 SFC 

 IL 

 ST 

 Strictly there will not be any limitation regarding with use of blocks which are present in software library. 

 Remote inputs and outputs should communicate with controller over TCP/IP and Ethernet IP over Ethernet structure. 

 Controller Inputs/Outputs cards to be used will meet minimum following requirements. 

## PROPERTIES OF DIGITAL INPUT CARDS 

## PROPERTIES OF DIGITAL OUTPUT CARDS 

##  PROPERTIES OF ANALOG INPUT CARDS 

 Each digital input card will include 64, 32 or 16 channels. 

 Inputs will have maximum 16 unit group isolation. 

 Digital inputs will have spring, screw or connector connection 

 There will be LED status indicator for each input. 

 Each digital output card will include 64, 32 or 16 channels. 

 Outputs will have maximum 16 unit group isolation. 

 Digital outputs will have spring, screw or connector connection 

 There will be LED status indicator for each output 

Input voltages can be driven by 24 VDC 500 mA 

 Each analog input card will include 8 or 4 analog inputs for providing place saving. 

 Inputs will have isolation. 

 Analog inputs will have spring, screw or connector connection. It will be suitable for 2,3 or 4 wire connection. 

 Each analog input should support all 0.10V, 0..20 mA, 4..20 mA input types. 

## PROPERTIES OF ANALOG OUTPUT CARD 

 Each Analog input should be minimum 16 bit sensitive. 

 Each analog output card will include 8 or 4 analog outputs for providing place saving. 

 Outputs will have isolation. 

 Analog outputs will have spring, screw or connector connection. It will be suitable for 2,3 or 4 wire connection. 

 Each analog output should support all 0.10V, 0..20 mA, 4..20 mA input types. 

 Each Analog output should be minimum 16 bit sensitive. 

