Guidance and Manufacturer’s Declaration – Electromagnetic Immunity POC-128 is intended for use in the electromagnetic environment specified below. The customer or the user of the model POC-128 should assure that it is used in such an environment. IEC 60601 Test Compliance Electromagnetic Environ- Immunity Test Level Level mental Guidance Floors should be wood, con- Electrostatic dis- crete or ceramic tile. If floors kV kV 6 6 contact contact charge (ESD) are covered with synthetic 8 8 kV air kV air IEC 61000-4-2 material, the relative humidity should be at least 30%. 2 2 kV for power kV for pow Electrical fast supply lines er supply lines Main power quality should be transient/burst that of a typical commercial or 1 1 hospital environment. kV for input/out- kV for input/ IEC 61000-4-4 put lines output lines 1 1 kV line(s) to kV line(s) to Main power quality should be Surge line(s) line(s) that of a typical commercial or 2 2 IEC 61000-4-5 kV line(s) to kV line(s) to hospital environment. earth earth <5% UT <5% UT (>95% dip (>95% dip in in UT) for 0,5 cycle UT) for 0,5 cycle Main power quality should be 40% UT that of a typical commercial or Interruptions and (60% dip in UT) 40% UT (60% hospital environment. If the voltage varia- for 5 cycles dip in UT) for 5 user of the model POC-128 tions on power cycles requires continued operation supply input lines 70% UT during main power interrup- (30% dip in UT) 70% UT (30% tion, it is recommended that IEC 61000-4-11 for 25 cycles dip in UT) for the model POC-128 be 25 cycles powered from an uninterrupt- <5% UT ible power supply or a battery. (>95% dip in UT) <5% UT for 5 sec (>95% dip in UT) for 5 sec Power frequency magnetic Power frequency fields should be at levels (50/60 Hz) 3 A/m 3 A/m characteristic of a typical magnetic field location in a typical commer- IEC 61000-4-8 cial or hospital environment. NOTE UT is the A.C. main voltage prior to application of the test level.
Guidance and Manufacturer’s Declaration – Electromagnetic Immunity POC-128 is intended for use in the electromagnetic environment specified below. The customer or the user of the model POC-128 should assure that it is used in such an environment. Immunity Test IEC 60601 Test Compliance Electromagnetic Environ- Level Level mental Guidance Electrostatic dis- Floors should be wood, con- 6 kV contact 6 kV contact crete or ceramic tile. If floors charge (ESD) are covered with synthetic 8 kV air 8 kV air IEC 61000-4-2 material, the relative humidity should be at least 30%. Electrical fast 2 kV for power 2 kV for pow supply lines er supply lines Main power quality should be transient/burst that of a typical commercial or 1 kV for input/out- 1 kV for input/ IEC 61000-4-4 hospital environment. put lines output lines 1 kV line(s) to 1 kV line(s) to Main power quality should be Surge line(s) line(s) that of a typical commercial or IEC 61000-4-5 2 kV line(s) to 2 kV line(s) to hospital environment. earth earth <5% UT (>95% dip <5% UT (>95% dip in in UT) for 0,5 cycle UT) for 0,5 Main power quality should be cycle 40% UT that of a typical commercial or Interruptions and (60% dip in UT) 40% UT (60% hospital environment. If the voltage varia- for 5 cycles dip in UT) for 5 user of the model POC-128 tions on power cycles requires continued operation supply input lines 70% UT during main power interrup- (30% dip in UT) 70% UT (30% tion, it is recommended that IEC 61000-4-11 for 25 cycles dip in UT) for the model POC-128 be 25 cycles powered from an uninterrupt- <5% UT <5% UT ible power supply or a battery. (>95% dip in UT) for 5 sec (>95% dip in UT) for 5 sec Power frequency Power frequency magnetic fields should be at levels (50/60 Hz) 3 A/m 3 A/m characteristic of a typical magnetic field location in a typical commer- IEC 61000-4-8 cial or hospital environment. NOTE UT is the A.C. main voltage prior to application of the test level.