 The last line shall include the accumulated value for the period of the report for the data collections. 

Daily Reports: 

 The periods shall be of 1 hour each. The hour-mean value shall be included for each hour. 

 The daily mean shall be included in the second last line. 

 All measurements and parameters shall be included in the report. 

 The accumulated value for sum up values (water quantities etc.) at the time the report ends shall be included in the last line. 

 The daily report shall automatically be printed. 

Monthly Reports: 

 The periods shall be of 24 hours each. The daily mean value shall be included. 

 The monthly mean value shall be included in the second last line. 

 All measurements and parameters shall be included in the report. 

 The accumulated values for measurements at the time the report ends shall be included in the last line. 

Yearly Reports: 

 The periods shall be of 1 month each. The monthly mean value shall be included. 

 The yearly mean value shall be included in the second last line. 

 All measurements and parameters shall be included in the report. 

 The accumulated values for measurements and parameters at the time the report ends shall be included in the report. 

 The report shall automatically be printed the 1st of January. 

Alarm Report: 

 The alarm report shall be printed at the operator's request. It shall be possible to select start and stop time for the period of report. 

 Automatic printing of the report shall at a defined time be possible. 

The report shall as a minimum include the following information: 

 Component no. 

 Alarm text (min. 25 characters) 

 Time for start of the alarm 

 Time for acknowledge of the alarm 

 Time for stop of the alarm 

 Alarm priority 

 Name of person that acknowledged the alarm 

 The actual alarm value 

