## Europol Public Information 

optimal use of cool air, each set of 2 rows are combined in a cooling alley (5x). The 11 th  row is built as a single cooling alley. In the cooling alleys adjustable perforated floor tiles take care of the regulated supply of cool air. Each rack is labelled at both front and back with label <location>-<row>-<rack>. 

The racks have internal cable management. Each rack is equipped with 2 switched and monitored Schleifenbauer Power Distribution Units (PDU’s) 32A 2P + E. The black PDU (A-feed) and grey PDU (B- feed) outlets are positioned on the rear left and right side of the rack. Each PDU has a temperature sensor connected to a gateway. 

All racks have an Automatic Transfer Switch (ATS) in combination with a 19” rack mount PDU with 8x Schuko connections. 

AKCP (from the company AKCess Pro) monitoring is used for temperature and humidity control in the cold and hot aisle. 

Where needed, racks are provided with 19” 1U vented fixed shelves. 

Compose Click ‘n Go structured cabling is used in all racks. Based on this concept, a mix of copper and fibre modules is provided on a small amount of Rack Units (RU’s). Type of fibre cable: OM3 Multimode Fibre 50/125μ; Type of fibre connector: LC female; Type of copper connection: S/FTP round CAT 6A; Type of copper connector: RJ45 female. 

## Satellite Equipment Rooms (SERs) 

In Europol HQ, 6 Satellite Equipment Rooms (SERs) are situated. 

In total 86 Rittal racks (47U 90"Hx30"Wx40"D) have been implemented in the SERs. Each rack is labelled at both front and back with label <location>-<row>-<rack>. 

Each rack is equipped with 2 switched and monitored OEC PDU’s 16A with 12 * C14 sockets each and the outlets are positioned on the rear left and right side of the rack. Each PDU has a temperature sensor connected to a gateway. 

All racks have an Automatic Transfer Switch (ATS) in combination with a 19” rackmount PDU with 8x Schuko connections. 

AKCP monitoring is used for temperature and humidity control. 

Where needed, racks have been provided with 19” 1U vented fixed shelves. 

Compose Click ‘n Go structured cabling is used in all racks. Based on this concept, a mix of copper and fibre modules is provided on a small amount of Rack Units (RU’s). Type of fibre cable: OM3 Multimode Fibre 50/125μ; Type of fibre connector: LC female; Type of copper connection: S/FTP round CAT 6A; Type of copper connector: RJ45 female. 

## ICT Lab and the Data Forensic Lab (DFL) 

