Pittsburgh = 985 EFLHfuel furnace Scranton = 1,056 Williamsport = 1,033 An EDC can either use the Alternate Alternate EFLH Table (See Optional EFLH Table or estimate own EFLH Section 2.19.3) or EDC Data it’s based on customer billing data analysis. Gathering Allentown = 1,334 1 Erie = 1,411 Harrisburg = 1,279 Default Philadelphia = 1,249 Pittsburgh = 1,283 EFLHfuel boiler Scranton = 1,371 Williamsport = 1,354 An EDC can either use the Alternate Alternate EFLH Table (See Optional EFLH Table or estimate own EFLH Section 2.19.3) or EDC Data it’s based on customer billing data analysis. Gathering HSPFASHP Variable Default = 7.7 2010 PA TRM Table 21 Nameplate EDC Data Gathering AFUEfuel heat Variable Default = 95% (natural gas/propane ENERGY STAR requirement furnace) 95% (natural gas/propane steam boiler) 95% (natural gas/propane hot water boiler) 85% (oil furnace) 85% (oil steam boiler) 85% (oil hot water boiler) Nameplate EDC Data Gathering HPmotor Variable Default = ½ hp Average blower motor capacity for gas furnace (typical range = ¼ hp to ¾ hp) Nameplate EDC Data Gathering Variable Default = 0.50 Typical efficiency of ½ hp blower ηmotor motor Nameplate EDC Data Gathering Alternate Equivalent Full Load Hour (EFLH) Tables Table 239 through Table 243 below, show heating EFLH by city and for each housing EDC’s demographics. In order to determine the most appropriate EFLH value to use for a project, first select the type of electric heating equipment being replaced, then the appropriate EDC. Next,
EFLHfuel furnace Pittsburgh = 985 Scranton = 1,056 Williamsport = 1,033 Optional An EDC can either use the Alternate EFLH Table or estimate it’s own EFLH based on customer billing data analysis. Alternate EFLH Table (See Section 2.19.3) or EDC Data Gathering EFLHfuel boiler Default Allentown = 1,334 Erie = 1,411 Harrisburg = 1,279 Philadelphia = 1,249 Pittsburgh = 1,283 Scranton = 1,371 Williamsport = 1,354 1 Optional An EDC can either use the Alternate EFLH Table or estimate it’s own EFLH based on customer billing data analysis. Alternate EFLH Table (See Section 2.19.3) or EDC Data Gathering HSPFASHP Variable Default = 7.7 2010 PA TRM Table 21 Nameplate EDC Data Gathering AFUEfuel heat Variable Default = 95% (natural gas/propane furnace) 95% (natural gas/propane steam boiler) 95% (natural gas/propane hot water boiler) 85% (oil furnace) 85% (oil steam boiler) 85% (oil hot water boiler) ENERGY STAR requirement Nameplate EDC Data Gathering HPmotor Variable Default = ½ hp Average blower motor capacity for gas furnace (typical range = ¼ hp to ¾ hp) Nameplate EDC Data Gathering ηmotor Variable Default = 0.50 Typical efficiency of ½ hp blower motor Nameplate EDC Data Gathering Alternate Equivalent Full Load Hour (EFLH) Tables Table 239 through Table 243 below, show heating EFLH by city and for each EDC’s housing demographics. In order to determine the most appropriate EFLH value to use for a project, first select the type of electric heating equipment being replaced, then the appropriate EDC. Next,
1265230.docx