8. The appropriate wiring diagrams shall be laminated or mounted under plexiglass within the frame on the inside of the cubicles and panels. 9. All indicating lamps and switches shall be accessible and mounted on the cubicle doors. 10. Meters shall be per the requirements of Section 25 10 10, ADVANCED UTILITY METERING. 11. The manufacturer shall coordinate the interconnection and programming of the generator controls with all related equipment, including automatic transfer switches and generator paralleling controls as applicable, specified in other sections. C. Engine generator Control Cubicle: 1. Starting and Stopping Controls: a. A three-position, maintained-contact type selector switch with positions marked "AUTOMATIC," "OFF," and "MANUAL." Provide flashing amber light for OFF and MANUAL positions. b. A momentary contact push-button switch with positions marked "MANUAL START" and "MANUAL STOP." c. Selector switch in AUTOMATIC position shall cause the engine to start automatically when a single pole contact in a remote device closes. When the generator's output voltage increases to not less than 90% of its rated voltage, and its frequency increases to not less than 58 Hz, the remote devices shall transfer the load to the generator. An adjustable time delay relay, in the 0 to 15 minute range, shall cause the engine generator to continue operating without any load after completion of the period of operation with Upon completion of the additional 0 to 15 minute (adjustable) period, the engine generator shall stop. d. Selector switch in OFF position shall prevent the engine from starting either automatically or manually. Selector switch in MANUAL position shall also cause the engine to start when the manual start push-button is depressed momentarily. e. With selector switch is in MANUAL position, depressing the MANUAL STOP push-button momentarily shall stop the engine after a period. f. A maintained-contact, red mushroom-head push-button switch marked "EMERGENCY STOP" will cause the engine to stop without a period, independent of the position of the selector switch.
8. The appropriate wiring diagrams shall be laminated or mounted under plexiglass within the frame on the inside of the cubicles and panels. 9. All indicating lamps and switches shall be accessible and mounted on the cubicle doors. 10. Meters shall be per the requirements of Section 25 10 10, ADVANCED UTILITY METERING. 11. The manufacturer shall coordinate the interconnection and programming of the generator controls with all related equipment, including automatic transfer switches and generator paralleling controls as applicable, specified in other sections. C. Engine generator Control Cubicle: 1. Starting and Stopping Controls: a. A three-position, maintained-contact type selector switch with positions marked "AUTOMATIC," "OFF," and "MANUAL." Provide flashing amber light for OFF and MANUAL positions. b. A momentary contact push-button switch with positions marked "MANUAL START" and "MANUAL STOP." c. Selector switch in AUTOMATIC position shall cause the engine to start automatically when a single pole contact in a remote device closes. When the generator's output voltage increases to not less than 90% of its rated voltage, and its frequency increases to not less than 58 Hz, the remote devices shall transfer the load to the generator. An adjustable time delay relay, in the 0 to 15 minute range, shall cause the engine generator to continue operating without any load after completion of the period of operation with Upon completion of the additional 0 to 15 minute (adjustable) period, the engine generator shall stop. d. Selector switch in OFF position shall prevent the engine from starting either automatically or manually. Selector switch in MANUAL position shall also cause the engine to start when the manual start push-button is depressed momentarily. e. With selector switch is in MANUAL position, depressing the MANUAL STOP push-button momentarily shall stop the engine after a period. f. A maintained-contact, red mushroom-head push-button switch marked "EMERGENCY STOP" will cause the engine to stop without a period, independent of the position of the selector switch.