FOR BANK OWN BUILDING Floor wise assessment of luminaries/light fittings Type of No of Lux level of Total electrical load Remarks Suggestions on improvement, if any luminaries/ consumption (Condition of light light fittings light fixtures fittings fittings acceptable or Watt Amp Not 2. Floor wise assessment of Air conditioning system Type of No of Air Capacity Total electrical load Condition of Remarks Suggestions on Air of Air consumption air (Condition of improvement, if any conditioning machine Watt Amp units (TR) system acceptable or Not 3.Floor wise assessment of UPS No P-P Voltage P-N Voltage Phase Total Neutral Remarks Suggestions on of of of each each UPS Currents electrical Earthing (Condition improvement, (KVA) UPS load & its of machine if any & acceptable its or Not R Y B R Y B R Y B KW A
FOR BANK OWN BUILDING Floor wise assessment of luminaries/light fittings Type of light fittings No of fittings Lux level of luminaries/ light fittings Total electrical load consumption Remarks (Condition of light fixtures acceptable or Not Suggestions on improvement, if any Watt Amp 2. Floor wise assessment of Air conditioning system Type of Air units No of Air Capacity of Air (TR) Total electrical load consumption Condition of air conditioning system Remarks (Condition of machine acceptable or Not Suggestions on improvement, if any Watt Amp 3.Floor wise assessment of UPS No of of (KVA) P-P Voltage of each UPS P-N Voltage each UPS Phase Currents Total electrical load Neutral Earthing & its & its Remarks (Condition of machine acceptable or Not Suggestions on improvement, if any R Y B R Y B R Y B KW A
NIT%20ELECT%20OWN%20BULD.DOCX