ETC-120 ETC-208/240 ETC-277 (UL Pending) OTS-F1, UL Listed Thermostat: 1. Thermostat shall be Ambient sensing. 2. Enclosure shall be NEMA 4X rated. 3. Thermostat shall have a fixed set point of 40° F. 4. Thermostat shall have an electrical rating of 22 Amps. 5. Thermostat rating shall be: 120 VAC 208 VAC 240 VAC 277 VAC Power Control Panel with G.F.P.E.: Controller shall have: NEMA 1 rated panel enclosure with one GFPE per circuit and one green LED and one LED per circuit. “working” red “trip” One red one green and one Amber “System On” LED, “Control Power On” LED, LED on panel door. “Trip Indicator” Interior G.F.P.E. Test button and include Dry alarm contacts. Power Control Panel Model shall be: GFPE-2-N GFPE-4-N GFPE-8-N GFPE-12-N 2.4 ACCESSORIES A. Fiberglass tape, caution labels, aluminum tape, and stainless steel banding, monitor light. PART 3 EXECUTION EXAMINATION Installer to verify field measurements are as shown on Drawings. Installer to verify that required power is available, in proper location, and ready for use. Do not begin installation until substrates have been properly prepared. If substrate preparation is the responsibility of another installer, notify Architect of unsatisfactory preparation before proceeding. INSTALLATION Complete installation shall conform to appropriate local codes. Install heating cables in accordance with detailed layout drawings and manufacturer's instructions. Locate heating cable on pipe per manufacturer's instructions. Where heating cable is scheduled to heat plastic pipe, attach aluminum tape length of pipe and band heating cable on aluminum tape to evenly distribute heat. FIELD QUALITY CONTROL
ETC-120 ETC-208/240 ETC-277 (UL Pending) OTS-F1, UL Listed Thermostat: 1. Thermostat shall be Ambient sensing. 2. Enclosure shall be NEMA 4X rated. 3. Thermostat shall have a fixed set point of 40° F. 4. Thermostat shall have an electrical rating of 22 Amps. 5. Thermostat rating shall be: 120 VAC 208 VAC 240 VAC 277 VAC Power Control Panel with G.F.P.E.: Controller shall have: NEMA 1 rated panel enclosure with one GFPE per circuit and one green “working” LED and one red “trip” LED per circuit. One red “System On” LED, one green “Control Power On” LED, and one Amber “Trip Indicator” LED on panel door. Interior G.F.P.E. Test button and include Dry alarm contacts. Power Control Panel Model shall be: GFPE-2-N GFPE-4-N GFPE-8-N GFPE-12-N 2.4 ACCESSORIES A. Fiberglass tape, caution labels, aluminum tape, and stainless steel banding, monitor light. PART 3 EXECUTION EXAMINATION Installer to verify field measurements are as shown on Drawings. Installer to verify that required power is available, in proper location, and ready for use. Do not begin installation until substrates have been properly prepared. If substrate preparation is the responsibility of another installer, notify Architect of unsatisfactory preparation before proceeding. INSTALLATION Complete installation shall conform to appropriate local codes. Install heating cables in accordance with detailed layout drawings and manufacturer's instructions. Locate heating cable on pipe per manufacturer's instructions. Where heating cable is scheduled to heat plastic pipe, attach aluminum tape length of pipe and band heating cable on aluminum tape to evenly distribute heat. FIELD QUALITY CONTROL