Cooling water: About 1500 gpm with a supply temperature of about 85 95 oF and allowable – rise in temperature of about 18 oF. Ventilation blower: 300 kW approx. Instrument air: 500 gpm approx. The major requirements to the CB building are: High bay area: x (Floor) with a 15 metric ton EOT crane and a side bay area. 50’ 125’ Electrical power: 3 phase, 480 VAC, 60 Hz with minimum power requirement of about 100 kW for auxiliary equipment; 1 phase, 120 VAC, 60 Hz incidental requirements (30 kW). Class 2 (AC power from UPS) for operating the control panels. Cooling water: About 200 gpm with a supply temperature of about 50 60 oF and allowable – rise in temperature of about 9 oF. Instrument air: 500 gpm approx.
Cooling water: About 1500 gpm with a supply temperature of about 85 – 95 oF and allowable rise in temperature of about 18 oF. Ventilation blower: 300 kW approx. Instrument air: 500 gpm approx. The major requirements to the CB building are: High bay area: 50’ x 125’ (Floor) with a 15 metric ton EOT crane and a side bay area. Electrical power: 3 phase, 480 VAC, 60 Hz with minimum power requirement of about 100 kW for auxiliary equipment; 1 phase, 120 VAC, 60 Hz incidental requirements (30 kW). Class 2 (AC power from UPS) for operating the control panels. Cooling water: About 200 gpm with a supply temperature of about 50 – 60 oF and allowable rise in temperature of about 9 oF. Instrument air: 500 gpm approx.
PIP-II_CDR_v.0.1.work4.docx