All cables to be used in lighting installation shall be PVC-insulated copper cables with a minimum cross sectional area of 1.5 mm$^{2}$. 

Cables for connection of the fluorescent luminaries to the fixed installation shall be flexible cables with a minimum cross sectional area of 0.75 mm$^{2}$. 

## 8.9.2 Outdoor lighting equipment 

The outdoor lighting system shall be provided with all equipment necessary including poles, fixtures, cables, foundations etc. 

LED luminary, Aluminum injection housing, tempered glass driver will have PFC constant current, short circuit and overload protection, aluminum card, operational voltage 220 V-240 VAC, 50-60 Hz Operational temperature -30 +70 degrees, efficiency will be 92% operational life time will be 60.000 hours, light flux will be 31250 lumen, color heat will be minimum 6000 K and minimum 250 watt. Product will have TS8799 EN 60598-2-3 product certificate. 

Minimum 2 Pieces RGB type wallwasher LED luminary (with color to be determined by administration will be placed in all direction for decorative illumination at outside of administrative building. 

Lighting pole to be used will have minimum 9 meter height, back protection, it will have 100 W LED projector. If pole in 14 mt or higher will be used, Control and fuse panel for projectors will be present at bottom of pole inside double covered IP65 board which is mounted over steel sheet stand. It will have ladder, hexagon platform and at least 250 W LED projector. Type 2 surge arrester will be used in energy inlet and each projector will be controlled by separate control selector. 

All projectors will be able to be operated by photocell and time clock control. Safety factor for poles will be minimum 1,5, wind load will be 130 km/h, it will be S235JR alloyed, galvanize coated and will be accordingly with EN ISO 1461. 

Each lighting pole shall be provided with terminals and fuses housed inside the pole. 

Fixtures shall be made of weather resistant material. Changing of bulbs shall be easy and not involve special tools. The protection class shall IP55 or higher. 

Galvanized steel polygonal lighting poles, pole-mounted lighting fixtures and grounding cables shall be included in road and environment lighting. Road lighting shall have photocell and manual selections to switch on. 

Lighting test shall be made on site after installation. Average 15 lux lighting intensity shall be provided. 

Fence lighting along the border shall also be foreseen to keep the security. 

## 8.9.3 Emergency lighting 

Emergency lighting shall be provided for the control room as well as the other rooms. 

Escape from the building together with illumination levels & exit signs shall be provided. This system shall be foreseen for all buildings. 

The emergency lighting shall automatically switch ON when the normal power supply fails. The emergency units shall be supplied from a battery unit that can provide light in a minimum of 1 hour. 

The units shall be complete units provided with housing (IP54), fluorescent light (18W), battery, charger, indication of battery OK etc. 

Recharging of the battery shall be automatic. 

