Fire Protection Equipment Directory (Latest Addition). Factory Mutual Engineering Corporation (FM): Approval Guild (Latest Addition). American National Standards Institute (ANSI): Z 53 Safety Color Code for Marking Physical Hazards. A 14 Safety Requirements for Fixed Ladders. Welding: Qualify welding procedures, welders, and operators in accordance with ANSI B31.1, Paragraph 127.5, for shop and job site welding of piping work. Make welded joints on the piping system with continuous welds, without backing rings and with pipe ends beveled before welding. Gas cuts shall be true and free from burned metal. Before welding, surfaces shall be thoroughly cleaned. The piping shall be carefully aligned and no weld metal shall project inside the pipe. Comply with requirements of Fire Prevention Office of Texas State Board of Insurance and submit Drawings to that agency for approval. Materials shall be installed in accordance with NFPA 13 and NFPA 14. All valves, fittings, hose, and equipment shall be UL or FM-labeled. All necessary points of city connections shall be matched to city equipment. All hose threads and coupling types shall conform to local fire department requirements. Acceptable Manufacturers: The model numbers listed in the Specifications establish a level of quality and material. The following manufacturers are acceptable subject to compliance with the requirements of these Specifications. Fire Protection Valves: Crane Company. Jenkins Bros. Valves. Lunkenheimer. Nibco. Victaulic. Stockham Valves and Fittings. Walworth Company. SUBMITTALS: Shop drawing submittals shall include, but not be limited to, the following: Cut sheets marked to clearly indicate all fire protection system materials, accessories and manufacturers to be used, including, but not limited to control panels, pipe and fittings, pipe hangers and supports, valves, sprinkler heads, specialties, waterflow switches, valve supervisory switches, and other required materials. This shall include cut sheets on all grooved piping system components and all manufacturers which will be used on the project. Final fire protection system fabrication/shop drawings showing all piping sizes and elevations, sprinkler head types and hydraulic calculations. Piping shall be sized and elevation of mains shall be indicated. Drawings shall be approved by state and local authorities prior to being submitted. Other items as required by Section 23 01 00 and 21 13 13. Additional information as required in Section 23 00 01, Mechanical General Provisions”.
Fire Protection Equipment Directory (Latest Addition). Factory Mutual Engineering Corporation (FM): Approval Guild (Latest Addition). American National Standards Institute (ANSI): Z 53 Safety Color Code for Marking Physical Hazards. A 14 Safety Requirements for Fixed Ladders. Welding: Qualify welding procedures, welders, and operators in accordance with ANSI B31.1, Paragraph 127.5, for shop and job site welding of piping work. Make welded joints on the piping system with continuous welds, without backing rings and with pipe ends beveled before welding. Gas cuts shall be true and free from burned metal. Before welding, surfaces shall be thoroughly cleaned. The piping shall be carefully aligned and no weld metal shall project inside the pipe. Comply with requirements of Fire Prevention Office of Texas State Board of Insurance and submit Drawings to that agency for approval. Materials shall be installed in accordance with NFPA 13 and NFPA 14. All valves, fittings, hose, and equipment shall be UL or FM-labeled. All necessary points of city connections shall be matched to city equipment. All hose threads and coupling types shall conform to local fire department requirements. Acceptable Manufacturers: The model numbers listed in the Specifications establish a level of quality and material. The following manufacturers are acceptable subject to compliance with the requirements of these Specifications. Fire Protection Valves: Crane Company. Jenkins Bros. Valves. Lunkenheimer. Nibco. Victaulic. Stockham Valves and Fittings. Walworth Company. SUBMITTALS: Shop drawing submittals shall include, but not be limited to, the following: Cut sheets marked to clearly indicate all fire protection system materials, accessories and manufacturers to be used, including, but not limited to control panels, pipe and fittings, pipe hangers and supports, valves, sprinkler heads, specialties, waterflow switches, valve supervisory switches, and other required materials. This shall include cut sheets on all grooved piping system components and all manufacturers which will be used on the project. Final fire protection system fabrication/shop drawings showing all piping sizes and elevations, sprinkler head types and hydraulic calculations. Piping shall be sized and elevation of mains shall be indicated. Drawings shall be approved by state and local authorities prior to being submitted. Other items as required by Section 23 01 00 and 21 13 13. Additional information as required in Section 23 00 01, Mechanical General Provisions”.
Exhibit%20F%20-%20Specifications1_B1723.docx