Attributes Inspection Activity Verify that equipment qualification is suitable for the environment Equipment/ expected under all conditions. Environmental Qualification Temperature Example: Verify equipment is qualified for room temperatures under Humidity accident conditions. Radiation Pressure Voltage Vibration Equipment Verify equipment is adequately protected. Protection Fire Example: Verify freeze protection adequate for condensate storage tank (CST) level instrumentation. Missile High energy Example: Verify that conditions and modifications identified by the line break licensee’s high energy line analysis have been implemented to HVAC protect selected highly risk-significant components. Freezing Component Verify that component inputs and outputs are suitable for application and Inputs/Outputs will be acceptable under accident/event conditions. Example: Verify that fails in the safe configuration. Example: Verify that required inputs to components, such as coolant flow, electrical voltage, and control air necessary for proper component operation are provided.
Attributes Equipment/ Environmental Qualification Temperature Humidity Radiation Pressure Voltage Vibration Inspection Activity Verify that equipment qualification is suitable for the environment expected under all conditions. Example: Verify equipment is qualified for room temperatures under accident conditions. Equipment Protection Fire Missile High energy line break HVAC Freezing Verify equipment is adequately protected. Example: Verify freeze protection adequate for condensate storage tank (CST) level instrumentation. Example: Verify that conditions and modifications identified by the licensee’s high energy line analysis have been implemented to protect selected highly risk-significant components. Component Inputs/Outputs Verify that component inputs and outputs are suitable for application and will be acceptable under accident/event conditions. Example: Verify that fails in the safe configuration. Example: Verify that required inputs to components, such as coolant flow, electrical voltage, and control air necessary for proper component operation are provided.
ip71111-21m.docx