Brunswick 1 Gd (TRM) Existing Operating Marion-Dillon Tap Whiteville-Brun EMC Loading Procedure [2032] 115 kV Line 1 Chadbourn Peacock and (90.0 %) Opens Weatherspoon (Weatherspoon Plant-Marion) Whiteville-Industrial Tap Terminal 230 kV Lines TABLE C DUKE ENERGY PROGRESS SUMMARY OF POTENTIAL RELIABILITY ISSUES 2024 SUMMER PEAK - WS3 Potential Potential Element Contingency Solution Issue ($2013) Brunswick 1 Gd (TRM) Existing Operating Marion-Dillon Tap Whiteville-Brun EMC Loading Procedure [2024] 115 kV Line 1 Chadbourn Peacock and (111.3 %) Opens Weatherspoon (Weatherspoon Plant-Marion) Whiteville-Industrial Tap Terminal 230 kV Lines West End-Central EMC Existing Operating Harris Gd (TRM) Center Church Loading Procedure [2024] Cumberland-Richmond 230 kV Line 1 (102.1 %) Opens West End 500 kV Line 1 (Cape Fear-West End) Terminal
Marion-Dillon Tap 115 kV Line 1 (Weatherspoon Plant-Marion) Brunswick 1 Gd (TRM) Whiteville-Brun EMC Chadbourn Peacock and Whiteville-Industrial Tap 230 kV Lines Loading (90.0 %) Existing Operating Procedure [2032] Opens Weatherspoon Terminal TABLE C DUKE ENERGY PROGRESS SUMMARY OF POTENTIAL RELIABILITY ISSUES 2024 SUMMER PEAK - WS3 Element Contingency Potential Issue Potential Solution ($2013) Marion-Dillon Tap 115 kV Line 1 (Weatherspoon Plant-Marion) Brunswick 1 Gd (TRM) Whiteville-Brun EMC Chadbourn Peacock and Whiteville-Industrial Tap 230 kV Lines Loading (111.3 %) Existing Operating Procedure [2024] Opens Weatherspoon Terminal West End-Central EMC Center Church 230 kV Line 1 (Cape Fear-West End) Harris Gd (TRM) Cumberland-Richmond 500 kV Line 1 Loading (102.1 %) Existing Operating Procedure [2024] Opens West End Terminal