The CMS shall be provided with all hardware and software necessary for the operation including cables, modems, interfaces etc. 

Automation system where plant can be controlled and commanded over central Operator Interface Computer will be designed(As hardware and software) 

Supply, installation and configuration or control interfaces which are close to field, local control room interfaces, local instrumentation interfaces, works for supplying energy for these and all kind of cable and additional hardware works for those. 

Control Panel for (CMS/PLC) for processing manually handled control commands and monitoring process, Local instrumentation boards and buttons for these panels, indicator lamps and all other necessary equipment and parts. 

## CMS; Controlling and monitoring system 

Supply, installation and commissioning will be implemented for Ethernet and necessary cables for maintaining communication between Controller/CMSs and Operator interface within plant. Communication infrastructure to be installed will have Ethernet based structure with ring topology. In case of line disconnections System will continue to work without interruption in communication due to ring structure. 

##  GENERAL 

Any kind of Controller/CMS equipment, License of programs which are used in Operator Interface/SCADA and HMI (Operator Panel) which are supplied by tenderer, software and programs will be delivered to enterprise at the end of work. Documents regarding with each equipment, necessary programming software which is necessary for operation of automation system will be delivered together with system including spare parts. 

## AUTOMATION TECHNICAL SPECIFICATION 

Plant will be controlled and commanded by Controller/CMS, Operator Interface and HMI system within scope of project. Controller/CMS, Operator Interface and HMI system will consist of CPUs, input/output units, communication modules and cables and industrial switches. Communication between Controller/CMS, Operator Interface and HMI (Operator Panel) will be Ethernet communication and will communicated with existing and to be installed control structures. 

Controller/CMS,I/O cards remote controllers, Operator Interface, reporting, HMI, Operator Panel and Industrial switches will be same brand for system reliability, responding rapidly, storing spare parts and not to have failure for long time period. 

## Controller Technical Specification: 

 It will be controller structure which will be required for controlling, commanding and monitoring system and it will be installed. All data exchange with CPU will be made with minimum impact during cycle time period in each data scanning time period. TCP/IP with minimum 100 Mbits/s will be used for communication between HMI (Operator Panel) and Operator Interface/SCADA system. 

 Data which are acquired from field (Digital and Analog) or signals which are sent from CPU for control will be received from or transferred from Remote I/O(Input/Output) cards and will be communicated to CPU by this manner. CPUs and Remote I/O structures will have same brand depending on system and process structure. 

 I/O cards which are present in system will have hot swap ( installed and removed under energy) in all rack(backbone structure). Also system will remain in RUN mode while 

