Smoke fans or vents activating. Occupant Warning System Services CM (Building Gate 3 Planning consultants / Operations) / CM Ensure system has been provided Contractor (Security) with a digital voice command (DVC) capability. Fire Hydrant System Services Consultant Gate 3 Planning / Contractor Ensure system is compliant with AS 2419.1. Fire Hydrant Water Supply Services Consultant CM (Engineering Gate 3 Planning / Contractor Services) / CM Coordinate with UWA to test fire / (Building irrigation system. Operations) Fire Hose Reel System Services Gate 3 Planning consultants / Ensure system complies fully with Contractor AS 2441. Fire Extinguisher Services CM (Engineering Gate 3 Planning consultants / Services) / CM Ensure dry powder provided unless Contractor (Building risks require alternative extinguisher Operations) Fire Extinguisher Services CM (Engineering Gate 3 Planning consultants / Services) / CM Ensure extinguishers are of Contractor (Building appropriate weight not exceeding Operations) 5kg. Mechanical Fire System Services Gate 3 Planning consultants / Ensure smoke exhaust fans are Contractor selected and sized to comply with NCC Specification E2.2b requirements Passive Fire Barriers Services Gate 3 Planning consultants / Ensure barrier complies with Contractor AS1530.4 for fire barriers or is considered non-combustible for smoke barriers. Fire / Smoke Walls Contractor CM (Building Gate 5 Construction Operations) Tag walls as per requirements outlined in this document. Fire / Smoke Doors Contractor CM (Building Gate 5 Construction Operations) Tag doors as required by AS1851. In relation to smoke doors, provide signage as appropriate. Fire / Smoke Doors Contractor CM (Building Gate 5 Construction Operations) / CM Where secured during normal (Security) operation, ensure interface for door to fail open on alarm has been coordinated. Fire & Smoke Curtains Gate 3 Planning consultants /
Smoke fans or vents activating. Occupant Warning System Ensure system has been provided with a digital voice command (DVC) capability. Services consultants / Contractor CM (Building Operations) / CM (Security) Gate 3 Planning Fire Hydrant System Ensure system is compliant with AS 2419.1. Services Consultant / Contractor Gate 3 Planning Fire Hydrant Water Supply Coordinate with UWA to test fire / irrigation system. Services Consultant / Contractor CM (Engineering Services) / CM (Building Operations) Gate 3 Planning Fire Hose Reel System Ensure system complies fully with AS 2441. Services consultants / Contractor Gate 3 Planning Fire Extinguisher Ensure dry powder provided unless risks require alternative extinguisher Services consultants / Contractor CM (Engineering Services) / CM (Building Operations) Gate 3 Planning Fire Extinguisher Ensure extinguishers are of appropriate weight not exceeding 5kg. Services consultants / Contractor CM (Engineering Services) / CM (Building Operations) Gate 3 Planning Mechanical Fire System Ensure smoke exhaust fans are selected and sized to comply with NCC Specification E2.2b requirements Services consultants / Contractor Gate 3 Planning Passive Fire Barriers Ensure barrier complies with AS1530.4 for fire barriers or is considered non-combustible for smoke barriers. Services consultants / Contractor Gate 3 Planning Fire / Smoke Walls Tag walls as per requirements outlined in this document. Contractor CM (Building Operations) Gate 5 Construction Fire / Smoke Doors Tag doors as required by AS1851. In relation to smoke doors, provide signage as appropriate. Contractor CM (Building Operations) Gate 5 Construction Fire / Smoke Doors Where secured during normal operation, ensure interface for door to fail open on alarm has been coordinated. Contractor CM (Building Operations) / CM (Security) Gate 5 Construction Fire & Smoke Curtains consultants / Gate 3 Planning
G-UWA-Design-and-Construction-Standards-Fire-Services-and-Fire-Safety-Engineering.docx