Air Conditioners Btu/h and Electric resistance (or 11.2 EER ≥65,000 (Air-cooled) <135,000 Btu/h none) All other 11.0 EER Btu/h and Electric resistance (or 10.0 EER ≥240,000 <760,000 Btu/h none) All other 9.8 EER Btu/h and Electric resistance (or 11.0 EER ≥135,000 <240,000 Btu/h none) All other 10.8 EER Btu/h and Electric resistance (or 10.0 EER ≥240,000 < 760,000 Btu/h none) All other 9.8 EER AHRI 1230 VRF Multi-Split <65,000 Btu/h All 13.0 SEER (omit Heat Pumps 7.7 HSPF sections 5.1.2 and Btu/h and Electric resistance (or 11.0 EER 6.6) ≥65,000 <135,000 Btu/h none) 3.3 COP All other 10.8 EER 3.3 COP Btu/h and Electric resistance (or 10.6 EER ≥135,000 <240,000 Btu/h none) 3.2 COP All other 10.4 EER 3.2 COP Btu/h and Electric resistance (or 9.5 EER ≥240,000 < 760,000 Btu/h none) 3.2 COP All other 9.8 EER VRF Multi-Split <17,000 Btu/h Without heat recovery 12.0 EER Air Conditioners 4.2 COP (Water-source) With heat recovery 11.8 EER 4.2 COP Btu/h and All 12.0 EER ≥17,000 <65,000 Btu/h 4.2 COP Btu/h and All 12.0 EER ≥65,000 <135,000 Btu/h 4.2 COP Btu/h and Without heat recovery 10.0 EER ≥135,000 <760,000 Btu/h 3.9 COP With heat recovery 9.8 EER 3.9 COP For SI : 1 British thermal unit per hour = 0.2931 W, oC = [(oF) 32]/1.8 –
Air Conditioners (Air-cooled) AHRI 1230 (omit sections 5.1.2 and 6.6) ≥65,000 Btu/h and <135,000 Btu/h Electric resistance (or none) 11.2 EER All other 11.0 EER ≥240,000 Btu/h and <760,000 Btu/h Electric resistance (or none) 10.0 EER All other 9.8 EER ≥135,000 Btu/h and <240,000 Btu/h Electric resistance (or none) 11.0 EER All other 10.8 EER ≥240,000 Btu/h and < 760,000 Btu/h Electric resistance (or none) 10.0 EER All other 9.8 EER VRF Multi-Split Heat Pumps <65,000 Btu/h All 13.0 SEER 7.7 HSPF ≥65,000 Btu/h and <135,000 Btu/h Electric resistance (or none) 11.0 EER 3.3 COP All other 10.8 EER 3.3 COP ≥135,000 Btu/h and <240,000 Btu/h Electric resistance (or none) 10.6 EER 3.2 COP All other 10.4 EER 3.2 COP ≥240,000 Btu/h and < 760,000 Btu/h Electric resistance (or none) 9.5 EER 3.2 COP All other 9.8 EER VRF Multi-Split Air Conditioners (Water-source) <17,000 Btu/h Without heat recovery 12.0 EER 4.2 COP With heat recovery 11.8 EER 4.2 COP ≥17,000 Btu/h and <65,000 Btu/h All 12.0 EER 4.2 COP ≥65,000 Btu/h and <135,000 Btu/h All 12.0 EER 4.2 COP ≥135,000 Btu/h and <760,000 Btu/h Without heat recovery 10.0 EER 3.9 COP With heat recovery 9.8 EER 3.9 COP For SI : 1 British thermal unit per hour = 0.2931 W, oC = [(oF) – 32]/1.8
Florida_Supplement_to_the_2012_IECC_ICC_EDIT_VERSION.docx