Measured SETTING Injected Measured Pick Drop Out IdAlarm (A) Current A Up Value (A) Value (A) 0.2 0.2 R 0.6 0.6 0.2 0.2 Y 0.6 0.6 0.2 0.2 B 0.6 0.6 R-Y 0.4 0.4 Y-B 0.4 0.4 B-R 0.4 0.4 R-Y-B 0.4 0.4 TIME FOR DIFFERENTIAL CURRENT ALARM Set IdAlarm = 0.2 IB PHASE Delay (sec) Operating time in sec zero R 5 zero Y 5 zero B 5 zero R-Y 5 zero Y-B 5 zero B-R 5 zero R-Y-B 5
SETTING IdAlarm (A) Injected Current A Measured Pick Up Value (A) Measured Drop Out Value (A) R 0.2 0.2 0.6 0.6 Y 0.2 0.2 0.6 0.6 B 0.2 0.2 0.6 0.6 R-Y 0.4 0.4 Y-B 0.4 0.4 B-R 0.4 0.4 R-Y-B 0.4 0.4 TIME FOR DIFFERENTIAL CURRENT ALARM Set IdAlarm = 0.2 IB PHASE Delay (sec) Operating time in sec R zero 5 Y zero 5 B zero 5 R-Y zero 5 Y-B zero 5 B-R zero 5 R-Y-B zero 5
red670_distance___line_differential.docx