> 65,000 BtuH and <135,000 BtuH N/A 11.2 EER / 11.4 IEER > 135,000 BtuH and < 240,000 BtuH N/A 11.0 EER / 11.2 IEER N/A > 240,000 BtuH and < 760,000 BtuH 10.0 EER / 10.1 IEER (IPLV for units with capacity-modulation only) N/A > 760,000 BtuH 9.7 EER / 9.8 IEER (IPLV for units with capacity-modulation only) Water-Source and Evaporatively-Cooled Air Conditioners < 65,000 BtuH 12.1 EER / 12.3 IEER N/A > 65,000 BtuH and <135,000 BtuH 11.5 EER / 11.7 IEER N/A > 135,000 BtuH and < 240,000 BtuH 11.0 EER / 11.2 IEER N/A > 240,000 BtuH 11.0 EER / 11.1 IEER N/A Air-Source Heat Pumps < 65,000 BtuH 13 SEER 7.7 HSPF > 65,000 BtuH and <135,000 BtuH 3.3 COP 11.0 EER / 11.2 IEER > 135,000 BtuH and < 240,000 BtuH 3.2 COP 10.6 EER / 10.7 IEER > 240,000 BtuH (IPLV for units with 3.2 COP 9.5 EER / 9.6 IEER capacity-modulation only) Water-Source Heat Pumps < 17,000 BtuH 4.2 COP 11.2 EER > 17,000 BtuH and < 65,000 BtuH 4.2 COP 12.0 EER Ground Water Source Heat Pumps < 135,000 BtuH 3.6 COP 16.2 EER Ground Source Heat Pumps < 135,000 BtuH 3.1 COP 13.4 EER Packaged Terminal Systems PTAC (cooling) N/A 12.5 - (0.213 x Cap / 1000) EER PTHP 3.2 - (0.026 x Cap / 1000) 12.3 - (0.213 x Cap / 1000) EER COP Note:
> 65,000 BtuH and <135,000 BtuH 11.2 EER / 11.4 IEER N/A > 135,000 BtuH and < 240,000 BtuH 11.0 EER / 11.2 IEER N/A > 240,000 BtuH and < 760,000 BtuH (IPLV for units with capacity-modulation only) 10.0 EER / 10.1 IEER N/A > 760,000 BtuH (IPLV for units with capacity-modulation only) 9.7 EER / 9.8 IEER N/A Water-Source and Evaporatively-Cooled Air Conditioners < 65,000 BtuH 12.1 EER / 12.3 IEER N/A > 65,000 BtuH and <135,000 BtuH 11.5 EER / 11.7 IEER N/A > 135,000 BtuH and < 240,000 BtuH 11.0 EER / 11.2 IEER N/A > 240,000 BtuH 11.0 EER / 11.1 IEER N/A Air-Source Heat Pumps < 65,000 BtuH 13 SEER 7.7 HSPF > 65,000 BtuH and <135,000 BtuH 11.0 EER / 11.2 IEER 3.3 COP > 135,000 BtuH and < 240,000 BtuH 10.6 EER / 10.7 IEER 3.2 COP > 240,000 BtuH (IPLV for units with capacity-modulation only) 9.5 EER / 9.6 IEER 3.2 COP Water-Source Heat Pumps < 17,000 BtuH 11.2 EER 4.2 COP > 17,000 BtuH and < 65,000 BtuH 12.0 EER 4.2 COP Ground Water Source Heat Pumps < 135,000 BtuH 16.2 EER 3.6 COP Ground Source Heat Pumps < 135,000 BtuH 13.4 EER 3.1 COP Packaged Terminal Systems PTAC (cooling) 12.5 - (0.213 x Cap / 1000) EER N/A PTHP 12.3 - (0.213 x Cap / 1000) EER 3.2 - (0.026 x Cap / 1000) COP Note: