As for monthly, plus: Tighten motor terminals. PMS 083 Fans Smoke Exhaust – – PMS 083 Fans Smoke Exhaust – – Maintenance or Test Procedure Monthly Maintenance Items Check operation for abnormal noise and vibration. Lubricate all bearings as necessary. Check security of mounting of fan. Quarterly Perform All Monthly Items and the Following – N/A Annually Perform All Monthly Items and the Following – Check for rain exclusion damper operation. Confirm padlocks are fitted to electrical isolators (if applicable). Ensure fan inlet and discharge are not blocked. Check casing for metal fatigue or failure. Check condition and connection of high temperature rated flexible duct connections. PMS 090 Fan Coil Units – PMS 090 Fan Coil Units – Maintain Fan coil units in accordance with AS 3666.2, Air Handling and Water System of Buildings Microbial Control – Maintenance or Test Procedure Monthly Maintenance Items
As for monthly, plus: Tighten motor terminals. PMS 083 – Fans – Smoke Exhaust PMS 083 – Fans – Smoke Exhaust Maintenance or Test Procedure Monthly Maintenance Items Check operation for abnormal noise and vibration. Lubricate all bearings as necessary. Check security of mounting of fan. Quarterly – Perform All Monthly Items and the Following N/A Annually – Perform All Monthly Items and the Following Check for rain exclusion damper operation. Confirm padlocks are fitted to electrical isolators (if applicable). Ensure fan inlet and discharge are not blocked. Check casing for metal fatigue or failure. Check condition and connection of high temperature rated flexible duct connections. PMS 090 – Fan Coil Units PMS 090 – Fan Coil Units Maintain Fan coil units in accordance with AS 3666.2, Air Handling and Water System of Buildings – Microbial Control Maintenance or Test Procedure Monthly Maintenance Items