Visual indication The Detectors shall provide dual bi-colour LED’s. Both LED’s enable red, amber and green local status indication also indicating that the Detector is operational and in regular communication with the C.I.E. The LED’s shall be configurable from the C.I.E to give visual indication of: Device Healthy Fire Fault Isolation in use – Detector Dirty Test Mode Chamber Fault If required, the flashing mode operation of the Detector LED’s shall be controlled through the system field program. An output connection shall also be provided in the base to connect an external remote alarm LED. Sensitivity settings The Detector sensitivity be set through the C.I.E, and shall be adjustable in the field through the field programming of the system. Sensitivity may be automatically adjusted by the panel on a time-of-day basis. Theses sensitivity levels not contravene EN54 part 7 unless placed in to thermal (heat) only mode in which case the unit shall comply with EN54 part 5. Drift compensation The Detector automatically compensate for dust accumulation and other slow environmental changes that may affect their performance. The use of this function not contravene EN54 part 7. Additional requirements Optional relay base and isolator base variants shall be available. Up to 99, intelligent Detectors may connect to one SLC loop. The C.I.E software, not the detector, shall make the alarm decision. The sensitivity of each detector shall be set in the C.I.E. The system operator shall be able to view the current analogue or digital value of each detector at the C.I.E. Addressable Thermal Heat Detector Specification Compliance with standards The Heat Detector shall be third party approved to EN54 part 5. Types A1R, A1, and BS shall be available. Functionality The Detectors shall use an electronic detector to measure thermal conditions caused by a fire and shall, on command from the C.I.E, send data to the panel representing the analogue or digital level (the temperature) at the detector. Heat Detectors be intelligent and addressable devices, and shall connect with two wires to one of the C.I.E. Signalling Line Circuits. The detector shall operate on a digital protocol loop to give reduced power consumption, upto 99 detectors and 99 modules may be connected to a single loop. The detectors shall be fitted with a loop isolation device in-built into the device.
Visual indication The Detectors shall provide dual bi-colour LED’s. Both LED’s enable red, amber and green local status indication also indicating that the Detector is operational and in regular communication with the C.I.E. The LED’s shall be configurable from the C.I.E to give visual indication of: Device Healthy Fire Fault – Isolation in use Detector Dirty Test Mode Chamber Fault If required, the flashing mode operation of the Detector LED’s shall be controlled through the system field program. An output connection shall also be provided in the base to connect an external remote alarm LED. Sensitivity settings The Detector sensitivity be set through the C.I.E, and shall be adjustable in the field through the field programming of the system. Sensitivity may be automatically adjusted by the panel on a time-of-day basis. Theses sensitivity levels not contravene EN54 part 7 unless placed in to thermal (heat) only mode in which case the unit shall comply with EN54 part 5. Drift compensation The Detector automatically compensate for dust accumulation and other slow environmental changes that may affect their performance. The use of this function not contravene EN54 part 7. Additional requirements Optional relay base and isolator base variants shall be available. Up to 99, intelligent Detectors may connect to one SLC loop. The C.I.E software, not the detector, shall make the alarm decision. The sensitivity of each detector shall be set in the C.I.E. The system operator shall be able to view the current analogue or digital value of each detector at the C.I.E. Addressable Thermal Heat Detector Specification Compliance with standards The Heat Detector shall be third party approved to EN54 part 5. Types A1R, A1, and BS shall be available. Functionality The Detectors shall use an electronic detector to measure thermal conditions caused by a fire and shall, on command from the C.I.E, send data to the panel representing the analogue or digital level (the temperature) at the detector. Heat Detectors be intelligent and addressable devices, and shall connect with two wires to one of the C.I.E. Signalling Line Circuits. The detector shall operate on a digital protocol loop to give reduced power consumption, upto 99 detectors and 99 modules may be connected to a single loop. The detectors shall be fitted with a loop isolation device in-built into the device.
NOTIFIER_ID3000_Addressable_Fire_System_Specification.docx