Provide quarterly maintenance for 1 year following substantial completion of the project. PROJECT CONDITIONS Maintain environmental conditions (temperature, humidity, and ventilation) within limits recommended by manufacturer for optimum results. Do not install products under environmental conditions outside absolute limits. manufacturer’s WARRANTY Standard Warranty: Manufacturer’s Access Control System Warranty: 1 year limited warranty. PRODUCTS MANUFACTURERS Acceptable Manufacturer: LiftMaster; 845 Larch Avenue; Elmhurst, IL 60126-1196. 800.282.6225; Email: specs@LiftMaster.com; Web: LiftMaster.com. Substitutions: Not permitted. Requests for substitutions will be considered in accordance with provisions of Section 01600. ACCESS CONTROL SYSTEMS Stand-Alone Proximity Access Control Device: LiftMaster PPLX Passport Stand-Alone Proximity Card Reader. Dimensions: Surface mount, 4-1/2 inches H x 3-1/5 inches W (115 mm H x 82 mm W). Power: 5 to 14V DC, 50 mA idle, 150 mA maximum. Enclosure: Surface-mount, vandal-resistant plastic faceplate and single-gang weatherproof outlet box. Operating Temperature Environment Access Control Unit and Cards: Ambient temp. degrees F (-40 degrees C) to 158 degrees F (70 degrees C). Operating Humidity: 0 to 95% non-condensing. System Components: Stand-Alone Proximity Reader (LiftMaster Model PPLX). Proximity Radio Programmer (LiftMaster Model PPRP). Power supply 12V DC 2.0A (LiftMaster Model PS12D2A). 34-Bit Passport Proximity Card (clamshell) (shipped in sleeves of 50) (LiftMaster Model PPCSC). Standard Features: 6-inch (152 mm) card reader range. Capacity: 50,000 users. Programmable Output Relay: (NO/NC). SPST solid-state relay, 1A max. at 60V AC or DC. to hold a door or gate open. “Latch Mode” Timed anti-passback logic. EXECUTION EXAMINATION AND PREPARATION
Provide quarterly maintenance for 1 year following substantial completion of the project. PROJECT CONDITIONS Maintain environmental conditions (temperature, humidity, and ventilation) within limits recommended by manufacturer for optimum results. Do not install products under environmental conditions outside manufacturer’s absolute limits. WARRANTY Manufacturer’s Standard Warranty: Access Control System Warranty: 1 year limited warranty. PRODUCTS MANUFACTURERS Acceptable Manufacturer: LiftMaster; 845 Larch Avenue; Elmhurst, IL 60126-1196. 800.282.6225; Email: specs@LiftMaster.com; Web: LiftMaster.com. Substitutions: Not permitted. Requests for substitutions will be considered in accordance with provisions of Section 01600. ACCESS CONTROL SYSTEMS Stand-Alone Proximity Access Control Device: LiftMaster PPLX Passport Stand-Alone Proximity Card Reader. Dimensions: Surface mount, 4-1/2 inches H x 3-1/5 inches W (115 mm H x 82 mm W). Power: 5 to 14V DC, 50 mA idle, 150 mA maximum. Enclosure: Surface-mount, vandal-resistant plastic faceplate and single-gang weatherproof outlet box. Operating Temperature Environment Access Control Unit and Cards: Ambient temp. degrees F (-40 degrees C) to 158 degrees F (70 degrees C). Operating Humidity: 0 to 95% non-condensing. System Components: Stand-Alone Proximity Reader (LiftMaster Model PPLX). Proximity Radio Programmer (LiftMaster Model PPRP). Power supply 12V DC 2.0A (LiftMaster Model PS12D2A). 34-Bit Passport Proximity Card (clamshell) (shipped in sleeves of 50) (LiftMaster Model PPCSC). Standard Features: 6-inch (152 mm) card reader range. Capacity: 50,000 users. Programmable Output Relay: (NO/NC). SPST solid-state relay, 1A max. at 60V AC or DC. “Latch Mode” to hold a door or gate open. Timed anti-passback logic. EXECUTION EXAMINATION AND PREPARATION