Drain the flow meters. the system to drain for a minimum of eight hours or until the opened ports quit dripping. draining is complete, reconnect all of the plumbing. REVERSE OSMOSIS TROUBLESHOOTING SYMPTOMS POSSIBLE CAUSES CORRECTIVE ACTION Low supply pressure Increase pressure Cartridge filters plugged Change filters Solenoid valve malfunction Replace sol. valve and/or coil Low Inlet Pressure Motor may not be drawing correct Use amp meter to check the current motor amp draw. Concentrate valve might be Replace needle damaged Leaks Fix any visible Low Permeate Flow Low inlet flow Adjust concentrate valve
Drain the flow meters. the system to drain for a minimum of eight hours or until the opened ports quit dripping. draining is complete, reconnect all of the plumbing. REVERSE OSMOSIS TROUBLESHOOTING SYMPTOMS POSSIBLE CAUSES CORRECTIVE ACTION Low Inlet Pressure Low supply pressure Increase pressure Cartridge filters plugged Change filters Solenoid valve malfunction Replace sol. valve and/or coil Motor may not be drawing correct current Use amp meter to check the motor amp draw. Concentrate valve might be damaged Replace needle Leaks Fix any visible Low Permeate Flow Low inlet flow Adjust concentrate valve
MKTF%20-%20207%20CT-SERIES%20USERS%20MANUAL.docx