Start feature carousel Stop feature carousel. MNsure is Minnesota's health insurance marketplace where individuals, families and small businesses can shop, compare and choose health insurance coverage. It's the only place to apply for financial help to lower the cost of your health coverage. The MNsure marketplace is open 4 a.m. to midnight every day.
Slowing blowers on a chiller coils allows the air to be colder and remove more moisture. Slow the air flow to minimum necessary to cool the space, reduce fresh air to minimal amount acceptable, and set the chiller temperature as low as possible. These are the easy things. Most consider 20 cfm of fresh air as the minimum for smoking/15 cfm for nonsmoking.
The requirement is still in place to keep the room at a target of 50% RH to reduce the risk of nosocomial infections. To keep the room at 50% relative humidity with the air temperature at 60-64F will require the air to be at a dew point temperature of 40-42F when delivered to the room.With the typical hospital having chilled water at 42-44F, this new requirement is impossible to achieve with what equipment is in place.ith the large amount of supply air (15 ACH), to maintain 68F temperature in the space, the supply air must be reheated to 56-59F at design conditions to prevent overcooling of the space.