substances is provided and protection and used by service providers. alcohol hand gel. Prior to occupancy days Criterion 1.4.2.4 PA Low The service has fully furnished and fitted out the building. Hot is not yet Provide evidence Water and power are connected, however, hot water has available. Since the that hot water The physical environment not been started as yet. draft report, the temperatures have minimises risk of harm, provider has reported been monitored and promotes safe mobility, aids that plumbers have recorded, at 45 independence and is adjusted the hot water degrees Celsius or appropriate to the needs of temperatures and below. the consumer/group. they will ensure that all hot taps are at 45°C to occupancy days Criterion 1.4.2.6 PA Low The entrance to the facility is complete with a covered The external Ensure that a safe portico and tar sealed drive and parking spaces. The environment is external environment Consumers are provided with dementia unit has two courtyards. The internal courtyard incomplete including is provided for all safe and accessible external has pathways and two raised garden beds; the courtyard at lawns, gardens and residents, including areas that meet their needs. the end of the building is not fully fenced or secure. The secure courtyard the secure external outdoor garden environment is not fully completed. fencing at the end of courtyard at the end the dementia unit. of the dementia unit. Prior to occupancy days Criterion 1.4.7.3 PA Low The Aspiring Enliven building is now complete. A certificate The service does not Provide evidence for public use has been issued. The fire service has been have an approved fire that the facility has Where required by legislation contacted for sign off of an approved evacuation scheme evacuation scheme. been issued with a there is an approved (emails sighted). New Zealand Fire evacuation plan. Service approved fire evacuation scheme.
substances is provided and used by service providers. protection and alcohol hand gel. Prior to occupancy days Criterion 1.4.2.4 The physical environment minimises risk of harm, promotes safe mobility, aids independence and is appropriate to the needs of the consumer/group. PA Low The service has fully furnished and fitted out the building. Water and power are connected, however, hot water has not been started as yet. Hot is not yet available. Since the draft report, the provider has reported that plumbers have adjusted the hot water temperatures and they will ensure that all hot taps are at 45°C Provide evidence that hot water temperatures have been monitored and recorded, at 45 degrees Celsius or below. to occupancy days Criterion 1.4.2.6 Consumers are provided with safe and accessible external areas that meet their needs. PA Low The entrance to the facility is complete with a covered portico and tar sealed drive and parking spaces. The dementia unit has two courtyards. The internal courtyard has pathways and two raised garden beds; the courtyard at the end of the building is not fully fenced or secure. The outdoor garden environment is not fully completed. The external environment is incomplete including lawns, gardens and secure courtyard fencing at the end of the dementia unit. Ensure that a safe external environment is provided for all residents, including the secure external courtyard at the end of the dementia unit. Prior to occupancy days Criterion 1.4.7.3 Where required by legislation there is an approved evacuation plan. PA Low The Aspiring Enliven building is now complete. A certificate for public use has been issued. The fire service has been contacted for sign off of an approved evacuation scheme (emails sighted). The service does not have an approved fire evacuation scheme. Provide evidence that the facility has been issued with a New Zealand Fire Service approved fire evacuation scheme.