INNOVAL
The hot climate at Le Port led the team in charge of the INNOVAL project to prepare a cooling strategy for different seasons. During the winter, natural ventilation is sufficient to cool offices and during the mid-season between the winter and the summer, natural ventilation is completed with ceiling fans. However, during the summer, natural ventilation coupled with ceiling fans are not sufficient, consequently, air conditioning has to be used. In buildings in Reunion Island, a significant percentage of the energy consumed is due to air conditioning, therefore, the air conditioning system selected here is an efficient one with a Variable Refrigerant Flow ensuring reliability and energy savings. Moreover, a software tool automatically regulates the power of cooling in relation to office use. Finally, while in Reunion Island, people are used to cooling below 24 °C, the air conditioning of the building cannot cool below 26 °C which is adequate with ceiling fans and natural ventilation. Indeed, with the assistance of ceiling fans, the felt temperature is reduced by 5 °C allowing a final felt temperature of 21 to 22 °C. In order to optimize the refrigerated unit power, the temperature adjustment consists of applying a difference of 5 °C between the outside and the inside. For example, if the outside temperature is 34 °C, the temperature adjustment will be 29 °C. All these choices in operation have led to a decrease from 100 kW to 30 kW in the power required by the refrigerated unit.
Chilled beam
The primary advantage of the chilled beam system is its lower operating cost. For example, because the temperature of cooled water is higher than the temperature of cooled air, but it delivers the same cooling ability, the costs of the cooled water system are lower. Because cooling and heating of air are no longer linked to the delivery of air, buildings also save money by being able to run fewer air circulation fans and at lower speeds. One estimate places the amount of air handled at 25 to 50 percent less using chilled beam systems. By being able to target the delivery of clean outdoor air where it is needed (rather than injecting it into the entire system and heating or cooling it), there is a reduced need to treat large amounts of outdoor air (also saving money). In one case, the Genomic Science Building at the University of North Carolina at Chapel Hill lowered its HVAC costs by 20 percent with an active chilled beam system. This is a typical energy cost savings. Chilled beam systems also have some advantages in that they are almost noiseless, require little maintenance, and are highly efficient. Traditional fan-driven HVAC systems create somewhat higher air velocities, which some people find uncomfortable. Chilled beam HVAC systems also require less ceiling space than forced-air HVAC systems, which can lead to lower building heights and higher ceilings. Since they do not require high forced air flows, chilled beam systems also require reduced air distribution duct networks (which also helps to lower cost).