pack) – 5 packs Data Sheet of Instrumentation rack - Server rack Sl.no Details Description Single Rittal Server Rack 1. Size 2000mm(H) x 600mm(W) x 1000mm(D) 2. Material type Sheet steel 3. Standard Color RAL 7035 4. Enclosure frame Epoxy Powder coated finish 5. Enclosure panels Epoxy Powder coated finish Front: toughened glass 6. Doors, front and rear Rear: perforated sheet steel, 78% perforated Mounting angles, mounting Zinc-plated frame and punched sections with 7. mounting flanges. Inter hole distance of 1U 482.6 mm (19˝) level, flat mounting angles on punched 8. 2 nos. sections with mounting flanges, front and rear, depth-variable. 482.6 mm (19˝) level, flat 2 nos. 9. mounting frames front and rear, depth-variable Provision for cable entry from to be provided with punched 10. false floor base plate 2 Nos., (bottom left & top 11. Cooling fan, 230 V AC 250 CFM right) 12. Side panels, lockable 2 Nos. 13. Side panel, plug-type, divided 1 Nos. 100mm Height Frame with 600mm x 1000mm clearance 14. Base mounting bracket frame for cable entry and to comply the specifications in IS-513 Comfort handle with security lock shall be provided for front and 15. rear doors. Internal Lighting to be provided with On/Off switch Accessories per Rack: 16. L-angle – 8 sets
pack) – 5 packs Data Sheet of Instrumentation rack - Server rack Sl.no Details Description 1. Size Single Rittal Server Rack 2000mm(H) x 600mm(W) x 1000mm(D) 2. Material type Sheet steel 3. Standard Color RAL 7035 4. Enclosure frame Epoxy Powder coated finish 5. Enclosure panels Epoxy Powder coated finish 6. Doors, front and rear Front: toughened glass Rear: perforated sheet steel, 78% perforated 7. Mounting angles, mounting frame and punched sections with mounting flanges. Inter hole distance of 1U Zinc-plated 8. 482.6 mm (19˝) level, flat mounting angles on punched sections with mounting flanges, front and rear, depth-variable. 2 nos. 9. 482.6 mm (19˝) level, flat mounting frames front and rear, depth-variable 2 nos. 10. Provision for cable entry from false floor to be provided with punched base plate 11. Cooling fan, 230 V AC 250 CFM 2 Nos., (bottom left & top right) 12. Side panels, lockable 2 Nos. 13. Side panel, plug-type, divided 1 Nos. 14. Base mounting bracket frame 100mm Height Frame with 600mm x 1000mm clearance for cable entry and to comply the specifications in IS-513 15. Comfort handle with security lock shall be provided for front and rear doors. Internal Lighting to be provided with On/Off switch 16. Accessories per Rack: L-angle – 8 sets