Table : Shaded Pole to PSC Deemed Savings Measure Wbase Wee LF DCEvap DG COP Demand Energy (Shaded (PSC) per Impact Impact Pole) case (kW) (kWh) Temp Cooler: Shaded 50 22 0.9 100% 0.98 2.5 0.0355 311 Pole to PSC: 1-14 Watt Cooler: Shaded 93 48 0.9 100% 0.98 2.5 0.0574 503 Pole to PSC: 16-23 Watt Cooler: Shaded 142 90 0.9 100% 0.98 2.5 0.0660 578 Pole to PSC: 1/20 HP (37 Watt) Freezer: Shaded 50 22 0.9 94.4% 0.98 1.3 0.0425 373 Pole to PSC: 1-14 Watt Freezer: Shaded 93 48 0.9 94.4% 0.98 1.3 0.0687 602 Pole to PSC: 16-23 Watt Freezer: Shaded 142 90 0.9 94.4% 0.98 1.3 0.0790 692 Pole to PSC: 1/20 HP (37 Watt)
Table : Shaded Pole to PSC Deemed Savings Measure Wbase (Shaded Pole) Wee (PSC) LF DCEvap DG COP per case Temp Demand Impact (kW) Energy Impact (kWh) Cooler: Shaded Pole to PSC: 1-14 Watt 50 22 0.9 100% 0.98 2.5 0.0355 311 Cooler: Shaded Pole to PSC: 16-23 Watt 93 48 0.9 100% 0.98 2.5 0.0574 503 Cooler: Shaded Pole to PSC: 1/20 HP (37 Watt) 142 90 0.9 100% 0.98 2.5 0.0660 578 Freezer: Shaded Pole to PSC: 1-14 Watt 50 22 0.9 94.4% 0.98 1.3 0.0425 373 Freezer: Shaded Pole to PSC: 16-23 Watt 93 48 0.9 94.4% 0.98 1.3 0.0687 602 Freezer: Shaded Pole to PSC: 1/20 HP (37 Watt) 142 90 0.9 94.4% 0.98 1.3 0.0790 692
1312192.docx