6 Operating Pressure 7 bar for low pressure & 48 bar for high pressure 7 Response Time 100ms (Maximum) 8 Power Consumption Max. 12 Watt 9 Service Life Greater than 50,000 Operations 10 End Connections 1/4” NPT (F) 11 Electrical Connection ½” NPT (F) 12 Time for Continuous 24 Hours Operation 13 Insulation Resistance >100 MΩ at 500V DC 14 Coil Insulation Class H 15 Pull-in voltage 18±1V DC 16 Drop out voltage 10±1V DC 17 Operating Temperature 273 to 318 K 18 Manual Override To be provided by screw – One per SOV 19 Area Classification NEC Class 1, Div. 1, Gas Gr. B, Temp. Class T6 20 Enclosure Protection Explosion-Proof to EExd IIC, T6, Zone 1, EN 50018 of IEC / CENELEC and WP to IP 67 21 Orifice 1.2 mm ± 1% 22 Seat Material VITON/PTFE 23 Material body SS316/12x18H10T 24 Mounting Panel mounting type bracket along with accessories to be supplied with each SOV. 25 Terminals Suitable for 2.5 mm2 cables 26 Housing Die Cast Aluminium Epoxy Painted 27 Silencer / Muffler To be fitted on Exhaust port 28 Special Feature Free wheeling Diode across each Coil 29 Tag Plate SS indicating Tag No, Model No., Sr. No, End Connection etc. 7. Junction Box : 1 Enclosure protection Weather Proof to IP 66 & Explosion proof to IIC 2 Material Stainless Steel 3 Cover Hinged and bolted with Neosprene gasket 4 Body Grounding Earthing Screws of SS material with washer. 5 Dimension Type I : 500 (H) x 500 (W) x 225 (D) approximate Type II : 775 (H) x 525 (W) x 225 (D) approximate Terminals : 6 No. of terminals Type I : 108 Terminal blocks Type II : 216 Terminal blocks
6 Operating Pressure 7 bar for low pressure & 48 bar for high pressure 7 Response Time 100ms (Maximum) 8 Power Consumption Max. 12 Watt 9 Service Life Greater than 50,000 Operations 10 End Connections 1/4” NPT (F) 11 Electrical Connection ½” NPT (F) 12 Time for Continuous Operation 24 Hours 13 Insulation Resistance >100 MΩ at 500V DC 14 Coil Insulation Class H 15 Pull-in voltage 18±1V DC 16 Drop out voltage 10±1V DC 17 Operating Temperature 273 to 318 K 18 Manual Override To be provided by screw – One per SOV 19 Area Classification NEC Class 1, Div. 1, Gas Gr. B, Temp. Class T6 20 Enclosure Protection Explosion-Proof to EExd IIC, T6, Zone 1, EN 50018 of IEC / CENELEC and WP to IP 67 21 Orifice 1.2 mm ± 1% 22 Seat Material VITON/PTFE 23 Material body SS316/12x18H10T 24 Mounting Panel mounting type bracket along with accessories to be supplied with each SOV. 25 Terminals Suitable for 2.5 mm2 cables 26 Housing Die Cast Aluminium Epoxy Painted 27 Silencer / Muffler To be fitted on Exhaust port 28 Special Feature Free wheeling Diode across each Coil 29 Tag Plate SS indicating Tag No, Model No., Sr. No, End Connection etc. 7. Junction Box : 1 Enclosure protection Weather Proof to IP 66 & Explosion proof to IIC 2 Material Stainless Steel 3 Cover Hinged and bolted with Neosprene gasket 4 Body Grounding Earthing Screws of SS material with washer. 5 Dimension Type I : 500 (H) x 500 (W) x 225 (D) approximate Type II : 775 (H) x 525 (W) x 225 (D) approximate Terminals : 6 No. of terminals Type I : 108 Terminal blocks Type II : 216 Terminal blocks
IDT00207900000000000isro05402.docx