Meter potential coils shall be 120V and current coils shall be 5A. Digital meters shall be provided as outlined on single line drawings. Controls Control devices, auxiliary contacts and small mechanisms shall be enclosed, protected and accessible for maintenance. Breaker control switches shall not be mounted adjacent to meter switches and shall have pistol grip handles. Switches are to be Electroswitch Series 24 or equivalent. Test switches shall be provided and wired in accordance with specified single line diagrams and data sheets and will only be mounted on low voltage compartment doors and panels. Test switches are to be ABB FT-1 type. switches shall have knurled knob handles. Switches are to Electroswitch Series 24 or equivalent. Nameplates Externally visible, permanent nameplates shall be provided to identify each instrument, instrument switch, meter, relay, control switch, indicating light, circuit breaker compartment, potential transformer compartment and auxiliary compartment. Relays shall be designated as to use and device to which they are connected. Nameplates shall be laminated plastic. Characters shall be black letters on a white background. Circuit identification nameplates be placed on the front and rear of each frame. ACCESSORIES AND SPARE PARTS Accessories All accessory items shall be shipped with switchgear. Boxes and crates containing accessories shall be clearly marked with the contents. Accessories shall include: Breaker lift truck to allow a circuit breaker or auxiliary draw-out unit to be elevated and then inserted or withdrawn. Breaker/PT/CPT racking crank Test Jumper to connect to the switchgear control circuit the breaker is withdrawn Test Cabinet with door mounted open and close pushbuttons shall be supplied for testing the circuit breaker away from the switchgear. SmartRack Remote Racking System to safely remote rack breakers. Minimum cord length shall be 50 feet.
Meter potential coils shall be 120V and current coils shall be 5A. Digital meters shall be provided as outlined on single line drawings. Controls Control devices, auxiliary contacts and small mechanisms shall be enclosed, protected and accessible for maintenance. Breaker control switches shall not be mounted adjacent to meter switches and shall have pistol grip handles. Switches are to be Electroswitch Series 24 or equivalent. Test switches shall be provided and wired in accordance with specified single line diagrams and data sheets and will only be mounted on low voltage compartment doors and panels. Test switches are to be ABB FT-1 type. switches shall have knurled knob handles. Switches are to Electroswitch Series 24 or equivalent. Nameplates Externally visible, permanent nameplates shall be provided to identify each instrument, instrument switch, meter, relay, control switch, indicating light, circuit breaker compartment, potential transformer compartment and auxiliary compartment. Relays shall be designated as to use and device to which they are connected. Nameplates shall be laminated plastic. Characters shall be black letters on a white background. Circuit identification nameplates be placed on the front and rear of each frame. ACCESSORIES AND SPARE PARTS Accessories All accessory items shall be shipped with switchgear. Boxes and crates containing accessories shall be clearly marked with the contents. Accessories shall include: Breaker lift truck to allow a circuit breaker or auxiliary draw-out unit to be elevated and then inserted or withdrawn. Breaker/PT/CPT racking crank Test Jumper to connect to the switchgear control circuit the breaker is withdrawn Test Cabinet with door mounted open and close pushbuttons shall be supplied for testing the circuit breaker away from the switchgear. SmartRack Remote Racking System to safely remote rack breakers. Minimum cord length shall be 50 feet.
1VAL107001-SS_Advance63samplespec.docx