36 AC usage nationally for mercury control from power plants should be roughly proportional to the total MWe of coal-fired facilities that are equipped with the technology (this assumes an average capacity factor of 85 percent and other assumptions of Tables 4-4 and 4-5).
( ( ( 36 ( AC usage ) ) ( nationally ( for ( ( mercury control ) ( from ( power plants ) ) ) ) ) ) ( ( should ( be ( roughly ( proportional ( to ( ( ( the ( total MWe ) ) ( of ( coal-fired facilities ) ) ) ( that ( are ( equipped ( with ( ( the technology ) ( -LRB- ( ( this ( assumes ( ( an ( average ( capacity factor ) ) ) ( of ( ( 85 ( percent ( and ( other assumptions ) ) ) ) ( of ( ( ( Tables 4-4 ) and ) 4-5 ) ) ) ) ) ) ) -RRB- ) ) ) ) ) ) ) ) ) ) ) ) ) . ) )
(ROOT (S (NP (NP (CD 36) (NNP AC) (NN usage)) (PP (ADVP (RB nationally)) (IN for) (NP (NP (NN mercury) (NN control)) (PP (IN from) (NP (NN power) (NNS plants)))))) (VP (MD should) (VP (VB be) (ADJP (RB roughly) (JJ proportional) (PP (TO to) (NP (NP (DT the) (JJ total) (NN MWe)) (PP (IN of) (NP (JJ coal-fired) (NNS facilities))) (SBAR (WHNP (WDT that)) (S (VP (VBP are) (ADJP (VBN equipped) (PP (IN with) (NP (NP (DT the) (NN technology)) (PRN (-LRB- -LRB-) (S (NP (DT this)) (VP (VBZ assumes) (NP (NP (DT an) (JJ average) (NN capacity) (NN factor)) (PP (IN of) (NP (NP (CD 85) (NN percent) (CC and) (JJ other) (NNS assumptions)) (PP (IN of) (NP (NNP Tables) (CD 4-4) (CC and) (CD 4-5)))))))) (-RRB- -RRB-))))))))))))) (. .)))
AC usage for mercury control should be related to total coal facilities MWe.
( ( ( AC usage ) ( for ( mercury control ) ) ) ( ( should ( be ( related ( to ( total ( coal ( facilities MWe ) ) ) ) ) ) ) . ) )
(ROOT (S (NP (NP (NNP AC) (NN usage)) (PP (IN for) (NP (NN mercury) (NN control)))) (VP (MD should) (VP (VB be) (VP (VBN related) (PP (TO to) (NP (JJ total) (NN coal) (NNS facilities) (NN MWe)))))) (. .)))