by this section. REFERENCES ASHRAEStandard 62 - Ventilation for Acceptable Indoor Air Quality. ASHRAE SSPC 135 - ASHRAE Standing Standard Project Committee 135: BACnet - A Data Communication Protocol for Building Automation and Control Networks. DESIGN / PERFORMANCE REQUIREMENTS Automatic temperature controls field monitoring and control system using field programmable microprocessor based units. Base system on distributed system of intelligent, stand-alone controllers, operating in a multi-tasking, multi-user environment on token passing network, with central and remote hardware, software, and interconnecting wire and conduit. Provide computer software and hardware, operator input/output devices, control units, local area networks (LAN), sensors, control devices, actuators. Provide controls for variable air volume terminals, radiation, reheat coils, unit heaters, fan coils, and other equipment when directly connected to control units. Individual terminal unit control is specified in Section 15905. Provide control systems consisting of thermostats, control valves, dampers and operators, indicating devices, interface equipment and other apparatus and accessories to operate mechanical systems, and to perform functions specified. Provide installation and calibration, supervision, adjustments, and fine tuning necessary for complete and fully operational system. SUBMITTALS Submit under provisions of Section 01300. Product Data: Manufacturer's data sheets on each product to be used, including: Dimensions, capacities, performance characteristics, electrical requirements, and material finishes. Storage and handling requirements and recommendations. Preparation instructions and recommendations. Installation and start-up methods. Shop Drawings: Network Block Diagrams or System Riser Diagrams depicting all DDC components that make up the network. Include specific detail on network terminations, and panel power requirements, stating where the DDC panels are to be powered from and the equipment that it is controlling for each DDC panel within the diagram. Point-to-point Termination Detail drawings for each unique control application type. Drawings that are typical of one another shall state the quantity that they represent, and the specifics for each including all wiring and piping required to install and operate the system. For terminations that are unknown at the time of submittal, properly designate these as "Field determined terminations," and include in the As-built Drawings after completion. All wiring and piping shall be either number or color-coded on the drawings. Provide individual details for each control type, as described in the Sequence of
by this section. REFERENCES ASHRAEStandard 62 - Ventilation for Acceptable Indoor Air Quality. ASHRAE SSPC 135 - ASHRAE Standing Standard Project Committee 135: BACnet - A Data Communication Protocol for Building Automation and Control Networks. DESIGN / PERFORMANCE REQUIREMENTS Automatic temperature controls field monitoring and control system using field programmable microprocessor based units. Base system on distributed system of intelligent, stand-alone controllers, operating in a multi-tasking, multi-user environment on token passing network, with central and remote hardware, software, and interconnecting wire and conduit. Provide computer software and hardware, operator input/output devices, control units, local area networks (LAN), sensors, control devices, actuators. Provide controls for variable air volume terminals, radiation, reheat coils, unit heaters, fan coils, and other equipment when directly connected to control units. Individual terminal unit control is specified in Section 15905. Provide control systems consisting of thermostats, control valves, dampers and operators, indicating devices, interface equipment and other apparatus and accessories to operate mechanical systems, and to perform functions specified. Provide installation and calibration, supervision, adjustments, and fine tuning necessary for complete and fully operational system. SUBMITTALS Submit under provisions of Section 01300. Product Data: Manufacturer's data sheets on each product to be used, including: Dimensions, capacities, performance characteristics, electrical requirements, and material finishes. Storage and handling requirements and recommendations. Preparation instructions and recommendations. Installation and start-up methods. Shop Drawings: Network Block Diagrams or System Riser Diagrams depicting all DDC components that make up the network. Include specific detail on network terminations, and panel power requirements, stating where the DDC panels are to be powered from and the equipment that it is controlling for each DDC panel within the diagram. Point-to-point Termination Detail drawings for each unique control application type. Drawings that are typical of one another shall state the quantity that they represent, and the specifics for each including all wiring and piping required to install and operate the system. For terminations that are unknown at the time of submittal, properly designate these as "Field determined terminations," and include in the As-built Drawings after completion. All wiring and piping shall be either number or color-coded on the drawings. Provide individual details for each control type, as described in the Sequence of
15915aam.docx