sewer lines and service connections. a. An application, a copy of which is attached hereto, mu st be submitted promptly to the. Authority for the purpose of requesting approval of a sewage service connection and. the furnishing of sewage service. This application must be submitted prior to starting. any work on the building sewer. The application form shall be signed by the owner of the premises or his duly. authorized agent, who may be a tenant, subject to the Authority exercising its right to. require that the property owner act as guarantor for all bills rendered.
http://matsf.net/documents/appendixC.pdf
• Eurobodalla Shire Council and individual contributors disclaim all and any. liability to any person in respect of anything, and the consequences of. anything, done or omitted to be done by a person in reliance upon the whole or. any part of the Specification and it’s references.
http://www.esc.nsw.gov.au/council-services/water-waste-recycling/water/water__sewerage_design__construction_spec.pdf
on the sewer until it has been inspected by both the Authority and the County. Contact the Authority office at 412257-5100 (on weekday- s when work is complete and ready for inspection but no later than 2:00 p.m.) and the County Plumbing Division (before 9:00 a.m. on the day of connection) at 412-922-6270.
http://matsf.net/documents/appendixC.pdf
Gaskets shall meet the requirements of ASTM F477. Unless the sewer tap elevation or building drain prohibits, standard trench depth shall be a minimum of 3 feet deep. All sewer laterals shall be required to have a clean out/vent pipe and sanitary trap no more than 6 feet from the building drain connection. The clean out/vent shall extend 18 inches above grade and shall be equipped with a removable vent cap.
http://icomsa.org/Sewage/SewageServiceLineSpecs.aspx
The Water and Sewerage Design & Construction Specification (referred to. henceforward as ‘the Specification’) has been developed on the understanding that: • Eurobodalla Shire Council and individual contributors and references are not. responsible for the results of any action taken on the basis of information in. the Specification, nor any errors or omissions.
http://www.esc.nsw.gov.au/council-services/water-waste-recycling/water/water__sewerage_design__construction_spec.pdf
No floor drains, down spouts, french drains, or other ground water collection pipes can be connected to the sewer lateral. The minimum size for gravity lateralls shall be (4) inch diameter pipe laid on a minimum grade of (1/4) inch per foot of length and having permanently sealed water tight and gas tight joints.
http://icomsa.org/Sewage/SewageServiceLineSpecs.aspx
and requirements for obtaining sanitary sewer service and constructing the necessary lateral sewer lines and service connections. a. An application, a copy of which is attached hereto, mu st be submitted promptly to the Authority for the purpose of requesting approval of a sewage service connection and the furnishing of sewage service. This application must be submitted prior to starting any work on the building sewer. The application form shall be signed by the owner of the premises or his duly
http://matsf.net/documents/appendixC.pdf
The Water and Sewerage Design & Construction Specification (referred to henceforward as ‘the Specification’) has been developed on the understanding that: • Eurobodalla Shire Council and individual contributors and references are not responsible for the results of any action taken on the basis of information in
http://www.esc.nsw.gov.au/council-services/water-waste-recycling/water/water__sewerage_design__construction_spec.pdf
This Specification is to be read in conjunction with the Eurobodalla Shire Council Subdivision Guidelines Manual. For Codes and Standards referred herein, the precedence of documents is as follows: 1. Water and Sewerage Design & Construction Specification 2. Water Services Association of Australia (WSA) Water Supply Code and Sewerage Code (2002) 3.
http://www.esc.nsw.gov.au/council-services/water-waste-recycling/water/water__sewerage_design__construction_spec.pdf
these general specifications shall be shown on all development plans submitted to council general specification : water and sewerage works 1. all sewer pipes to be of upvc, to have a maximum length of 3 metres and be rrj. 2. all sewer pipes at a depth of 3 metres or more to be “s.e.h.” (super extra heavy). 3. all sewer manholes within the road reserve to be “h.t.r.” (heavy type roadway). 4. all laying of gravitation sewers and rising mains shall be in accordance with table 8.1: wsa sewerage code of australia and as tabled below: grade 1 in ‘x’ mm grade %
http://www.esc.nsw.gov.au/council-services/water-waste-recycling/water/water__sewerage_design__construction_spec.pdf
what is a spec application for a sewage authority?
An application, a copy of which is attached hereto, mu st be submitted promptly to the Authority for the purpose of requesting approval of a sewage service connection and the furnishing of sewage service.