Economic Simplified Boiling Water Reactor  The Economic Simplified Boiling Water Reactor (ESBWR) is a passively safe generation III+ reactor design derived from its predecessor, the Simplified Boiling Water Reactor (SBWR) and from the Advanced Boiling Water Reactor (ABWR). All are designs by GE Hitachi Nuclear Energy (GEH), and are based on previous Boiling Water Reactor designs. The passive safety systems in an ESBWR operate without using any pumps, which creates increased design safety, integrity, and reliability, while simultaneously reducing overall reactor cost. It also uses natural circulation to drive coolant flow within the reactor pressure vessel (RPV); this results in fewer systems to maintain, and precludes significant BWR casualties such as recirculation line breaks. There are no circulation pumps or associated piping, power supplies, heat exchangers, instrumentation, or controls needed for these systems. ESBWR's passive safety systems include a combination of three systems that allow for the efficient transfer of decay heat (created from nuclear decay) from the reactor to pools of water outside containmentthe Isolation Condenser System, the Gravity Driven Cooling System, and the Passive Containment Cooling System. These systems utilize natural circulation based on simple laws of physics to transfer the decay heat outside containment while maintaining water levels inside the reactor, keeping the nuclear fuel submerged in water and adequately cooled. In events where the reactor coolant pressure boundary remains intact, the Isolation Condenser System (ICS) is used to remove decay heat from the reactor and transfer it outside containment. The ICS system is a closed loop system that connects the reactor pressure vessel to a heat exchanger located in the upper elevation of the reactor building. Steam leaves the reactor through the ICS piping and travels to the ICS heat exchangers which are submerged in a large pool. The steam is condensed in the heat exchangers and the denser condensate then flows back down to the reactor to complete the cooling loop. Reactor coolant is cycled through this flow path to provide continuous cooling and to add water to the reactor core. In cases where the reactor coolant pressure boundary does not remain intact and water inventory in the core is being lost, the Passive Containment Cooling System (PCCS) and Gravity Driven Cooling System (GDCS) work in concert to maintain the water level in the core and remove decay heat from the reactor by transferring it outside containment. If the water level inside the reactor pressure vessel drops to a predetermined level, due to the loss of water inventory, the reactor is depressurized and the GDCS is initiated.