7 Heat recovery + Air/water heat pump The Unit can be specified without impact of Included water heat pump NRVU: The condenser/evaporator is considered as additional component and not included in SFP int. RVU: The condenser/evaporator is not included in SFI. 8 Heat recovery + add heating The additional heating does not affect the Included heat recovery NRVU: The heating coil is add. Component RES. The impact of the re heater on the electrical power input should be corrected 9 Run around coil Heat recovery only Included 10 Run around Coil + add heating The RAC can be measured without add. Included heating or cooling inside the water/brine circuit 11 Run around Coil + add heat pump in the The RAC can be measured without add. Included water/brine circuit heat pump inside the water/brine circuit. 12 Heat recovery plus frost protection Included 12 UVU plus Hot Water Heat Pump The evaporator/condenser in the air stream Included has no impact on ventilation function and shall be considered as an additional component. 13 Positive Input Ventilation with reheater Included 14 Secondary air fan-coil with outdoor air and Is predominantly a fan coil SEK 2 fans. Excluded Using some outdoor air ODA LOT 21 included
7 Heat recovery + Air/water heat pump The Unit can be specified without impact of water heat pump NRVU: The condenser/evaporator is considered as additional component and not included in SFP int. RVU: The condenser/evaporator is not included in SFI. Included 8 Heat recovery + add heating The additional heating does not affect the heat recovery NRVU: The heating coil is add. Component RES. The impact of the re heater on the electrical power input should be corrected Included 9 Run around coil Heat recovery only Included 10 Run around Coil + add heating The RAC can be measured without add. heating or cooling inside the water/brine circuit Included 11 Run around Coil + add heat pump in the water/brine circuit The RAC can be measured without add. heat pump inside the water/brine circuit. Included 12 Heat recovery plus frost protection Included 12 UVU plus Hot Water Heat Pump The evaporator/condenser in the air stream has no impact on ventilation function and shall be considered as an additional component. Included 13 Positive Input Ventilation with reheater Included 14 Secondary air fan-coil with outdoor air and 2 fans. Is predominantly a fan coil Using some outdoor air LOT 21 SEK Excluded ODA included
EVIA_FAQ_1253_V30_REL_2_160303.docx