_:n2affc8eeee2e4bf589c2610ae237f0a2xb0
<http://schema.org/description>
"INVERTER FOUR-WAY CASSETTE Model no: ALCA-C24/4DR3HI Brand: AUX ALU: 21601 Size: 24000BTU\n\n\nSpecifications\n\n\nAux - Inverter 4-Way Cassette (24000BTU)\nBrand: Aux\nModel: ALCA-C24/4DR3HI\nCapacity: 24000BTU\nWarranty: 1 Year Warranty plus 5 Years Compressor Warranty\n \nIndoor Unit:\nIndoor Unit (Power Supply): 220-240V, 50/60Hz, 1Ph\nCapacity (Cooling):\n\n\n25000 (7370 – 25590) Btu/h\n7.33 (2.16 - 7.50) kW\n\n\nElectric Data\n\n\n\nRated Cooling Power Input: 2.27 (0.67 – 2.55) kW\n\nRated Cooling Current: 9.87 (2.91 – 11.09) A\n\n\nPerformance:\n\n\n\nEER (T1): 3.23 W/W, 11.02 (Btu/h)/W\n\nISEER: 4.0 W/W, 13.65 (Btu/h)/W\n\n\nIndoor Coil:\n\n\n\nNumber Of Row: 2\n\nTube Pitch (a) x Row Pitch (b): 20.5 x 12.7mm\n\nFin Pitch: 1.4mm\n\nFin Material: Window Cutting Hydrophilic aluminum foil\n\nTube outside Dia. And Material: Ø7mm, Inner grooved\n\nCoil (Length x Height x Width): 2084 x 205 x 25.4mm\n\nNumber of circuit: 8\n\n\nIndoor Fan Motor:\n\n\n\nOutput Power: 100W x1\nCapacitor: -\n\nSpeed (Hi/Mi/Lo): 670/600/550 r/min\n\n\nIndoor Air Flow (Hi/Mi/Lo):\n\n\n1600/1400/1260 m3/h\n941/824/741 CFM\n\n\nNoise Level (Hi/Mi/Lo): 48/46/44 dB (A)\nSound Power Level (Hi/Mi/Lo): 59/56/53 dB (A)\nRefrigerant Pipe:\n\n\n\nLiquid Side: Ø9.52mm\n\nGas Side: Ø15.88mm\n\n\nDrainage pipe: R3/4in (DN20)\n \nOutdoor Unit:\nMax. Input Consumption: 2980W\nMax. Current: 14.5A\nDC Inverter Compressor:\n\n\n\nType: Rotary\n\nCapacity: 4690W\n\nInput: 1250W\n\nFrequency range: 8-120Hz\n\nRated Current (RLA): 7.1A\n\nRefrigerant Oil: 450ml (VG74)\n\n\nOutdoor Fan Motor\n\n\n\nOutput Power x Fan quantity: 69W x1\n\nSpeed: 870 r/min\n\n\nCoil:\n\n\n\nNumber Of Row: 2\n\nTube Pitch (a)x Row Pitch (b): 20.5 x 12.7mm\n\nFin Pitch: 1.5mm\n\nFin Material: Window Cutting\n\nTube outside Dia. And Material: Ø7mm, Inner grooved\n\nCoil (Length x Height x Width): 777 x 616 x 25.4mm\n\nNumber of circuit: 4\n\n\nAir Flow Volume: 1882 CFM, 3200 m3/h\nNoise Level:\n\n\n\nSound Pressure Noise Level: 55 dB(A)\n\nSound Power Noise Level: 62 dB(A)\n\n\nDesign Pressure: 4.2 MPa\nRefrigerant: R32, 1.20kg\nRefrigerant Piping:\n\n\n\nLiquid Side: Ø9.52mm\n\nGas Side: Ø15.88mm\n\nLength: 30m\n\nHeight: 20m\n\n\nOperation Temperature Range: 16°C ~ 32°C\nAmbient Temperature Range (Cooling): 5°C ~ 52°C\nConnection Wiring:\n\n\n\nPower Wiring (Indoor): /\n\nPower Wiring (Outdoor): 3 x 2.5mm2\n\n\nConnection Wiring (IDU&amp;ODU): 3 x 0.75mm2\n\n\nSignal Wiring (IDU&amp;ODU): 2 x 0.2mm2\n\n\n\n \nDimension &amp; Weight:\nWeight x Depth x Height\nIndoor Unit:\n\n\n\nProduct Dimension: 840 x 840 x 246mm\n\nPacking Dimension: 910 x 910 x 310mm\n\nNet Weight: 26kg\n\nGross Weight: 30kg\n\n\nPanel:\n\n\n\nProduct Dimension: 950 x 950 x 55mm\n\nPacking Dimension: 1000 x 1000 x 100mm\n\nNet Weight: 5.3kg\n\nGross Weight: 7.8kg\n\n\nOutdoor Unit:\n\n\n\nProduct Dimension: 825 x 310 x 655mm\n\nPacking Dimension: 945 x 435 x 725mm\n\nNet Weight: 42kg\n\nGross Weight: 45kg\n\n\n\n\n"
<https://www.astersonline.com/products/aux-24000btu-ac-inverter-4-way-cassette-alca-c24-4dr3hi>