Add a table for variable refrigerant flow multi-split air conditioners and heat pumps as shown. Define this equipment and add to Chapter 5, Referenced Standards as shown. TABLE C403.2.3(11) MINIMUM EFFICIENCY REQUIREMENTS VARIABLE REFRIGERANT FLOW MULTI-SPLIT AIR CONDITIONERS AND HEAT PUMPS Equipment Type Size Category Heating Typea Minimum Test Efficiency Procedureb VRF Multi-Split <65,000 Btu/h All 13.0 SEER Air Conditioners Btu/h and Electric resistance (or 11.2 EER ≥65,000 (Air-cooled) <135,000 Btu/h none) All other 11.0 EER Btu/h and Electric resistance (or 10.0 EER ≥240,000 <760,000 Btu/h none) All other 9.8 EER Btu/h and Electric resistance (or 11.0 EER ≥135,000 <240,000 Btu/h none) All other 10.8 EER Btu/h and Electric resistance (or 10.0 EER ≥240,000 < 760,000 Btu/h none) All other 9.8 EER AHRI 1230 VRF Multi-Split <65,000 Btu/h All 13.0 SEER (omit Heat Pumps 7.7 HSPF sections 5.1.2 and 6.6) Btu/h and Electric resistance (or 11.0 EER ≥65,000 <135,000 Btu/h none) 3.3 COP All other 10.8 EER 3.3 COP Btu/h and Electric resistance (or 10.6 EER ≥135,000 <240,000 Btu/h none) 3.2 COP All other 10.4 EER 3.2 COP Btu/h and Electric resistance (or 9.5 EER ≥240,000 < 760,000 Btu/h none) 3.2 COP
Add a table for variable refrigerant flow multi-split air conditioners and heat pumps as shown. Define this equipment and add to Chapter 5, Referenced Standards as shown. TABLE C403.2.3(11) MINIMUM EFFICIENCY REQUIREMENTS VARIABLE REFRIGERANT FLOW MULTI-SPLIT AIR CONDITIONERS AND HEAT PUMPS Equipment Type Size Category Heating Typea Minimum Efficiency Test Procedureb VRF Multi-Split Air Conditioners (Air-cooled) <65,000 Btu/h All 13.0 SEER AHRI 1230 (omit sections 5.1.2 and 6.6) ≥65,000 Btu/h and <135,000 Btu/h Electric resistance (or none) 11.2 EER All other 11.0 EER ≥240,000 Btu/h and <760,000 Btu/h Electric resistance (or none) 10.0 EER All other 9.8 EER ≥135,000 Btu/h and <240,000 Btu/h Electric resistance (or none) 11.0 EER All other 10.8 EER ≥240,000 Btu/h and < 760,000 Btu/h Electric resistance (or none) 10.0 EER All other 9.8 EER VRF Multi-Split Heat Pumps <65,000 Btu/h All 13.0 SEER 7.7 HSPF ≥65,000 Btu/h and <135,000 Btu/h Electric resistance (or none) 11.0 EER 3.3 COP All other 10.8 EER 3.3 COP ≥135,000 Btu/h and <240,000 Btu/h Electric resistance (or none) 10.6 EER 3.2 COP All other 10.4 EER 3.2 COP ≥240,000 Btu/h and < 760,000 Btu/h Electric resistance (or none) 9.5 EER 3.2 COP
Florida_Supplement_to_the_2015_IECC-ICC_EDIT_VERSION.docx