or 14 SEER (ASHP) Early Retirement EDC Data Gathering 13; EDC Data Default = 11 (Central Gathering A/C) or 12 (ASHP) or 11.3 (Room A/C),or 13 (no existing cooling) AEPS Application; SEERe , Seasonal Energy Efficiency Ratio EDC Data Gathering EDC Data of the qualifying unit being installed Gathering EDC Data Gathering SEERm , Seasonal Energy Efficiency Ratio 13; EDC Data Default= 11 (Central of the Unit receiving maintenance Gathering A/C) or 12 (ASHP) Replace on Burnout: 11.3 (Central AC) or 2 12 (ASHP) Early Retirement: EERb , Energy Efficiency Ratio of the Baseline Unit EDC Data Gathering 14; EDC Data Default= 8.69 or 9.8 Gathering (Room AC) or 11.3 (no existing cooling) For Central A/C: EERe , Energy Efficiency Ratio of the unit 2; EDC Data Or for ASHP: being installed Gathering EERg , EER of the ground source heat pump being installed. Note that EERs of GSHPs are measured differently than AEPS Application; EERs of air source heat pumps (focusing EDC Data Gathering Data EDC’s on entering water temperatures rather than Gathering ambient air temperatures). The equivalent SEER of a GSHP can be estimated by multiplying EERg by 1.02 EERsys , Ground Source Heat Pump Calculated Calculated effective system EER EERm , Energy Efficiency Ratio of the Unit EDC Data Gathering 14; EDC Data receiving maintenance Gathering Default= 8.69 GSER , Factor used to determine the 1.02 3 SEER of a GSHP based on its EERg Allentown Cooling = 487 Hours Erie Cooling = 389 Hours EFLHcool , Equivalent Full Load Hours of Harrisburg Cooling = operation during the cooling season for the 551 Hours 4 average unit Philadelphia Cooling = 591 Hours Pittsburgh Cooling = 432 Hours Scranton Cooling =
or 14 SEER (ASHP) Early Retirement EDC Data Gathering Default = 11 (Central A/C) or 12 (ASHP) or 11.3 (Room A/C),or 13 (no existing cooling) 13; EDC Data Gathering SEERe , Seasonal Energy Efficiency Ratio of the qualifying unit being installed EDC Data Gathering AEPS Application; EDC Data Gathering SEERm , Seasonal Energy Efficiency Ratio of the Unit receiving maintenance EDC Data Gathering Default= 11 (Central A/C) or 12 (ASHP) 13; EDC Data Gathering EERb , Energy Efficiency Ratio of the Baseline Unit Replace on Burnout: 11.3 (Central AC) or 12 (ASHP) 2 Early Retirement: EDC Data Gathering Default= 8.69 or 9.8 (Room AC) or 11.3 (no existing cooling) 14; EDC Data Gathering EERe , Energy Efficiency Ratio of the unit being installed For Central A/C: Or for ASHP: 2; EDC Data Gathering EERg , EER of the ground source heat pump being installed. Note that EERs of GSHPs are measured differently than EERs of air source heat pumps (focusing on entering water temperatures rather than ambient air temperatures). The equivalent SEER of a GSHP can be estimated by multiplying EERg by 1.02 EDC Data Gathering AEPS Application; EDC’s Data Gathering EERsys , Ground Source Heat Pump effective system EER Calculated Calculated EERm , Energy Efficiency Ratio of the Unit receiving maintenance EDC Data Gathering Default= 8.69 14; EDC Data Gathering GSER , Factor used to determine the SEER of a GSHP based on its EERg 1.02 3 EFLHcool , Equivalent Full Load Hours of operation during the cooling season for the average unit Allentown Cooling = 487 Hours Erie Cooling = 389 Hours Harrisburg Cooling = 551 Hours Philadelphia Cooling = 591 Hours Pittsburgh Cooling = 432 Hours Scranton Cooling = 4
1370278.docx