5 EXPLANATIONS of LOGGING UPS will beep when any problem is detected. You can see the first information about the situation on the front monitor panel. This may not be enough most of the time. In this case, you can see the following warnings by using log screen. Event Explanations RS232 Start 1 UPS was started by RS232 communication software. Command RS232 Stop 2 UPS was stopped by RS232 communication software. Command After the batteries discharge totally, UPS restarted itself automatically after the 3 Auto Restart mean time which adjusted that follows the mains getting back to normal values. 4 UPS Startup The main board of the UPS is energized. 5 Soft Start Fail UPS could not ramp the DC bus up. 6 Quick Battery Test Quick battery test has began. 7 Deep Battery Test Battery capacity test has began. 8 Battery Self Test Periodical battery test has began. Batteries’ voltage has gone below cut off voltage value while UPS was 9 End Of Discharge operating on the battery mode. UPS has operated at overload more than time limit adjusted.The Loads will be 10 Overload Timeout transferred to bypass line. Battery test has completed.You can see the all results via front panel status 11 End of Battery Test menu.. Test was aborted manually or by UPS since the criterias were not provided 12 Batt. Test Aborted during battery test. Manuel Switch To Static switchs directions were changed manually to the bypass line via UPS 13 BYP command menu. 14 No Battery No battery detected. 15 Maint. BYP. Sw. On Maintenance bypass switch has been activated. Ambient Abnor. 16 The ambient temperature is over limit. Check the ventilation of UPS room. Temp. Inverter's temperature is out of limit, in case of 5 degrees more increment 17 Inverter Overtemp. ,Load will be transferred to Bypass line. Rectifier 's temperature is out of limit, in case of 5 degrees more increment 18 PFC Overtemp. ,Load will be transferred to Bypass line. 19 STS Overtemp. Static Transfer Switches’ temperatures are out of limits.UPS will be stopped. Outp.PL1 Cur. 20 Short circuit protection is activated for output L1 phase. Limit. Outp.PL2 Cur. 21 Short circuit protection is activated for output L2 phase. Limit. Outp.PL3 Cur. 22 Short circuit protection is activated for output L3 phase. Limit.
5 EXPLANATIONS of LOGGING UPS will beep when any problem is detected. You can see the first information about the situation on the front monitor panel. This may not be enough most of the time. In this case, you can see the following warnings by using log screen. Event Explanations 1 RS232 Start Command UPS was started by RS232 communication software. 2 RS232 Stop Command UPS was stopped by RS232 communication software. 3 Auto Restart After the batteries discharge totally, UPS restarted itself automatically after the mean time which adjusted that follows the mains getting back to normal values. 4 UPS Startup The main board of the UPS is energized. 5 Soft Start Fail UPS could not ramp the DC bus up. 6 Quick Battery Test Quick battery test has began. 7 Deep Battery Test Battery capacity test has began. 8 Battery Self Test Periodical battery test has began. 9 End Of Discharge Batteries’ voltage has gone below cut off voltage value while UPS was operating on the battery mode. 10 Overload Timeout UPS has operated at overload more than time limit adjusted.The Loads will be transferred to bypass line. 11 End of Battery Test Battery test has completed.You can see the all results via front panel status menu.. 12 Batt. Test Aborted Test was aborted manually or by UPS since the criterias were not provided during battery test. 13 Manuel Switch To BYP Static switchs directions were changed manually to the bypass line via UPS command menu. 14 No Battery No battery detected. 15 Maint. BYP. Sw. On Maintenance bypass switch has been activated. 16 Ambient Abnor. Temp. The ambient temperature is over limit. Check the ventilation of UPS room. 17 Inverter Overtemp. Inverter's temperature is out of limit, in case of 5 degrees more increment ,Load will be transferred to Bypass line. 18 PFC Overtemp. Rectifier 's temperature is out of limit, in case of 5 degrees more increment ,Load will be transferred to Bypass line. 19 STS Overtemp. Static Transfer Switches’ temperatures are out of limits.UPS will be stopped. 20 Outp.PL1 Cur. Limit. Short circuit protection is activated for output L1 phase. 21 Outp.PL2 Cur. Limit. Short circuit protection is activated for output L2 phase. 22 Outp.PL3 Cur. Limit. Short circuit protection is activated for output L3 phase.