Table : Ice Machine Reference Values for Algorithm Components Term Unit Values Source , Baseline ice machine energy usage per 1 Table 3132 100 lbs. of ice , High-efficiency ice machine energy Table 3133 2 usage per 100 lbs. of ice , Ice harvest rate per 24 hrs. Manufacturer Specs EDC Data Gathering Custom EDC Data Gathering , Duty cycle of ice machine expressed as a None percentage of time machine produces ice Default: 0.4 3 365, Days per year 365 Conversion Factor 100, Conversion to obtain energy per 100 Conversion pound of ice Factor 8760, Hours per year 8,760 Conversion Factor Ice maker type None Manufacturer Specs EDC Data Gathering , Demand Coincidence Factor Decimal 0.77 4 Table : Batch-Type Ice Machine Baseline Efficiencies (PY8-PY9) Baseline energy use per Ice machine type Ice harvest rate (H) 100 lbs. of ice <450 10.26 0.0086*H – Ice-Making Head 6.89 0.0011*H ≥450 – <1000 8.85 0.0038*H – Remote-Condensing w/out remote compressor 5.1 ≥1000 <934 8.85 0.0038*H – Remote-Condensing with remote compressor 5.3 ≥934 <175 18 0.0469*H – Self-Contained 9.8 ≥175
Table : Ice Machine Reference Values for Algorithm Components Term Unit Values Source , Baseline ice machine energy usage per 100 lbs. of ice Table 3132 1 , High-efficiency ice machine energy usage per 100 lbs. of ice Table 3133 2 , Ice harvest rate per 24 hrs. Manufacturer Specs EDC Data Gathering , Duty cycle of ice machine expressed as a percentage of time machine produces ice None Custom EDC Data Gathering Default: 0.4 3 365, Days per year 365 Conversion Factor 100, Conversion to obtain energy per pound of ice 100 Conversion Factor 8760, Hours per year 8,760 Conversion Factor Ice maker type None Manufacturer Specs EDC Data Gathering , Demand Coincidence Factor Decimal 0.77 4 Table : Batch-Type Ice Machine Baseline Efficiencies (PY8-PY9) Ice machine type Ice harvest rate (H) Baseline energy use per 100 lbs. of ice Ice-Making Head <450 10.26 – 0.0086*H ≥450 6.89 – 0.0011*H Remote-Condensing w/out remote compressor <1000 8.85 – 0.0038*H ≥1000 5.1 Remote-Condensing with remote compressor <934 8.85 – 0.0038*H ≥934 5.3 Self-Contained <175 18 – 0.0469*H ≥175 9.8
1350348.docx