Identify cable in line with DSR 01 018 identification of LV cables Prepare cable for testing at the location in which the neutral is being identified Confirm current status of cable by completing full test using approved test lamps Select an appropriate test point in which the signal can be injected via an approved instrument. This can be a street furniture or LV customer’s cut-out, equipment where the neutral can be clearly identified. Select an approved neutral conductor identifier and use the procedure in the relevant appendix to prove the neutral. Carry out identification of neutral conductor and clearly mark up the neutral core with identification tape. Repeat identification of the neutral to ensure the correct conductor is taped. Carry out jointing activities as per job requirements Once the circuit has been energised, carry out testing in accordance with DSR 01 016 Process on how to Ensure Customers have Correct Polarity and Phase Rotation.
Identify cable in line with DSR 01 018 identification of LV cables Prepare cable for testing at the location in which the neutral is being identified Confirm current status of cable by completing full test using approved test lamps Select an appropriate test point in which the signal can be injected via an approved instrument. This can be a customer’s cut-out, street furniture or LV equipment where the neutral can be clearly identified. Select an approved neutral conductor identifier and use the procedure in the relevant appendix to prove the neutral. Carry out identification of neutral conductor and clearly mark up the neutral core with identification tape. Repeat identification of the neutral to ensure the correct conductor is taped. Carry out jointing activities as per job requirements Once the circuit has been energised, carry out testing in accordance with DSR 01 016 Process on how to Ensure Customers have Correct Polarity and Phase Rotation.