Shall allow on-screen viewing and All time statistics downloading of the corresponding First start up Operation Manual in the chosen language. On time COMMUNICATION PROTOCOL CAPABILITY First and last service statistics Modbus with TCP/IP frame format and First setup shielded female RJ45 connector On time STATE AND ALARM VISUAL INDICATORS Motor Statistics: Shall visually indicate and differentiate the On time criticalness by color: Start count Locked rotor current Last start time Fail to start Minimum, maximum, average Under current system pressure Over current Minimum, maximum, average Under voltage pump room temperature Over voltage Jockey Pump controller Phase unbalance On time Check weekly test solenoid valve Start count Weekly test cut-in not reached Last start time Transducer fault Generator: Control voltage not healthy On time Motor trouble Start count Pump room alarm Last start time Invalid cut-in Power statistics Phase reversal Voltage between phases with date Power loss stamp Phase Loss L1 Amperage per phase with date Phase Loss L2 stamp Phase Loss L3 WETTED PARTS Low water level Shall be supplied with a pressure transducer Pump on demand and run test solenoid valve assembly rated Low ambient temp for 500psi working pressure (calibrated at Service required 0-300psi) and be externally mounted with a Transfer switch trouble protective cover. Alternate power phase reversal Pressure sensing line connection to shall be Alternate isolating switch ½” FNPT. Open/Tripped Provision for a redundant pressure Alternate circuit breaker Open/Tripped transducer shall be provided. Alternate side locked rotor current SERVICE/FLOW TESTING CAPABILITIES PRESSURE AND EVENT RECORDING Shall have capability of scheduling Shall be capable of logging pressure data maintenance reminders. and operational events with time and date Shall have capability of inputting pump flow stamp. test data, generate and display the pump Shall be able to display operational events curve and store this information in memory for the life of the controller, and display the for the lifetime of the controller. pressure data in text and/or graphic form. CONNECTION FOR EXTERNAL DEVICES Data shall be retrievable and downloadable Manual remote start device to a flash memory disk via the USB port Automatic remote start device accessible to the user without having to Deluge valve start open the controller door. Generator start signal
Shall allow on-screen viewing and downloading of the corresponding Operation Manual in the chosen language. COMMUNICATION PROTOCOL CAPABILITY Modbus with TCP/IP frame format and shielded female RJ45 connector STATE AND ALARM VISUAL INDICATORS Shall visually indicate and differentiate the criticalness by color: Locked rotor current Fail to start Under current Over current Under voltage Over voltage Phase unbalance Check weekly test solenoid valve Weekly test cut-in not reached Transducer fault Control voltage not healthy Motor trouble Pump room alarm Invalid cut-in Phase reversal Power loss Phase Loss L1 Phase Loss L2 Phase Loss L3 Low water level Pump on demand Low ambient temp Service required Transfer switch trouble Alternate power phase reversal Alternate isolating switch Open/Tripped Alternate circuit breaker Open/Tripped Alternate side locked rotor current PRESSURE AND EVENT RECORDING Shall be capable of logging pressure data and operational events with time and date stamp. Shall be able to display operational events for the life of the controller, and display the pressure data in text and/or graphic form. Data shall be retrievable and downloadable to a flash memory disk via the USB port accessible to the user without having to open the controller door. All time statistics First start up On time First and last service statistics First setup On time Motor Statistics: On time Start count Last start time Minimum, maximum, average system pressure Minimum, maximum, average pump room temperature Jockey Pump controller On time Start count Last start time Generator: On time Start count Last start time Power statistics Voltage between phases with date stamp Amperage per phase with date stamp WETTED PARTS Shall be supplied with a pressure transducer and run test solenoid valve assembly rated for 500psi working pressure (calibrated at 0-300psi) and be externally mounted with a protective cover. Pressure sensing line connection to shall be ½” FNPT. Provision for a redundant pressure transducer shall be provided. SERVICE/FLOW TESTING CAPABILITIES Shall have capability of scheduling maintenance reminders. Shall have capability of inputting pump flow test data, generate and display the pump curve and store this information in memory for the lifetime of the controller. CONNECTION FOR EXTERNAL DEVICES Manual remote start device Automatic remote start device Deluge valve start Generator start signal
GPRGPU-SPE-003-E.docx