Description Code Section A-3 The required capacity of means of egress is free of F1031 obstructions. B-2 Exterior exits are free from obstruction, including ice F1031 and snow. C-2 Curtains, drapes, and decorations shall not be placed F1031 to obstruct exits or visibility thereof. D-2 Exit signs are provided in rooms or areas which F1013 require two or more exits. E-1 Exit sign placement shall be such that no point in an F1013 exit access corridor is more than 100 feet from the nearest visible exit sign. F-3 shall be readily operable from the egress side without use of a key or special knowledge or effort. Electromagnetic locking devices are not allowed. G-1 Occupant load is conspicuously posted in all assembly F1004 spaces occupant load exceeds 49 persons. H-2 Means of egress are provided with emergency lighting. F1008 I-2 Tactile signs stating and complying with F1013 “EXIT” ICC/ANSI, A117.1 are provided adjacent to each door to an egress stairway. J-1 Aisles are provided in all occupied spaces containing F1018 seats, tables, furnishings, displays, and similar fixtures of equipment and are unobstructed at all times. K-1 Stairways that travel below the level of exit discharge are clearly defined. Required exit signs are provided with emergency L-1 F1013 illumination. Flammable Finishes Description Code Section A-2 Electrical wiring and equipment in spray areas shall be explosion proof. B-2 Welding” shall be posted in the vicinity of the “No paint spraying areas and paint storage areas. C-2 Portable fire extinguishers for high hazard shall be F2404 provided in paint spraying areas. D-2 Spraying areas, exhaust fan blades, and exhaust F2403 ducts shall be kept free from the accumulation of deposits of combustible residues. Fuel-Dispensing Facilities & Repair Garages Description Code Section A-3 An approved, clearly identified and readily accessible emergency disconnect switch shall be provided for fuel dispensers and distinctly labeled Fuel “Emergency Shutoff.” B-2 Approved fire extinguishers, with a minimum rating of F2305 2-A: 20-B:C, shall be located within 75 feet of pumps, dispensers, and storage tanks.
Description Code Section A-3 The required capacity of means of egress is free of obstructions. F1031 B-2 Exterior exits are free from obstruction, including ice and snow. F1031 C-2 Curtains, drapes, and decorations shall not be placed to obstruct exits or visibility thereof. F1031 D-2 Exit signs are provided in rooms or areas which require two or more exits. F1013 E-1 Exit sign placement shall be such that no point in an exit access corridor is more than 100 feet from the nearest visible exit sign. F1013 F-3 shall be readily operable from the egress side without use of a key or special knowledge or effort. Electromagnetic locking devices are not allowed. G-1 Occupant load is conspicuously posted in all assembly spaces occupant load exceeds 49 persons. F1004 H-2 Means of egress are provided with emergency lighting. F1008 I-2 Tactile signs stating “EXIT” and complying with ICC/ANSI, A117.1 are provided adjacent to each door to an egress stairway. F1013 J-1 Aisles are provided in all occupied spaces containing seats, tables, furnishings, displays, and similar fixtures of equipment and are unobstructed at all times. F1018 K-1 Stairways that travel below the level of exit discharge are clearly defined. L-1 Required exit signs are provided with emergency illumination. F1013 Flammable Finishes Description Code Section A-2 Electrical wiring and equipment in spray areas shall be explosion proof. B-2 “No Welding” shall be posted in the vicinity of the paint spraying areas and paint storage areas. C-2 Portable fire extinguishers for high hazard shall be provided in paint spraying areas. F2404 D-2 Spraying areas, exhaust fan blades, and exhaust ducts shall be kept free from the accumulation of deposits of combustible residues. F2403 Fuel-Dispensing Facilities & Repair Garages Description Code Section A-3 An approved, clearly identified and readily accessible emergency disconnect switch shall be provided for fuel dispensers and distinctly labeled “Emergency Fuel Shutoff.” B-2 Approved fire extinguishers, with a minimum rating of 2-A: 20-B:C, shall be located within 75 feet of pumps, dispensers, and storage tanks. F2305
Nonpublic_School_BEDS_Initial_Application_2018.docx