A license-free graphical PC tool be provided, to configure the programmable logic. The IED shall be supplied with pre-loaded default PSL schemes that provide a typical application scheme, to save on engineering / implementation time in projects. Measurements The device include capabilities for real-time AC measurements, derived power and energy quantities, and demand values. Setting Groups The device shall offer four programmable setting groups, including independent logic schemes. PC Toolsuite The device shall be supported by a license-free Windows®-based toolsuite, with support for operating systems up to Windows 7. The toolsuite shall support: Creation of offline protection settings, downloading and uploading to the device. Standard application template creation for protection settings, such that the utility can standardize on a number of global templates, where only local (feeder-specific) thresholds change at each site. Settings file export and import in format. Graphical creation and editing of programmable logic. Comparison of setting and programmable files to identify any differences between versions. Creation of IEC 61850 configuration and reports. Retrieval of fault, event and disturbance records, and cybersecurity logs. Display of extracted records, including disturbance record waveform graphics. Changing of settings groups, control and resetting commands. Polling of measurement values. Export of settings files in .xrio format, for compatibility with protection testing equipment. Communications Station Bus IEC – The relay shall support up to 16 concurrent IEC61850 client connections. The relay shall support up to 64 GOOSE Inputs and Outputs Simple Network Management Protocol (SNMP) shall be provided to manage the device in an IP network. Two versions of SNMP shall be supported: version 2c, and a cybersecure implementation of version 3. Serial Communication based on EIA RS485 The relay shall have a serial communication port based on EIA RS485, that supports the communication protocols Courier, MODBUS, IEC60870-5-103, and DNP3 which shall be selected by an ordering option. Cyber Security The relay shall be provided with a NERC compliant display
A license-free graphical PC tool be provided, to configure the programmable logic. The IED shall be supplied with pre-loaded default PSL schemes that provide a typical application scheme, to save on engineering / implementation time in projects. Measurements The device include capabilities for real-time AC measurements, derived power and energy quantities, and demand values. Setting Groups The device shall offer four programmable setting groups, including independent logic schemes. PC Toolsuite The device shall be supported by a license-free Windows®-based toolsuite, with support for operating systems up to Windows 7. The toolsuite shall support: Creation of offline protection settings, downloading and uploading to the device. Standard application template creation for protection settings, such that the utility can standardize on a number of global templates, where only local (feeder-specific) thresholds change at each site. Settings file export and import in format. Graphical creation and editing of programmable logic. Comparison of setting and programmable files to identify any differences between versions. Creation of IEC 61850 configuration and reports. Retrieval of fault, event and disturbance records, and cybersecurity logs. Display of extracted records, including disturbance record waveform graphics. Changing of settings groups, control and resetting commands. Polling of measurement values. Export of settings files in .xrio format, for compatibility with protection testing equipment. Communications Station Bus – IEC The relay shall support up to 16 concurrent IEC61850 client connections. The relay shall support up to 64 GOOSE Inputs and Outputs Simple Network Management Protocol (SNMP) shall be provided to manage the device in an IP network. Two versions of SNMP shall be supported: version 2c, and a cybersecure implementation of version 3. Serial Communication based on EIA RS485 The relay shall have a serial communication port based on EIA RS485, that supports the communication protocols Courier, MODBUS, IEC60870-5-103, and DNP3 which shall be selected by an ordering option. Cyber Security The relay shall be provided with a NERC compliant display
P341_spec.docx