If no, no further action is necessary. Will the project include If yes, AST must have: removing or installing any Secondary containment greater than or equal to Aboveground Storage Tanks 110% of the tank capacity; (ASTs)? A minimum of a 3 gallon spill bucket at the fill pipe; The tank capacity and type of fuel identified on the tank near the fill pipe; All fuel lines will be protected by secondary containment Tanks must be added/removed from the SPCC plan. If no, no further action is necessary. Will the project be adding or If yes, all oil containing equipment with a capacity removing any equipment that of 55 gallons or more are subject to the Federal Oil contains 55 gallons or more of oil Spill Prevention. Additions and subtractions must (e.g. elevators, transformers, be made to the SPCC plan through coordination switches)? with the Project Manager. Oil from equipment being removed must be tested for PCBs before disposal. If no, no further action is necessary. Soils Yes No Required Activities Will the project include the If yes, Contractors shall not sample or remove any excavation of any soil at UNH soils off-site without prior approval from the UNH property? Project Manager. The Project Manager must work with an Environmental Contractor involving contaminated soil or potentially contaminated soil to meet regulatory guidelines. Impacted soils kept onsite must remain covered at all times. If no, no further action is necessary. Will the project include the If yes, the Contractor shall be responsible for addition of any fill material at providing clean fill. All volumes and the origin of UNH property? the soil shall be documented. If no, no further action is necessary. Stormwater Yes No Required Activities Will the project disturb more If yes, the project is required to get a Stormwater than one (1) acre of land? Discharge permit from the CT DEEP If no, no formal actions required, however runoff controls should be put in place to limit runoff (e.g. hay bales). Radiation Safety Yes No Required Activities Will the project include If yes, contact the Project Manager and work with removing of exit signs that the disposal contractor to ensure proper radiation contain tritium as their power safety and disposal procedures are followed.
If no, no further action is necessary. Will the project include removing or installing any Aboveground Storage Tanks (ASTs)? If yes, AST must have: Secondary containment greater than or equal to 110% of the tank capacity; A minimum of a 3 gallon spill bucket at the fill pipe; The tank capacity and type of fuel identified on the tank near the fill pipe; All fuel lines will be protected by secondary containment Tanks must be added/removed from the SPCC plan. If no, no further action is necessary. Will the project be adding or removing any equipment that contains 55 gallons or more of oil (e.g. elevators, transformers, switches)? If yes, all oil containing equipment with a capacity of 55 gallons or more are subject to the Federal Oil Spill Prevention. Additions and subtractions must be made to the SPCC plan through coordination with the Project Manager. Oil from equipment being removed must be tested for PCBs before disposal. If no, no further action is necessary. Soils Yes No Required Activities Will the project include the excavation of any soil at UNH property? If yes, Contractors shall not sample or remove any soils off-site without prior approval from the UNH Project Manager. The Project Manager must work with an Environmental Contractor involving contaminated soil or potentially contaminated soil to meet regulatory guidelines. Impacted soils kept onsite must remain covered at all times. If no, no further action is necessary. Will the project include the addition of any fill material at UNH property? If yes, the Contractor shall be responsible for providing clean fill. All volumes and the origin of the soil shall be documented. If no, no further action is necessary. Stormwater Yes No Required Activities Will the project disturb more than one (1) acre of land? If yes, the project is required to get a Stormwater Discharge permit from the CT DEEP If no, no formal actions required, however runoff controls should be put in place to limit runoff (e.g. hay bales). Radiation Safety Yes No Required Activities Will the project include removing of exit signs that contain tritium as their power If yes, contact the Project Manager and work with the disposal contractor to ensure proper radiation safety and disposal procedures are followed.