Station Static and/or Protocol Section 6.5.5.2, Operational Data Dynamic Reactive Requirements.(Typical QSE telemetry point) 10 sec ICCP Device(s) status for RE Comment: each device Station Static and/or Protocol Section 6.5.5.2, Operational Data Dynamic Reactive Requirements.(Typical QSE telemetry point) Device(s) MVAR 10 sec ICCP output for each RE Comment: device Generator Step-Up Protocol Section 6.5.5.2, Operational Data (GSU) Transformer Requirements.(Typical QSE telemetry point) High-Side MW and 10 sec ICCP MVAR for each RE Comment: modeled GSU Generation Resource Protocol Section 6.5.5.2, Operational Data auxiliary load and/or Requirements.(Typical QSE telemetry point) station service MW 10 sec ICCP and MVAR for each RE Comment: modeled load Protocol Section 6.5.5.2, Operational Data Requirements. (RE has confirmed that TSP is providing required points; Transmission Line Flow has telemetry for both the sending and receiving end of the Transmission Line 10 sec ICCP interconnecting line if the Generation Resource is Flow registered at a different station in the Network Operations Model). RE Comment: New Generator Telemetry Data Frequency Mode Reference/Comments Real Time data for reliability purposes must be accurate to within three percent (3%). This telemetry may be provided Real Time data from relaying accuracy instrumentation transformers. accuracy QSE Comment: Protocol Section 6.5.5.2, Operational Data Requirements. Net Generation Generation is preferred. Otherwise, aux load should also be Resource gross 2 sec ICCP provided. and net MW output QSE Comment: Protocol Section 6.5.5.2, Operational Data Requirements. Net Generation Generation is preferred. Otherwise, aux load should also be Resource gross 2 sec ICCP provided. and net MVar output QSE Comment:
Station Static and/or Dynamic Reactive Device(s) status for each device 10 sec ICCP Protocol Section 6.5.5.2, Operational Data Requirements.(Typical QSE telemetry point) RE Comment: Station Static and/or Dynamic Reactive Device(s) MVAR output for each device 10 sec ICCP Protocol Section 6.5.5.2, Operational Data Requirements.(Typical QSE telemetry point) RE Comment: Generator Step-Up (GSU) Transformer High-Side MW and MVAR for each modeled GSU 10 sec ICCP Protocol Section 6.5.5.2, Operational Data Requirements.(Typical QSE telemetry point) RE Comment: Generation Resource auxiliary load and/or station service MW and MVAR for each modeled load 10 sec ICCP Protocol Section 6.5.5.2, Operational Data Requirements.(Typical QSE telemetry point) RE Comment: Transmission Line Flow 10 sec ICCP Protocol Section 6.5.5.2, Operational Data Requirements. (RE has confirmed that TSP is providing required points; Transmission Line Flow has telemetry for both the sending and receiving end of the interconnecting line if the Generation Resource is registered at a different station in the Network Operations Model). RE Comment: New Generator Telemetry Data Frequency Mode Reference/Comments Real Time data accuracy Real Time data for reliability purposes must be accurate to within three percent (3%). This telemetry may be provided from relaying accuracy instrumentation transformers. QSE Comment: Generation Resource gross and net MW output 2 sec ICCP Protocol Section 6.5.5.2, Operational Data Requirements. Net Generation is preferred. Otherwise, aux load should also be provided. QSE Comment: Generation Resource gross and net MVar output 2 sec ICCP Protocol Section 6.5.5.2, Operational Data Requirements. Net Generation is preferred. Otherwise, aux load should also be provided. QSE Comment:
ERCOT_New_Generator_Commissioning_Checklist_05022018.docx