70°c / 24 H Dry Heat Test Storage IEC Test Bd : – +70°C / 96h Powered On at +70°C Enclosure Protection IEC 60529 Front : IP=52 Rear : IP=30 Inrush current (start-up) T < 1,5 ms / I < 20 A T < 150 ms / I < 10 A T > 500 ms / I < 1,2 In Supply variation IEC 60255-6 Vn 20% Vn+30% and Vn-25% for information Overvoltage (peak withstand) IEC 60255-6 1,32 Vn max 2 Vn during 10 ms (for information) Supply interruption IEC 60255-11 From 2,5 ms to 1 s at 0,8 Vn 50 ms at Vn, no malfunction (for information) 40 s interruption IEC 60255-11 Ripple (frequency fluctuations) IEC 60255-11 12% Vn at f=100Hz or 120Hz 12% Vn at f=200Hz for information Supply variations IEC 60255-6 Vn 20% AC Voltage dips and short EN 61000-4-11 2ms to 20ms and 50ms to 1s interruptions 50 ms at Vn, no malfunction (for information Frequency fluctuations IEC 60255-6 50 Hz : from 47 to 54 Hz 60 Hz : from 57 to 63 Hz Voltage withstand 2 Vn during 10 ms (for information) High Frequency Disturbance IEC 60255-22-1 Class 3 : 2.5kV (CM) / 1kV (DM) IEC 61000-4-12 Class 2 : 1kV (CM) IEEE C37.90.1 Electrostatic discharge IEC 60255-22-2 Class 4 : IEC 61000-4-2 8kV contact / 15 kV air Radiated Immunity IEC 60255-22-3 Class 3 : IEC 61000-4-3 10 V/m 80 to 1000 MHz – and spot tests IEEE C37.90.2 35 V/m 25 to 1000 MHz – Fast Transient Burst IEC 60255-22-4 Class 4 : IEC 61000-4-4 4kV 2.5kHz (CM and DM) – IEEE C37.90.1 Class 3 2 kV - 2,5 kHz MC Class 3 : 2kV 5kHz (CM) –
70°c / 24 H Dry Heat Test – Storage IEC Test Bd : +70°C / 96h Powered On at +70°C Enclosure Protection IEC 60529 Front : IP=52 Rear : IP=30 Inrush current (start-up) T < 1,5 ms / I < 20 A T < 150 ms / I < 10 A T > 500 ms / I < 1,2 In Supply variation IEC 60255-6 Vn 20% Vn+30% and Vn-25% for information Overvoltage (peak withstand) IEC 60255-6 1,32 Vn max 2 Vn during 10 ms (for information) Supply interruption IEC 60255-11 From 2,5 ms to 1 s at 0,8 Vn 50 ms at Vn, no malfunction (for information) 40 s interruption IEC 60255-11 Ripple (frequency fluctuations) IEC 60255-11 12% Vn at f=100Hz or 120Hz 12% Vn at f=200Hz for information Supply variations IEC 60255-6 Vn 20% AC Voltage dips and short interruptions EN 61000-4-11 2ms to 20ms and 50ms to 1s 50 ms at Vn, no malfunction (for information Frequency fluctuations IEC 60255-6 50 Hz : from 47 to 54 Hz 60 Hz : from 57 to 63 Hz Voltage withstand 2 Vn during 10 ms (for information) High Frequency Disturbance IEC 60255-22-1 IEC 61000-4-12 IEEE C37.90.1 Class 3 : 2.5kV (CM) / 1kV (DM) Class 2 : 1kV (CM) Electrostatic discharge IEC 60255-22-2 IEC 61000-4-2 Class 4 : 8kV contact / 15 kV air Radiated Immunity IEC 60255-22-3 IEC 61000-4-3 Class 3 : 10 V/m – 80 to 1000 MHz and spot tests IEEE C37.90.2 35 V/m – 25 to 1000 MHz Fast Transient Burst IEC 60255-22-4 IEC 61000-4-4 IEEE C37.90.1 Class 4 : 4kV – 2.5kHz (CM and DM) Class 3 2 kV - 2,5 kHz MC Class 3 : 2kV – 5kHz (CM)
16%20Protection%20Relays.docx