<https://rtce.co.th/product/%e0%b9%80%e0%b8%9a%e0%b8%a3%e0%b8%84%e0%b9%80%e0%b8%81%e0%b8%ad%e0%b8%a3%e0%b9%8c-ezs160f3100-3p-100a-36ka-schneider/#product>
<http://schema.org/description>
"รายละเอียดสินค้า\r\n\r\nเบรคเกอร์ EZS160F-3100 3P 100A 36kA EasyPact EZS Schneider  \r\n\r\n-ง่ายต่อการเลือกใช้  \r\n &gt;ขนาดกระแสตั้งแต่ 16-600Amp \r\n &gt;ทริปยูนิตแบบ Thermal Magnetic \r\n &gt;กระแสรัดวงจร 25-50kA at 415Vac \r\n\r\n-งายต่อการติดตั้ง\r\n &gt;3 ขนาดเฟรม ง่ายต่อการออกแบบติดตั้งและการซ่อมบำรุง\r\n &gt;ติดตั้งอุปกรณ์เสริม ( Auxilary และ Accessories ) ได้ \r\n &gt;ดูวีดีโอแนะนำการติดตั้งเบรคเกอร์และอุปกรณ์เสริมได้จาก QR code บนผลิตภัณฑ์ \r\n\r\n-ง่ายต่อการใช้งาน\r\n &gt;ไม่ต้องปรับค่า ลดความยุ่งยากและความผิดพลาด\r\n &gt;เหมาะสำหรับงานอาคารขนาดเล็กทั่วไป\r\n\r\nSpecifications \r\n\r\nMain\r\nrange of product                       EasyPact EZS\r\nproduct or component type              Circuit breaker\r\ndevice short name                      EZS160F\r\ncircuit breaker application            Distribution\r\npoles description                      3P\r\nprotected poles description            3D\r\nsuitability for isolation              Yes\r\n\r\nComplementary                         \r\nneutral position                       Left\r\n[In] rated current                     160 A at 40 °C\r\nbreaking capacity code                 F\r\nnetwork type                           AC\r\nnetwork frequency                      50/60 Hz\r\ncontrol type                           Toggle\r\nmounting mode                          Fixed\r\nmounting support                       \r\nBackplate\r\nupside connection                      Front\r\ndownside connection                    Front\r\n[Ui] rated insulation voltage          690 V conforming to EN/IEC 60947-2\r\n[Uimp] rated impulse withstand voltage 8 kV conforming to EN/IEC 60947-2\r\n[Ue] rated operational voltage         440 V AC 50/60 Hz conforming to EN/IEC 60947-2\r\n                                       400 V AC 50/60 Hz conforming to GB 14048.2\r\nbreaking capacity                      70 kA Icu at 220/240 V AC 50/60 Hz conforming to EN/IEC 60947-2\r\n                                       36 kA Icu at 380/400 V AC 50/60 Hz conforming to EN/IEC 60947-2\r\n                                       36 kA Icu at 415 V AC 50/60 Hz conforming to EN/IEC 60947-2\r\n                                       36 kA Icu at 440 V AC 50/60 Hz conforming to EN/IEC 60947-2\r\n                                       35 kA Icu at 220/230 V AC 50/60 Hz conforming to GB 14048.2\r\n                                       70 kA Icu at 380/400 V AC 50/60 Hz conforming to GB 14048.2\r\nutilisation category                   Category A\r\n \r\n[Ics] rated service breaking capacity  53 kA at 220/230 V AC 50/60 Hz conforming to GB 14048.2\r\n                                       26 kA at 380/400 V AC 50/60 Hz conforming to GB 14048.2\r\n                                       70 kA at 220/240 V AC 50/60 Hz conforming to EN/IEC 60947-2\r\n                                       36 kA at 380/400 V AC 50/60 Hz conforming to EN/IEC 60947-2\r\n                                       36 kA at 415 V AC 50/60 Hz conforming to EN/IEC 60947-2\r\n                                       18 kA at 440 V AC 50/60 Hz conforming to EN/IEC 60947-2\r\n\r\nmechanical durability                  25000 cycles conforming to EN/IEC 60947-2\r\n                                       20000 cycles conforming to GB 14048.2\r\nelectrical durability                  25000 cycles 415 V In/2 conforming to EN/IEC 60947-2\r\n                                       8000 cycles 400 V In conforming to GB 14048.2\r\nconnection pitch                       35 mm\r\ntrip unit name                         TM-D\r\ntrip unit technology                   Thermal-magnetic\r\ntrip unit rating                       160 A at 40 °C\r\n\r\nprotection type                        Overload protection (thermal)\r\n                                       Short-circuit protection (magnetic)\r\n\r\nlong time pick-up adjustment type Ir      Fixed\r\nlong time pick-up adjustment range        1 In\r\nlong time delay adjustment type           Fixed \r\ninstantaneous pick-up adjustment type Ii  Fixed\r\nintegral instant protection               1250 kA\r\n\r\nheight                                     161 mm\r\nwidth                                      105 mm\r\ndepth                                      86 mm\r\nnet weight                                 2.2 kg\r\n\r\nEnvironment                             \r\nstandards                                  IEC 60947-2\r\n                                           EN 60947-2\r\nIP degree of protection                    IP40 conforming to IEC 60529\r\nIK degree of protection                    IK07 conforming to IEC 62262\r\npollution degree                           3 conforming to IEC 60947-1\r\nambient air temperature for operation      -35…70 °C\r\nambient air temperature for storage        -50…85 °C\r\n\r\nPacking Units                              \r\nUnit Type of Package 1                       PCE\r\nNumber of Units in Package 1                 1\r\nPackage 1 Weight                             1.723 kg\r\nPackage 1 Height                             13.4 cm\r\nPackage 1 width                              19.1 cm\r\nPackage 1 Length                             11.7 cm\r\nUnit Type of Package 2                       PAL\r\nNumber of Units in Package 2                 144\r\nPackage 2 Weight                             248.112 kg\r\nPackage 2 Height                             92 cm\r\nPackage 2 width                              80 cm\r\nPackage 2 Length                             120 cm\r\nUnit Type of Package 3                       CAR\r\nNumber of Units in Package 3                 9\r\nPackage 3 Weight                             16.691 kg\r\nPackage 3 Height                             23.4 cm\r\nPackage 3 width                              36.2 cm \r\nPackage 3 Length                             48.9 cm"
<https://rtce.co.th/product/%E0%B9%80%E0%B8%9A%E0%B8%A3%E0%B8%84%E0%B9%80%E0%B8%81%E0%B8%AD%E0%B8%A3%E0%B9%8C-ezs160f3100-3p-100a-36ka-schneider/>