SECTION 26 05 53 IDENTIFICATION FOR ELECTRICAL SYSTEMS BASED ON DFD MASTER ELECTRICAL SPEC DATED 6/22/17 This section has been written to cover most (but not all) situations that you will encounter. Depending on the requirements of your specific project, you may have to add material, delete items, or modify what is currently written. The Division of Facilities Development expects changes and comments from you. The consultant is to review the requirements of the project and include all aspects of identification necessary. This is to include a determination of the appropriate items as they apply to the project. PART 1 - GENERAL SCOPE The work under this section includes the products and execution requirements relating to labeling of power, control, signaling and fire alarm wiring. Further, this section includes the installation of labels, nameplates, and directories for electrical boxes, wiring devices, and equipment. Included are the following topics: PART 1 - GENERAL Scope Related Work Submittals PART 2 - PRODUCTS Materials PART 3 - EXECUTION General Box Identification Communication Conduit Labeling Power, Control and Signal Wire Identification Wiring Device Identification Support Wire Identification Nameplate Engraving for Electrical Equipment Panelboard Directories RELATED WORK Applicable provisions of Division 1 shall govern work under this section. Section 26 05 19 Low-Voltage Electrical Power Conductors and Cables – Section 26 05 23 Control-Voltage Electrical Power Cables – Section 01 91 01 or 01 91 02 Commissioning Process – SUBMITTALS Include schedule for nameplates. Prior to installation, the Contractor shall provide samples of all label types planned for the project. These samples shall include examples of the lettering to be used. Samples shall be mounted on 8 1/2” x 11” sheets annotated, explaining their purposed use. PART 2 - PRODUCTS MATERIALS Labels: All labels shall be permanent, and machine generated. NO HANDWRITTEN OR LABELS ARE ALLOWED. Wire Labels: All wiring labels shall be white/transparent vinyl or vinyl-cloth, self-laminating, wraparound type. Flag type labels are not allowed. The labels shall be of adequate size to accommodate the circumference of the cable being labeled and properly self-laminate over the full extent of the printed area of the label. Tape (wiring phase identification only): Scotch #35 tape in appropriate colors for system voltage and phase.
SECTION 26 05 53 IDENTIFICATION FOR ELECTRICAL SYSTEMS BASED ON DFD MASTER ELECTRICAL SPEC DATED 6/22/17 This section has been written to cover most (but not all) situations that you will encounter. Depending on the requirements of your specific project, you may have to add material, delete items, or modify what is currently written. The Division of Facilities Development expects changes and comments from you. The consultant is to review the requirements of the project and include all aspects of identification necessary. This is to include a determination of the appropriate items as they apply to the project. PART 1 - GENERAL SCOPE The work under this section includes the products and execution requirements relating to labeling of power, control, signaling and fire alarm wiring. Further, this section includes the installation of labels, nameplates, and directories for electrical boxes, wiring devices, and equipment. Included are the following topics: PART 1 - GENERAL Scope Related Work Submittals PART 2 - PRODUCTS Materials PART 3 - EXECUTION General Box Identification Communication Conduit Labeling Power, Control and Signal Wire Identification Wiring Device Identification Support Wire Identification Nameplate Engraving for Electrical Equipment Panelboard Directories RELATED WORK Applicable provisions of Division 1 shall govern work under this section. Section 26 05 19 – Low-Voltage Electrical Power Conductors and Cables Section 26 05 23 – Control-Voltage Electrical Power Cables Section 01 91 01 or 01 91 02 – Commissioning Process SUBMITTALS Include schedule for nameplates. Prior to installation, the Contractor shall provide samples of all label types planned for the project. These samples shall include examples of the lettering to be used. Samples shall be mounted on 8 1/2” x 11” sheets annotated, explaining their purposed use. PART 2 - PRODUCTS MATERIALS Labels: All labels shall be permanent, and machine generated. NO HANDWRITTEN OR LABELS ARE ALLOWED. Wire Labels: All wiring labels shall be white/transparent vinyl or vinyl-cloth, self-laminating, wraparound type. Flag type labels are not allowed. The labels shall be of adequate size to accommodate the circumference of the cable being labeled and properly self-laminate over the full extent of the printed area of the label. Tape (wiring phase identification only): Scotch #35 tape in appropriate colors for system voltage and phase.