Provide system control software (Acoustic Network Manager) for: System startup, including initialization and addressing of networked devices. Masking signal volume and equalization. Audio signal volume and equalization. Masking timer scheduling. All system zoning. In-room occupant control setup. Reporting of all system settings. System diagnostics. Provide audio broadcast zoning software (Page Director) for: Setup of user-defined audio zones. User zone selection via software interface. Provide monitoring/notification software (Acoustic Network Supervisor) for: Email notification of errors to user-defined addresses. Email notification of system status at user-defined periods. Provide in-room occupant controls with: Network connectivity. A display indicating function selection and settings. A keypad interface for controlling all functions, including masking/audio selection, volume, increase/decrease, audio source selection, and masking/audio mute. An infrared remote control receiver. A single gang enclosure. Provide assemblies that: Carry power, audio and control signals over a single cable assembly. Provide overmolded micro-connectors with positive locking mechanisms. Provide audio input modules for: input for microphone, telephone or auxiliary audio sources. Analog to digital (D/A) conversion of audio signals. Input sensitivity adjustment. Provide ceiling mount adaptors to: Attach on-site to convert plenum loudspeakers to ceiling loudspeakers. Provide power supplies to: Power the system components. REGULATORY TESTING AND CERTIFICATIONS Provide system components conforming to and labeled for: [Spec Note: Delete irrelevant sections.] United States Safety and Electrical: UL 6500 Plenum Rated Components: UL 2043 [Spec Note: For air-handling plenum installation.] Plenum Rated Cabling: UL CL3P/CMP 75C [Spec Note: For air-handling plenum installation.] Electromagnetic Interference (EMI): FCC Part 15, Subpart B, Class A – Metals: RoHS [Spec Note: Voluntary best practice.] Low Voltage Supplies: UL 1310 Canada
Provide system control software (Acoustic Network Manager) for: System startup, including initialization and addressing of networked devices. Masking signal volume and equalization. Audio signal volume and equalization. Masking timer scheduling. All system zoning. In-room occupant control setup. Reporting of all system settings. System diagnostics. Provide audio broadcast zoning software (Page Director) for: Setup of user-defined audio zones. User zone selection via software interface. Provide monitoring/notification software (Acoustic Network Supervisor) for: Email notification of errors to user-defined addresses. Email notification of system status at user-defined periods. Provide in-room occupant controls with: Network connectivity. A display indicating function selection and settings. A keypad interface for controlling all functions, including masking/audio selection, volume, increase/decrease, audio source selection, and masking/audio mute. An infrared remote control receiver. A single gang enclosure. Provide assemblies that: Carry power, audio and control signals over a single cable assembly. Provide overmolded micro-connectors with positive locking mechanisms. Provide audio input modules for: input for microphone, telephone or auxiliary audio sources. Analog to digital (D/A) conversion of audio signals. Input sensitivity adjustment. Provide ceiling mount adaptors to: Attach on-site to convert plenum loudspeakers to ceiling loudspeakers. Provide power supplies to: Power the system components. REGULATORY TESTING AND CERTIFICATIONS Provide system components conforming to and labeled for: [Spec Note: Delete irrelevant sections.] United States Safety and Electrical: UL 6500 Plenum Rated Components: UL 2043 [Spec Note: For air-handling plenum installation.] Plenum Rated Cabling: UL CL3P/CMP 75C [Spec Note: For air-handling plenum installation.] Electromagnetic Interference (EMI): FCC – Part 15, Subpart B, Class A Metals: RoHS [Spec Note: Voluntary best practice.] Low Voltage Supplies: UL 1310 Canada
1_LogiSon-Sound-Masking-3-Part-Specification-CSI-Compliant.docx