Optical Varifocal Lens: 2.8 ~ 12mm, IR-corrected, remote motorized zoom and focus adjustment Iris Control: electronic auto-iris of View (H): 91.0° (wide) ~ 27.0° (tele) Electrical: Input Power: 12VDC or Power over Ethernet (PoE), IEEE 802.3af Power Consumption (with IR LED On): PoE or 12VDC: maximum 9W Mechanical: Cast-aluminum, weather resistant housing Complete bullet housing to be IP67 rated IR LED 98ft (30M) maximum range indoor, under the best conditions Secondary Power Input: barrel connector Audio: 1 / 1; RCA Alarm: 1 / 1; Terminal Block Dimensions (L x W x H): 9.98 x 3.4 x 2.8in (253.4 x 86 x 71.7mm) Weight: 1.28lbs (0.58kg) Operating Temperature: -31ºF ~ 140ºF (-35ºC ~ 60ºC) Operating Humidity: 10 to 95% RH (non-condensing) Conformity Certifications: Federal Communications Commission (FCC) European Conformity (CE) NEMA-4X (IP67) IEC (IK-10) Accessories TR-UP06-A-IN: Pole Mount TR-JB07-B-IN: Junction Box Remote Management Software Uniview tec Guard Station Software is complimentary and provided at no cost. Get the latest version at: Available in Windows and Mac operating system versions Uniview tec Guard Tool Utility Software is also complimentary and available through the same link provided above EXECUTION EXISTING WORK Disconnect and remove abandoned video surveillance equipment. Extend existing video surveillance installations using materials and methods compatible with existing installations as specified.
Optical Varifocal Lens: 2.8 ~ 12mm, IR-corrected, remote motorized zoom and focus adjustment Iris Control: electronic auto-iris of View (H): 91.0° (wide) ~ 27.0° (tele) Electrical: Input Power: 12VDC or Power over Ethernet (PoE), IEEE 802.3af Power Consumption (with IR LED On): PoE or 12VDC: maximum 9W Mechanical: Cast-aluminum, weather resistant housing Complete bullet housing to be IP67 rated IR LED 98ft (30M) maximum range indoor, under the best conditions Secondary Power Input: barrel connector Audio: 1 / 1; RCA Alarm: 1 / 1; Terminal Block Dimensions (L x W x H): 9.98 x 3.4 x 2.8in (253.4 x 86 x 71.7mm) Weight: 1.28lbs (0.58kg) Operating Temperature: -31ºF ~ 140ºF (-35ºC ~ 60ºC) Operating Humidity: 10 to 95% RH (non-condensing) Conformity Certifications: Federal Communications Commission (FCC) European Conformity (CE) NEMA-4X (IP67) IEC (IK-10) Accessories TR-UP06-A-IN: Pole Mount TR-JB07-B-IN: Junction Box Remote Management Software Uniview tec Guard Station Software is complimentary and provided at no cost. Get the latest version at: Available in Windows and Mac operating system versions Uniview tec Guard Tool Utility Software is also complimentary and available through the same link provided above EXECUTION EXISTING WORK Disconnect and remove abandoned video surveillance equipment. Extend existing video surveillance installations using materials and methods compatible with existing installations as specified.
IPB4212M_AE-Guide-Spec-28_23_29.docx