Eye bolts are normally used to secure high level access Further Info: equipment and are normally found next to windows in buildings. The eyebolt must conform to BS EN 795 and be CE marked. Fire Alarm SWP: Work Equipment and Fire Safety Competency Responsible Person and Competent Person Requirement: Inspection RP Function test – Requirement: CP Testing and inspection (Service / Maintenance) – RP Layperson – Qualification CP Member of Institute of fire engineers or a electrician – Requirement: specialised in fire systems with British Standard 54 RP Weekly (Different activation point) – Frequency: CP - 12 Monthly RP Weekly (Different activation point) – Best Practice: CP - 12 Monthly Information Exchange RP Quarterly – Upload Frequency: CP - 12 Monthly Further Info: Fire Alarm test and activation of call point(s) (red break glass box, to ensure a 100% check is carried out of all activation call points over a 12 month period. Fire Extinguishers SWP: Work Equipment and Fire Safety Competency Responsible Person and Competent Person Requirement: Inspection RP Charge check – Requirement: CP Testing and inspection (Service / Maintenance) – RP Layperson – Qualification CP Certification to Part 1 BAFE scheme SP101 / ST104 – Requirement: and FETA certification RP Monthly – Frequency: CP 12 Monthly – CP 5 12 Monthly (Discharge) – RP Monthly – Best Practice: CP 12 Monthly – CP 5 12 Monthly (Discharge) – RP Quarterly – Information Exchange CP 12 Monthly – Upload Frequency: CP 5 12 Monthly (Discharge) –
Further Info: Eye bolts are normally used to secure high level access equipment and are normally found next to windows in buildings. The eyebolt must conform to BS EN 795 and be CE marked. Fire Alarm SWP: Work Equipment and Fire Safety Competency Requirement: Responsible Person and Competent Person Inspection Requirement: RP – Function test CP – Testing and inspection (Service / Maintenance) Qualification Requirement: RP – Layperson CP – Member of Institute of fire engineers or a electrician specialised in fire systems with British Standard 54 Frequency: RP – Weekly (Different activation point) CP - 12 Monthly Best Practice: RP – Weekly (Different activation point) CP - 12 Monthly Information Exchange Upload Frequency: RP – Quarterly CP - 12 Monthly Further Info: Fire Alarm test and activation of call point(s) (red break glass box, to ensure a 100% check is carried out of all activation call points over a 12 month period. Fire Extinguishers SWP: Work Equipment and Fire Safety Competency Requirement: Responsible Person and Competent Person Inspection Requirement: RP – Charge check CP – Testing and inspection (Service / Maintenance) Qualification Requirement: RP – Layperson CP – Certification to Part 1 BAFE scheme SP101 / ST104 and FETA certification Frequency: RP – Monthly CP – 12 Monthly CP – 5 12 Monthly (Discharge) Best Practice: RP – Monthly CP – 12 Monthly CP – 5 12 Monthly (Discharge) Information Exchange Upload Frequency: RP – Quarterly CP – 12 Monthly CP – 5 12 Monthly (Discharge)