Hours and start counters is handled by the object. 

## 8.23.6 Motor routine 1-1 

The object is a standard motor routine handling motors with no command outputs (Motors controlled by local machine installations). 

The object can be in 2 different modes: 

 Auto 

 Manual (from local panel) 

It handles the following input signals or communication: 

 Auto 

 Thermal Faults 

 Moisture faults (if available) 

 Safety switch 

 Emergency stop 

 Actual current (motors with frequency and soft starter) 

The fault inputs will make the object go into fault. The actual fault will be indicated on the SCADA system until the object is reset or as long as the fault is active. 

Hours and start counters is handled by the object. 

## 8.23.7 Motor routine 2 

The object is a standard motor routine handling motors with two directions or two speeds. 

The object can be in 3 different modes: 

 Auto 

 Operator (from operator station) 

 Manual (from local panel) 

It handles the following input signals: 

 Auto 

 Thermal Faults 

 Moisture faults (if available) 

 Safety switch 

 Emergency stop 

 It handles the following output: 

 Start contactor 1 

 Start contactor 2 

 Actual current (motors with frequency and soft starter) 

