SECTION 019100 PROJECT COMMISSIONING – GENERAL RELATED DOCUMENTS The Drawings and the general provisions of the Contract, including the Standard General Conditions and the Supplemental General Conditions, apply to this Section. Refer to other Division 01 Specification Sections, including the following, for related requirements which apply to this Section. Division 01 Section Project Management and Coordination. – Division 01 Section Submittal Procedures. – Division 01 Section Operation and Maintenance Manuals. – Testing, balancing, commissioning, operation and maintenance manual, and Owner training requirements referenced in the other Technical Specification Sections apply to this Section. SUMMARY Each Contractor perform the commissioning activities for the systems, equipment and materials they install. When the equipment and materials are part of a larger system, each Contractor shall commission their portion of the work as part of the overall system commissioning. The commissioning activities will be coordinated by the University’s Commissioning Authority (CxA). Perform the commissioning activities as outlined in Part 3, and as “Execution” described in the U-M Sample Commissioning Plan” available “Generic for review at . Where terms, procedures, forms, etc. are indicated in this specification, the requirements for such items shall be as described in the U-M Sample Commissioning “Generic Plan”. Perform commissioning activities on the following: Divisions 02 through 14: Systems and equipment include but are not limited to: Power operated doors, windows, fire shutters, roof hatches, and related items. Operable partitions. Electric signs and graphics systems. Motorized projection screens and projector lifts. Fume hoods, bio-safety cabinets and snorkels. Laboratory plumbing and electrical fixtures specified as part of laboratory casework.
SECTION 019100 – PROJECT COMMISSIONING GENERAL RELATED DOCUMENTS The Drawings and the general provisions of the Contract, including the Standard General Conditions and the Supplemental General Conditions, apply to this Section. Refer to other Division 01 Specification Sections, including the following, for related requirements which apply to this Section. Division 01 Section – Project Management and Coordination. Division 01 Section – Submittal Procedures. Division 01 Section – Operation and Maintenance Manuals. Testing, balancing, commissioning, operation and maintenance manual, and Owner training requirements referenced in the other Technical Specification Sections apply to this Section. SUMMARY Each Contractor perform the commissioning activities for the systems, equipment and materials they install. When the equipment and materials are part of a larger system, each Contractor shall commission their portion of the work as part of the overall system commissioning. The commissioning activities will be coordinated by the University’s Commissioning Authority (CxA). Perform the commissioning activities as outlined in Part 3, “Execution” and as described in the U-M “Generic Sample Commissioning Plan” available for review at . Where terms, procedures, forms, etc. are indicated in this specification, the requirements for such items shall be as described in the U-M “Generic Sample Commissioning Plan”. Perform commissioning activities on the following: Divisions 02 through 14: Systems and equipment include but are not limited to: Power operated doors, windows, fire shutters, roof hatches, and related items. Operable partitions. Electric signs and graphics systems. Motorized projection screens and projector lifts. Fume hoods, bio-safety cabinets and snorkels. Laboratory plumbing and electrical fixtures specified as part of laboratory casework.
MS010000.docx