XX ppm carbon monoxide (CO) by volume on a dry corrected to 3% O2, as a 30-day rolling average. OR output limits (option) XX lb of PM/MMBtu of steam output; or XX lb of PM/MWh; or XX lb of TSM/ of steam output; or XX lb of TSM/MWh; and XX lb of hydrogen chloride (HCl)/MMBtu of steam output; or XX lb HCl/MWh; and XX lb of mercury (Hg)/MMBtu of steam output; or XX lb Hg/MWh; and XX lb CO/MMBtu of steam output, 3-run average; or XX lb CO/MWh, 3-run average Boilers subject to emission standards in Table 2 shall also meet the work practice standards identified in Table 3 during startup and shutdown of the unit and the tune-up requirements, as applicable, in Table 3. Boilers not subject to emission standards shall meet the tune-up requirements identified in Table 3 as applicable to the unit. The permittee demonstrate compliance with the limits published in the final amendments to Subpart DDDDD, as required by the subpart. b. OAC rule 3745-110-03 for very Emissions of nitrogen oxides (NOx) shall not large boilers (>250 MMBtu/hr); exceed: large boilers (>100 and 250 ≤ 0.30 lbs/MMBtu for coal-fired units; or MMBtu/hr); and mid-sized boilers (>50 MMBtu/hr and 100 ≤ 0.23 for residual oil-fired units; or MMBtu) 0.12 for distillate oil-fired units; or (see applicability for existing 0.10 lbs/MMBtu for gas only-fired units. sources in OAC & new units issued a PTI after 1/1/08) c. OAC rule 3745-110-03(A) for Must perform an annual tune-up and maintain small boilers >20 and 50 records of the date and person conducting it. ≤ MMBtu/hr
XX ppm carbon monoxide (CO) by volume on a dry corrected to 3% O2, as a 30-day rolling average. OR output limits (option) XX lb of PM/MMBtu of steam output; or XX lb of PM/MWh; or XX lb of TSM/ of steam output; or XX lb of TSM/MWh; and XX lb of hydrogen chloride (HCl)/MMBtu of steam output; or XX lb HCl/MWh; and XX lb of mercury (Hg)/MMBtu of steam output; or XX lb Hg/MWh; and XX lb CO/MMBtu of steam output, 3-run average; or XX lb CO/MWh, 3-run average Boilers subject to emission standards in Table 2 shall also meet the work practice standards identified in Table 3 during startup and shutdown of the unit and the tune-up requirements, as applicable, in Table 3. Boilers not subject to emission standards shall meet the tune-up requirements identified in Table 3 as applicable to the unit. The permittee demonstrate compliance with the limits published in the final amendments to Subpart DDDDD, as required by the subpart. b. OAC rule 3745-110-03 for very large boilers (>250 MMBtu/hr); large boilers (>100 and ≤ 250 MMBtu/hr); and mid-sized boilers (>50 MMBtu/hr and ≤ 100 MMBtu) (see applicability for existing sources in OAC & new units issued a PTI after 1/1/08) Emissions of nitrogen oxides (NOx) shall not exceed: 0.30 lbs/MMBtu for coal-fired units; or 0.23 for residual oil-fired units; or 0.12 for distillate oil-fired units; or 0.10 lbs/MMBtu for gas only-fired units. c. OAC rule 3745-110-03(A) for small boilers >20 and ≤ 50 MMBtu/hr Must perform an annual tune-up and maintain records of the date and person conducting it.