After power reset, the setting value is restored Automatic stop setting Specified Function Each Each Group Setting time range: 0-12 hours Setting/Viewing indoor unit option code Viewing indoor unit RMC address Viewing indoor unit data Setting/Viewing temperature sensor compensation of the wired remote controller (-9°~ +9°) Service Mode Each Group Each Group Viewing the RPM compensation Viewing the filter time (1,000 hours or 2,000 hours) Viewing indoor unit temperature sensor compensation under Heating (+2 or +5°) Viewing the H/W option setting When an error is currently occurring on an air Error conditioner unit, the afflicted unit and the error Each Group Each Group code are displayed Permit / Prohibit Setting/releasing of simplified locking for remote Each Group N/A Local Operation control buttons can be performed Select the Quiet mode to run the indoor unit to Quiet Mode Each Group N/A the set mode to lower the fan noise level. Displays set temperature. Room Temperature Room temperature is viewable when Each Group Each Group room temperature button is pressed Other Standard Controller features Different button permission levels Temperature limit setting option room temperature sensor Indoor unit operation state display Service mode support (indoor unit cycle data monitoring, option code monitoring and setting, and dip switch state monitoring) Specifications wire connection DC 12V (V1/V2) power supplied by indoor unit RS485 communication (F3/F4) Can sense temperature via internal sensor, temperature sensor inside the air handler, or use the average temperature between controller and air indoor unit sensors The Standard Controller shall require no addressing. The Standard Controller shall connect using four-wire (2 wires for power supply and the other two for communication), untwisted, shielded control wire to the connection terminal on the indoor unit. The Standard Controller shall require cross-over wiring for
After power reset, the setting value is restored Specified Function Automatic stop setting Setting time range: 0-12 hours Each Each Group Service Mode Setting/Viewing indoor unit option code Viewing indoor unit RMC address Viewing indoor unit data Setting/Viewing temperature sensor compensation of the wired remote controller (-9°~ +9°) Viewing the RPM compensation Viewing the filter time (1,000 hours or 2,000 hours) Viewing indoor unit temperature sensor compensation under Heating (+2 or +5°) Viewing the H/W option setting Each Group Each Group Error When an error is currently occurring on an air conditioner unit, the afflicted unit and the error code are displayed Each Group Each Group Permit / Prohibit Local Operation Setting/releasing of simplified locking for remote control buttons can be performed Each Group N/A Quiet Mode Select the Quiet mode to run the indoor unit to the set mode to lower the fan noise level. Each Group N/A Room Temperature Displays set temperature. Room temperature is viewable when room temperature button is pressed Each Group Each Group Other Standard Controller features Different button permission levels Temperature limit setting option room temperature sensor Indoor unit operation state display Service mode support (indoor unit cycle data monitoring, option code monitoring and setting, and dip switch state monitoring) Specifications wire connection DC 12V (V1/V2) power supplied by indoor unit RS485 communication (F3/F4) Can sense temperature via internal sensor, temperature sensor inside the air handler, or use the average temperature between controller and air indoor unit sensors The Standard Controller shall require no addressing. The Standard Controller shall connect using four-wire (2 wires for power supply and the other two for communication), untwisted, shielded control wire to the connection terminal on the indoor unit. The Standard Controller shall require cross-over wiring for