STANDARD, LISTING AND APPROVAL Emergency Start and run handle mechanism NFPA 20 latchable in the “ON” position UL (UL218, UL1008 and CSA C22.2 No. 14) TOUCH SCREEN OPERATOR INTERFACE FM Global (Approvals Class 1321/1323) 7.0” LCD color touch screen (HMI City of New York for fire pump service technology) powered by an embedded MANUFACTURER AND MODEL microcomputer with software PLC logic. Tornatech model GPS+GPU Keypad type pushbuttons: SEISMIC CERTIFICATION Start Test criteria Stop ICC-ES AC156 Run test Building Code Transfer switch test IBC 2015 On-Screen Menu: CBC 2016 Home OSHPD Special Seismic Certification Alarms Preapproval – OSP Configuration Seismic Parameters History ASCE 7-10 Chapter 13 Service OPERATION AND STARTING METHOD Manuals Full service combined manual and Language automatic Shall graphically display: Reduced voltage electronic soft starting Normal and alternate voltage and SHORT CIRCUIT WITHSTAND RATING amperage readings of all three phases 200V - 480V = 100 kA / 600V = 50kA simultaneously and independently ENCLOSURE displayed with true RMS technology. NEMA 2 Transfer switch status Bottom conduit entry gland plate Motor starting transition Lifting lugs Motor stopped / running POWER CIRCUIT COMPONENTS Type of starting cause Voltage surge arrestor Actuation mode Isolating switch and circuit breaker Type of controller assembly rated not less than 115% of the Method of shutdown motor FLC. Time and date Circuit breaker overcurrent sensing shall be Pump room temperature (⁰F or ⁰C) non-thermal type, magnetic only. Digital pressure gauge Locked rotor protector to trip circuit System pressure selectable units of breaker within 8 to 20 seconds at 600% of measure: FLC. PSI Electronic soft starter kPA Automatic power transfer switch electrically Bar and manually operated and mechanically Feet of head held. Meter of water OPERATIONAL COMPONENTS Shall allow programming and display of: Externally flange mounted common Cut-In and Cut-Out pressure settings operating handles for both normal and Minimum run period timer alternate power isolating switch and circuit Sequential start timer breaker assemblies. Periodic test timer Mechanically interlocked with enclosure Shall allow selection of the language of door to prohibit access in the "ON" position. operation.
STANDARD, LISTING AND APPROVAL NFPA 20 UL (UL218, UL1008 and CSA C22.2 No. 14) FM Global (Approvals Class 1321/1323) City of New York for fire pump service MANUFACTURER AND MODEL Tornatech model GPS+GPU SEISMIC CERTIFICATION Test criteria ICC-ES AC156 Building Code IBC 2015 CBC 2016 OSHPD Special Seismic Certification Preapproval – OSP Seismic Parameters ASCE 7-10 Chapter 13 OPERATION AND STARTING METHOD Full service combined manual and automatic Reduced voltage electronic soft starting SHORT CIRCUIT WITHSTAND RATING 200V - 480V = 100 kA / 600V = 50kA ENCLOSURE NEMA 2 Bottom conduit entry gland plate Lifting lugs POWER CIRCUIT COMPONENTS Voltage surge arrestor Isolating switch and circuit breaker assembly rated not less than 115% of the motor FLC. Circuit breaker overcurrent sensing shall be non-thermal type, magnetic only. Locked rotor protector to trip circuit breaker within 8 to 20 seconds at 600% of FLC. Electronic soft starter Automatic power transfer switch electrically and manually operated and mechanically held. OPERATIONAL COMPONENTS Externally flange mounted common operating handles for both normal and alternate power isolating switch and circuit breaker assemblies. Mechanically interlocked with enclosure door to prohibit access in the "ON" position. Emergency Start and run handle mechanism latchable in the “ON” position TOUCH SCREEN OPERATOR INTERFACE 7.0” LCD color touch screen (HMI technology) powered by an embedded microcomputer with software PLC logic. Keypad type pushbuttons: Start Stop Run test Transfer switch test On-Screen Menu: Home Alarms Configuration History Service Manuals Language Shall graphically display: Normal and alternate voltage and amperage readings of all three phases simultaneously and independently displayed with true RMS technology. Transfer switch status Motor starting transition Motor stopped / running Type of starting cause Actuation mode Type of controller Method of shutdown Time and date Pump room temperature (⁰F or ⁰C) Digital pressure gauge System pressure selectable units of measure: PSI kPA Bar Feet of head Meter of water Shall allow programming and display of: Cut-In and Cut-Out pressure settings Minimum run period timer Sequential start timer Periodic test timer Shall allow selection of the language of operation.
GPSGPU-SPE-003-E.docx