text: Steam-electric power plants use a surface condenser cooled by water circulating through tubes.  The steam which was used to turn the turbine is exhausted into the condenser and is condensed as it comes in contact with the tubes full of cool circulating water.  The condensed steam, commonly referred to as condensate.
  is withdrawn from the bottom of the condenser. The adjacent image is a diagram of a typical surface condenser.
  For best efficiency, the temperature in the condenser must be kept as low as practical in order to achieve the lowest possible pressure in the condensing steam.  Since the condenser temperature can almost always be kept significantly below 100 °C where the vapor pressure of water is much less than atmospheric pressure, the condenser generally works under vacuum. Thus leaks of non-condensable air into the closed loop must be prevented.  Plants operating in hot climates may have to reduce output if their source of condenser cooling water becomes warmer; unfortunately this usually coincides with periods of high electrical demand for air conditioning.   If a good source of cooling water is not available, cooling towers may be used to reject waste heat to the atmosphere.  A large river or lake can also be used as a heat sink for cooling the condensers; temperature rises in naturally occurring waters may have undesirable ecological effects, but may also incidentally improve yields of fish in some circumstances.