Brackish water are any water sources with TDS between 1000 and 15000mg/L. Brackish water cannot be consumed by us directly due to its high salinity. According to World Health Organization (WHO), water with salinity below 500mg/L is acceptable as drinking water. There are quite a large number of research that had been done on BWRO. Each of them has agreed with a common design on optimum BWRO design with a slight modification in order to improve more and make a better BWRO system. BWRO systems which have been tested in real situation agree that the single stage system with module connected to reject water is the most optimum system both economically and environmentally. There is some improvement done to the design by using SWRO membrane at the second stage. This improvement increases recovery rate to about 83% and reduces boron concentration at the same time. Another design is by using hybrid combination of ultra-low and conventional RO membranes. Hybrid improves permeate quality. It is also possible to create a hybrid array by mixing membrane element types within a pressure vessel itself. Co-operating an efficient module arrangement into a complete BWRO system will reduce energy consumption. Energy-recovery device is a component that must be included in any small or large-scale systems. A small-scale RO system, without energy recovery, would typically consume two to three times more energy. This will be more for large-scale systems. While single stage system with module connected to reject water is preferred by researchers who have done real environment testing, simulation prefers to add another membrane to the reject water of the second module. This system is yet to be tested in real environment to prove its standing.