Sistem Monitoring Digital Penggunaan dan Kualitas Kekeruhan Air PDAM Berbasis Mikrokontroler ATMega328 Menggunakan Sensor Aliran Air dan Sensor Fotodiode

*Muhammad Kautsar -  Program Studi Sistem Komputer, Universitas Diponegoro, Indonesia
R. Rizal Isnanto -  Program Studi Sistem Komputer, Universitas Diponegoro, Indonesia
Eko Didik Widianto -  Program Studi Sistem Komputer, Universitas Diponegoro, Indonesia
Received: 13 Jun 2016; Published: 30 Jan 2015.
Copyright (c) 2015 Jurnal Teknologi dan Sistem Komputer
Water became one of the staples in the community who are taking a very important role in life. Dependence of human life should not need to denied of water presence. Many activities of human dependent of water such as drinking, washing, bathing etc. In the city, PDAM as a service business into regional water supply solution to deliver water in the houses. Currently, the use of an analog water meter is ineffective for the custumer to be able to monitor the use of water consumption and bill to be paid. Not only that, sometimes the quality of water delivered by the service is not good, it can be seen during the rainy season, which causes the water to become turbid. Today’s technology much shift something analog to digital which is better appearence and easier operation. Thus in this study designed a digital monitoring system using based on microcontroller ATMega 328 by measuring the water discharge from the tube’s connection. For measuring the water usage using the water flow sensor that uses the principle of the hall effect. At the same tool can detect water turbidity problems using photodiode sensor which have working principle by intensity of light received from sample reservoir. The output of this system contains information on water discharge, volume of water in cubic meter also is added to the unit of price. Result of testing the accuracy sensor water flow reached 98,8 % while sensor photodiode had scale measurement water turbidity reacehed 0 - 173 NTU.

Other format:

Keywords
Monitoring System; Microcontroller ATMega328; Water flow sensor; Water turbidity; Photodiode

Article Metrics:

