Table 31: EISA 2007 Standards for General Service Fluorescent Bulbs Minimum Average Nominal Lamp Minimum (Color Rendering Lamp Type Lamp Efficacy Wattage Index) CRI (LPW) >35 W 69 75.0 4-foot medium bi-pin W 45 75.0 ≤35 >35 W 69 68.0 2-foot U-shaped W 45 64.0 ≤35 65 W 69 80.0 8-foot slimline W 45 80.0 ≤65 >100 W 69 80.0 8-foot high output W 45 80.0 ≤100 Table 32: Assumed T-8 Baseline Fixtures for Removed T-12 Fixtures Assumed T-8 T-12 Lamp Baseline Fixture Assumed T-8 Length T-12 Lamp Type T-12 Lamp Count Code Baseline Wattage Standard 1 F21ILL 20 24” Standard 2 F22ILL 33 24” Standard 3 F23ILL 47 24” Standard 4 F24ILL 61 24” Standard 1 F31ILL 26 36” Standard 2 F32ILL 46 36” Standard 3 F33ILL 67 36” Standard 4 F34ILL 87 36” Standard 1 F41ILL 31 48” Standard 2 F42ILL 59 48” Standard 3 F43ILL 89 48” Standard 4 F44ILL 112 48” Standard 6 F46ILL 175 48” Standard 8 F48ILL 224 48” Standard 1 F51ILL 36 60” Standard 2 F52ILL 72 60” Standard 1 F61ILL 55 72” Standard 2 F62ILL 111 72” Standard 1 F81ILL 58 96” Standard 2 F82ILL 109 96”
Table 31: EISA 2007 Standards for General Service Fluorescent Bulbs Lamp Type Nominal Lamp Wattage Minimum (Color Rendering Index) CRI Minimum Average Lamp Efficacy (LPW) 4-foot medium bi-pin >35 W 69 75.0 ≤35 W 45 75.0 2-foot U-shaped >35 W 69 68.0 ≤35 W 45 64.0 8-foot slimline 65 W 69 80.0 ≤65 W 45 80.0 8-foot high output >100 W 69 80.0 ≤100 W 45 80.0 Table 32: Assumed T-8 Baseline Fixtures for Removed T-12 Fixtures T-12 Lamp Length T-12 Lamp Type T-12 Lamp Count Assumed T-8 Baseline Fixture Code Assumed T-8 Baseline Wattage 24” Standard 1 F21ILL 20 24” Standard 2 F22ILL 33 24” Standard 3 F23ILL 47 24” Standard 4 F24ILL 61 36” Standard 1 F31ILL 26 36” Standard 2 F32ILL 46 36” Standard 3 F33ILL 67 36” Standard 4 F34ILL 87 48” Standard 1 F41ILL 31 48” Standard 2 F42ILL 59 48” Standard 3 F43ILL 89 48” Standard 4 F44ILL 112 48” Standard 6 F46ILL 175 48” Standard 8 F48ILL 224 60” Standard 1 F51ILL 36 60” Standard 2 F52ILL 72 72” Standard 1 F61ILL 55 72” Standard 2 F62ILL 111 96” Standard 1 F81ILL 58 96” Standard 2 F82ILL 109
1370278.docx