Sudden Pressure Relaying identified in Section 4.2, time-based or time-based or time-based or whether four or more Facilities. performance-based performance-based performance-based Component Types are maintenance, or a maintenance, or a maintenance, or a being addressed by combination of both combination of both combination of both. time-based or (Part 1.1). (Part 1.1). (Part 1.1). performance-based OR maintenance, or a The PSMP combination of both entity’s failed to include the (Part 1.1). applicable monitoring OR attributes applied to The PSMP entity’s each Component Type failed to include consistent with the applicable station maintenance intervals batteries in a specified in Tables 1-1 program (Part through 1-5, Table 2, 1.1). Table 3, Tables 4-1 through 4-2, and Table 5 where monitoring is used to extend the maintenance intervals beyond those specified for unmonitored Components (Part 1.2). R2. Each Transmission Owner, Generator Owner, and The entity uses NA The entity uses The entity uses PRC-005-5 Distribution Provider that uses performance-based performance-based performance-based performance-based maintenance intervals in its PSMP shall follow the maintenance intervals maintenance intervals maintenance intervals procedure established in PRC-005 Attachment A to in its PSMP but failed in its PSMP but failed in its PSMP but: establish and maintain its performance-based to reduce Countable to reduce Countable Failed to establish intervals. Events to no more Events to no more than the technical than 4% within three 4% within four years. justification years. described within Requirement R2 for the initial use of the performance-based PSMP OR Failed to reduce Countable Events to no more than
Sudden Pressure Relaying identified in Section 4.2, Facilities. time-based or performance-based maintenance, or a combination of both (Part 1.1). time-based or performance-based maintenance, or a combination of both (Part 1.1). time-based or performance-based maintenance, or a combination of both. (Part 1.1). OR The entity’s PSMP failed to include the applicable monitoring attributes applied to each Component Type consistent with the maintenance intervals specified in Tables 1-1 through 1-5, Table 2, Table 3, Tables 4-1 through 4-2, and Table 5 where monitoring is used to extend the maintenance intervals beyond those specified for unmonitored Components (Part 1.2). whether four or more Component Types are being addressed by time-based or performance-based maintenance, or a combination of both (Part 1.1). OR The entity’s PSMP failed to include applicable station batteries in a program (Part 1.1). PRC-005-5 R2. Each Transmission Owner, Generator Owner, and Distribution Provider that uses performance-based maintenance intervals in its PSMP shall follow the procedure established in PRC-005 Attachment A to establish and maintain its performance-based intervals. The entity uses performance-based maintenance intervals in its PSMP but failed to reduce Countable Events to no more than 4% within three years. NA The entity uses performance-based maintenance intervals in its PSMP but failed to reduce Countable Events to no more than 4% within four years. The entity uses performance-based maintenance intervals in its PSMP but: Failed to establish the technical justification described within Requirement R2 for the initial use of the performance-based PSMP OR Failed to reduce Countable Events to no more than