ELECTRICALLY OPERATED UNITARY AND APPLIED HEAT PUMPS Equipment Type Size Category Heating Subcategory or Minimum Test Section Rating Condition Efficiency Procedurea Type Air Cooled (Cooling <65,000 Btu/hb All Split System 13.0 SEER AHRI mode) 210/240 Single Package 13.0 SEER Through-the Wall, space Btu/hb All Split System 12.0 13.0 ≤30,000 constrained Air-cooled SEER cooling mode Single Package 12.0 13.0 SEER Small Single-duct, <65,000 Btu/hb All Split system 11.0 10.0 air cooled SEER (before 1/1/2015) 12.0 SEER (as of 1/1/2015) Btu/h and Electric Split System and 11.0 EER AHRI ≥65,000 <135,000 Btu/h resistance (or Single Package 11.2 IEER 340/360 none) All other Split System and 10.8 EER Single Package 11.0 IEER Air cooled (cooling mode) Btu/h and Electric Split System and 10.6 EER ≥135,000 <240,000 Btu/h resistance (or Single Package 10.7 IEER none) All other Split System and 10.4 EER Single Package 10.5 IEER Btu/h Electric Split System and 9.5 EER ≥240,000 resistance (or Single Package 9.6 IEER none) All other Split System and 9.3 EER Single Package 9.4 IEER Water source <17,000 Btu/h All 86oF entering 11.2 EER ISO 13256-1 (cooling mode) water Btu/h and All 86oF entering 12.0 EER ≥17,000 <65,000 Btu/h water Btu/h and All 86oF entering 12.0 EER ≥65,000 <135,000 Btu/h water Ground water source <135,000 Btu/h All 59oF entering 16.2 EER
ELECTRICALLY OPERATED UNITARY AND APPLIED HEAT PUMPS Equipment Type Size Category Heating Section Type Subcategory or Rating Condition Minimum Efficiency Test Procedurea Air Cooled (Cooling mode) <65,000 Btu/hb All Split System 13.0 SEER AHRI 210/240 Single Package 13.0 SEER Through-the Wall, space constrained Air-cooled cooling mode ≤30,000 Btu/hb All Split System 12.0 13.0 SEER Single Package 12.0 13.0 SEER Small Single-duct, air cooled <65,000 Btu/hb All Split system 11.0 10.0 SEER (before 1/1/2015) 12.0 SEER (as of 1/1/2015) Air cooled (cooling mode) ≥65,000 Btu/h and <135,000 Btu/h Electric resistance (or none) Split System and Single Package 11.0 EER 11.2 IEER AHRI 340/360 All other Split System and Single Package 10.8 EER 11.0 IEER ≥135,000 Btu/h and <240,000 Btu/h Electric resistance (or none) Split System and Single Package 10.6 EER 10.7 IEER All other Split System and Single Package 10.4 EER 10.5 IEER ≥240,000 Btu/h Electric resistance (or none) Split System and Single Package 9.5 EER 9.6 IEER All other Split System and Single Package 9.3 EER 9.4 IEER Water source (cooling mode) <17,000 Btu/h All 86oF entering water 11.2 EER ISO 13256-1 ≥17,000 Btu/h and <65,000 Btu/h All 86oF entering water 12.0 EER ≥65,000 Btu/h and <135,000 Btu/h All 86oF entering water 12.0 EER Ground water source <135,000 Btu/h All 59oF entering 16.2 EER
Florida%20Supplement%20to%20the%202012%20IECC%20-%20ICC%20EDIT%20VERSION.docx