Special Modules 1606-XL Special Modules Buffer Module UPS DC/DC N+1 Redundancy N+1 Redundancy Converter 1606-XL60DR 1606-XL120DR Output Volts/Watts 22.5V...27.8V/480 22.5V...30V/240 DC 5.1V ±1% 24V/60 W 24V/120 W W W Input Voltage 24V DC 24V DC 18...36V DC 100...120V/200...240V AC 100...120/200...240V AC (47...63 Hz) (24...28.8V DC) (22.5...30V DC) manual select; manual select; 160...375V DC 210...375V DC Operational Range 23...35V DC 22.5...30V DC 18...36V DC 85...132/176...264V AC — Hold-up Time >0.2 s (20 A) battery >10 ms (DC >20 ms (AC 196V) >37 ms (AC 196V) dependent 24 Vin) Input Current charging current <0.12 A <2.9 A/<1.5 <1.3 A (115V)/<0.7 A <2.6 A (115V)/<1.4 A <600 mA (standby) A (230V) (230V) <1.3 A (charging) Efficiency N/A N/A typ. 82% typ. 86.5% typ. 89% Output Voltage Vin -1V: 22.4V 5.1V DC ±1% 24V 24V 23...27.8V selectable 22.5V fixed 4.5...5.5V 0...20 A 10 A 8 A 2.5 A 5 A Output Current Power Boost 15 A 6 A — — — Ripple/Noise <200 mVPP <50 mVPP <30 mVPP <30 mVPP —
Special Modules 1606-XL Special Modules Buffer Module UPS DC/DC Converter N+1 Redundancy N+1 Redundancy 1606-XL60DR 1606-XL120DR Output Volts/Watts 22.5V...27.8V/480 W 22.5V...30V/240 W DC 5.1V ±1% 24V/60 W 24V/120 W Input Voltage (47...63 Hz) 24V DC (24...28.8V DC) 24V DC (22.5...30V DC) 18...36V DC 100...120V/200...240V AC manual select; 160...375V DC 100...120/200...240V AC manual select; 210...375V DC Operational Range 23...35V DC 22.5...30V DC 18...36V DC — 85...132/176...264V AC Hold-up Time >0.2 s (20 A) battery dependent >10 ms (DC 24 Vin) >20 ms (AC 196V) >37 ms (AC 196V) Input Current charging current <600 mA <0.12 A (standby) <1.3 A (charging) <2.9 A/<1.5 A <1.3 A (115V)/<0.7 A (230V) <2.6 A (115V)/<1.4 A (230V) Efficiency N/A N/A typ. 82% typ. 86.5% typ. 89% Output Voltage Vin -1V: 23...27.8V 22.5V fixed 22.4V 5.1V DC ±1% selectable 4.5...5.5V 24V 24V Output Current 0...20 A 10 A 8 A 2.5 A 5 A Power Boost — 15 A — — 6 A Ripple/Noise <200 mVPP — <50 mVPP <30 mVPP <30 mVPP
1606%20power%20supply.docx