Transmission Owners or Generator Owners shall repair and place back in service within 22 hours the Protection System or RAS that misoperated. If this cannot be done, then Transmission Owners and Generator Owners shall perform the following. [Violation Risk Factor: High] [Time Horizon: Same-day Operations] R2.3.1. When a FEPS is not available, the Transmission Owners shall remove the associated Element from service. R2.3.2. When FERAS is not available, then 2.3.2.1. The Generator Owners shall adjust generation to a reliable operating level, or 2.3.2.2. Transmission Operators shall adjust the SOL and operate the facilities within established limits. R2.4. If the Protection System or RAS has a Dependability-Based Misoperation but has one or more FEPS or FERAS that operated correctly, the associated Element or transmission path may remain in service without removing from service the Protection System or RAS that failed, provided one of the following is performed. R2.4.1. Transmission Owners or Generator Owners shall repair or replace any Protection System or RAS that misoperated with FEPS and FERAS within 20 business days of the date of the Misoperation identification, or R2.4.2. Transmission Owners or
Transmission Owners or Generator Owners shall repair and place back in service within 22 hours the Protection System or RAS that misoperated. If this cannot be done, then Transmission Owners and Generator Owners shall perform the following. [Violation Risk Factor: High] [Time Horizon: Same-day Operations] R2.3.1. When a FEPS is not available, the Transmission Owners shall remove the associated Element from service. R2.3.2. When FERAS is not available, then 2.3.2.1. The Generator Owners shall adjust generation to a reliable operating level, or 2.3.2.2. Transmission Operators shall adjust the SOL and operate the facilities within established limits. R2.4. If the Protection System or RAS has a Dependability-Based Misoperation but has one or more FEPS or FERAS that operated correctly, the associated Element or transmission path may remain in service without removing from service the Protection System or RAS that failed, provided one of the following is performed. R2.4.1. Transmission Owners or Generator Owners shall repair or replace any Protection System or RAS that misoperated with FEPS and FERAS within 20 business days of the date of the Misoperation identification, or R2.4.2. Transmission Owners or