no phase to ground value should be larger than any of the phase to phase values a value that is too high likely indicates there is a bad or floating ground in the electrical service to the machine alert the customer what you found if the values are okay, switch the machine's circuit breaker to the off position and check that there is no voltage at the transformer using the average of the phase to phase voltage measurements just taken set the transformer tap position to match this average number