e. Addition of fresh water 5.23 Addition of The treatment process should also include the addition of fresh water ST fresh water at frequent intervals. The recommended rate is 30 L per bather per (dilution of day. pollutants) Monitoring 5.24 Water quality The water quality parameters which are listed in Table (page 104) ST parameters and Table (page 105) should be monitored according to the given frequency and should be within the acceptable ranges. 5.25 Test kits Test kits for measuring free halogen residual, pH and ST total halogen should be available (a cyanuric acid test kit is also required when using a cyanurate for disinfectant stabilisation). The test kits should be cared for and used by trained individuals.
e. Addition of fresh water 5.23 Addition of fresh water (dilution of pollutants) The treatment process should also include the addition of fresh water at frequent intervals. The recommended rate is 30 L per bather per day. ST Monitoring 5.24 Water quality parameters The water quality parameters which are listed in Table (page 104) and Table (page 105) should be monitored according to the given frequency and should be within the acceptable ranges. ST 5.25 Test kits Test kits for measuring free halogen residual, pH and total halogen should be available (a cyanuric acid test kit is also required when using a cyanurate for disinfectant stabilisation). The test kits should be cared for and used by trained individuals. ST