_:nd450a18b6b21451ba7eacc796ae7dc38xb0
<http://schema.org/description>
"Model: Fluke CV400 ClirVu® 95 mm (4 in) Infrared Window\nPart Number: CV400 (4 in)\nOrdering Number: 1C6700\nDatasheet\nA company's greatest investment is not the equipment that's behind the panel door; top priority is to offer the ultimate protection for the electricians, engineers and inspectors who risk their lives every day doing their jobs.\nThe ClirVu® coating - exclusive to Fluke infrared windows - seals the optic prior to assembly to protect against moisture degradation making it perfect for very hot and very cold environments.\nEach Fluke infrared window is delivered with an identification plate attached for unique, on-site numbering for rapid location confirmation and faster repairs.\n\n\n\nWarranty\nLifetime replacement against manufacturing defects\n\n\n\n \nInstalls and grounds in less than 5 minutes\nSave time with quick and easy installation with the CV Series – 5 minutes or less.\n\nOne technician\nOne hole with standard Greenlee® punch\nPanel door does not need to be removed\nGrounds instantly to metal enclosure with patent-pending AutoGround™ process\nMaintains panel arc test ratings up to 63kA when properly installed\n\nWork more efficiently with Fluke ClirVu® CV400 95 mm (4 in) Infrared Windows\n\nNFPA 70E processes significantly reduced due to less work permit requirements\nFaster and more comfortable inspections because full PPE is often not required\nReduce the risk of arc-flash and electrocution, increase the safety of your personnel and reduce the time and cost of preventive maintenance\nCV400 is Torture Tested™ to the highest arc blast test ratings IEEE C37.20.7: 63 kA Arc tested at KEMA, UL 50/50E/50V, UL1558, IEC60529-1: IP67, IEC 60068, NEMA 4/12, CSA C22.2 NO. 14-13:2012, and CE\nConvenience of both quick turn or security keyed access\n\n \n\n\n\n\nIncludes:\n\n4 in (95 mm) IR Window\nHand turn door latch\nWarranty statement \nFluke IR Windows are complete, assembled and ready for installation\n\n\n\n\n\n \nSpecifications\n\n\n\nSize\n95 mm (4 in)\n\n\nVoltage range\nAny\n\n\nNEMA environment type\nType 4/12 (indoor/outdoor)\n\n\nAutoGround™\nYes\n\n\nClirVu® optic\nYes\n\n\nOperating temperature\n-40°C to +232°C (-40° F to +450°F) and +260°C (500°F) intermittent\n\n\nCompatible with all Fluke cameras\nYes\n\n\nJam nut locking system\nYes\n\n\nCover and fastener permanently attached\nYes\n\n\nSingle-hole install\nYes\n\n\nHand turn and security key door latch options\nYes\n\n\nVisual inspection and fusion capable\nYes\n\n\nShort/Mid/Long-wave IR and UV capable\nYes\n\n\n\n \nRatings and Testing\n\n\n\nArc-tested (IEEE C37.20.7)\n63 kA for 30 cycles @ 60 Hz at KEMA\n\n\nUL 50 V component recognition\nYes\n\n\nUL 50 / NEMA environmental rating\nNEMA Type 4/12\n\n\nUL1558\nYes\n\n\nCSA C22.2 No.\nYes\n\n\nCSA type rating\nType 4\n\n\nIP rating\nIP67 at TUV\n\n\nLloyds register\nUp to 11 kV marine switchgear, indoor or outdoor (offshore only)\n\n\nVibration rating\nIEC60068-2-6 at TUV\n\n\nHumidity rating\nIEC60068-2-3 at TUV\n\n\n\n \nInstall\n\n\n\nActual mounting hole diameter required\n115.42 mm (4.544 in)\n\n\nGreenlee® punch kit = punch/die\n742BB = 2984AV/2983AV\n\n\nRecommended max panel thickness\n10 gage\n\n\nOverall window height\n189.3 mm (7.45 in)\n\n\nOverall window width\n147.1 mm (5.79 in)\n\n\nOverall window thickness\n23.0 mm (0.90 in)\n\n\nDoor latch\nHand Turn\n\n\n\n \nOptics\n\n\n\nOptic insert diameter\n95 mm (3.74 in)\n\n\nViewing aperture diameter\n87.63 mm (3.450 in)\n\n\nViewing aperture area\n6032 mm2 (9.35 in2)\n\n\nThickness\n4 mm (0.16 in)\n\n\n"
<https://shop.byramlabs.com/products/fluke-cv400-clirvu%C2%AE-95-mm-4-in-infrared-window>