ANSUL® INERGEN® FIRE SUPPRESSION SYSTEM WITH AUTOPULSE Z-20 AGENT RELEASING CONTROL PANEL ENGINEERING SPECIFICATIONS 2016-NOVEMBER Tyco Fire Protection Products One Stanton Street, Marinette, WI 54143-2542 1-800-862-6785/1-715-735-7415 PART 1 GENERAL – DESCRIPTION OF WORK: Design and installation of an engineered fire detection and INERGEN total flooding, gaseous agent, fire suppression system as manufactured by Tyco Fire Protection Products, Marinette, Wisconsin, or approved equal. System design is based on the use of Selector valves to direct the flow of INERGEN agent into the protected zone where indicated on drawings. Quantity of INERGEN cylinders is to be based on the largest zone of protection. Cylinders shall be provided to offer adequate protection of the largest zone of protection. Selector valves shall be provided to supply discharge of proper design concentration of INERGEN agent into the protected zone. Drawings: The contract drawings indicate the general arrangements of the areas to receive detection and INERGEN system protection. Contractor is to review all drawings so that all items affecting the operation of the fire detection/INERGEN fire suppression system (such as equipment location, air diffusers, damper closures, and door openings) are considered in the design of the engineered system. APPLICABLE PUBLICATIONS: The following publications of the issues listed but referred to thereafter by basic designation only, form a part of this specification to the extent indicated by the reference thereto (latest edition): National Fire Protection Association (NFPA) Standards: No. 2001 Clean Agent Fire Extinguishing Systems No. 70 National Electrical Code No. 72 National Fire Alarm Code No. 75 Protection of Information Technology Equipment No. 76 Fire Protection for Telecommunication Systems Factory Mutual Systems (FM) Publication Factory Mutual Approval Guide Underwriters Laboratories, Inc. (UL) Publication UL 217: Smoke Detectors, Single and Multiple Stations UL 228: Door Closers–Holders for Fire Protective Signaling Systems UL 268: Standard for Smoke Detectors for Open Areas UL 268A: Standard for Smoke Detectors for Duct Application UL 521: Heat Detectors for Fire Protective Signaling Systems UL 864 9th ed: Control Units and Accessories for Fire Alarm Systems UL 1638: Visual Signaling Appliances UL 1971: Signaling Devices for Hearing Impaired Fire Protection Equipment Directory with quarterly supplements
ANSUL® INERGEN® FIRE SUPPRESSION SYSTEM WITH AUTOPULSE Z-20 AGENT RELEASING CONTROL PANEL ENGINEERING SPECIFICATIONS 2016-NOVEMBER Tyco Fire Protection Products One Stanton Street, Marinette, WI 54143-2542 1-800-862-6785/1-715-735-7415 PART 1 – GENERAL DESCRIPTION OF WORK: Design and installation of an engineered fire detection and INERGEN total flooding, gaseous agent, fire suppression system as manufactured by Tyco Fire Protection Products, Marinette, Wisconsin, or approved equal. System design is based on the use of Selector valves to direct the flow of INERGEN agent into the protected zone where indicated on drawings. Quantity of INERGEN cylinders is to be based on the largest zone of protection. Cylinders shall be provided to offer adequate protection of the largest zone of protection. Selector valves shall be provided to supply discharge of proper design concentration of INERGEN agent into the protected zone. Drawings: The contract drawings indicate the general arrangements of the areas to receive detection and INERGEN system protection. Contractor is to review all drawings so that all items affecting the operation of the fire detection/INERGEN fire suppression system (such as equipment location, air diffusers, damper closures, and door openings) are considered in the design of the engineered system. APPLICABLE PUBLICATIONS: The following publications of the issues listed but referred to thereafter by basic designation only, form a part of this specification to the extent indicated by the reference thereto (latest edition): National Fire Protection Association (NFPA) Standards: No. 2001 Clean Agent Fire Extinguishing Systems No. 70 National Electrical Code No. 72 National Fire Alarm Code No. 75 Protection of Information Technology Equipment No. 76 Fire Protection for Telecommunication Systems Factory Mutual Systems (FM) Publication Factory Mutual Approval Guide Underwriters Laboratories, Inc. (UL) Publication UL 217: Smoke Detectors, Single and Multiple Stations UL 228: Door Closers–Holders for Fire Protective Signaling Systems UL 268: Standard for Smoke Detectors for Open Areas UL 268A: Standard for Smoke Detectors for Duct Application UL 521: Heat Detectors for Fire Protective Signaling Systems UL 864 9th ed: Control Units and Accessories for Fire Alarm Systems UL 1638: Visual Signaling Appliances UL 1971: Signaling Devices for Hearing Impaired Fire Protection Equipment Directory with quarterly supplements