Technical Specifications Battery power consumption 48 V The device shall have the following Technical Specifications: Mechanical Master Unit Dimensions (H x W x D) Electrical For rack use, with 88 x 483 x 400 mm 19” brackets (3.5 x 19 x 15.7 in) Mains power supply in front of brackets 40 mm (1.6 in) Voltage 115 / 230 VAC, ±10%, 50/60 Hz behind brackets 360 mm (14.2 in) Fuse rating T6.3 A, 250 V Weight 15.9 kg (35.05 lb) Inrush current Time: < 10 A ms; ≤ 30 Mounting rack 19” Max power consumption 150 W Color Charcoal with silver Battery power supply Environmental Voltage 18 56 VDC nominal 24 or – Operating temperature -5 ºC to +55 ºC 48 VDC (+23 ºF to +131 ºF) Backup fault detection 21 ± 1 VDC Storage temperature -20 ºC to +70 ºC level (-4 ºF to +158 ºF) Max backup power 4.5 A Relative humidity 15% to 90% current Air pressure 600 to 1100 hPa Hardware Interfaces 100 V audio I/O Pluggable screw connector Isolator Board (loop 1-6) Electrical Fault output (loop 1-6) Floating contacts 24 V, 1 A Fault relays except general OK state is Loudspeaker loop 120 VAC audio, max 5 A fault relay normally connection energized Maximum loop though 500 W NO is open loudspeaker load General fault relay OK state is Maximum tapoff load 100 W Failsafe, normally Test fault indicating LED Yellow NC is open Test button Momentary (failsafe) Mechanical Performance Max. number of Isolator 50 Dimensions (H x W x D) 78 x 60 x 32 mm Boards in loop (3.0 x 2.3 x 0.6 in) Power handling capacity 500 W Housing 150 x 150 x 75 mm per loop (5.9 x 5.9 x 2.9 in) Frequency range 50 Hz 20 kHz – Mounting options Ready mounted in the supplied housing Battery power consumption 24 V
Technical Specifications The device shall have the following Technical Specifications: Master Unit Electrical Mains power supply Voltage 115 / 230 VAC, ±10%, 50/60 Hz Fuse rating T6.3 A, 250 V Inrush current Time: < 10 ms; ≤ 30 A Max power consumption 150 W Battery power supply Voltage 18 – 56 VDC nominal 24 or 48 VDC Backup fault detection level 21 ± 1 VDC Max backup power current 4.5 A Hardware Interfaces 100 V audio I/O (loop 1-6) Pluggable screw connector Fault output (loop 1-6) Floating contacts 24 V, 1 A Fault relays except general fault relay OK state is normally NO is open General fault relay OK state is Failsafe, normally energized NC is open (failsafe) Performance Max. number of Isolator Boards in loop 50 Power handling capacity per loop 500 W Frequency range 50 Hz – 20 kHz Battery power consumption 24 V Battery power consumption 48 V Mechanical Dimensions (H x W x D) For 19” rack use, with brackets 88 x 483 x 400 mm (3.5 x 19 x 15.7 in) in front of brackets 40 mm (1.6 in) behind brackets 360 mm (14.2 in) Weight 15.9 kg (35.05 lb) Mounting 19” rack Color Charcoal with silver Environmental Operating temperature -5 ºC to +55 ºC (+23 ºF to +131 ºF) Storage temperature -20 ºC to +70 ºC (-4 ºF to +158 ºF) Relative humidity 15% to 90% Air pressure 600 to 1100 hPa Isolator Board Electrical Loudspeaker loop connection 120 VAC audio, max 5 A Maximum loop though loudspeaker load 500 W Maximum tapoff load 100 W Test fault indicating LED Yellow Test button Momentary Mechanical Dimensions (H x W x D) 78 x 60 x 32 mm (3.0 x 2.3 x 0.6 in) Housing 150 x 150 x 75 mm (5.9 x 5.9 x 2.9 in) Mounting options Ready mounted in the supplied housing