Provision of the approval and evidence of training shall constitute a HOLD POINT. 6.3 Inspection The Contractor must: arrange for Certificates of Compliance of all electrical work; provide copies of the certificates to the Principal; and ensure that any applicable fees are paid for the connections. 7. SUPPLY POINTS 7.1 General If the Principal has made arrangements for supply point locations, the locations will be shown on the drawings. The Contractor must confirm the position of the supply points before installing conduit runs to these points. If the Contractor is to arrange service points, the Contractor must: complete and submit a SA Power Networks Form; provide a copy of the form to the Principal; and the DPTI Electrical Asset Management group. provide Certificates of Compliance to the Principal in accordance with the Electricity Act. 7.2 Temporary Supply and Service Points For details of any temporary overhead supply points and/or service points refer to the Contract Specific Requirements. 8. SERVICE POINTS 8.1 General SA Power Networks underground supply must be connected to lighting circuits in accordance with SA Power Networks service supply rules and regulations. SA Power Networks Stobie pole supply must be connected to lighting circuits in accordance with relevant DPTI Standard Drawings. 8.2 Layout The layout of switchboards and general circuit arrangement of service points must be substantially as shown on the drawings. 8.3 Location Services fuses must not be located in DPTI switchboards. Isolation pit & fuse must be installed in accordance with DPTI standard drawings. Three phase installation must have all phases identified on both sides of the isolation fuse with heat shrink. 9. WIRING 9.1 Combination / Combo Mast Arm poles Unless specified otherwise, combination/combo mast arm poles must be fed from the traffic signal controller. 9.2 Four Way Lighting Poles Four way lighting poles must have two circuits fed from the same phase.
Provision of the approval and evidence of training shall constitute a HOLD POINT. 6.3 Inspection The Contractor must: arrange for Certificates of Compliance of all electrical work; provide copies of the certificates to the Principal; and ensure that any applicable fees are paid for the connections. 7. SUPPLY POINTS 7.1 General If the Principal has made arrangements for supply point locations, the locations will be shown on the drawings. The Contractor must confirm the position of the supply points before installing conduit runs to these points. If the Contractor is to arrange service points, the Contractor must: complete and submit a SA Power Networks Form; provide a copy of the form to the Principal; and the DPTI Electrical Asset Management group. provide Certificates of Compliance to the Principal in accordance with the Electricity Act. 7.2 Temporary Supply and Service Points For details of any temporary overhead supply points and/or service points refer to the Contract Specific Requirements. 8. SERVICE POINTS 8.1 General SA Power Networks underground supply must be connected to lighting circuits in accordance with SA Power Networks service supply rules and regulations. SA Power Networks Stobie pole supply must be connected to lighting circuits in accordance with relevant DPTI Standard Drawings. 8.2 Layout The layout of switchboards and general circuit arrangement of service points must be substantially as shown on the drawings. 8.3 Location Services fuses must not be located in DPTI switchboards. Isolation pit & fuse must be installed in accordance with DPTI standard drawings. Three phase installation must have all phases identified on both sides of the isolation fuse with heat shrink. 9. WIRING 9.1 Combination / Combo Mast Arm poles Unless specified otherwise, combination/combo mast arm poles must be fed from the traffic signal controller. 9.2 Four Way Lighting Poles Four way lighting poles must have two circuits fed from the same phase.
Part_R52_Installation_of_Lighting_December_2016.docx