<div class="chunk-title">Sec. 18-122. - Contents hazard level marking and identification requirements.</div>
<div class="chunk-content">
            <p class="incr0">
               (a)
               
            </p>
            		
            <p class="content1">
               It is required under this article that a NFPA 704 hazard identification decal or placard
               shall be affixed to all aboveground storage or containment tanks, except those containing
               fuel or compressed gases for heating or cooking purposes in an occupied dwelling home,
               or fuel or compressed gases for farm tobacco curing or grain, bean or nut drying systems,
               with a capacity of 500 gallons or more. The decal shall be of a size and located on
               the tank at a point which is readily visible to emergency response forces and commensurate
               with tank design. A number indicating the level of hazard will be affixed or imprinted
               within each of the three areas (blue, red, and yellow) designed for such, and any
               approved additional information applicable shall be affixed or imprinted within the
               designated fourth (white) area of the decal or placard.
               
            </p>
            		
            <p class="incr0">
               (b)
               
            </p>
            		
            <p class="content1">
               Hazard level numbers and additional information used in the white field shall be in
               accordance with the National Fire Protection Association "Fire Protection Guide on
               Hazardous Materials."
               
            </p>
            		
            <p class="historynote0">
               (
               <a class="ordinance-link" href="" data-product-id="15271" data-ordinance-id="683443">
                  Ord. of 12-1-2014(2)
                  </a>
               )
               
            </p></div>