ENERPOS
Finally, large ceiling fans are installed in every room, even those using air conditioning. Ceiling fans ensure that even in the absence of the necessary breezes, the airflow needed to feel comfortable in the room is provided for the users. This solution significantly reduces the amount of energy consumed. The overall consumption of the ceiling fans and the split system (the latter used to cool the technical rooms) is only 3.7kWh/m².yr compared to a classic air conditioning system in a standard building consuming 80kWh/m².yr.
Fan coil unit
Speed control of the fan motors within a fan coil unit is partly used to control the heating and cooling output desired from the unit. Some manufacturers accomplish speed control by adjusting the taps on an AC transformer supplying the power to the fan motor. Typically this would require adjustment at the commissioning stage of the building construction process and is therefore set for life at a fixed speed. Other manufacturers provide custom-wound Permanent Split Capacitor (PSC) motors with speed taps in the windings, set to the desired speed levels for the fan coil unit design. A simple speed selector switch (Off-High-Medium-Low) is provided for the local room occupant to control the fan speed. Typically this speed selector switch is integral to the room thermostat, and is set manually or is controlled automatically by the digital room thermostat. Building Energy Management Systems can be used for automatic fan speed and temperature control. Fan motors are typically AC Shaded Pole or Permanent Split Capacitor. More recent developments include brushless DC designs with electronic commutation. Compared to units with asynchronous 3-speed motors, the fan coil units with brushless motors will reduce the power consumption up to 70%.