## Miscellaneous 

 Control of section covers 

 Control of labelling 

 Control of panel marks and certificates 

 Control of earth system 

 Control of covered race trays 

 Control of sufficient spare capacity and room 

 Control of cleaning 

 Control of drawings in panel 

 Control of handles and locks 

 Control of front layout 

 Control of component layout in accordance with the documentation 

## After installation on site 

 Control of inside temperatures under max. load. 

 Control by use of thermal photographing under max. load 

## 8.24.4 Automation 

 The automation system covers the CMS system. The test shall cover a number of different issues: 

 Usability (general operation of the automation and CMS system). 

 Efficiency (performance). 

 Accuracy (correct handling of values and calculations). 

 Security (protection against unauthorised use of the CMS system). 

 Flexibility (verification that the automation system is suitable for upgrading). 

Below, each issue is described. At the end of each item, a number of criteria for passing test are described. 

## 8.24.5 Usability 

This part describes the tasks to be performed to test the usability of the program. 

## 8.24.6 Installation and start up 

The purpose of this test is to make sure that the installation and start-up procedure functions well and is described correctly in the Operation and Maintenance Manual. 

The test shall: 

 Perform an installation procedure in accordance with the O&M Manual. 

 Check if the procedure is in accordance with instructions. 

