The dry air travels up to and out of the discharge port. There are two basic types of coalescing elements. The first type utilizes a cast material that is dominated with an internal microscopic lattice. The air is forced to flow through the lattice which, in turn, allows the water vapor to wet to the internal surfaces. The second type is generally referred to as a stacked plate element. In this case, fine discs are stacked with microscopic gaps between them. The air is forced to flow through the gaps which, in turn, allows the water vapor to wet to the internal surfaces. In principle, a coalescing filter is an ideal way to separate water from the compressed air stream. Practically speaking, this is not the case. Coalescing elements are extremely sensitive to oil and particulate contamination and therefore would be better placed as a second stage dryer. However, the dew point performance of a coalescing filter places it in the primary category of compressed air dryers. In order to use coalescing filters as primary dryers, they are typically set-up in pairs. The first filter has an element with larger gaps that are designed to remove oil from the stream. The second filter uses a finer element that is intended to remove water vapor. Because of the sensitivity of the elements, coalescing filters are not particularly common. One area where these filters have found acceptance is with dental compressors. The way that dental compressors are designed and used makes a two-stage coalescing filter an almost ideal solution for water contamination in these systems. Refrigerated dryers are the most common type of compressed air dryer. They remove water from the air stream by cooling the air to approximately 3 °C (38 °F) and effectively condensing out the moisture in a controlled environment. 3 °C (38 °F) is the realistic lower limit for a refrigerated dryer because a lower temperature runs the risk of freezing the separated water. They are typically specified as primary dryers and generally produce air quality that is appropriate for approximately 95% of all compressed air applications. Refrigerated dryers employ two heat exchangers, one for air-to-air and one for air-to-refrigeration. However, there is also a single TRISAB heat exchanger that combines both functions. The compressors used in this type of dryer are usually of the hermetic type and the most common gas used is R-134a and R-410a for smaller air dryers up to 100 cfm.