Table : DHP – Values and References Term Unit Values Sources CAPYcool , The cooling (at 47° F) EDC Data Gathering AEPS capacity of the Ductless Heat Pump Application; unit EDC Data Gathering CAPYheat , The heating (at 47° F) EDC Data Gathering AEPS capacity of the Ductless Heat Pump Application; unit EDC Data Gathering EFLH primary , Equivalent Full Load Allentown Cooling = 487 Hours 1 Hours of the primary system If the – Allentown Heating = 1,193 Hours unit is installed as the primary Erie Cooling = 389 Hours heating or cooling system, as defined Erie Heating = 1,349 Hours in Table 221 Harrisburg Cooling = 551 Hours Harrisburg Heating = 1,103 Hours Philadelphia Cooling = 591 Hours Philadelphia Heating = 1,060 Hours Pittsburgh Cooling = 432 Hours Pittsburgh Heating = 1,209 Hours Scranton Cooling = 417 Hours Scranton Heating = 1,296 Hours Williamsport Cooling = 422 Hours Williamsport Heating = 1,251 Hours An EDC can either use the Alternate EFLH Table 213 or estimate its own EDC Data EFLH based on customer billing Gathering data analysis EFLH secondary , Equivalent Full Allentown Cooling = 243 Hours 2, 3 Load Hours of the secondary system Allentown Heating = 800 Hours If the unit is installed as the – Erie Cooling = 149 Hours secondary heating or cooling system, Erie Heating = 994 Hours as defined in Table 221 Harrisburg Cooling = 288 Hours Harrisburg Heating = 782 Hours Philadelphia Cooling = 320 Hours Philadelphia Heating = 712 Hours Pittsburgh Cooling = 228 Hours Pittsburgh Heating = 848 Hours Scranton Cooling = 193 Hours Scranton Heating = 925 Hours Williamsport Cooling = 204 Hours Williamsport Heating = 875 hours HSPFbase , Seasonal Standard DHP: 8.2 4, 6 “Heating Performance heating Factor”- Electric resistance: 3.413 efficiency of baseline unit ASHP: 8.2 Electric furnace: 3.242 No existing or non-electric heating: use standard DHP: 8.2
Table : DHP – Values and References Term Unit Values Sources CAPYcool , The cooling (at 47° F) capacity of the Ductless Heat Pump unit EDC Data Gathering AEPS Application; EDC Data Gathering CAPYheat , The heating (at 47° F) capacity of the Ductless Heat Pump unit EDC Data Gathering AEPS Application; EDC Data Gathering EFLH primary , Equivalent Full Load Hours of the primary system – If the unit is installed as the primary heating or cooling system, as defined in Table 221 Allentown Cooling = 487 Hours Allentown Heating = 1,193 Hours Erie Cooling = 389 Hours Erie Heating = 1,349 Hours Harrisburg Cooling = 551 Hours Harrisburg Heating = 1,103 Hours Philadelphia Cooling = 591 Hours Philadelphia Heating = 1,060 Hours Pittsburgh Cooling = 432 Hours Pittsburgh Heating = 1,209 Hours Scranton Cooling = 417 Hours Scranton Heating = 1,296 Hours Williamsport Cooling = 422 Hours Williamsport Heating = 1,251 Hours 1 An EDC can either use the Alternate EFLH Table 213 or estimate its own EFLH based on customer billing data analysis EDC Data Gathering EFLH secondary , Equivalent Full Load Hours of the secondary system – If the unit is installed as the secondary heating or cooling system, as defined in Table 221 Allentown Cooling = 243 Hours Allentown Heating = 800 Hours Erie Cooling = 149 Hours Erie Heating = 994 Hours Harrisburg Cooling = 288 Hours Harrisburg Heating = 782 Hours Philadelphia Cooling = 320 Hours Philadelphia Heating = 712 Hours Pittsburgh Cooling = 228 Hours Pittsburgh Heating = 848 Hours Scranton Cooling = 193 Hours Scranton Heating = 925 Hours Williamsport Cooling = 204 Hours Williamsport Heating = 875 hours 2, 3 HSPFbase , “Heating Seasonal Performance Factor”- heating efficiency of baseline unit Standard DHP: 8.2 Electric resistance: 3.413 ASHP: 8.2 Electric furnace: 3.242 No existing or non-electric heating: use standard DHP: 8.2 4, 6
1312192.docx