(2) A residential type fire sprinkler system complying with AS 2118.4—1995 must be installed in each building to this regulation applies. (3) If the sprinkler system referred to in subregulation (2) has more than 100 heads or the building to which this regulation applies accommodates more than 32 residents, the sprinkler system must be connected to a fire station or other approved monitoring service in accordance with Practice Note 2008-07 issued by the Building Commission in May 2008. Note The Victorian Building Authority became the successor in law to the Building Commission on 1 July 2013. (4) This regulation must be complied with by the owner of the building. (5) A person who to comply with this regulation is guilty of an offence and liable to a penalty not exceeding 10 penalty units. 709 smoke alarms or detection system (1) This regulation applies to— Class 9a building that is a residential care building; and Class 1b or 3 building—
(2) A residential type fire sprinkler system complying with AS 2118.4—1995 must be installed in each building to this regulation applies. (3) If the sprinkler system referred to in subregulation (2) has more than 100 heads or the building to which this regulation applies accommodates more than 32 residents, the sprinkler system must be connected to a fire station or other approved monitoring service in accordance with Practice Note 2008-07 issued by the Building Commission in May 2008. Note The Victorian Building Authority became the successor in law to the Building Commission on 1 July 2013. (4) This regulation must be complied with by the owner of the building. (5) A person who to comply with this regulation is guilty of an offence and liable to a penalty not exceeding 10 penalty units. 709 smoke alarms or detection system (1) This regulation applies to— Class 9a building that is a residential care building; and Class 1b or 3 building—
17-031sr.DOCX