Savings adjustment factors and reduced EULs for standard T-8, HPT8 and T5 measures are in Table 32, Table 33, and Table 34 below. For all lighting fixture improvements (without control improvements), the following algorithms apply: Table 31: Variables for Retrofit Lighting Term Unit Values Source See Standard ,Connected load of the baseline lighting as defined by kW Wattage Table in Appendix project classification Appendix C See Standard , Connected load of the post-retrofit or kW Wattage Table in Appendix lgithing system Appendix EDC Data EDC Data Gathering Gathering , Savings factor for existing lighting control (percent of None time the lights are off) Default: See Table See Table 35 35 EDC Data EDC Data Gathering Gathering , Demand Coincidence Factor Decimal Default: See 36 Table 36 See Table EDC Data EDC Data Gathering , Hours of Use the average annual operating hours – Gathering of the baseline lighting equipment, which if applied to Default: 36 full connected load will yield annual energy use. See Table 36 See Table , Interactive Energy Factor applies to C&I interior – lighting in space that has air conditioning or Default: 37 refrigeration only. This represents the secondary None See Table 37 See Table energy savings in cooling required which results from decreased indoor lighting wattage. , Interactive Demand Factor applies to C&I interior – lighting in space that has air conditioning or Default: 37 refrigeration only. This represents the secondary None See Table 37 See Table demand savings in cooling required which results from decreased indoor lighting wattage. Table 32: 2016 Savings Adjustment Factors and Adjusted EULs for Standard T-8 Measures Savings Adjustment Factor Adjusted EUL T12 T12 T12 T12 Fixture Type T12 mag EEmag EEmag EEmag EEmag T12 mag ballast ballast ballast ballast ballast ballast and and 40 w and 34 w and 40 w and 34 w and 40 w 40 w lamps lamps lamps lamps lamps lamps
Savings adjustment factors and reduced EULs for standard T-8, HPT8 and T5 measures are in Table 32, Table 33, and Table 34 below. For all lighting fixture improvements (without control improvements), the following algorithms apply: Table 31: Variables for Retrofit Lighting Term Unit Values Source ,Connected load of the baseline lighting as defined by project classification kW See Standard Wattage Table in Appendix C Appendix , Connected load of the post-retrofit or lgithing system kW See Standard Wattage Table in Appendix Appendix , Savings factor for existing lighting control (percent of time the lights are off) None EDC Data Gathering EDC Data Gathering Default: See Table 35 See Table 35 , Demand Coincidence Factor Decimal EDC Data Gathering EDC Data Gathering Default: See Table 36 See Table 36 , Hours of Use – the average annual operating hours of the baseline lighting equipment, which if applied to full connected load will yield annual energy use. EDC Data Gathering EDC Data Gathering Default: See Table 36 See Table 36 , Interactive Energy Factor – applies to C&I interior lighting in space that has air conditioning or refrigeration only. This represents the secondary energy savings in cooling required which results from decreased indoor lighting wattage. None Default: See Table 37 See Table 37 , Interactive Demand Factor – applies to C&I interior lighting in space that has air conditioning or refrigeration only. This represents the secondary demand savings in cooling required which results from decreased indoor lighting wattage. None Default: See Table 37 See Table 37 Table 32: 2016 Savings Adjustment Factors and Adjusted EULs for Standard T-8 Measures Fixture Type Savings Adjustment Factor Adjusted EUL T12 EEmag ballast and 34 w lamps T12 EEmag ballast and 40 w lamps T12 mag ballast and 40 w lamps T12 EEmag ballast and 34 w lamps T12 EEmag ballast and 40 w lamps T12 mag ballast and 40 w lamps
1354189.docx