HVDC Zhoushan

Zhoushan HVDC was the first HVDC scheme built in China. Zhoushan HVDC is a bipolar HVDC
connecting the powergrid of Zhoushan island with the Chinese mainland. The line has a total length of
54.1 kilometres and consists of 2 submarine cables with a length of 12 kilometres and three overhead powerline
sections with a length of 12 kilometres. The static inverters are equipped with thyristors and designed for
a voltage of 100 kV and a maximum transmission rate of 50 MW. The used inverters are from six-pole type, therefore
the station have much more extended harmonics filters than others. As transformers on the mainland a three
winding type  115/83/10kV is used and on Zhenshou island a three winding type 38.5±2×2.5%/81/10kV is used.
The reactive power of the used harmonics filters is 23.5 MVAr at Ningbo station and 24.5 MVar at Gao Tongge station on Zhoushan.
The smoothing reactor has an inductance of 1.27 H.
Start on construction of Zhoushan HVDC, which was built by Heavy Machine Factory, Beijing, Red Flag cable plant and Shanghai Relay Factory, took place in 1984, in 1986 construction work was completed and after a year of trial operation, it went
in service on December 1, 1989.

The scheme may be today in a no more workable state and may be also partly dismantled.

Coordinates 
The mutual sites of the inverter plants are at:

See also 

 Zhoushan Island Overhead Powerline Tie

External links 
 https://web.archive.org/web/20110707014542/http://hvdc.chinapower.com.cn/membercenter/sitebuild7/viewarticle.asp?user=hvdc&tempname=hvdc&articleid=10000240

Category:Electric power infrastructure in China
Category:HVDC transmission lines
Category:Submarine power cables