about multiple Points of Interconnection is requested. Subject to Section 1.3.3, the Pre-Application Report will include the following information: Total capacity (in MW) of substation/area bus, bank or circuit based on normal or operating ratings likely to serve the proposed Point of Interconnection. Existing aggregate generation capacity (in MW) interconnected to a substation/area bus, bank or circuit (i.e., amount of generation online) likely to serve the proposed Point of Interconnection. Aggregate queued generation capacity (in MW) for a substation/area bus, bank or circuit (i.e., amount of generation in the queue) likely to serve the proposed Point of Interconnection. Substation nominal distribution voltage and/or transmission nominal voltage if applicable. Nominal distribution circuit voltage at the proposed Point of Interconnection. Approximate circuit distance between the proposed of Interconnection and the substation. Relevant line section(s) actual or estimated peak load and minimum load data, including daytime minimum load and absolute minimum load, when available. Number and rating of protective devices and number and type (standard, bi-directional) of voltage regulating devices between the proposed of Interconnection and the substation/area. Identify whether the substation has a load tap changer. Number of phases available at the proposed Point of Interconnection. If a single phase, distance from the three- phase circuit. Limiting conductor ratings from the proposed Point of Interconnection to the distribution substation. Whether the Point of Interconnection is located on a spot network, grid network, or radial supply. Based on the proposed Point of Interconnection, existing or known constraints such as, but not limited to, electrical dependencies at that location, short circuit interrupting capacity issues, power quality or stability issues on the circuit, capacity constraints, or secondary networks. information regarding an Affected System the Cooperative deems relevant to the Interconnection Customer.
about multiple Points of Interconnection is requested. Subject to Section 1.3.3, the Pre-Application Report will include the following information: Total capacity (in MW) of substation/area bus, bank or circuit based on normal or operating ratings likely to serve the proposed Point of Interconnection. Existing aggregate generation capacity (in MW) interconnected to a substation/area bus, bank or circuit (i.e., amount of generation online) likely to serve the proposed Point of Interconnection. Aggregate queued generation capacity (in MW) for a substation/area bus, bank or circuit (i.e., amount of generation in the queue) likely to serve the proposed Point of Interconnection. Substation nominal distribution voltage and/or transmission nominal voltage if applicable. Nominal distribution circuit voltage at the proposed Point of Interconnection. Approximate circuit distance between the proposed of Interconnection and the substation. Relevant line section(s) actual or estimated peak load and minimum load data, including daytime minimum load and absolute minimum load, when available. Number and rating of protective devices and number and type (standard, bi-directional) of voltage regulating devices between the proposed of Interconnection and the substation/area. Identify whether the substation has a load tap changer. Number of phases available at the proposed Point of Interconnection. If a single phase, distance from the three- phase circuit. Limiting conductor ratings from the proposed Point of Interconnection to the distribution substation. Whether the Point of Interconnection is located on a spot network, grid network, or radial supply. Based on the proposed Point of Interconnection, existing or known constraints such as, but not limited to, electrical dependencies at that location, short circuit interrupting capacity issues, power quality or stability issues on the circuit, capacity constraints, or secondary networks. information regarding an Affected System the Cooperative deems relevant to the Interconnection Customer.
INTERCONNECTION%20PROCEDURES.docx