Chiller 2 15 AI 12 Hours 3 days N/A Percent Load Minutes Chiller 2 KW 15 AI 12 Hours 3 days N/A Consumption Minutes Chiller 2 15 AI 12 Hours 3 days N/A Tonnage Minutes Primary Loop 15 Decoupler AI 12 Hours 3 days N/A Minutes Flow Primary Loop 15 AI 12 Hours 3 days N/A Flow Minutes Primary Loop 15 Supply AI 12 Hours 3 days N/A Minutes Temperature Secondary Loop 15 ±5% 10 AI 12 3 days P Differential Minutes from SP Min Pressure Secondary 15 AI 12 Hours 3 days N/A Loop Flow Minutes Secondary 15 Loop Supply AI 12 Hours 3 days N/A Minutes Temperature Secondary 15 Loop Return AI 12 3 days N/A Minutes Temperature Secondary 15 AI 12 3 days N/A Loop Tonnage Minutes Status Primary Loop 30 DI COV 12 Hours 3 days C <> Pump 1 Status min Command Status Primary Loop 30 DI COV 12 3 days C <> Pump 2 Status min Command Secondary Status 30 Loop Pump 1 DI COV 12 3 days C <> min Status Command Secondary Status 30 Loop Pump 2 DI COV 12 3 days C <> min Status Command Status Chiller 1 30 DI COV 12 Hours 3 days C <> Status min Command Chiller 1 Evaporator DI COV 12 Hours 3 days N/A Iso-Valve
Chiller 2 Percent Load AI 15 Minutes 12 Hours 3 days N/A Chiller 2 KW Consumption AI 15 Minutes 12 Hours 3 days N/A Chiller 2 Tonnage AI 15 Minutes 12 Hours 3 days N/A Primary Loop Decoupler Flow AI 15 Minutes 12 Hours 3 days N/A Primary Loop Flow AI 15 Minutes 12 Hours 3 days N/A Primary Loop Supply Temperature AI 15 Minutes 12 Hours 3 days N/A Secondary Loop Differential Pressure AI 15 Minutes 12 3 days P ±5% from SP 10 Min Secondary Loop Flow AI 15 Minutes 12 Hours 3 days N/A Secondary Loop Supply Temperature AI 15 Minutes 12 Hours 3 days N/A Secondary Loop Return Temperature AI 15 Minutes 12 3 days N/A Secondary Loop Tonnage AI 15 Minutes 12 3 days N/A Primary Loop Pump 1 Status DI COV 12 Hours 3 days C Status <> Command 30 min Primary Loop Pump 2 Status DI COV 12 3 days C Status <> Command 30 min Secondary Loop Pump 1 Status DI COV 12 3 days C Status <> Command 30 min Secondary Loop Pump 2 Status DI COV 12 3 days C Status <> Command 30 min Chiller 1 Status DI COV 12 Hours 3 days C Status <> Command 30 min Chiller 1 Evaporator Iso-Valve DI COV 12 Hours 3 days N/A