All fire and smoke walls shall comply with requirements and the relevant standards as follows: BCA Fire wall Comply with AS 1530.4 to achieve a FRL – Smoke wall Comply with AS 1530.1 as non-combustible – Floors Comply with AS 1530.4 to achieve a FRL – All services penetrations through a fire wall shall be sealed in accordance with BCA C3.15. All services penetrations through a smoke wall shall be sealed with appropriate fire rated mastic seals. The area of works shall be clearly labelled and marked with the following information: Standards the system is compliant with (i.e. AS 1530.4 and AS 4072.1) FRL of the system Name and contact details of the installer Installation date Reference number for the specific area Name and contact details of the manufacturer The following figure is an example of the expected label. Documentation Upon completion of the works, the area of works shall be inspected to ensure satisfactory completion. The Contractor is required to provide documentation as per AS 4072.1 as follows: The system used is identical with the tested specimen; AND The system has been correctly installed in accordance with the specification manufacturer’s In addition to the above documentation, the Contractor shall provide a record of each installation which outlines the following information as noted in AS 4072.1: Name, address and contact details of installation company Date of final inspection Description of system Identification of the position of the installation on a drawing Photo Fire Dampers Fire dampers shall be constructed and installed to meet all requirements of AS 1682 and AS 1668. Manufacturer certification of compliance is required. The free area of any fire damper shall not be less than 85% of the adjoining duct area. Where necessary the duct size shall be increased above the nominal airway size of the adjoining ductwork to accommodate the fire damper
All fire and smoke walls shall comply with BCA requirements and the relevant standards as follows: Fire wall – Comply with AS 1530.4 to achieve a FRL Smoke wall – Comply with AS 1530.1 as non-combustible Floors – Comply with AS 1530.4 to achieve a FRL All services penetrations through a fire wall shall be sealed in accordance with BCA C3.15. All services penetrations through a smoke wall shall be sealed with appropriate fire rated mastic seals. The area of works shall be clearly labelled and marked with the following information: Standards the system is compliant with (i.e. AS 1530.4 and AS 4072.1) FRL of the system Name and contact details of the installer Installation date Reference number for the specific area Name and contact details of the manufacturer The following figure is an example of the expected label. Documentation Upon completion of the works, the area of works shall be inspected to ensure satisfactory completion. The Contractor is required to provide documentation as per AS 4072.1 as follows: The system used is identical with the tested specimen; AND The system has been correctly installed in accordance with the manufacturer’s specification In addition to the above documentation, the Contractor shall provide a record of each installation which outlines the following information as noted in AS 4072.1: Name, address and contact details of installation company Date of final inspection Description of system Identification of the position of the installation on a drawing Photo Fire Dampers Fire dampers shall be constructed and installed to meet all requirements of AS 1682 and AS 1668. Manufacturer certification of compliance is required. The free area of any fire damper shall not be less than 85% of the adjoining duct area. Where necessary the duct size shall be increased above the nominal airway size of the adjoining ductwork to accommodate the fire damper
G-UWA-Design-and-Construction-Standards-Fire-Services-and-Fire-Safety-Engineering.docx