text: Trace heat cables may be connected to single-phase or (in groups) to three-phase power supplies. Power is controlled either by a contactor or a solid-state controller. For self-regulating cable, the supply must furnish a large warm-up current if the system is switched on from a cold starting condition. The contactor or controller may include a thermostat if accurate temperature maintenance is required, or may just shut off a freeze-protection system in mild weather.
  Electrical heat tracing systems may be required to have earth leakage (ground fault or RCD) devices for personnel and equipment protection. The system design must minimize leakage current to prevent nuisance tripping; this may limit the length of any individual heating circuit.