A corroded shackle connecting the Otahuhu to Penrose 220 kV line's earth wire had dislodged in 90 kmph winds, letting the earth wire fall across the 220 kV line and the 110 kV busbar below it, tripping both the line and three sections of the busbar, disconnecting lines to Mount Roskill, Penrose and Pakuranga.