Station Telemetry Data Frequency Mode Reference/Comments Protocol Section 6.5.5.2, Operational Data Requirements. (High side Typical TSP telemetry point; Station Switching 10 sec ICCP Low side typical QSE telemetry point) Device status RE Comment: Protocol Section 6.5.5.2, Operational Data Station Breaker Requirements. (Typical QSE telemetry point) 10 sec ICCP status RE Comment: Protocol Section 3.15, Voltage Support. May be supplied by the TDSP (Typical TDSP telemetry point) or Low Side Generation Resource voltage with appropriate transformer model may be 10 sec ICCP High Side bus voltage substituted (Typical QSE telemetry point). RE Comment: Station Static and/or Protocol Section 6.5.5.2, Operational Data Dynamic Reactive Requirements.(Typical QSE telemetry point) 10 sec ICCP Device(s) status for RE Comment: each device Station Static and/or Protocol Section 6.5.5.2, Operational Data Dynamic Reactive Requirements.(Typical QSE telemetry point) Device(s) MVAR 10 sec ICCP output for each RE Comment: device Generator Step-Up Protocol Section 6.5.5.2, Operational Data (GSU) Transformer Requirements.(Typical QSE telemetry point) High-Side MW and 10 sec ICCP MVAR for each RE Comment: modeled GSU Generation Resource Protocol Section 6.5.5.2, Operational Data auxiliary load and/or Requirements.(Typical QSE telemetry point) station service MW 10 sec ICCP and MVAR for each RE Comment: modeled load Protocol Section 6.5.5.2, Operational Data Requirements. (RE has confirmed that TSP is providing required points; Transmission Line Flow has telemetry for both the sending and receiving end of the Transmission Line 10 sec ICCP interconnecting line if the Generation Resource is Flow registered at a different station in the Network Operations Model). RE Comment: By signing below I attest that information provided on this form (PART 1) is true, correct and complete, and that any substantial changes in such information will promptly be provided to the Electric Reliability Council of Texas (ERCOT). Signature: (RE Authorized Representative)
Station Telemetry Data Frequency Mode Reference/Comments Station Switching Device status 10 sec ICCP Protocol Section 6.5.5.2, Operational Data Requirements. (High side Typical TSP telemetry point; Low side typical QSE telemetry point) RE Comment: Station Breaker status 10 sec ICCP Protocol Section 6.5.5.2, Operational Data Requirements. (Typical QSE telemetry point) RE Comment: Generation Resource High Side bus voltage 10 sec ICCP Protocol Section 3.15, Voltage Support. May be supplied by the TDSP (Typical TDSP telemetry point) or Low Side voltage with appropriate transformer model may be substituted (Typical QSE telemetry point). RE Comment: Station Static and/or Dynamic Reactive Device(s) status for each device 10 sec ICCP Protocol Section 6.5.5.2, Operational Data Requirements.(Typical QSE telemetry point) RE Comment: Station Static and/or Dynamic Reactive Device(s) MVAR output for each device 10 sec ICCP Protocol Section 6.5.5.2, Operational Data Requirements.(Typical QSE telemetry point) RE Comment: Generator Step-Up (GSU) Transformer High-Side MW and MVAR for each modeled GSU 10 sec ICCP Protocol Section 6.5.5.2, Operational Data Requirements.(Typical QSE telemetry point) RE Comment: Generation Resource auxiliary load and/or station service MW and MVAR for each modeled load 10 sec ICCP Protocol Section 6.5.5.2, Operational Data Requirements.(Typical QSE telemetry point) RE Comment: Transmission Line Flow 10 sec ICCP Protocol Section 6.5.5.2, Operational Data Requirements. (RE has confirmed that TSP is providing required points; Transmission Line Flow has telemetry for both the sending and receiving end of the interconnecting line if the Generation Resource is registered at a different station in the Network Operations Model). RE Comment: By signing below I attest that information provided on this form (PART 1) is true, correct and complete, and that any substantial changes in such information will promptly be provided to the Electric Reliability Council of Texas (ERCOT). Signature: (RE Authorized Representative)
ERCOT_New_Generator_Commissioning_Checklist_05022018.docx