to change the customer password and to enable or disable password protection. Pressing “F1” “F2” “ESC/BACK” will return the user to the Control” screen. “Menu 11.2.5 Controller Screen: Password” “Change This screen is used to change the customer password. The user enters the existing password and the new password. If the existing password is correct, the new password will be stored in the Password” data “Customer table. This screen is accessed by pressing on the Extras” screen. Pressing will “F1” “Password “ESC/BACK” return the user to the Extras” screen. “Password 11.2.6 Controller Screen: Entry” “Password This screen is used for entry of the customer password. It is accessed by pressing the key on the front “EDIT” panel. Once the password has been successfully entered, the user will be returned to the previous screen. 11.2.7 Controller Screen: Password” “Disable This screen is accessed by pressing the key on the Extras” screen. On this screen, of the “F2” “Password customer password will disable the password function. When the password is active, the text above the entry box displays. When the password is disabled, the text below the entry box displays. To enable the password, the user enters the customer password. Pressing will return the user to the Extras” screen. “ESC/BACK” “Password 11.2.8 Controller Screen: Test” “Lamp This screen is displayed while the Test” is in progress. Upon pressing the TEST” button, the “Lamp “LAMP Status” screen will re-appear. “System 11.2.9 Controller Screen: Running” “Pulse This screen is displayed when the NGR test is running. It displays the pulse rate in seconds and the real-time values for the voltage across and the current through the NGR. Pressing will return the user to the “PULSE” Status” screen. “System
“F1” to change the customer password and “F2” to enable or disable password protection. Pressing “ESC/BACK” will return the user to the “Menu Control” screen. 11.2.5 Controller Screen: “Change Password” This screen is used to change the customer password. The user enters the existing password and the new password. If the existing password is correct, the new password will be stored in the “Customer Password” data table. This screen is accessed by pressing “F1” on the “Password Extras” screen. Pressing “ESC/BACK” will return the user to the “Password Extras” screen. 11.2.6 Controller Screen: “Password Entry” This screen is used for entry of the customer password. It is accessed by pressing the “EDIT” key on the front panel. Once the password has been successfully entered, the user will be returned to the previous screen. 11.2.7 Controller Screen: “Disable Password” This screen is accessed by pressing the “F2” key on the “Password Extras” screen. On this screen, of the customer password will disable the password function. When the password is active, the text above the entry box displays. When the password is disabled, the text below the entry box displays. To enable the password, the user enters the customer password. Pressing “ESC/BACK” will return the user to the “Password Extras” screen. 11.2.8 Controller Screen: “Lamp Test” This screen is displayed while the “Lamp Test” is in progress. Upon pressing the “LAMP TEST” button, the “System Status” screen will re-appear. 11.2.9 Controller Screen: “Pulse Running” This screen is displayed when the NGR test is running. It displays the pulse rate in seconds and the real-time values for the voltage across and the current through the NGR. Pressing “PULSE” will return the user to the “System Status” screen.