electrical possible electrocution to impact to electrical equipment mobile equipment to Jamboree staff or attendees. (holes in tent roofs, etc.). production moisture. facilities and Ensure all electrical components temporary are protected by an approved electrical feeds Ground Fault Circuit Interrupter are completed (GFCI) device. by qualified personnel. All electrical equipment, including temporary wiring, is installed so as to minimize potential exposure to precipitation or runoff (overhead wiring runs, etc.). All electrical equipment, including temporary wiring, is Food installed so as to minimize production potential exposure to food activities cause Severe injuries such as electrical production water (overhead water to shock, electrical burns or I D wiring runs, etc.). Same I E contact possible electrocution to Same energized Jamboree staff or attendees. All electrical supplies to food electrical production facilities protected by components. approved Ground Fault Circuit Interrupter (GFCI) devices. Secondary electrical connections should be inspected daily by If damage is An excessive qualified personnel to look for noted, power current draw signs of overheating, arcing or should be Secondary electrical connections occurs on a similar damage. immediately Electrical overheating, short (multiplugs, power strips, etc.) secondary cut to the circuiting or arcing of are overloaded causing electrical I D Tripped circuit breakers should secondary I E components could lead to an overheating, short circuiting or supply be thoroughly investigated by electrical electrical fire. arcing to occur. (multiplug, qualified personnel to determine connection power strip, the cause PRIOR to reenergizing until the issue etc.). the line. can be corrected.
electrical equipment to moisture. possible electrocution to Jamboree staff or attendees. impact to electrical equipment (holes in tent roofs, etc.). Ensure all electrical components are protected by an approved Ground Fault Circuit Interrupter (GFCI) device. All electrical equipment, including temporary wiring, is installed so as to minimize potential exposure to precipitation or runoff (overhead wiring runs, etc.). mobile production facilities and temporary electrical feeds are completed by qualified personnel. Same Food production activities cause water to contact energized electrical components. Severe injuries such as electrical shock, electrical burns or possible electrocution to Jamboree staff or attendees. I D All electrical equipment, including temporary wiring, is installed so as to minimize potential exposure to food production water (overhead wiring runs, etc.). All electrical supplies to food production facilities protected by approved Ground Fault Circuit Interrupter (GFCI) devices. Same I E Secondary electrical connections (multiplugs, power strips, etc.) are overloaded causing overheating, short circuiting or arcing to occur. An excessive current draw occurs on a secondary electrical supply (multiplug, power strip, etc.). Electrical overheating, short circuiting or arcing of components could lead to an electrical fire. I D Secondary electrical connections should be inspected daily by qualified personnel to look for signs of overheating, arcing or similar damage. Tripped circuit breakers should be thoroughly investigated by qualified personnel to determine the cause PRIOR to reenergizing the line. If damage is noted, power should be immediately cut to the secondary electrical connection until the issue can be corrected. I E