Table : PSC to ECM Deemed Savings Measure Wbase Wee LF DCEvap DG COP Demand Energy (PSC) (ECM) per Impact Impact case (kW) (kWh) Temp Cooler: PSC to 22 14 0.9 100% 0.98 2.5 0.0105 92 ECM: 1-14 Watt Cooler: PSC to 48 30 0.9 100% 0.98 2.5 0.0228 200 ECM: 16-23 Watt Cooler: PSC to 90 56 0.9 100% 0.98 2.5 0.0433 380 ECM: 1/20 HP (37 Watt) Freezer: PSC to 22 14 0.9 94.4% 0.98 1.3 0.0126 110 ECM: 1-14 Watt Freezer: PSC to 48 30 0.9 94.4% 0.98 1.3 0.0273 239 ECM: 16-23 Watt Freezer: PSC to 90 56 0.9 94.4% 0.98 1.3 0.0518 454 ECM: 1/20 HP (37 Watt) Table : Shaded Pole to ECM Deemed Savings Measure Wbase Wee LF DCEvap DG COP Demand Energy (Shaded (ECM) per Impact Impact Pole) case (kW) (kWh) Temp Cooler: Shaded 50 14 0.9 100% 0.98 2.5 0.0461 404 Pole to ECM: 1-14 Watt Cooler: Shaded 93 30 0.9 100% 0.98 2.5 0.0802 703 Pole to ECM: 16-23 Watt Cooler: Shaded 142 56 0.9 100% 0.98 2.5 0.1093 958 Pole to ECM: 1/20 HP (37 Watt) Freezer: Shaded 50 14 0.9 94.4% 0.98 1.3 0.0551 483 Pole to ECM: 1-14 Watt Freezer: Shaded 93 30 0.9 94.4% 0.98 1.3 0.0960 841 Pole to ECM: 16-23 Watt Freezer: Shaded 142 56 0.9 94.4% 0.98 1.3 0.1308 1146 Pole to ECM:
Table : PSC to ECM Deemed Savings Measure Wbase (PSC) Wee (ECM) LF DCEvap DG COP per case Temp Demand Impact (kW) Energy Impact (kWh) Cooler: PSC to ECM: 1-14 Watt 22 14 0.9 100% 0.98 2.5 0.0105 92 Cooler: PSC to ECM: 16-23 Watt 48 30 0.9 100% 0.98 2.5 0.0228 200 Cooler: PSC to ECM: 1/20 HP (37 Watt) 90 56 0.9 100% 0.98 2.5 0.0433 380 Freezer: PSC to ECM: 1-14 Watt 22 14 0.9 94.4% 0.98 1.3 0.0126 110 Freezer: PSC to ECM: 16-23 Watt 48 30 0.9 94.4% 0.98 1.3 0.0273 239 Freezer: PSC to ECM: 1/20 HP (37 Watt) 90 56 0.9 94.4% 0.98 1.3 0.0518 454 Table : Shaded Pole to ECM Deemed Savings Measure Wbase (Shaded Pole) Wee (ECM) LF DCEvap DG COP per case Temp Demand Impact (kW) Energy Impact (kWh) Cooler: Shaded Pole to ECM: 1-14 Watt 50 14 0.9 100% 0.98 2.5 0.0461 404 Cooler: Shaded Pole to ECM: 16-23 Watt 93 30 0.9 100% 0.98 2.5 0.0802 703 Cooler: Shaded Pole to ECM: 1/20 HP (37 Watt) 142 56 0.9 100% 0.98 2.5 0.1093 958 Freezer: Shaded Pole to ECM: 1-14 Watt 50 14 0.9 94.4% 0.98 1.3 0.0551 483 Freezer: Shaded Pole to ECM: 16-23 Watt 93 30 0.9 94.4% 0.98 1.3 0.0960 841 Freezer: Shaded Pole to ECM: 142 56 0.9 94.4% 0.98 1.3 0.1308 1146
1312192.docx