Notification Appliance Circuit Continuous Output – Notification Appliance Circuit ANSI Temporal Output – Notification Appliance Circuit Sounder Base Power – Notification Appliance Circuit Synchronized Output – Auxiliary Power Constant – Auxiliary Power Resettable – Door Holder Power Constant – Door Holder Power Low AC Dropout – City Tie - Reverse Polarity Output for applications in compliance with applicable NFPA standards. Releasing Circuit For use with either a chemical or water based releasing system – The FACP NAC circuits shall include the capability to automatically synchronize notification appliances from multiple manufacturers simultaneously on the same FACP without the need for a synchronization module. Systems that do not allow for multiple brands of strobes to be synchronized together on the same panel are not acceptable. The following manufacturers synchronization protocol shall be supported as a minimum: Amseco Gentex Gentex Sync with T4 Wheelock System Sensor The FACP include a 4-wire serial P-LINK bus for communication with system annunciators, power supplies, expansion modules, and other accessories. The P-LINK bus shall support a wiring distance of no less than 6500 feet from the panel to the furthest device. The FACP shall have two (2) programmable I/O Circuits rated at 1 amp per circuit and capable of being wired in a Class B configuration. These circuits shall be programmable for the following input / output types. Notification Appliance Circuit Continuous Output – Notification Appliance Circuit ANSI Temporal Output – Notification Appliance Circuit Synchronized Output – Notification Appliance Circuit Sounder Base Power – Auxiliary Power Constant – Auxiliary Power Resettable – Door Holder Power Constant – Door Holder Power Low AC Dropout – City Tie - Reverse Polarity Output for applications in compliance with applicable NFPA standards. NAC Release Solenoid Contact Input Pull Station Contact Water flow Contact Supervisory Contact Tamper Contact Fire Drill Contact Input Trouble Monitor Contact Input Aux. Contact Abort Contact Input Release Follower Trigger IO Reverse Polarity Trigger IO Reverse Polarity No Trouble Contact Input Reset Contact Input Silence Contact Input Fire Alarm Contact Disable Inputs Contact Input Disable Outputs Contact Input Disable Inputs & Outputs Contact Input Lamp Test Contact Input CO Alarm
Notification Appliance Circuit – Continuous Output Notification Appliance Circuit – ANSI Temporal Output Notification Appliance Circuit – Sounder Base Power Notification Appliance Circuit – Synchronized Output Auxiliary Power – Constant Auxiliary Power – Resettable Door Holder Power – Constant Door Holder Power – Low AC Dropout City Tie - Reverse Polarity Output for applications in compliance with applicable NFPA standards. Releasing Circuit – For use with either a chemical or water based releasing system The FACP NAC circuits shall include the capability to automatically synchronize notification appliances from multiple manufacturers simultaneously on the same FACP without the need for a synchronization module. Systems that do not allow for multiple brands of strobes to be synchronized together on the same panel are not acceptable. The following manufacturers synchronization protocol shall be supported as a minimum: Amseco Gentex Gentex Sync with T4 Wheelock System Sensor The FACP include a 4-wire serial P-LINK bus for communication with system annunciators, power supplies, expansion modules, and other accessories. The P-LINK bus shall support a wiring distance of no less than 6500 feet from the panel to the furthest device. The FACP shall have two (2) programmable I/O Circuits rated at 1 amp per circuit and capable of being wired in a Class B configuration. These circuits shall be programmable for the following input / output types. Notification Appliance Circuit – Continuous Output Notification Appliance Circuit – ANSI Temporal Output Notification Appliance Circuit – Synchronized Output Notification Appliance Circuit – Sounder Base Power Auxiliary Power – Constant Auxiliary Power – Resettable Door Holder Power – Constant Door Holder Power – Low AC Dropout City Tie - Reverse Polarity Output for applications in compliance with applicable NFPA standards. NAC Release Solenoid Contact Input Pull Station Contact Water flow Contact Supervisory Contact Tamper Contact Fire Drill Contact Input Trouble Monitor Contact Input Aux. Contact Abort Contact Input Release Follower Trigger IO Reverse Polarity Trigger IO Reverse Polarity No Trouble Contact Input Reset Contact Input Silence Contact Input Fire Alarm Contact Disable Inputs Contact Input Disable Outputs Contact Input Disable Inputs & Outputs Contact Input Lamp Test Contact Input CO Alarm
IPA-60_specification.docx