The PLC shall have user selectable remote communications capabilities. The PLC memory maintain an event log with error review and tracking for 500 events. The PLC shall have a save” mode to conserve power and “power extend unit life. The controls shall be designed to run on 24/120 volts. Monitoring shall consist of the following functions: Utility power available Door open/close Cycle table High Pressure Low Pressure Pump status Generator interlock Filter Status with automatic notification feature level Filter leak Pump leak Sump basin full Motor overload Exterior lights to include: White lamp –“ready” Blue lamp – “running” Amber warning” lamp – “ Red lamp – “error” Two dry contacts for facility interface for the following: Tank over-flow Tank leak detector Spare filters shall be supplied to include the following: Six 10 micron filter replacement cartridges
The PLC shall have user selectable remote communications capabilities. The PLC memory maintain an event log with error review and tracking for 500 events. The PLC shall have a “power save” mode to conserve power and extend unit life. The controls shall be designed to run on 24/120 volts. Monitoring shall consist of the following functions: Utility power available Door open/close Cycle table High Pressure Low Pressure Pump status Generator interlock Filter Status with automatic notification feature level Filter leak Pump leak Sump basin full Motor overload Exterior lights to include: White –“ready” lamp Blue – “running” lamp Amber – “ warning” lamp Red – “error” lamp Two dry contacts for facility interface for the following: Tank over-flow Tank leak detector Spare filters shall be supplied to include the following: Six 10 micron filter replacement cartridges
15a_spec.docx