Tank failure 275 #5 & #6 (2) 275 Contained in room. B St. Thomas Hall #2 Fuel Oil Spill during transfer 28 Tank failure 275 #7 & #8 (2) 275 Towards floor drain. A Sullivan Hall #2 Fuel Oil Spill during transfer 28 #9 Tank failure 132 132 Ashwood Hall Towards ? Area A,B Diesel Spill during transfer 13 For fire pump generator Tank failure 275 #10 275 Outside of building A Maguire-Gabriel Garage #2 Fuel Oil Spill during transfer 28 #11 & #12 (2) 275 Tank failure 275 Contained in building B Maguire Windrim Hall #2 Fuel Oil Spill during transfer 28 – #13 500 Tank failure 500 Outside of building A Maguire Fine Arts East #2 Fuel Oil Spill during transfer 50 – 275 #14, #15 Tank failure (2) 275 A,B Contained in Building, Merion maintenance concrete floor Diesel /#2 Fuel Spill during transfer 28 garage Tank Failure 275 #16, 17 St. Mary’s Hall (2) 275 Above Ground C Spill During Transfer 28 UNDERGROUND STORAGE TANKS Double wall containment, Tank failure 7,000 #1 7,000 leak detection, overflow C Moore Hall #2 Fuel Oil protection, alarm during transfer 700 system... Double wall containment, #2 1000 Tank failure 1000 leak detection, overflow c Moore Hall Diesel Spill during transfer protection, system Double wall containment, Tank failure 10,000 #3 10,000 leak detection, overflow C Power Plant #2 Fuel Oil during transfer 1,000 protection, alarm system. #4 Tank Failure 10,000 10,000 leak detection, overflow C Maguire O’Pake – #2 Fuel Oil protection, alarm system. Sports Spill during transfer 1,000 Tank Failure 4,000 #5 4,000 leak detection, overflow C Maguire Merion Hall #2 Fuel Oil protection, alarm system. – Spill during transfer 400
#5 & #6 St. Thomas Hall (2) 275 #2 Fuel Oil Tank failure 275 Contained in room. B Spill during transfer 28 #7 & #8 Sullivan Hall (2) 275 #2 Fuel Oil Tank failure 275 Towards floor drain. A Spill during transfer 28 #9 Ashwood Hall For fire pump generator 132 Diesel Tank failure 132 Towards ? Area A,B Spill during transfer 13 #10 Maguire-Gabriel Garage 275 #2 Fuel Oil Tank failure 275 Outside of building A Spill during transfer 28 #11 & #12 Maguire – Windrim Hall (2) 275 #2 Fuel Oil Tank failure Spill during transfer 275 28 Contained in building B #13 Maguire – Fine Arts East 500 #2 Fuel Oil Tank failure Spill during transfer 500 50 Outside of building A #14, #15 Merion maintenance garage (2) 275 Diesel /#2 Fuel Tank failure 275 Contained in Building, concrete floor A,B Spill during transfer 28 #16, 17 St. Mary’s Hall (2) 275 Tank Failure 275 Above Ground C Spill During Transfer 28 UNDERGROUND STORAGE TANKS #1 Moore Hall 7,000 #2 Fuel Oil Tank failure 7,000 Double wall containment, leak detection, overflow protection, alarm system... C during transfer 700 #2 Moore Hall 1000 Diesel Tank failure Spill during transfer 1000 Double wall containment, leak detection, overflow protection, system c #3 Power Plant 10,000 #2 Fuel Oil Tank failure 10,000 Double wall containment, leak detection, overflow protection, alarm system. C during transfer 1,000 #4 Maguire – O’Pake Sports 10,000 #2 Fuel Oil Tank Failure 10,000 leak detection, overflow protection, alarm system. C Spill during transfer 1,000 #5 Maguire – Merion Hall 4,000 #2 Fuel Oil Tank Failure 4,000 leak detection, overflow protection, alarm system. C Spill during transfer 400