Protocol Section 6.5.5.2, Operational Data Requirements. (RE has confirmed that TSP is providing required points; Transmission Line Flow has telemetry for both the sending and receiving end of the Transmission Line 10 sec ICCP interconnecting line if the Generation Resource is Flow registered at a different station in the Network Operations Model). RE Comment: New Generator Telemetry Data Frequency Mode Reference/Comments Real Time data for reliability purposes must be accurate to within three percent (3%). This telemetry may be provided Real Time data from relaying accuracy instrumentation transformers. accuracy QSE Comment: Protocol Section 6.5.5.2, Operational Data Requirements. Net Generation Generation is preferred. Otherwise, aux load should also be Resource gross 2 sec ICCP provided. and net MW output QSE Comment: Protocol Section 6.5.5.2, Operational Data Requirements. Net Generation Generation is preferred. Otherwise, aux load should also be Resource gross 2 sec ICCP provided. and net MVar output QSE Comment: Switching Device Protocol Section 6.5.5.2, Operational Data Requirements. status other than 2 sec ICCP QSE Comment: reported in PART 1 Breaker status Protocol Section 6.5.5.2, Operational Data Requirements other than reported 2 sec ICCP QSE Comment: in PART 1 Generation Protocol Section 6.5.5.2, Operational Data Requirements. Resource High 2 sec ICCP QSE Comment: Sustainable Limit Generation Protocol Section 6.5.5.2, Operational Data Requirements. Resource Low 2 sec ICCP QSE Comment: Sustainable Limit Protocol Section 3.15.3, QSE Responsibilities Related to Generation Voltage Support. Applies to Generation Resources required to Resource 2 sec ICCP provide VSS. Automatic Voltage Regulator status QSE Comment:
Transmission Line Flow 10 sec ICCP Protocol Section 6.5.5.2, Operational Data Requirements. (RE has confirmed that TSP is providing required points; Transmission Line Flow has telemetry for both the sending and receiving end of the interconnecting line if the Generation Resource is registered at a different station in the Network Operations Model). RE Comment: New Generator Telemetry Data Frequency Mode Reference/Comments Real Time data accuracy Real Time data for reliability purposes must be accurate to within three percent (3%). This telemetry may be provided from relaying accuracy instrumentation transformers. QSE Comment: Generation Resource gross and net MW output 2 sec ICCP Protocol Section 6.5.5.2, Operational Data Requirements. Net Generation is preferred. Otherwise, aux load should also be provided. QSE Comment: Generation Resource gross and net MVar output 2 sec ICCP Protocol Section 6.5.5.2, Operational Data Requirements. Net Generation is preferred. Otherwise, aux load should also be provided. QSE Comment: Switching Device status other than reported in PART 1 2 sec ICCP Protocol Section 6.5.5.2, Operational Data Requirements. QSE Comment: Breaker status other than reported in PART 1 2 sec ICCP Protocol Section 6.5.5.2, Operational Data Requirements QSE Comment: Generation Resource High Sustainable Limit 2 sec ICCP Protocol Section 6.5.5.2, Operational Data Requirements. QSE Comment: Generation Resource Low Sustainable Limit 2 sec ICCP Protocol Section 6.5.5.2, Operational Data Requirements. QSE Comment: Generation Resource Automatic Voltage Regulator status 2 sec ICCP Protocol Section 3.15.3, QSE Responsibilities Related to Voltage Support. Applies to Generation Resources required to provide VSS. QSE Comment:
ERCOT_New_Generator_Commissioning_Checklist_05022018.docx