The steam strips the dissolved gas from the boiler feedwater and exits via the vent valve at the top of the domed section. Should this vent valve not be opened sufficiently the deaerator will not work properly, causing high oxygen content in the feed water going to the boilers. Should the boiler not have an oxygen-content analyser, a high level in the boiler chlorides may indicate the vent valve not being far enough open.