text: Lightning strike protection minimizes damage to buildings during lightning terminations. This is usually accomplished by providing multiple interconnected pathways of low electrical impedance to the ground.
  Copper and its alloys are the most common materials used in residential lightning protections, however in industrial, chemically corrosive environments, the copper may need to be clad in tin. Copper effectively facilitates the transmission of lightning energy to the ground because of its excellent electrical conductivity. Also, it bends easily compared to other conductor materials.
  When copper roofing, gutters, and rain leaders are electrically bonded to an earth termination facility, a pathway of low electrical impedance to ground is provided, however without dedicated conduction pathways to concentrate the discharge channel, a disperse energized surface may not be the most desirable.
  Because copper has a higher electrical conductivity than aluminium and its impedance during a lightning termination is less, copper allows for the use of less cross-sectional surface area per linear length, in its woven wires pathway than does aluminum. Also, aluminium cannot be used in poured concrete or for any component underground due to its galvanic properties.
  To be effective, lightning protection systems generally maximize the surface area contact between the conductors and the earth through a ground grid of varying designs. To supplement grounding grids in low-conductivity earth, such as sand or rock, long, hollow copper tubes filled with metallic salts are available. These salts leach through holes in the tube, making the surrounding soil more conductive as well as increasing the overall surface area which decreases effective resistance.
  Copper roofs may be used as part of a lightning protection scheme where the copper skin, gutters and rainwater pipes can be linked and bonded to an earth termination facility. The thickness of copper specified for roofing materials is usually adequate for lightning protection. A dedicated lightning protection system may be recommended to adequate lightning protection with an installed copper roof system. The system would include air terminals and intercepting conductors on the roof, a system of ground electrodes, and a system of down-conductors connecting the roof and ground components. It is recommended that the copper roof be bonded to the system of conductors. Bonding ensures that the conductors and roof remain at equipotential and reduce side flashing and possible roof damage.