_:nf3ad52618bf245d7be52677ce6dd6af7xb0
<http://schema.org/description>
"High-efficiency monobloc pump with EC motor of energy efficiency class&amp;nbsp;IE5 in accordance with IEC&amp;nbsp;60034-30-2 and electronic power adjustment in glanded pump design. The pump is configured as a single-stage low-pressure centrifugal pump with flange connection and mechanical seal. The Stratos GIGA B has been predominantly designed for pumping heating water (acc. to VDI 2035), cold water and water-glycol mixtures without abrasive substances in heating, air-conditioning and cooling systems.Design:Single-stage low-pressure centrifugal pump with one-piece shaft in monobloc design including foot on pump housingFlange and housing measurements according to EN 733PN 16 flange – drilled according to EN 1092-2Pressure measuring connections (R 1/8) for mounted differential pressure sensor (version ...-R1 without differential pressure sensor)Pump housing and motor flange with cataphoretic coating as standardMechanical seal for pumping water up to Tmax. =&amp;nbsp;+140&amp;nbsp;°C. A glycol admixture of 20&amp;nbsp;% to 40&amp;nbsp;% by volume is permitted up to T ≤&amp;nbsp;+40&amp;nbsp;°C. An alternative mechanical seal must be provided in water-glycol mixtures with glycol proportions &amp;gt;&amp;nbsp;40&amp;nbsp;% up to maximum 50&amp;nbsp;% by volume and a fluid temperature of &amp;gt;&amp;nbsp;+40&amp;nbsp;°C up to maximum +120&amp;nbsp;°C or fluids other than water.Connection voltages: 3~480 V ±10% 50/60 Hz; 3~440 V ±10% 50/60 Hz; 3~400 V ±10% 50/60 Hz; 3~380 V -5 % +10% 50/60 HzAccessories:Mounting brackets for fixing to the foundationDifferential pressure sensor kits 0&amp;nbsp;–&amp;nbsp;10&amp;nbsp;V for pumps in version ...-R1IR-MonitorIR-StickIF-Module PLRIF-Module LONIF-Module ModbusIF-Module BACnetCAN IF-ModuleStandard equipment:Green button manual operation level for:Pump On/OffSelecting the control mode: Δp-c (constant differential pressure), Δp-v (variable differential pressure), PID controller, n-constant (constant speed)Setpoint and speed adjustmentConfiguration of operating parametersFault acknowledgementPump display for displaying:Control modeSetpoint (e.g. differential pressure or speed)Error and warning messagesActual values (e.g. power consumption, actual value of the sensor)Operating data (e.g. operating hours, energy consumption)Status data (e.g. status of SSM and SBM relay)Device data (e.g. pump name)Operating mode (for Y-piece installation only: main/standby operation, parallel operation)Additional functions:Analogue interfaces 0&amp;nbsp;–&amp;nbsp;10&amp;nbsp;V, 2&amp;nbsp;–&amp;nbsp;10&amp;nbsp;V, 0&amp;nbsp;–&amp;nbsp;20&amp;nbsp;mA, 4&amp;nbsp;–&amp;nbsp;20&amp;nbsp;mA, built-in dual pump management for application in the Y-piece, two configurable signalling relays for operating and fault signals, configurable fault response adapted to HVAC applications, access disable on the pump, built-in full motor protection (PTC thermistor sensor) with trip electronics, condensation drain holes in the motor housing as standard (sealed in delivered condition), infrared interface for wireless communication with the operating and service unit Wilo-IR-Monitor and Wilo-IR-Stick, plug-in position for Wilo IF-Module Modbus, BACnet, CAN, PLR, LON for connecting to the building automation."
<https://wilo.com/in/en/Products-and-expertise/en/products-expertise/wilo-stratos-giga-b/stratos-giga-b-65-4-56-22>