Oil / VPI/ Cast Resin 10.18.1.1 No load Loss capitalization Rs 4,09,980 per kw Figure 10.18.1.2 Load loss capitalization figure Rs 2,26,720 per kw 10.18.2. Limiting Dimensions of Cast Dimensions indicated are Resin Transformers maximum. Manufacturer shall try the best design for optimizing the dimensions further. Note 1: The transformers will be evaluated against no load and load losses guaranteed by the bidders with capitalization of losses as per CBIP guidelines for loss capitalization. The corresponding capitalization figures for no load and load losses shall be as per cl. 7.20.1.1 and 7.20.1.2 above. However, the maximum loss figures acceptable are as per indicated in the relevant specifications. In the event of measured loss figures during testing / challenge testing exceeding the guaranteed loss figures of the successful bidder, penalty shall be applied at a rate of 1.5 times the figures mentioned above for both no load and load losses for all the units purchased from the successful vendor. 11. Technical parameters to be monitored through SCADA from Remote. Transformer healthiness : Winding temperature Safety parameter breach / transformer door open 12. L.V Switchgear Panels 12.1 Technical parameters to be monitored from SCADA Feeder data : switch ON/OFF Energy consumption data System power quality (Power factor / THD content) recording Make of the ACB– Schneider Masterpack NW/ABB Emax/Siemens 3WL 12.1 System:- Declared voltage :– 3 Phase,400V (±6%) 50 Hz, Neutral :– Solidly earthed at substation. Busbar– Aluminium finish:- Tropical, totally enclosed, metal-clad, weather-proof, vermin and dust proof. : Enclosure:- Dead type of enclosure shall be able to provide the degree of Protection IP:4X.
Oil / VPI/ Cast Resin 10.18.1.1 No load Loss capitalization Rs 4,09,980 per kw Figure 10.18.1.2 Load loss capitalization figure Rs 2,26,720 per kw 10.18.2. Limiting Dimensions of Cast Dimensions indicated are Resin Transformers maximum. Manufacturer shall try the best design for optimizing the dimensions further. Note 1: The transformers will be evaluated against no load and load losses guaranteed by the bidders with capitalization of losses as per CBIP guidelines for loss capitalization. The corresponding capitalization figures for no load and load losses shall be as per cl. 7.20.1.1 and 7.20.1.2 above. However, the maximum loss figures acceptable are as per indicated in the relevant specifications. In the event of measured loss figures during testing / challenge testing exceeding the guaranteed loss figures of the successful bidder, penalty shall be applied at a rate of 1.5 times the figures mentioned above for both no load and load losses for all the units purchased from the successful vendor. 11. Technical parameters to be monitored through SCADA from Remote. Transformer healthiness : Winding temperature Safety parameter breach / transformer door open 12. L.V Switchgear Panels 12.1 Technical parameters to be monitored from SCADA Feeder data : switch ON/OFF Energy consumption data System power quality (Power factor / THD content) recording Make of the ACB– Schneider Masterpack NW/ABB Emax/Siemens 3WL 12.1 System:- Declared voltage :– 3 Phase,400V (±6%) 50 Hz, Neutral :– Solidly earthed at substation. Busbar– Aluminium finish:- Tropical, totally enclosed, metal-clad, weather-proof, vermin and dust proof. : Enclosure:- Dead type of enclosure shall be able to provide the degree of Protection IP:4X.