Checklist for Project Team Activity Responsibility Stakeholder(s) Timeframe Determine if the building or area of Services CM (Engineering Gate 2 Feasibility works has previous Performance consultants Services) / CM Solutions. (Building Operations) Consult with UWA approved Fire Services CM (Engineering Gate 2 Feasibility Engineer to ascertain impact on consultants Services) / CM previous solutions. (Building Operations) Determine if an upgrade to current Services CM (Capital Works) Gate 2 Feasibility Australian Standards is required for consultants works in existing buildings. If not possible to comply, consult Services CM (Engineering Gate 2 Feasibility with UWA approved fire engineer to consultants Services) ascertain possible Performance Solutions. Provide baseline data for all fire Services CM (Engineering Gate 3 Planning safety systems to UWA consultants / Services) / CM Contractor (Building Operations) Fire Engineering Contractor CM (Building Gate 5 Construction Operations) Where Alternative Solutions are prepared, ensure a copy of FSER is provided to UWA for record. Fire Engineering Contractor CM (Building Gate 5 Construction Operations) Ensure FSER clearly outlines information in a separate section outlining list of non-compliances, fire safety strategies, maintenance requirements and Management in Use requirements Detection System Services CM (Building Gate 3 Planning consultants / Operations) Ensure detection system is Notifier Contractor panel with network capability Detection System Services CM (Building Gate 3 Planning consultants / Operations) / CM Ensure interface to all existing Contractor (Security) systems has been retained Detection System Services CM (Building Gate 3 Planning consultants / Operations) / CM Ensure system been programmed Contractor (Security) to interface with other fire safety system including: Mechanical system shut down Secured doors unlocked Occupant warning system activated Fire/smoke curtains closing
Checklist for Project Team Activity Responsibility Stakeholder(s) Timeframe Determine if the building or area of works has previous Performance Solutions. Services consultants CM (Engineering Services) / CM (Building Operations) Gate 2 Feasibility Consult with UWA approved Fire Engineer to ascertain impact on previous solutions. Services consultants CM (Engineering Services) / CM (Building Operations) Gate 2 Feasibility Determine if an upgrade to current Australian Standards is required for works in existing buildings. Services consultants CM (Capital Works) Gate 2 Feasibility If not possible to comply, consult with UWA approved fire engineer to ascertain possible Performance Solutions. Services consultants CM (Engineering Services) Gate 2 Feasibility Provide baseline data for all fire safety systems to UWA Services consultants / Contractor CM (Engineering Services) / CM (Building Operations) Gate 3 Planning Fire Engineering Where Alternative Solutions are prepared, ensure a copy of FSER is provided to UWA for record. Contractor CM (Building Operations) Gate 5 Construction Fire Engineering Ensure FSER clearly outlines information in a separate section outlining list of non-compliances, fire safety strategies, maintenance requirements and Management in Use requirements Contractor CM (Building Operations) Gate 5 Construction Detection System Ensure detection system is Notifier panel with network capability Services consultants / Contractor CM (Building Operations) Gate 3 Planning Detection System Ensure interface to all existing systems has been retained Services consultants / Contractor CM (Building Operations) / CM (Security) Gate 3 Planning Detection System Ensure system been programmed to interface with other fire safety system including: Mechanical system shut down Secured doors unlocked Occupant warning system activated Fire/smoke curtains closing Services consultants / Contractor CM (Building Operations) / CM (Security) Gate 3 Planning
G-UWA-Design-and-Construction-Standards-Fire-Services-and-Fire-Safety-Engineering.docx