GENERAL DESCRIPTION The unit shall be a highly visible, outdoor-rated LED Blue Light, model ETP-EL, no substitutions, with built-in flash activation relay. Unit shall operate from -40ºF to 150ºF. Unit shall be housed in a vandal resistant, blue polycarbonate refractor housing measuring approximately 6.9" H x 5" Diameter (6.6” diameter base) Gasket shall be made from UV-resistant EPDM foam rubber Unit shall weigh approximately 4 lbs. Refractor housing shall have a prismatic pattern to increase visibility at greater distances. Unit shall have ultra-bright LEDs that produce a peak of 209 lumens (exceeds 1,000,000 candle power). Unit shall flash approximately 78 times per minute. Unit shall continue to produce 70% of the iniital lumens after 50,000 hours of operation Unit shall operate on 96-132VAC. 12VDC and 24VAC/DC version is also available. Unit shall have two 18GA pairs, approximately 15 feet in length: one for power and one for activation of the built-in relay. Light shall consume 7.8 watts maximum, 35A peak inrush current Unit shall use Mounting Bracket, model ETP-MBKT, to mount to 4" square box. Low voltage version, model ETP-EL 12/24, shall accept 12VDC or 24VAC/DC. This version shall have a low-power mode. Unit shall be Certified to UL Standard 1598.
GENERAL DESCRIPTION The unit shall be a highly visible, outdoor-rated LED Blue Light, model ETP-EL, no substitutions, with built-in flash activation relay. Unit shall operate from -40ºF to 150ºF. Unit shall be housed in a vandal resistant, blue polycarbonate refractor housing measuring approximately 6.9" H x 5" Diameter (6.6” diameter base) Gasket shall be made from UV-resistant EPDM foam rubber Unit shall weigh approximately 4 lbs. Refractor housing shall have a prismatic pattern to increase visibility at greater distances. Unit shall have ultra-bright LEDs that produce a peak of 209 lumens (exceeds 1,000,000 candle power). Unit shall flash approximately 78 times per minute. Unit shall continue to produce 70% of the iniital lumens after 50,000 hours of operation Unit shall operate on 96-132VAC. 12VDC and 24VAC/DC version is also available. Unit shall have two 18GA pairs, approximately 15 feet in length: one for power and one for activation of the built-in relay. Light shall consume 7.8 watts maximum, 35A peak inrush current Unit shall use Mounting Bracket, model ETP-MBKT, to mount to 4" square box. Low voltage version, model ETP-EL 12/24, shall accept 12VDC or 24VAC/DC. This version shall have a low-power mode. Unit shall be Certified to UL Standard 1598.
ETP-EL_AE_REV_1_1_03252013.docx