Details of Power Generating Module(s) – Power Generating Module Registered Equipment Capacity in kW Date of Technology certicate Manufacturer / Reference Single Phase Units Installation Type reference as Power applicable Factor PH1 PH2 PH3 Units Information to be enclosed Description Confirmation Final copy of circuit diagram Yes / No* Schedule of protection settings ( may be included in circuit diagram ) Yes / No* Commissioning Checks Installation satisfies the requirements of BS7671 (IET Wiring Regulations). Yes / No* Suitable lockable points of isolation have been provided between the PGMs and Yes / No* the rest of the installation. Labels have been installed at all points of isolation in accordance with EREC G99. Yes / No* Interlocking that prevents PGMs being connected in parallel with the DNO system Yes / No* (without synchronising) is in place and operates correctly. The Interface Protection settings have been checked and comply with EREC Yes / No* G99 (refer to 13.4) PGMs successfully synchronise with the DNO system without causing significant Yes / No* voltage disturbance. PGMs successfully run in parallel with the DNO system without tripping and Yes / No* without causing significant voltage disturbances. PGMs successfully disconnect without causing a significant voltage disturbance, Yes / No* when they are shut down. Interface Protection operates and disconnects the PGMs quickly (within 1s) Yes / No* when a suitably rated switch, located between the PGMs and the DNOs incoming connection, is opened. PGMs remain disconnected for at least 20s after switch is reclosed. Yes / No* PGMs disconnects when one phase of the supply is removed (PGMs with LV protection settings only) Loss of tripping and auxiliary supplies Where applicable, loss of supplies to Yes / No* tripping and protection relays results in either Power Generating Module lockout or an alarm to a 24hr manned control centre.
Details of Power Generating Module(s) – Manufacturer / Reference Date of Installation Technology Type Equipment certicate reference as applicable Power Generating Module Registered Capacity in kW Units Single Phase Units Power Factor PH1 PH2 PH3 Information to be enclosed Description Confirmation Final copy of circuit diagram Yes / No* Schedule of protection settings ( may be included in circuit diagram ) Yes / No* Commissioning Checks Installation satisfies the requirements of BS7671 (IET Wiring Regulations). Yes / No* Suitable lockable points of isolation have been provided between the PGMs and the rest of the installation. Yes / No* Labels have been installed at all points of isolation in accordance with EREC G99. Yes / No* Interlocking that prevents PGMs being connected in parallel with the DNO system (without synchronising) is in place and operates correctly. Yes / No* The Interface Protection settings have been checked and comply with EREC G99 (refer to 13.4) Yes / No* PGMs successfully synchronise with the DNO system without causing significant voltage disturbance. Yes / No* PGMs successfully run in parallel with the DNO system without tripping and without causing significant voltage disturbances. Yes / No* PGMs successfully disconnect without causing a significant voltage disturbance, when they are shut down. Yes / No* Interface Protection operates and disconnects the PGMs quickly (within 1s) when a suitably rated switch, located between the PGMs and the DNOs incoming connection, is opened. Yes / No* PGMs remain disconnected for at least 20s after switch is reclosed. Yes / No* PGMs disconnects when one phase of the supply is removed (PGMs with LV protection settings only) Loss of tripping and auxiliary supplies Where applicable, loss of supplies to tripping and protection relays results in either Power Generating Module lockout or an alarm to a 24hr manned control centre. Yes / No*
G99_v7_02102017_for_compliance.docx