No. CIPS/day CCP Membrane Auto As per As per rack & PLC controlled supplier’s supplier’s system as advice advice required Chlorine residual CCP Post softening Daily 2.0 mg/L 1.0 mg/L pH QCP Daily Outside of n/a Chemical addition. Inspect and 7.5-8.0 Softening Residual disinfection repair in accordance with operating procedures Conductivity (EC) QCP n/a > 350 µS/cm E coli CCP Holding tank Per batch Nil detected Nil detected Re-process or dump batch. System audit/assessment to determine Product contributing problem Hold tank - verification storage pH QCP Verification Per batch <7.0 and > n/a Chemical addition 8.0 * levels and critical limits are examples only. Equipment suppliers should be consulted for appropriate values.
No. CIPS/day CCP Membrane rack & PLC system Auto controlled as required As per supplier’s advice As per supplier’s advice Softening Residual disinfection Chlorine residual CCP Post softening Daily 2.0 mg/L 1.0 mg/L Chemical addition. Inspect and repair in accordance with operating procedures pH QCP Daily Outside of 7.5-8.0 n/a Conductivity (EC) QCP > 350 µS/cm n/a Product storage Hold tank - verification E coli CCP Holding tank Per batch Nil detected Nil detected Re-process or dump batch. System audit/assessment to determine contributing problem pH QCP Verification Per batch <7.0 and > 8.0 n/a Chemical addition * levels and critical limits are examples only. Equipment suppliers should be consulted for appropriate values.
Recycled-Water-Management-Plan-Template-Final.docx