Manufacture Recommendation" (what the manufactures would like to see performed to optimize the generator reliability); The "Manufacture Required" (the minimum that is required to ensure any type of reliability) services for each generator; and If the listed in Section 3.2, Minimum Requirements, are not included in either the "Manufacture Recommendation" or "Manufacture Required," they must be quoted individually. MINIMUM REQUIREMENTS The following requirements will need to be provided annually for preventative maintenance: Level I Service to be performed once a year (January or February.) Inspect/adjust/clean as needed all hoses, belts, battery cables, governor linkage, wiring, supports, verify grounding, exhaust system, fuel lines, fuel tank, fuel level, transfer pump and/or day tank for proper operations; Adjust injectors; Inspect air filters; Inspect all hoses, belts, battery cables and fuel line;
RFP%203227%20Final.docx