The basic functions are: Wired Remote Controller (PAR-21MAA) Item Description Number of Units Controllable 16 units as 1 group ON/OFF Run and stop operation Operation Mode Switches between Cool/Dry/Auto/Fan/Heat. Temperature Setting Sets the setpoint temperature in the following range (Range and modes depend Cool/Dry: 67°F-87°F on connected unit model) Heat: 63°F-83°F Auto: 67°F-83°F Fan Speed Setting Hi/Mid-2/Mid-1/Low/Auto (Range and modes depend on connected unit model) Air Flow Direction Setting Air flow direction angles 100%-80%-60%-40%, Swing. (Air flow direction settings depend on the unit model) Weekly Scheduler ON/OFF/Temperature setting can be done up to 8 times one day in the week. The time can be set by the 1-minute interval. Operating Conditions Display Setpoint and room temperature. Sensing can be done at the remote controller or the indoor unit depending on the indoor unit dipswitch setting Liquid, discharge, indoor and outdoor pipe temperatures LEV opening pulses, sub cooling and discharge super heat Compressor Operating Conditions: Running current, frequency, input voltage, On/Off status and operating time Error When an error is currently occurring on an air conditioner unit, the afflicted unit and the error code are displayed Ventilation Equipment Up to 16 indoor units can be connected to an interlocked system that has one LOSSNAY unit. LOSSNAY items that can be set are and “Hi”, “Low”, Ventilation mode switching is not available. “Stop”. Auto Lock Out Function Setting/releasing of simplified locking for remote control buttons can be performed. Locking of all buttons Locking of all buttons except ON/OFF button C. Wireless Remote Controller Kit (PAR-FL32MA) The wireless had held remote controller (PAR-FL32MA) shall be used with a wireless receiver (PAR-SA9FA-E). The controller shall perform input functions
The basic functions are: Wired Remote Controller (PAR-21MAA) Item Description Number of Units Controllable 16 units as 1 group ON/OFF Run and stop operation Operation Mode Switches between Cool/Dry/Auto/Fan/Heat. Temperature Setting (Range and modes depend on connected unit model) Sets the setpoint temperature in the following range Cool/Dry: 67°F-87°F Heat: 63°F-83°F Auto: 67°F-83°F Fan Speed Setting (Range and modes depend on connected unit model) Hi/Mid-2/Mid-1/Low/Auto Air Flow Direction Setting (Air flow direction settings depend on the unit model) Air flow direction angles 100%-80%-60%-40%, Swing. Weekly Scheduler ON/OFF/Temperature setting can be done up to 8 times one day in the week. The time can be set by the 1-minute interval. Operating Conditions Display Setpoint and room temperature. Sensing can be done at the remote controller or the indoor unit depending on the indoor unit dipswitch setting Liquid, discharge, indoor and outdoor pipe temperatures LEV opening pulses, sub cooling and discharge super heat Compressor Operating Conditions: Running current, frequency, input voltage, On/Off status and operating time Error When an error is currently occurring on an air conditioner unit, the afflicted unit and the error code are displayed Ventilation Equipment Up to 16 indoor units can be connected to an interlocked system that has one LOSSNAY unit. LOSSNAY items that can be set are “Hi”, “Low”, and “Stop”. Ventilation mode switching is not available. Auto Lock Out Function Setting/releasing of simplified locking for remote control buttons can be performed. Locking of all buttons Locking of all buttons except ON/OFF button C. Wireless Remote Controller Kit (PAR-FL32MA) The wireless had held remote controller (PAR-FL32MA) shall be used with a wireless receiver (PAR-SA9FA-E). The controller shall perform input functions
guide_specs_p-series_hyper_heat_heat_pump_us_(rev_07-11).docx