wash basins maintenance and dose), maintenance schedules (including in rooms xxx services (BEMS) flushing regimes) and structural integrity supervisor 2. Flush water through until sufficient disinfectant residual is achieved at sampling point 3. Resample after responses are completed Legionella spp. Quarterly Distal warm Greater than BEMS manager 1. Check operational measurements, Remove patient/s from water taps 10 CFU/100 mL and CEO maintenance schedules and structural integrity of affected room – wash basins system in room with 2. and sanitise TMV and outlet fitting low risk 3. If resample positive, move to next row patients Legionella spp. Quarterly Distal warm Greater than BEMS manager 1. Check operational measurements, Remove patient/s from water taps 10 CFU/mL and CEO maintenance schedules and structural integrity affected room — wash basins of system in room with 2. and sanitise TMV and outlet fitting high risk 3. Clean pipework patients 4. Superchlorinate system
wash basins in rooms xxx maintenance services (BEMS) supervisor and dose), maintenance schedules (including flushing regimes) and structural integrity 2. Flush water through until sufficient disinfectant residual is achieved at sampling point 3. Resample after responses are completed Legionella spp. Quarterly Distal warm water taps – wash basins in room with low risk patients Greater than 10 CFU/100 mL BEMS manager and CEO 1. Check operational measurements, maintenance schedules and structural integrity of system 2. and sanitise TMV and outlet fitting 3. If resample positive, move to next row Remove patient/s from affected room Legionella spp. Quarterly Distal warm water taps — wash basins in room with high risk patients Greater than 10 CFU/mL BEMS manager and CEO 1. Check operational measurements, maintenance schedules and structural integrity of system 2. and sanitise TMV and outlet fitting 3. Clean pipework 4. Superchlorinate system Remove patient/s from affected room
national-risk-manag-plan-template.docx