F Table 223: ENERGY STAR Room AC - References Component Unit Value Sources CAPY , The cooling capacity of the room air EDC Data Gathering conditioner (RAC) being installed CEERbase , Combined Energy Efficiency ratio Federal Standard Values in: of the baseline unit Table 224 1 Table 225 Table 226 CEERee , Combined Energy efficiency ratio of EDC Data Gathering the RAC being installed Default = ENERGY STAR values in: 2 Table 224 Table 225 Table 226 EFLHRAC , Equivalent full load hours of the RAC being installed Table 227 3 or alternate EFLHcool values an Adjustment Factor in Section 2.2.5 Demand coincidence factor Default: 0.30 CF , Fraction 4 Or EDC data gathering Table 224 lists the minimum federal efficiency standards as of June 2014 and minimum ENERGY STAR efficiency standards for RAC units of various capacity ranges and with and without louvered sides. Units without louvered sides are also referred to as the units or “through wall” units. Note that the new federal standards are based on the Combined Energy Efficiency “built-in” Ratio metric (CEER), which is a metric that incorporates energy use in all modes, including standby and off modes.
Table 223: ENERGY STAR Room AC - References Component Unit Value Sources CAPY , The cooling capacity of the room air conditioner (RAC) being installed EDC Data Gathering CEERbase , Combined Energy Efficiency ratio of the baseline unit Federal Standard Values in: Table 224 Table 225 Table 226 1 CEERee , Combined Energy efficiency ratio of the RAC being installed EDC Data Gathering Default = ENERGY STAR values in: Table 224 Table 225 Table 226 2 EFLHRAC , Equivalent full load hours of the RAC being installed Table 227 or alternate EFLHcool values an Adjustment Factor in Section 2.2.5 3 CF , Demand coincidence factor Fraction Default: 0.30 Or EDC data gathering 4 Table 224 lists the minimum federal efficiency standards as of June 2014 and minimum ENERGY STAR efficiency standards for RAC units of various capacity ranges and with and without louvered sides. Units without louvered sides are also referred to as “through the wall” units or “built-in” units. Note that the new federal standards are based on the Combined Energy Efficiency Ratio metric (CEER), which is a metric that incorporates energy use in all modes, including standby and off modes. F
1370278.docx