Factor Refrigerator/Cooler , Per door power consumption of cooler case ASHs kW 0.109 1 without controls , Percent of time cooler case ASH with controls will be off None 20% 1 during the peak period , Percent of time cooler case ASH with controls will be off None 85% 1 annually , Demand diversity factor of cooler, accounting for the fact that not all anti-sweat heaters in all buildings in the None 1 3 population are operating at the same time. , Coefficient of performance of cooler None 2.5 1 Freezer , Per door power consumption of freezer case ASHs kW 0.191 1 without controls , Percent of time freezer case ASH with controls will be None 10% 1 off during the peak period , Percent of time freezer case ASH with controls will be None 75% 1 off annually , Demand diversity factor of freezer, accounting for the fact that not all anti-sweat heaters in all buildings in the None 1 3 population are operating at the same time. , Coefficient of performance of freezer None 1.3 1 , Typical percent of cases that are medium-temperature 68% 4 None refrigerator/cooler cases
Factor Refrigerator/Cooler , Per door power consumption of cooler case ASHs without controls kW 0.109 1 , Percent of time cooler case ASH with controls will be off during the peak period None 20% 1 , Percent of time cooler case ASH with controls will be off annually None 85% 1 , Demand diversity factor of cooler, accounting for the fact that not all anti-sweat heaters in all buildings in the population are operating at the same time. None 1 3 , Coefficient of performance of cooler None 2.5 1 Freezer , Per door power consumption of freezer case ASHs without controls kW 0.191 1 , Percent of time freezer case ASH with controls will be off during the peak period None 10% 1 , Percent of time freezer case ASH with controls will be off annually None 75% 1 , Demand diversity factor of freezer, accounting for the fact that not all anti-sweat heaters in all buildings in the population are operating at the same time. None 1 3 , Coefficient of performance of freezer None 1.3 1 , Typical percent of cases that are medium-temperature refrigerator/cooler cases None 68% 4
1354189.docx