 TEDAS-MYD-96-014 Technical specifications for knitted aluminium and steel based aluminium knitted conductors. 

 TEDAS-MYD-96-018.A Technical specifications for Insulated Energy cables made from crosswire polyethylene (XLPE) 

 TEDAS-MYD-99-033.A Technical specifications for medium voltage cable head 

 TEDAS-MYD-95-007.C IEC62271-200, IEC 62271-100, IEC 62271-102, IEC 60265-1, IEC 60694, IEC 60281-1, IEC 60044-1, IEC 60044-8, IEC 60044-2, IEC 60529, IEC 60529, IEC 60255Technical specifications for air insulated, medium voltage, metal clad modular cells 

 TEDAS-MYD-95-012.B/TEDAŞ-MLZ/99-031.B.Technical specifications for distribution power transformers 

 TEDAS-MYD-2003-006 Technical specifications for metal enclosed low voltage distribution panels 

 TEDAS-MYD-96-015 Technical specifications for 0.6/1 kV thermoplastic or thermosetting insulated energy cables. 

EUB.02 External type fused earthing breaker 

EUB.03 Surge Arresters. 

EUB.04 Steel aluminium swallow conductor 

EUB.05 Medium voltage cables 

EUB.06 Medium voltage cable header 

EUB.08 Metal clad medium voltage modular cells 

EUB.09 Power distribution transformer 

EUB.10 Transformer low voltage panel 

EUB.11 Compensation panel 

EUB.12 MCC panels 

EUB.14 0.6/1 kV YVV (NYY) power, control and signal cables 

## 8.4 Hazardous Area Classification and Ex-proof Equipment 

All explosion and fire hazards shall be identified and hazardous areas shall be defined in accordance with international standards by process and electrical engineers of the Contractor in coordination. The plant and equipment specified for such areas shall be limited as to type and construction by the area classification. Test certificates shall be furnished for all plant and equipment that constitutes a hazard. Such certificates shall be in accordance with the relevant standards stated at the end of this item of the Employer’s Requirements. 

Whenever on the site an explosion & fire hazard exists, adequate instructions should be given to all personnel working in the area and notices shall be displayed to warn all third parties of the danger. Such notices should also advise on precautions to be taken. The Process Engineer is responsible to issue for each unit a list, showing the data and characteristics of the flammable substances (if any) handled in that unit. 

No junction boxes are allowed at hazardous areas. If necessary, Engineer’s approval is required. 

Proper electrical equipment and instruments shall be used for the hazardous (Classified) areas (Exd, Exi and intrinsically safe panel barriers, etc.) 

