Window units shall be designed to comply with ASTM E1996 Wind Zone 3 Missile Level D Rating +65/-65 psf Air leakage shall not exceed the following when tested at 1.57 psf according to ASTM E283: 0.30 cfm per square foot of frame No water penetration when tested at the following pressure according to ASTM E547: 9.75 psf Assembly shall withstand a positive or negative uniform static air pressure difference of psf without damage when tested according to ASTM E330 Impact and Cycling per ASTM E1996 and E 1886 with passing results for Missile Level D and Pressure Cycling of +65/-65 psf Submittals Shop Drawings: Submit shop drawings under provision of Section 01 33 23 Product Data: Submit catalog data under provision of Section 01 33 23 Samples: Submit corner section under provision of section 01 33 23 Include glazing system, quality of construction and specified finish Quality Control Submittals: Certificates: submit manufacturer’s certification indicating compliance with specified performance and design requirement under provision of section 01 33 23 Quality Assurance Requirements: consult local code for IBC [International Building Code] and IRC [International Residential Code] adoption year and pertinent revisions for information on: Egress, emergency escape and rescue requirements Basement window requirements Windows fall prevention and/or window opening control device requirements Delivery Comply with provisions of Section 01 65 00 Deliver in original packaging and protect from weather
Window units shall be designed to comply with ASTM E1996 Wind Zone 3 Missile Level D Rating +65/-65 psf Air leakage shall not exceed the following when tested at 1.57 psf according to ASTM E283: 0.30 cfm per square foot of frame No water penetration when tested at the following pressure according to ASTM E547: 9.75 psf Assembly shall withstand a positive or negative uniform static air pressure difference of psf without damage when tested according to ASTM E330 Impact and Cycling per ASTM E1996 and E 1886 with passing results for Missile Level D and Pressure Cycling of +65/-65 psf Submittals Shop Drawings: Submit shop drawings under provision of Section 01 33 23 Product Data: Submit catalog data under provision of Section 01 33 23 Samples: Submit corner section under provision of section 01 33 23 Include glazing system, quality of construction and specified finish Quality Control Submittals: Certificates: submit manufacturer’s certification indicating compliance with specified performance and design requirement under provision of section 01 33 23 Quality Assurance Requirements: consult local code for IBC [International Building Code] and IRC [International Residential Code] adoption year and pertinent revisions for information on: Egress, emergency escape and rescue requirements Basement window requirements Windows fall prevention and/or window opening control device requirements Delivery Comply with provisions of Section 01 65 00 Deliver in original packaging and protect from weather