separately, omit from "I” and add to "J”). b. To consider separately, in K use only if greater loss than above. TABLE E103.3(2) LOAD VALUES ASSIGNED TO FIXTURESa LOAD VALUES, IN WATER SUPPLY FIXTURE TYPE OF UNITS (wsfu) SUPPLY FIXTURE OCCUPANCY CONTROL Cold Hot Bathroom Private Flush tank 2.7 1.5 3.6 group Bathroom Flushometer Private 6.0 3.0 8.0 group Bathtub Private Faucet 1.0 1.0 1.4 Bathtub Public Faucet 3.0 3.0 4.0 Private Faucet 1.5 1.5 2.0 Combination Private Faucet 2.25 2.25 3.0 fixture Dishwashing Private Automatic 1.4 1.4 — machine Drinking Offices, etc. 3/8″ 0.25 0.25 — fountain Kitchen sink Private Faucet 1.0 1.0 1.4 Hotel, Kitchen sink Faucet 3.0 3.0 4.0 restaurant Laundry Private Faucet 1.0 1.0 1.4 trays (1 to 3) Lavatory Private Faucet 0.5 0.5 0.7
separately, omit from "I” and add to "J”). b. To consider separately, in K use only if greater loss than above. TABLE E103.3(2) LOAD VALUES ASSIGNED TO FIXTURESa FIXTURE OCCUPANCY TYPE OF SUPPLY CONTROL LOAD VALUES, IN WATER SUPPLY FIXTURE UNITS (wsfu) Cold Hot Bathroom group Private Flush tank 2.7 1.5 3.6 Bathroom group Private Flushometer 6.0 3.0 8.0 Bathtub Private Faucet 1.0 1.0 1.4 Bathtub Public Faucet 3.0 3.0 4.0 Private Faucet 1.5 1.5 2.0 Combination fixture Private Faucet 2.25 2.25 3.0 Dishwashing machine Private Automatic — 1.4 1.4 Drinking fountain Offices, etc. 3/8″ 0.25 — 0.25 Kitchen sink Private Faucet 1.0 1.0 1.4 Kitchen sink Hotel, restaurant Faucet 3.0 3.0 4.0 Laundry trays (1 to 3) Private Faucet 1.0 1.0 1.4 Lavatory Private Faucet 0.5 0.5 0.7