Model Z1203-N-XB. Vertical Waste Fitting: Model Z1204-N-XH. Model Z1204-N-XB. Standard, Adjustable Blowout Style Water Closet Carriers: Basis-of-Design: Zurn Industries, LLC: Horizontal Waste Fitting: Model Z1203-N. Model Z1203-N-XH. Model Z1203-N-XB. Vertical Waste Fitting: Model Z1204-N. Model Z1204-N-XH. Model Z1204-N-XB. Water Closet Waste Carrier Attributes: Standard: ASME A112.6.1M. Load Rating: H = 300 lbs (227 kg). N = 300 lbs (136 kg). XH = 750 lbs (340 kg). XB = 1,000 lbs (454 kg). Waste-fitting to match drainage piping material and arrangement. Couplings gaskets, faceplate, and feet; Hardware to match fixture. Wide space installation: Extension coupling. Connection Type: No-Hub "N". Hub and Spigot "H". Flow Direction: Right "R". Left "L". Double "D". Waste Pipe Diameter: 3 in (76 mm). 4 in (102 mm). Faceplate: B (blowout style faceplate). Water Consumption: Per flush. 1.1 gal (4.2 L). 1.28 gal (4.8 L) 1.6 gal (6 L). Water-Closet Mounting Height: Standard. Child. Handicapped/elderly according to ICC A117.1. Coupling/Waste Orifice Diameter: 3 in (76 mm). Foot Type: Universal (standard or pre-fab installations). Bariatric. Material: Cast Iron. SUPPORT FIXTURES Lavatory, Support Fixtures: Basis-of-Design: Zurn Industries, LLC: Model Z1224 - Plate Type System; Lavatory Back Carrier. Lavatory support system with top support plate.
Model Z1203-N-XB. Vertical Waste Fitting: Model Z1204-N-XH. Model Z1204-N-XB. Standard, Adjustable Blowout Style Water Closet Carriers: Basis-of-Design: Zurn Industries, LLC: Horizontal Waste Fitting: Model Z1203-N. Model Z1203-N-XH. Model Z1203-N-XB. Vertical Waste Fitting: Model Z1204-N. Model Z1204-N-XH. Model Z1204-N-XB. Water Closet Waste Carrier Attributes: Standard: ASME A112.6.1M. Load Rating: H = 300 lbs (227 kg). N = 300 lbs (136 kg). XH = 750 lbs (340 kg). XB = 1,000 lbs (454 kg). Waste-fitting to match drainage piping material and arrangement. Couplings gaskets, faceplate, and feet; Hardware to match fixture. Wide space installation: Extension coupling. Connection Type: No-Hub "N". Hub and Spigot "H". Flow Direction: Right "R". Left "L". Double "D". Waste Pipe Diameter: 3 in (76 mm). 4 in (102 mm). Faceplate: B (blowout style faceplate). Water Consumption: Per flush. 1.1 gal (4.2 L). 1.28 gal (4.8 L) 1.6 gal (6 L). Water-Closet Mounting Height: Standard. Child. Handicapped/elderly according to ICC A117.1. Coupling/Waste Orifice Diameter: 3 in (76 mm). Foot Type: Universal (standard or pre-fab installations). Bariatric. Material: Cast Iron. SUPPORT FIXTURES Lavatory, Support Fixtures: Basis-of-Design: Zurn Industries, LLC: Model Z1224 - Plate Type System; Lavatory Back Carrier. Lavatory support system with top support plate.