beside the harmonic filters, equipment is also provided to eliminate spurious signals in the frequency range of power-line carrier equipment in the range of 30 khz to 500 khz. these filters are usually near the alternating current terminal of the static inverter transformer. they consist of a coil which passes the load current, with a parallel capacitor to form a resonant circuit.