UNIVERSITY OF WISCONSIN-MADISON SPECIFICATION UW-MDN-11-LATS-2015 SINGLE SIDE ACCESSIBLE CLEAN ANIMALTRANSFER STATION A ALONE WORK ENCLOSURE DESIGNED FOR ISO CLASS 5 PRODUCT PROTECTION WORKZONE AIRFLOW IS PARTIALLY RECIRCULATED AND THE REMAINING PORTION SIMULTANEOUSLY DISCHARGED INTO THE ROOM ATMOSPHERE AIR RECIRCULATED SPECIFICATION OUTLINE 1.0 SCOPE, OBJECTIVE, CLASSIFICATION, INNOVATIVE DESIGN, DEFINITIONS 1.1 Scope 1.2 Objective 1.2.1 Noncompliance 1.3 Classification 1.3.1 Sizes 1.3.2 1.4 Innovative Design 1.5 Definitions 2.0 APPLICABLE DOCUMENTS 2.1 Specifications and Standards International Standards National Standards Federal Specifications Federal Standards Military Specifications Military Standards 2.2 Other Publications Air Moving and Conditioning Association (AMCA) American National Standards Institute, Inc. (ANSI) Illuminating Engineering Society (IES) National Electrical Code (NEC) Underwriters Laboratories (UL) United States Atomic Energy Commission (AEC) Canadian Standards Association (CSA) Institute of Environmental Sciences and Technology (IEST) 3.0 REQUIREMENTS 3.1 Bid Submittal Requirements 3.1.1 Motor and Fan Graphs 3.1.1.1 Motor Performance Graph 3.1.1.2 Fan/Motor Performance Graph 3.1.2 Fabrication Drawings and Performance Data 3.1.3 Submitted Bids 3.1.4 Selected Vendor 3.1.5 Field Fan/Motor Performance Test 3.1.6 Field Specification Compliance Inspection 3.2 General Description 3.2.11 Construction and Fabrication Requirements 3.2.12 Fabrication Welding Requirements 3.2.13 Services in Air Passages 3.2.14 Service Control Center 3.3 Dimensions 3.3.1 Overall Dimensions 3.3.2 Dimensions of Work Area 3.4 Assembly 3.5 Materials and Components 3.5.5 Metal and Finishes 3.5.5.4 Carbon Finish 3.5.5.4.5 Finish Color: White 3.5.5.7 Supply Air 3.6 View Screen 3.7 Filters and Clamps 3.8 Gaskets and Seals
UNIVERSITY OF WISCONSIN-MADISON SPECIFICATION UW-MDN-11-LATS-2015 SINGLE SIDE ACCESSIBLE CLEAN ANIMALTRANSFER STATION A ALONE WORK ENCLOSURE DESIGNED FOR ISO CLASS 5 PRODUCT PROTECTION WORKZONE AIRFLOW IS PARTIALLY RECIRCULATED AND THE REMAINING PORTION SIMULTANEOUSLY DISCHARGED INTO THE ROOM ATMOSPHERE AIR RECIRCULATED SPECIFICATION OUTLINE 1.0 SCOPE, OBJECTIVE, CLASSIFICATION, INNOVATIVE DESIGN, DEFINITIONS 1.1 Scope 1.2 Objective 1.2.1 Noncompliance 1.3 Classification 1.3.1 Sizes 1.3.2 1.4 Innovative Design 1.5 Definitions 2.0 APPLICABLE DOCUMENTS 2.1 Specifications and Standards International Standards National Standards Federal Specifications Federal Standards Military Specifications Military Standards 2.2 Other Publications Air Moving and Conditioning Association (AMCA) American National Standards Institute, Inc. (ANSI) Illuminating Engineering Society (IES) National Electrical Code (NEC) Underwriters Laboratories (UL) United States Atomic Energy Commission (AEC) Canadian Standards Association (CSA) Institute of Environmental Sciences and Technology (IEST) 3.0 REQUIREMENTS 3.1 Bid Submittal Requirements 3.1.1 Motor and Fan Graphs 3.1.1.1 Motor Performance Graph 3.1.1.2 Fan/Motor Performance Graph 3.1.2 Fabrication Drawings and Performance Data 3.1.3 Submitted Bids 3.1.4 Selected Vendor 3.1.5 Field Fan/Motor Performance Test 3.1.6 Field Specification Compliance Inspection 3.2 General Description 3.2.11 Construction and Fabrication Requirements 3.2.12 Fabrication Welding Requirements 3.2.13 Services in Air Passages 3.2.14 Service Control Center 3.3 Dimensions 3.3.1 Overall Dimensions 3.3.2 Dimensions of Work Area 3.4 Assembly 3.5 Materials and Components 3.5.5 Metal and Finishes 3.5.5.4 Carbon Finish 3.5.5.4.5 Finish Color: White 3.5.5.7 Supply Air 3.6 View Screen 3.7 Filters and Clamps 3.8 Gaskets and Seals
165770SPECIFICATIONUW-MDN-11-LATS-2015.docx