Base Frame Heavy Duty Fabricated Steel – Circuit Breaker Type 3 pole MCCB – Fuel capacity For a running time minimum – of 24 hours at maximum 70% Load Casing - Generator should be supplied with Casing of galvanised steel with double point lifting capability, adapted to an external use, under open area, casing should have openable panel-doors from all sides, observation window for the generator’s control main board. Emergency stop button accessible from the outside Changeover Panel - Must correspond to the generator set Alternator: 3 phase output Voltage Regulator + or 1% – Isolation class H Type: IP 23 Connection Type - Star: 50 Hz Efficiency minimum 90% Noise level from 1m distance maximum 85 dBA
Base Frame – Heavy Duty Fabricated Steel Circuit Breaker Type – 3 pole MCCB Fuel capacity – For a running time minimum of 24 hours at maximum 70% Load Casing - Generator should be supplied with Casing of galvanised steel with double point lifting capability, adapted to an external use, under open area, casing should have openable panel-doors from all sides, observation window for the generator’s control main board. Emergency stop button accessible from the outside Changeover Panel - Must correspond to the generator set Alternator: 3 phase output Voltage Regulator + or – 1% Isolation class H Type: IP 23 Connection Type - Star: 50 Hz Efficiency minimum 90% Noise level from 1m distance maximum 85 dBA