Ensure that jointing or mating surfaces are clean, and where necessary lubricated, immediately before assembly. Form junctions using fittings intended for the purpose ensuring that jointing material does not project into bore of pipes, fittings and appliances. Remove surplus flux/solvent/cement/sealant from joints. 675 COATED PIPEWORK/GUTTERS: Make good to coatings after cutting and any other damage or recoat, as recommended by the manufacturer. 690 ELECTRICAL CONTINUITY: Where specified , use clips or suitable standard couplings supplied for the purpose by pipework manufacturer to ensure electrical continuity at all joints in metal pipes with flexible couplings and which are to be earth bonded. 700 ACCESS FOR TESTING AND MAINTENANCE: Install pipework and gutters with adequate clearance to permit testing, cleaning and maintenance. Position access fittings and rodding eyes so that they are not obstructed by other pipework, framing, etc. COMPLETION 900 TESTING GENERALLY: Inform CA sufficiently in advance to give him a reasonable opportunity to observe tests. Check that all sections of installation are free from obstruction and debris before testing. Provide clean water, assistance and apparatus for testing as required. Carry out tests as specified. After testing, locate and remedy all defects without delay and retest as instructed. Keep a record of all tests and provide a copy of each to the CA. 910 GUTTER TEST: Block all outlets, fill gutters to overflow level and after 5 minutes closely inspect for leakage. 915 MAINTENANCE INSTRUCTIONS At completion, submit printed instructions recommending procedures for maintenance of the rainwater installation including full details of the recommended inspection, cleaning and repair procedures. 920 IMMEDIATELY BEFORE HANDOVER: Remove construction rubbish and debris from all roofs and gutters. Where possible, sweep and remove fine dust which may enter rainwater systems. Do not sweep or flush dust or debris into the rainwater system. Remove swarf, debris and temporary caps from the entire rainwater installation. Ensure that all access covers, rodding eyes, outlet gratings etc. are secured complete with all fixings.
Ensure that jointing or mating surfaces are clean, and where necessary lubricated, immediately before assembly. Form junctions using fittings intended for the purpose ensuring that jointing material does not project into bore of pipes, fittings and appliances. Remove surplus flux/solvent/cement/sealant from joints. 675 COATED PIPEWORK/GUTTERS: Make good to coatings after cutting and any other damage or recoat, as recommended by the manufacturer. 690 ELECTRICAL CONTINUITY: Where specified , use clips or suitable standard couplings supplied for the purpose by pipework manufacturer to ensure electrical continuity at all joints in metal pipes with flexible couplings and which are to be earth bonded. 700 ACCESS FOR TESTING AND MAINTENANCE: Install pipework and gutters with adequate clearance to permit testing, cleaning and maintenance. Position access fittings and rodding eyes so that they are not obstructed by other pipework, framing, etc. COMPLETION 900 TESTING GENERALLY: Inform CA sufficiently in advance to give him a reasonable opportunity to observe tests. Check that all sections of installation are free from obstruction and debris before testing. Provide clean water, assistance and apparatus for testing as required. Carry out tests as specified. After testing, locate and remedy all defects without delay and retest as instructed. Keep a record of all tests and provide a copy of each to the CA. 910 GUTTER TEST: Block all outlets, fill gutters to overflow level and after 5 minutes closely inspect for leakage. 915 MAINTENANCE INSTRUCTIONS At completion, submit printed instructions recommending procedures for maintenance of the rainwater installation including full details of the recommended inspection, cleaning and repair procedures. 920 IMMEDIATELY BEFORE HANDOVER: Remove construction rubbish and debris from all roofs and gutters. Where possible, sweep and remove fine dust which may enter rainwater systems. Do not sweep or flush dust or debris into the rainwater system. Remove swarf, debris and temporary caps from the entire rainwater installation. Ensure that all access covers, rodding eyes, outlet gratings etc. are secured complete with all fixings.