V.I.5 - Boiler/Industrial Furnace Permit Conditions, Monitoring and Automatic Waste Feed Cutoff Systems - Short-Term Operation [Use this for each new or modified Boiler/Industrial Furnace unit and in all columns with the appropriate information] Parameter Monitoring Monitoring Device Operating Permit Limits Primary Secondary Basis1 Device Location Combustion Combustion Pre-Trial Burn Trial Post Chamber Chamber - Shakedown Burn Burn AWFCO AWFCO Y/N2 Y/N2 Operating Parameters Maximum Hazardous Waste [Volumetric Feed System lb/hr Y Y Feed Rate [Additional hazardous Flow Meter3 or waste feed limits shall be added as Mass Flow determined necessary based upon Meter as feed mechanism and/or applicable to the needs] feed mechanism] Maximum Total Pumpable Volumetric Flow Feed System lb/hr Hazardous Waste Mass Feed Rate Meter3 or Mass [Not applicable for Tier I or Tier I Flow Meter adjusted metals screening limits] Minimum Primary Combustion Thermocouple Primary °F Y N Chamber Temperature [or other device] Chamber Exit Minimum Secondary Combustion Thermocouple Secondary °F Y Y Chamber Temperature [or other device] Chamber Exit Maximum Secondary and/or Thermocouple Secondary °F Y Y Primary Combustion Chamber [or other device] Chamber Exit Temperature [Include if using Tier II/ III metals controls.] Maximum Flue Gas Temperature at Thermocouple At entrance to °F Y Y PM Control Device Inlet [Tier II/III [or other device] PM Control metals controls as applicable.] Device Maximum Combustion Gas Velocity Y Y Indicator [If condition is something than "maximum combustion gas velocity", write specific name of condition]
V.I.5 - Boiler/Industrial Furnace Permit Conditions, Monitoring and Automatic Waste Feed Cutoff Systems - Short-Term Operation [Use this for each new or modified Boiler/Industrial Furnace unit and in all columns with the appropriate information] Parameter Monitoring Basis1 Monitoring Device Device Location Operating Permit Limits Primary Combustion Chamber AWFCO Y/N2 Secondary Combustion Chamber AWFCO Y/N2 Pre-Trial Burn - Shakedown Trial Burn Post Burn Operating Parameters Maximum Hazardous Waste Feed Rate [Additional hazardous waste feed limits shall be added as determined necessary based upon feed mechanism and/or needs] [Volumetric Flow Meter3 or Mass Flow Meter as applicable to the feed mechanism] Feed System lb/hr Y Y Maximum Total Pumpable Hazardous Waste Mass Feed Rate [Not applicable for Tier I or Tier I adjusted metals screening limits] Volumetric Flow Meter3 or Mass Flow Meter Feed System lb/hr Minimum Primary Combustion Chamber Temperature Thermocouple [or other device] Primary Chamber Exit °F Y N Minimum Secondary Combustion Chamber Temperature Thermocouple [or other device] Secondary Chamber Exit °F Y Y Maximum Secondary and/or Primary Combustion Chamber Temperature [Include if using Tier II/ III metals controls.] Thermocouple [or other device] Secondary Chamber Exit °F Y Y Maximum Flue Gas Temperature at PM Control Device Inlet [Tier II/III metals controls as applicable.] Thermocouple [or other device] At entrance to PM Control Device °F Y Y Maximum Combustion Gas Velocity Indicator [If condition is something than "maximum combustion gas velocity", write specific name of condition] Y Y