STANDARD, LISTING AND APPROVAL 7.0” LCD color touch screen (HMI NFPA 20 technology) powered by an embedded UL (UL218, UL1008 and CSA C22.2 No. 14) microcomputer with software PLC logic. FM Global (Approvals Class 1321/1323) Keypad type pushbuttons: City of New York for fire pump service Start MANUFACTURER AND MODEL Stop Tornatech model GPY Run test SEISMIC CERTIFICATION On-Screen Menu: Test criteria Home ICC-ES AC156 Alarms Building Code Configuration IBC 2015 History CBC 2016 Service OSHPD Special Seismic Certification Manuals Preapproval – OSP Language Seismic Parameters Shall graphically display: ASCE 7-10 Chapter 13 Voltage and amperage readings of all OPERATION AND STARTING METHOD three phases simultaneously and Full service combined manual and independently displayed with true RMS automatic technology. Reduced voltage wye-delta open transition Motor starting transition starting Motor stopped / running SHORT CIRCUIT WITHSTAND RATING Type of starting cause 200V - 480V = 100 kA / 600V = 50kA Actuation mode ENCLOSURE Type of controller NEMA 2 Method of shutdown Bottom conduit entry gland plate Time and date Lifting lugs Pump room temperature (⁰F or ⁰C) POWER CIRCUIT COMPONENTS Digital pressure gauge Voltage surge arrestor System pressure selectable units of Isolating switch and circuit breaker measure: assembly rated not less than 115% of the PSI motor FLC. kPA Circuit breaker overcurrent sensing shall be Bar non-thermal type, magnetic only. Feet of head Locked rotor protector to trip circuit Meter of water breaker within 8 to 20 seconds at 600% of Shall allow programming and display of: FLC. Cut-In and Cut-Out pressure settings Wye-Delta open transition starter Minimum run period timer OPERATIONAL COMPONENTS Sequential start timer Externally flange mounted common Periodic test timer operating handles for both isolating switch Shall allow selection of the language of and the circuit breaker assembly. operation. Mechanically interlocked with enclosure Shall allow on-screen viewing and door to prohibit access in the "ON" position. downloading of the corresponding Emergency Start and run handle mechanism Operation Manual in the chosen language. latchable in the “ON” position TOUCH SCREEN OPERATOR INTERFACE COMMUNICATION PROTOCOL CAPABILITY
STANDARD, LISTING AND APPROVAL NFPA 20 UL (UL218, UL1008 and CSA C22.2 No. 14) FM Global (Approvals Class 1321/1323) City of New York for fire pump service MANUFACTURER AND MODEL Tornatech model GPY SEISMIC CERTIFICATION Test criteria ICC-ES AC156 Building Code IBC 2015 CBC 2016 OSHPD Special Seismic Certification Preapproval – OSP Seismic Parameters ASCE 7-10 Chapter 13 OPERATION AND STARTING METHOD Full service combined manual and automatic Reduced voltage wye-delta open transition starting SHORT CIRCUIT WITHSTAND RATING 200V - 480V = 100 kA / 600V = 50kA ENCLOSURE NEMA 2 Bottom conduit entry gland plate Lifting lugs POWER CIRCUIT COMPONENTS Voltage surge arrestor Isolating switch and circuit breaker assembly rated not less than 115% of the motor FLC. Circuit breaker overcurrent sensing shall be non-thermal type, magnetic only. Locked rotor protector to trip circuit breaker within 8 to 20 seconds at 600% of FLC. Wye-Delta open transition starter OPERATIONAL COMPONENTS Externally flange mounted common operating handles for both isolating switch and the circuit breaker assembly. Mechanically interlocked with enclosure door to prohibit access in the "ON" position. Emergency Start and run handle mechanism latchable in the “ON” position TOUCH SCREEN OPERATOR INTERFACE 7.0” LCD color touch screen (HMI technology) powered by an embedded microcomputer with software PLC logic. Keypad type pushbuttons: Start Stop Run test On-Screen Menu: Home Alarms Configuration History Service Manuals Language Shall graphically display: Voltage and amperage readings of all three phases simultaneously and independently displayed with true RMS technology. Motor starting transition Motor stopped / running Type of starting cause Actuation mode Type of controller Method of shutdown Time and date Pump room temperature (⁰F or ⁰C) Digital pressure gauge System pressure selectable units of measure: PSI kPA Bar Feet of head Meter of water Shall allow programming and display of: Cut-In and Cut-Out pressure settings Minimum run period timer Sequential start timer Periodic test timer Shall allow selection of the language of operation. Shall allow on-screen viewing and downloading of the corresponding Operation Manual in the chosen language. COMMUNICATION PROTOCOL CAPABILITY
GPY-SPE-FOAM-001-E.docx