a. Certification by the manufacturer that the busway conforms to the requirements of the drawings and specifications. b. Certification by the Contractor that the busway has been properly installed, adjusted, and tested. 1.5 APPLICABLE PUBLICATIONS A. Publications listed below (including amendments, addenda, revisions, supplement and errata) form a part of this specification to the extent referenced. Publications are referenced in the text by the basic designation only. B. International Code Council (ICC): IBC-15 International Building Code C. National Electrical Manufacturers Association (NEMA): BU 1.1-10 General Instructions for Handling, Installation, Operation and Maintenance of Busway Rated 600 Volts or Less BU 1.2-13 Application Information for Busway Rated 600 Volts or Less D. National Fire Protection Association (NFPA): 70-17 National Electrical Code (NEC) E. Underwriters Laboratories Inc. (UL): 857-09 Busways PART 2 - PRODUCTS 2.1 MATERIAL A. Busway shall be in accordance with NEMA and UL. B. Busway shall be rated as shown on the drawings. C. Busway have the following features: SPEC WRITER NOTE: A/E shall show on drawings the type of busway, feeder type or plug-in type. //1. For indoor locations; //plug-in// //feeder// type, totally enclosed and moisture resistant.// //2. For outdoor locations; feeder type only, totally enclosed and listed for outdoor use. Plug-in busway is not allowed for outdoor installation.// 3. Short circuit current rating shall not be less than 42,000 A, or as required to withstand the available fault current shown on the drawings, whichever is higher.
a. Certification by the manufacturer that the busway conforms to the requirements of the drawings and specifications. b. Certification by the Contractor that the busway has been properly installed, adjusted, and tested. 1.5 APPLICABLE PUBLICATIONS A. Publications listed below (including amendments, addenda, revisions, supplement and errata) form a part of this specification to the extent referenced. Publications are referenced in the text by the basic designation only. B. International Code Council (ICC): IBC-15 International Building Code C. National Electrical Manufacturers Association (NEMA): BU 1.1-10 General Instructions for Handling, Installation, Operation and Maintenance of Busway Rated 600 Volts or Less BU 1.2-13 Application Information for Busway Rated 600 Volts or Less D. National Fire Protection Association (NFPA): 70-17 National Electrical Code (NEC) E. Underwriters Laboratories Inc. (UL): 857-09 Busways PART 2 - PRODUCTS 2.1 MATERIAL A. Busway shall be in accordance with NEMA and UL. B. Busway shall be rated as shown on the drawings. C. Busway have the following features: SPEC WRITER NOTE: A/E shall show on drawings the type of busway, feeder type or plug-in type. //1. For indoor locations; //plug-in// //feeder// type, totally enclosed and moisture resistant.// //2. For outdoor locations; feeder type only, totally enclosed and listed for outdoor use. Plug-in busway is not allowed for outdoor installation.// 3. Short circuit current rating shall not be less than 42,000 A, or as required to withstand the available fault current shown on the drawings, whichever is higher.