b. Remote piping system (overhead or below floor) // with pump //. 6. Extended discharge chute. 7. Extended stand. 8. Pulp level detection. 9. Bus Communication. SPEC WRITER NOTE: Select size according to anticipated use; actual use should not exceed 90% of capacity of unit. F. Size: Manufacturer rates waste-processing capacity at not less than // 272 kg (600 lb) // 317 kg (700 lb) // 408 kg (900 lb) // of waste per hour. SPEC WRITER NOTES: 1. Symbols below correspond with "Room Equipment Guide" identification system. Verify project requirements before specifying equipment that deviates from "Room Equipment Guide." 2. Edit symbols to coordinate with identification shown on drawings. G. Pulper/Water Extractor Equipment Nomenclature: SYMBOL PULPER/WATER EXTRACTOR DESCRIPTION Cover Trough connection K2401 Slurry pump Control panel Extractor Feed hood Slurry pump K2402 Control panel Extractor Feed hood and tray Slurry pump K2403 Control panel Extractor Cover Trough connection K2404 Slurry pump Control panel Remote extractor
b. Remote piping system (overhead or below floor) // with pump //. 6. Extended discharge chute. 7. Extended stand. 8. Pulp level detection. 9. Bus Communication. SPEC WRITER NOTE: Select size according to anticipated use; actual use should not exceed 90% of capacity of unit. F. Size: Manufacturer rates waste-processing capacity at not less than // 272 kg (600 lb) // 317 kg (700 lb) // 408 kg (900 lb) // of waste per hour. SPEC WRITER NOTES: 1. Symbols below correspond with "Room Equipment Guide" identification system. Verify project requirements before specifying equipment that deviates from "Room Equipment Guide." 2. Edit symbols to coordinate with identification shown on drawings. G. Pulper/Water Extractor Equipment Nomenclature: SYMBOL PULPER/WATER EXTRACTOR DESCRIPTION K2401 Cover Trough connection Slurry pump Control panel Extractor K2402 Feed hood Slurry pump Control panel Extractor K2403 Feed hood and tray Slurry pump Control panel Extractor K2404 Cover Trough connection Slurry pump Control panel Remote extractor