ESQCR Reg 21 Ensure that switched alternative sources X X of energy to distribution networks cannot operate in parallel with those networks and that such equipment which is part of an LV installation complies consumer’s with BS 7671. ESQCR Reg 22 Not install or operate sources of energy X X in parallel with distribution networks unless there are: appropriate equipment, personnel and procedures to prevent danger, so far as is reasonably practicable; LV equipment consumers’ complies with BS 7671; and specific requirements are agreed with the DNO. ESQCR Reg 24 DNO equipment which is on a X premises but not under the consumer’s control is protected by a consumer’s suitable fused cut-out or circuit breaker which is situated as close as reasonably practicable to the supply terminals, which is enclosed in a locked or sealed container. ESQCR Reg 25 Not give consent to making or altering of X connections where there are reasonable grounds to believe that the consumer’s installation does not comply with ESQCR / BS 7671 or, so far as is reasonably practicable, is not protected to prevent danger or interruption of supply. ESQCR Reg 27 Declare the number of phases, X frequency and voltage of the supply and, save in exceptional circumstances, keep this within permitted variations. ESQCR Reg 28 Provide a written statement of the type X and rating of protective devices. EAWR Reg 4 Construct systems including suitable X X X protective devices that can handle the likely load and fault conditions. EAWR Reg 5 Not put into service electrical equipment X X X where it strength and capability may be exceeded in such a way as to pose a danger.
ESQCR Reg 21 Ensure that switched alternative sources of energy to distribution networks cannot operate in parallel with those networks and that such equipment which is part of an LV consumer’s installation complies with BS 7671. X X ESQCR Reg 22 Not install or operate sources of energy in parallel with distribution networks unless there are: appropriate equipment, personnel and procedures to prevent danger, so far as is reasonably practicable; LV consumers’ equipment complies with BS 7671; and specific requirements are agreed with the DNO. X X ESQCR Reg 24 DNO equipment which is on a consumer’s premises but not under the consumer’s control is protected by a suitable fused cut-out or circuit breaker which is situated as close as reasonably practicable to the supply terminals, which is enclosed in a locked or sealed container. X ESQCR Reg 25 Not give consent to making or altering of connections where there are reasonable grounds to believe that the consumer’s installation does not comply with ESQCR / BS 7671 or, so far as is reasonably practicable, is not protected to prevent danger or interruption of supply. X ESQCR Reg 27 Declare the number of phases, frequency and voltage of the supply and, save in exceptional circumstances, keep this within permitted variations. X ESQCR Reg 28 Provide a written statement of the type and rating of protective devices. X EAWR Reg 4 Construct systems including suitable protective devices that can handle the likely load and fault conditions. X X X EAWR Reg 5 Not put into service electrical equipment where it strength and capability may be exceeded in such a way as to pose a danger. X X X
G99_v7_02102017_for_compliance.docx