Kiwa Unit Background ed Sentence "... taken into consider change to: We will take the proposition into ExVision when assessing of the is not " ... taken into consideration when account. …" correct assessing of the …" LCIE If the surge protective device is The matter should be transfer to FR assessed according to the standard MT of IEC 60079-11 and IEC IEC 60079-11 and meets every 60079-25 in order to align requirement, nothing prevents to requirements. issue an IECEx certificate with the In addition, as a provisional marking Ex ia IIC Ga T .... measure, it shall be required to add : condition for safe use to CoC : the surge protection device Further step for MT. must be installed outside but as near to the boundary of Zone 0 as is practicable, preferably within 1 m a marking on the product : WARNING: SURGE PROTECTION DEVICE MUST BE INSTALLED OUTSIDE THE ZONE 0 SEE – INSTRUCTIONS
Kiwa Unit ExVision Background ed Sentence "... taken into consider when assessing of the …" is not correct change to: " ... taken into consideration when assessing of the …" We will take the proposition into account. LCIE FR If the surge protective device is assessed according to the standard IEC 60079-11 and meets every requirement, nothing prevents to issue an IECEx certificate with the marking Ex ia IIC Ga T .... The matter should be transfer to MT of IEC 60079-11 and IEC 60079-25 in order to align requirements. In addition, as a provisional measure, it shall be required to add : condition for safe use to CoC : the surge protection device must be installed outside but as near to the boundary of Zone 0 as is practicable, preferably within 1 m a marking on the product : WARNING: SURGE PROTECTION DEVICE MUST BE INSTALLED OUTSIDE THE ZONE 0 – SEE INSTRUCTIONS Further step for MT.
ExTAG_427A_CC_Compilation.docx