/try=x Number of seconds to wait before trying to re-establish a lost connection to the DCS. Optional Sometimes a node in the DCS becomes unreachable. In the Default: 300 interface log file, this is reported by error messages like “… object’s node not In this case, the PI Interface for ABB Advant reachable”. will try to re-establish the connection after a while. The default setting is /try=300, which means that an attempt to reconnect is made after 5 minutes. If the attempt fails, the next one is launched after another 5 minutes. It is possible to configure a different retry rate via /try=. You can choose an integer value between 0 and 3600. Note that the /try parameter has no effect if the ABB patch for fixing the problem has been applied (discussed in “Node Down” this manual) and the workaround (which actually uses the value set via /try) has therefore been disabled via /ndw=0 (see this parameter in this table). /UFO_ID=# Failover ID. This value must be different from the Failover ID of the other interface in the failover pair. It can be any positive, non-zero integer. Required for UniInt Failover Phase 1 or 2 /UFO_Interval=# Failover Update Interval Specifies the heartbeat Update Interval in milliseconds and must be the same on both interface computers. Optional This is the rate at which UniInt updates the Failover Heartbeat tags Default: 1000 for Phase 1 as well as how often UniInt checks on the status of the other copy Failover of the interface. Default: 5000 for Phase 2 Failover Valid values are 5020000. /UFO_OtherID=# Other Failover ID. This value must be equal to the Failover ID configured for the other interface in the failover pair. Required for UniInt Failover Phase 1 or 2
/try=x Optional Default: 300 Number of seconds to wait before trying to re-establish a lost connection to the DCS. Sometimes a node in the DCS becomes unreachable. In the interface log file, this is reported by error messages like “… object’s node not reachable”. In this case, the PI Interface for ABB Advant will try to re-establish the connection after a while. The default setting is /try=300, which means that an attempt to reconnect is made after 5 minutes. If the attempt fails, the next one is launched after another 5 minutes. It is possible to configure a different retry rate via /try=. You can choose an integer value between 0 and 3600. Note that the /try parameter has no effect if the ABB patch for fixing the “Node Down” problem has been applied (discussed in this manual) and the workaround (which actually uses the value set via /try) has therefore been disabled via /ndw=0 (see this parameter in this table). /UFO_ID=# Required for UniInt Failover Phase 1 or 2 Failover ID. This value must be different from the Failover ID of the other interface in the failover pair. It can be any positive, non-zero integer. /UFO_Interval=# Optional Default: 1000 for Phase 1 Failover Default: 5000 for Phase 2 Failover Valid values are 5020000. Failover Update Interval Specifies the heartbeat Update Interval in milliseconds and must be the same on both interface computers. This is the rate at which UniInt updates the Failover Heartbeat tags as well as how often UniInt checks on the status of the other copy of the interface. /UFO_OtherID=# Required for UniInt Failover Phase 1 or 2 Other Failover ID. This value must be equal to the Failover ID configured for the other interface in the failover pair.
PI_ABBIMS_5.82.0.58.docx