within a Local Government hazard area” are (a) bulk tanks are anchored so they cannot “flood located and designed in a manner to minimise the float if submerged or inundated by water; and likelihood of inundation of flood waters from creeks, (b) tank openings not provided with a liquid tight rivers, lakes or estuaries. seal, i.e. an atmospheric vent, are extended above the relevant flood height level. Note To assist in demonstrating compliance with the – AO15.2 performance outcomes, a Hazard Assessment Report may be required to be prepared and submitted by a suitably qualified The lowest point of any storage area for packages person in accordance with the Model Planning Scheme >2,500 L or kg is higher than any relevant flood development Code for Hazardous Industries and Chemicals. height level identified in an area’s flood hazard area. Alternatively, package stores are provided with impervious bund walls or racking systems higher than the relevant flood height level. 9.4.5.3.b Self-assessable development thresholds – Hazardous PG or Applicable storage Threshold Exclusions chemical type and handling type quantity Flammable N/A Cylinder stores with > 1,000 (a) connected to a – gases DG natural ventilation < 5,000 L consuming device, fuel – class 2.1 burning appliance or within a refrigeration Oxidising N/A Cylinder stores with > 1,000 – – system DG class 2.2, natural ventilation < 20,000 L (b) Tanks with a WC > 500 sub risk 5.1 L (c) Aerosols with a WC < 1 Non-toxic, N/A Cylinder stores with > 2,000 – L natural ventilation < 200,000 L (d) Cylinder exchange gases DG – facilities that comply class 2.2 with AS1596, (e) Cylinders stores with any of the following attributes: within or attached to a building, mechanically ventilated.
within a Local Government “flood hazard area” are located and designed in a manner to minimise the likelihood of inundation of flood waters from creeks, rivers, lakes or estuaries. Note – To assist in demonstrating compliance with the performance outcomes, a Hazard Assessment Report may be required to be prepared and submitted by a suitably qualified person in accordance with the Model Planning Scheme development Code for Hazardous Industries and Chemicals. (a) bulk tanks are anchored so they cannot float if submerged or inundated by water; and (b) tank openings not provided with a liquid tight seal, i.e. an atmospheric vent, are extended above the relevant flood height level. AO15.2 The lowest point of any storage area for packages >2,500 L or kg is higher than any relevant flood height level identified in an area’s flood hazard area. Alternatively, package stores are provided with impervious bund walls or racking systems higher than the relevant flood height level. 9.4.5.3.b – Self-assessable development thresholds Hazardous chemical PG or type Applicable storage and handling type Threshold quantity Exclusions Flammable gases – DG class 2.1 N/A Cylinder stores with natural ventilation > 1,000 – < 5,000 L (a) connected to a consuming device, fuel burning appliance or within a refrigeration system (b) Tanks with a WC > 500 L (c) Aerosols with a WC < 1 L (d) Cylinder exchange facilities that comply with AS1596, (e) Cylinders stores with any of the following attributes: within or attached to a building, mechanically ventilated. Oxidising – DG class 2.2, sub risk 5.1 N/A Cylinder stores with natural ventilation > 1,000 – < 20,000 L Non-toxic, gases – DG class 2.2 N/A Cylinder stores with natural ventilation > 2,000 – < 200,000 L
Industry-design-v1.1.docx