Hydrostatic tests and water-flow tests Every 5 years NFPA 25 on standpipe systems Hydrostatic tests on standpipe 5 years after NFPA 1962 occupant hoses installation and 3 NFPA 25 years thereafter Dry Chemical Kitchen automatic fire extinguishing Semiannually NFPA 96 Suppression systems Systems Carbon dioxide and other gaseous Annually NFPA 13 automatic fire extinguishing systems NFPA 12A Portable Fire Portable fire extinguishers Inspected monthly NFPA 10 Extinguishers Maintained annually Smoke and Smoke and fire dampers Operated for full NFPA 90A Fire closure, 1 year after NFPA 80 Management installation and NFPA 105 Systems every 6 years thereafter Automatic smoke detection shutdown Annually NFPA 90A devices for air handling equipment Sliding and rolling fire doors. Smoke Annually NFPA 80 barrier sliding or rolling doors, and NFPA 105 corridor walls and partitions for proper operation and full closure Elevators Elevators with fire emergency Monthly NFPA 101 fighters’ operations
Hydrostatic tests and water-flow tests on standpipe systems Every 5 years NFPA 25 Hydrostatic tests on standpipe occupant hoses 5 years after installation and 3 years thereafter NFPA 1962 NFPA 25 Dry Chemical Suppression Systems Kitchen automatic fire extinguishing systems Semiannually NFPA 96 Carbon dioxide and other gaseous automatic fire extinguishing systems Annually NFPA 13 NFPA 12A Portable Fire Extinguishers Portable fire extinguishers Inspected monthly Maintained annually NFPA 10 Smoke and Fire Management Systems Smoke and fire dampers Operated for full closure, 1 year after installation and every 6 years thereafter NFPA 90A NFPA 80 NFPA 105 Automatic smoke detection shutdown devices for air handling equipment Annually NFPA 90A Sliding and rolling fire doors. Smoke barrier sliding or rolling doors, and corridor walls and partitions for proper operation and full closure Annually NFPA 80 NFPA 105 Elevators Elevators with fire fighters’ emergency operations Monthly NFPA 101
EnvironmentofCareManagementPlansforBusinessOccupancies.docx