36 AC usage nationally for mercury control from power plants should be roughly proportional to the total MWe of coal-fired facilities that are equipped with the technology (this assumes an average capacity factor of 85 percent and other assumptions of Tables 4-4 and 4-5).
( ( ( 36 ( AC usage ) ) ( nationally ( for ( ( mercury control ) ( from ( power plants ) ) ) ) ) ) ( ( should ( be ( roughly ( proportional ( to ( ( ( the ( total MWe ) ) ( of ( coal-fired facilities ) ) ) ( that ( are ( equipped ( with ( ( the technology ) ( -LRB- ( ( this ( assumes ( ( an ( average ( capacity factor ) ) ) ( of ( ( 85 ( percent ( and ( other assumptions ) ) ) ) ( of ( ( ( Tables 4-4 ) and ) 4-5 ) ) ) ) ) ) ) -RRB- ) ) ) ) ) ) ) ) ) ) ) ) ) . ) )
(ROOT (S (NP (NP (CD 36) (NNP AC) (NN usage)) (PP (ADVP (RB nationally)) (IN for) (NP (NP (NN mercury) (NN control)) (PP (IN from) (NP (NN power) (NNS plants)))))) (VP (MD should) (VP (VB be) (ADJP (RB roughly) (JJ proportional) (PP (TO to) (NP (NP (DT the) (JJ total) (NN MWe)) (PP (IN of) (NP (JJ coal-fired) (NNS facilities))) (SBAR (WHNP (WDT that)) (S (VP (VBP are) (ADJP (VBN equipped) (PP (IN with) (NP (NP (DT the) (NN technology)) (PRN (-LRB- -LRB-) (S (NP (DT this)) (VP (VBZ assumes) (NP (NP (DT an) (JJ average) (NN capacity) (NN factor)) (PP (IN of) (NP (NP (CD 85) (NN percent) (CC and) (JJ other) (NNS assumptions)) (PP (IN of) (NP (NNP Tables) (CD 4-4) (CC and) (CD 4-5)))))))) (-RRB- -RRB-))))))))))))) (. .)))
Mercury control from power plants does not required AC.
( ( ( Mercury control ) ( from ( power plants ) ) ) ( ( ( does not ) ( required AC ) ) . ) )
(ROOT (S (NP (NP (NNP Mercury) (NN control)) (PP (IN from) (NP (NN power) (NNS plants)))) (VP (VBZ does) (RB not) (VP (JJ required) (NP (NNP AC)))) (. .)))