1910.147(d)(5) Lockout/Tagout Verification that energy is isolated to starting work and de- energized 1910.147(e)(1) Lockout/Tagout Ensure components are operational Prior to removing lock or tag intact, employees safety positioned 1910.156(d) Fire brigades Fire fighting equipment Annually; fire extinguishers and respirators monthly 1910.157(e) Portable fire Portable extinguishers or hoses used in Visual inspection monthly; maintenance extinguishers lieu other systems annually; Dry chemical every 6 years 1910.157(f)(2)(1) Portable fire Hydrostatic checks of cylinders and hose As stated in Table L-1; extinguishers assembly When in evidence of corrosion or injury 1910.158(e)(1)(i) Standpipe and hose Hydrostatic checks of Class II After installation systems and III systems 1910.158(e)(2)(iii) Standpipe and hose Hose systems Annually; each use systems 1910.158(e)(2)(v) Standpipe and hose Hemp or linen hose Annually systems 1910.159(c)(2) Automatic sprinkler Main drain flow, test valve Main drain flow - annually; systems Test valve - every 2 years Standard Subject Required Coverage Frequency 1910.159(c)(3) Automatic sprinkler Acceptance tests After installation systems 1910.159(c)(8)(ii) Automatic sprinkler When using older style sprinklers to Prior to installation systems replace standard sprinklers 1910.160(b)(6)-(8) extinguishing All such systems and containers Systems - annually systems Containers - semi-annually
1910.147(d)(5) Lockout/Tagout Verification that energy is isolated and de- energized to starting work 1910.147(e)(1) Lockout/Tagout Ensure components are operational intact, employees safety positioned Prior to removing lock or tag 1910.156(d) Fire brigades Fire fighting equipment Annually; fire extinguishers and respirators monthly 1910.157(e) Portable fire extinguishers Portable extinguishers or hoses used in lieu other systems Visual inspection monthly; maintenance annually; Dry chemical every 6 years 1910.157(f)(2)(1) Portable fire extinguishers Hydrostatic checks of cylinders and hose assembly As stated in Table L-1; When in evidence of corrosion or injury 1910.158(e)(1)(i) Standpipe and hose systems Hydrostatic checks of Class II and III systems After installation 1910.158(e)(2)(iii) Standpipe and hose systems Hose systems Annually; each use 1910.158(e)(2)(v) Standpipe and hose systems Hemp or linen hose Annually 1910.159(c)(2) Automatic sprinkler systems Main drain flow, test valve Main drain flow - annually; Test valve - every 2 years Standard Subject Required Coverage Frequency 1910.159(c)(3) Automatic sprinkler systems Acceptance tests After installation 1910.159(c)(8)(ii) Automatic sprinkler systems When using older style sprinklers to replace standard sprinklers Prior to installation 1910.160(b)(6)-(8) extinguishing systems All such systems and containers Systems - annually Containers - semi-annually