Voltage Regulating Devices Consensus that voltage regulating devices should be “unlocked” (float) within iterative methodology, but no regarding process and timing of implementation. IOUs recommend each IOU models voltage regulating devices in Non 11 10.2.1 initial systemwide rollout as it did for Consensus Demo A and work with software vendors (CYME) to include this functionality. Other WG members recommend IOUs work with software vendors to develop this functionality before initial systemwide rollout. Operational Flexibility ICA values should be calculated with and without the No Reverse Flow at Supervisory Control and Data Acquisition 12 10.2.2 Consensus (SCADA) Devices constraint for initial systemwide rollout (see section 9), which is how the IOUs modeled these scenarios in Demo A per ACR requirements. Treatment of PreExisting Conditions ICA should be limited by preexisting 13 10.4 conditions (i.e., display an ICA value of Consensus zero) when adding Distributed Energy Resources (DER) degrades pre existing condition; ICA should not be limited by preexisting condition when adding DER improves preexisting condition.
11 10.2.1 Voltage Regulating Devices Consensus that voltage regulating devices should be “unlocked” (float) within iterative methodology, but no regarding process and timing of implementation. IOUs recommend each IOU models voltage regulating devices in initial systemwide rollout as it did for Demo A and work with software vendors (CYME) to include this functionality. Other WG members recommend IOUs work with software vendors to develop this functionality before initial systemwide rollout. Non Consensus 12 10.2.2 Operational Flexibility ICA values should be calculated with and without the No Reverse Flow at Supervisory Control and Data Acquisition (SCADA) Devices constraint for initial systemwide rollout (see section 9), which is how the IOUs modeled these scenarios in Demo A per ACR requirements. Consensus 13 10.4 Treatment of PreExisting Conditions ICA should be limited by preexisting conditions (i.e., display an ICA value of zero) when adding Distributed Energy Resources (DER) degrades pre existing condition; ICA should not be limited by preexisting condition when adding DER improves preexisting condition. Consensus
196355766.docx