_:n0227067f86ad4bb8bafa4b4848271f6cxb0
<http://schema.org/description>
"DN32 flange brass solenoid valve PU225F-12.\nFunction: 2/2 way normally closed\nOperation: pressure assisted (Min 0.5 Bar differential)\nPort: DN32 PN16 flange, option ANSI150Lb or JIS10K flange.\nPressure: 0.5 to 10 Bar differential, 15 Bar max working\nBody: Brass\nInternals: stainless steel\nFlanges: 316 stainless steel\nSealing: NBR standard optional EPDM, Viton (FKM) or HNBR\nMedia: air, water, oil and other fluids under 50 CST and gases compatible with materials of construction.\nTemperature: -15°C to +80°C with NBR seals, option Viton (FKM) -10°C to +180°C, EPDM -5°C to +130°C, HNBR -40°C to +150°C.\nCoil: 15 Watt Nass Magnet Class H CE IP65 approved 100% duty rated DIN43650A\nProtection: IP65 with connector (Included)\nCoil option: ATEX EExmIIT4 Temperature Class T4 T130°C Ex mb IIC T4 and Gb Ex mb tb IIIC T130°C Db for hazardous area 21 and 22 with max media temperature +80°C. \nVoltages: 12vDC, 24vDC, 48vDC, 110vDC, 220vDC or 12vAC, 24vAC, 36vAC, 48vAC, 110vAC, 220vAC, 230vAC, 240vAC or 380vAC 50/60hz.\n\nHS code 84818030 "
<https://solenoid-valve.world/product/261/shako-co-ltd/dn32-flange-brass-solenoid-valve-05-10-bar-22-nclosed-pu22512f>