Shut-down: A QSE representing a Generation Resource that is not actively providing A/S (with the exception of Off-line Non-Spin) may only use a Resource Status of SHUTDOWN through telemetry that the Resource is operating in a shutdown sequence requiring manual control and is not available for Dispatch. Shutdown/ Startup Start-up: A QSE representing a Generation Resource that is not actively providing A/S may only use a Resource Status of STARTUP through telemetry that the Resource is operating in a start-up sequence requiring manual control and is not available for Dispatch. QSEs can manage basepoint deviations by adjusting their telemetered NOTE ramp rate. When a Resource is carrying Non-spin and that Non-Spin is “Off-Line” being recalled, the QSE would continue to show the Non-Spin NOTE responsibility on the Resource that is shutting down. Combine Generation Resources WHEN: Combine Cycle Generation Resources are changing configuration creating basepoint deviations NOTE THEN: QSEs will need to manage their telemetered HSL for proper basepoints. Telemetry Issues that could affect SCED and/or LMPs REVIEW REFERENCE DISPLAY: EMS Applications>Generation Control>Resource Calculation>RLC Unit Input Data and RLC Unit Output Data WHEN: Not A QSE has telemetered more A/S on a specific Resource that is greater than their HSL, OR Dispatchable to SCED A Resource is generating more than their telemetered HSL; THEN: SCED will set the HDL=LDL=MW making the Resource undispatchable, Request the QSE to make corrections to their telemetry (Resource status, Resource limits, A/S responsibilities, etc.) Real-Time Data Issues by the QSE
Shutdown/ Startup Shut-down: A QSE representing a Generation Resource that is not actively providing A/S (with the exception of Off-line Non-Spin) may only use a Resource Status of SHUTDOWN through telemetry that the Resource is operating in a shutdown sequence requiring manual control and is not available for Dispatch. Start-up: A QSE representing a Generation Resource that is not actively providing A/S may only use a Resource Status of STARTUP through telemetry that the Resource is operating in a start-up sequence requiring manual control and is not available for Dispatch. NOTE QSEs can manage basepoint deviations by adjusting their telemetered ramp rate. NOTE When a Resource is carrying “Off-Line” Non-spin and that Non-Spin is being recalled, the QSE would continue to show the Non-Spin responsibility on the Resource that is shutting down. Combine Generation Resources NOTE WHEN: Combine Cycle Generation Resources are changing configuration creating basepoint deviations THEN: QSEs will need to manage their telemetered HSL for proper basepoints. Telemetry Issues that could affect SCED and/or LMPs Not Dispatchable to SCED REVIEW REFERENCE DISPLAY: EMS Applications>Generation Control>Resource Calculation>RLC Unit Input Data and RLC Unit Output Data WHEN: A QSE has telemetered more A/S on a specific Resource that is greater than their HSL, OR A Resource is generating more than their telemetered HSL; THEN: SCED will set the HDL=LDL=MW making the Resource undispatchable, Request the QSE to make corrections to their telemetry (Resource status, Resource limits, A/S responsibilities, etc.) Real-Time Data Issues by the QSE
Real_Time_Desk_Operating_Procedure.docx