little bit of a challenge as the surveyors in accordingly without necessarily going to site. the market are used to charging in the five Be advised that proper survey and designs guide the aspects. approving authority in making decisions regarding Kindly consider if it could be possible to wayleaves acquisition to be done by the employer. have a similar breakdown for convenient Note that we are hereby dealing with premises that engagement with surveyors are not more than 600M from the Transformer 59. Section a Bidder shall submit the Attached above in Response No.17 Manufacturer’s Authorization letter, using the form included in Section IV. However Section IV refers to Price schedule. Please clarify. 60. As per Employer requirement, scope of The Cable is as 10MM2 with two core works calls for 16mm2 aluminum single communication cables as described in the B.O.Q. The core cables. However, Price Schedule calls specifications for the cable are also provided. Read for 10mm2. specifications of this cable in the tender document. 61. Further in the same section scope of works KPLC shall issue the meters to Contractors, The calls for installation of approximately Meters are being purchased under Lot 11 of this 255,545 electronic energy meters. Please tender. confirm that the KPLC would be supplying electronic energy meters 62. Price Schedule calls for supply and Provide the materials as requested in the B.O.Q installation of complete Single phase LV fittings. However ongoing through the drawings we find LV Intermediate pole (for angle upto 60 deg) Ref Drg LV 2 LV Sectional pole (for angle upto 30 deg) Ref Drg LV 3 LV Sectional pole (for angle upto 30 deg & for 3 or 4 -way arrangement) Ref Drg LV 4. LV intermediate pole (with tee-off connetion) Ref Drg LV 5. LV intermediate pole (with Underground cable connection) Ref Drg LV 6 Please send us the break up of quantities for these type of fittings to be used. 63. Ongoing through the drawings we find Provide the materials as requested in the B.O.Q the below LV Terminal pole (with Aerial Cable connection) Ref Drg LV 7 House Termination (Aerial attachment to buildings) Ref Drg LV 8 However we do not find quantities for LV Terminal pole and also Aerial conductor quantity. Please clarify.
little bit of a challenge as the surveyors in the market are used to charging in the five aspects. Kindly consider if it could be possible to have a similar breakdown for convenient engagement with surveyors accordingly without necessarily going to site. Be advised that proper survey and designs guide the approving authority in making decisions regarding wayleaves acquisition to be done by the employer. Note that we are hereby dealing with premises that are not more than 600M from the Transformer 59. Section a Bidder shall submit the Manufacturer’s Authorization letter, using the form included in Section IV. However Section IV refers to Price schedule. Please clarify. Attached above in Response No.17 60. As per Employer requirement, scope of works calls for 16mm2 aluminum single core cables. However, Price Schedule calls for 10mm2. The Cable is as 10MM2 with two core communication cables as described in the B.O.Q. The specifications for the cable are also provided. Read specifications of this cable in the tender document. 61. Further in the same section scope of works calls for installation of approximately 255,545 electronic energy meters. Please confirm that the KPLC would be supplying electronic energy meters KPLC shall issue the meters to Contractors, The Meters are being purchased under Lot 11 of this tender. 62. Price Schedule calls for supply and installation of complete Single phase LV fittings. However ongoing through the drawings we find LV Intermediate pole (for angle upto 60 deg) Ref Drg LV 2 LV Sectional pole (for angle upto 30 deg) Ref Drg LV 3 LV Sectional pole (for angle upto 30 deg & for 3 or 4 -way arrangement) Ref Drg LV 4. LV intermediate pole (with tee-off connetion) Ref Drg LV 5. LV intermediate pole (with Underground cable connection) Ref Drg LV 6 Please send us the break up of quantities for these type of fittings to be used. Provide the materials as requested in the B.O.Q 63. Ongoing through the drawings we find the below LV Terminal pole (with Aerial Cable connection) Ref Drg LV 7 House Termination (Aerial attachment to buildings) Ref Drg LV 8 However we do not find quantities for LV Terminal pole and also Aerial conductor quantity. Please clarify. Provide the materials as requested in the B.O.Q