_:nc7481c1b59d3479da38ae033688a9380xb0
<http://schema.org/description>
"Keypower KPC 60S merupakan generator tipe silent memiliki daya output 48000 Watt dengan voltase 380 V, yang membuat generator mampu berjalan dengan baik.\n\n\n\nType\nKPC-60S (SILENT TYPE)\n\n\n\n\n\nSPESIFIKASI UMUM / GENERAL SPECIFICATION\n\n\n\n\n\nDaya Utama /\nPrime Rating Power\n48000 Watt\n\n\nDaya Maksimal /\nMaximum Power\n52800 Watt\n\n\nPhasa /\nPhase\nTHREE\n\n\nTegangan Rata Rata /\nRated Voltage\n380/220 Volt\n\n\nFrekuensi Rata Rata /\nRated Frequency\n50 Hz\n\n\nArus Rata Rata /\nRated Current\n94 Ampere\n\n\nKapasitas Tanki Bahan Bakar /\nFuel Tank Capacity\n100 Liter\n\n\n\n\n\nSPESIFIKASI MESIN / ENGINE SPECIFICATION\n\n\n\n\n\nPabrikan Mesin /\nEngine Manufacture\nCummins\n\n\nModel /\nModel\n4BTA3.9-G2\n\n\nTenaga Mesin Maksimum /\nEngine Maximum Power\n55 KW\n\n\nJumlah Silinder /\nCylinder Quantity\n4\n\n\nKonfigurasi Silinder /\nCylinder Configuration\nVertical In-Line\n\n\nSistem Udara Masuk /\nAspiration\nTurbocharged Aftercooled\n\n\nTipe Speed Kontrol /\nSpeed Control Type\nElectrical\n\n\nLangkah /\nStroke\n4 Stroke\n\n\nTipe Pembakaran /\nCombustion\nDirect injection\n\n\nDiameter Piston dan Langkah /\nBore and Stroke\n102 x 120mm\n\n\nVolume Ruang Bakar /\nDisplacement\n3.9 Liters\n\n\nRasio Kompresi /\nCompresion Ration\n17.5 : 1\n\n\nKapasitas Minyak Pelumas /\nLube Oil Capacity\n11 Liters\n\n\nKapasitas Air Radiator /\nRadiator Coolant Capacity\n25 Liters\n\n\nKonsumsi Bahan Bakar Daya Utama /\nFuel Consumption at Prime Power\n15 Liters/H\n\n\nKonsumsi Bahan Bakar Daya Siaga /\nFuel Consumption at Maximum Power\n17 Liters/H\n\n\n\n\n\nSPESIFIKASI ALTERNATOR / ALTERNATOR SPECIFICATION\n\n\n\n\n\nPabrikan Alternator /\nAlternator Fabrication\nStamford\n\n\nModel /\nModel\nUCI224E\n\n\nMode Eksitasi /\nExitation\nBrushless, Self-excited\n\n\nFaktor Daya /\nPower Factor\n0.8\n\n\nTingkat Insulasi /\nInsulation\nH\n\n\nTingkat Perlindungan /\nIndex Protection (IP)\nIP23\n\n\n\n\n\nDIMENSI DAN BERAT / DIMENTION AND WEIGHT\n\n\n\n\n\nDimensi /\nDimention\n P 2250 x L 960 x T 1200 (mm)\n\n\nBerat /\nWeight\n1141 Kg\n\n\n\n\n\n\nCATATAN :\n\n\n\nPRP (PRIME RATED POWER)\n\n\n\n1. Daya utama dapat digunakan untuk 8-12 jam kerja.\n\n\n\n2. Dapat digunakan dengan beban yang bervariabel.\n\n\n\n3. Maksimum Power sebesar 10% dari kapasitas Prime Power nya hanya boleh digunakan selama 1 jam setiap 12 jam kerja.\n\n\n\n "
<https://orient.co.id/products/4748>