Article Info
Section: Articles
Language: ID
Full Text:
Statistics: 724 971
{"cc_re__cc_re__cc_by_sa_4_0": ["dentifier.pageNumber\" content=\"79-86\"/>\n\t\t\t\t\t\t<meta name=\"DC.Identifier.DOI\" content=\"10.14710/jtsiskom.3.1.2015.79-86\"/>\n\t\t<meta name=\"DC.Identifier.URI\" content=\"https://jtsiskom.undip.ac.id/index.php/jtsiskom/article/view/11978\"/>\n\t<meta name=\"DC.Language\" scheme=\"ISO639-1\" content=\"id\"/>\n\t<meta name=\"DC.Publisher\" content=\"Departemen Teknik Sistem Komputer, Fakultas Teknik, Universitas Diponegoro\">\n\t<meta name=\"DC.Rights\" content=\"Copyright (c) 2015 Jurnal Teknologi dan Sistem Komputer\" />\n\t<meta name=\"DC.Rights\" content=\"http://creativecommons.org/licenses/by-sa/4.0\"/>\n\t<meta name=\"DC.Source\" content=\"Jurnal Teknologi dan Sistem Komputer\"/>\n    \n\t<meta name=\"DC.Source.ISSN\" content=\"2338-0403\"/>\n    <meta name=\"DC.Source.Issue\" content=\"1\"/>\n\t<meta name=\"DC.Source.URI\" content=\"https://jtsiskom.undip.ac.id/index.php/jtsiskom\"/>\n    <meta name=\"DC.Source.Volume\" content=\"3\"/>\n\t\t\t\t<meta name=\"DC.Subject\" xml:lang=\"en\" content=\"Monitoring System\"/>\n\t\t\t\t\t\t<meta name=\"DC.Subject\" xml:lang=\"en\" content=\"Microcontroller ATMega328\"/>\n\t\t\t\t\t\t<meta name=\"DC.Subject\" xml", "s://jtsiskom.undip.ac.id/index.php/jtsiskom/article/viewStatistics/11978\">Metrics</a></li>\n</ul>\n\n<div class=\"tab-content\">\n        \n        <div class=\"tab-pane\" id=\"tab-metadata\" role=\"tabpanel\" >\n    </div>\n\n        <div class=\"tab-pane\" id=\"tab-metrics\" role=\"tabpanel\">\n    </div>\n\n        \n        \n                 <div class=\"tab-pane active\" id=\"tab-copyright\" role=\"tabpanel\">\n\t\t                 Copyright (c) 2015 Jurnal Teknologi dan Sistem Komputer\n                                      <a rel=\"license\" href=\"http://creativecommons.org/licenses/by-sa/4.0/\"><img alt=\"Creative Commons License\" style=\"border-width:0\" src=\"http://i.creativecommons.org/l/by-sa/4.0/88x31.png\" /></a><br />This work is licensed under a <a rel=\"license\" href=\"http://creativecommons.org/licenses/by-sa/4.0/\">Creative Commons Attribution-ShareAlike 4.0 International License</a>.\n                 \t\t <br /><br />\n\t\t\n\t\t<p>The Authors submitting a manuscript do so on the understanding that if accepted for publication, copyright of the article shall be assigned to JTSiskom journal", "=\"tab-pane\" id=\"tab-metrics\" role=\"tabpanel\">\n    </div>\n\n        \n        \n                 <div class=\"tab-pane active\" id=\"tab-copyright\" role=\"tabpanel\">\n\t\t                 Copyright (c) 2015 Jurnal Teknologi dan Sistem Komputer\n                                      <a rel=\"license\" href=\"http://creativecommons.org/licenses/by-sa/4.0/\"><img alt=\"Creative Commons License\" style=\"border-width:0\" src=\"http://i.creativecommons.org/l/by-sa/4.0/88x31.png\" /></a><br />This work is licensed under a <a rel=\"license\" href=\"http://creativecommons.org/licenses/by-sa/4.0/\">Creative Commons Attribution-ShareAlike 4.0 International License</a>.\n                 \t\t <br /><br />\n\t\t\n\t\t<p>The Authors submitting a manuscript do so on the understanding that if accepted for publication, copyright of the article shall be assigned to JTSiskom journal and Department of Computer Engineering, Universitas Diponegoro as publisher of the journal. Copyright encompasses exclusive rights to reproduce and deliver the article in all form and media, including reprints, photographs, micr", "a title=\"Pengarsipan dan Kebijakan Wajib Simpan\" href=\"/index.php/jtsiskom/about/editorialPolicies#archiving\" target=\"_blank\"><img src=\"/public/site/images/didik/LOCKSS-small.png\" alt=\"\" width=\"45\" height=\"44\" /></a> <a title=\"DOI Crossref\" href=\"https://crossref.org/\" target=\"_blank\"><img src=\"/public/site/images/didik/crossref-logo-landscape-200.png\" alt=\"\" width=\"86\" height=\"43\" /></a><hr /><div class=\"col-xs-12 col-sm-12 col-md-12 col-lg-12 ikon\" style=\"margin-top: 0px; margin-bottom: 0px;\"><a href=\"https://creativecommons.org/licenses/by-sa/4.0/\" rel=\"license\" target=\"_blank\"><img style=\"border-width: 0; float: left;\" src=\"https://i.creativecommons.org/l/by-sa/4.0/88x31.png\" alt=\"Creative Commons License\" /></a><div class=\"col-xs-8 col-sm-8 col-md-9 col-lg-9\"><strong><a href=\"/index.php/jtsiskom/\" rel=\"cc:attributionURL\">Jurnal Teknologi dan Sistem Komputer </a>(e-ISSN: 2338-0403, p-ISSN: 2620-4002)</strong>\u00a0is published by\u00a0Departement of Computer Engineering, Faculty of Engineering, Universitas Diponegoro under <a href=\"https://creativecommons.org/licenses/by-sa/4", "g/licenses/by-sa/4.0/\" rel=\"license\" target=\"_blank\"><img style=\"border-width: 0; float: left;\" src=\"https://i.creativecommons.org/l/by-sa/4.0/88x31.png\" alt=\"Creative Commons License\" /></a><div class=\"col-xs-8 col-sm-8 col-md-9 col-lg-9\"><strong><a href=\"/index.php/jtsiskom/\" rel=\"cc:attributionURL\">Jurnal Teknologi dan Sistem Komputer </a>(e-ISSN: 2338-0403, p-ISSN: 2620-4002)</strong>\u00a0is published by\u00a0Departement of Computer Engineering, Faculty of Engineering, Universitas Diponegoro under <a href=\"https://creativecommons.org/licenses/by-sa/4.0/\" rel=\"license\">Creative Commons Attribution-ShareAlike 4.0 International License</a>.</div></div><div class=\"col-xs-12 col-sm-12 col-md-12 col-lg-12 ikon\" style=\"margin-top: 6px; margin-bottom: 0px;\"><a title=\"Training Division Bulletin of Chemical Reaction Engineering &amp; Catalysis\" href=\"https://training.bcrec.web.id/\" target=\"_blank\"><img style=\"float: left;\" src=\"/public/site/images/didik/bcrec.jpg\" alt=\"\" /></a><div class=\"col-xs-9 col-sm-9 col-md-10 col-lg-10\">Supported by: <strong><a title=\"Training D"], "copyright__copyright__copyright": ["rvoir. The output of this system contains i", "rvoir. The output of this system contains information on water discharge, volume of water in cubic meter also is added to the unit of price. Result of testing the accuracy sensor water flow reached 98,8 % while sensor photodiode had scale measurement water turbidity reacehed 0 - 173 NTU.\n\nOther format:\n\nKeywords\nMonitoring System; Microcontroller ATMega328; Water flow sensor; Water turbidity; Photodiode\n\nArticle Metrics:\n\nArticle Info\nSection: Articles\nLanguage: ID\nFull Text:\nStatistics: 724 971", "rvoir. The output of this system contains information on water discharge, volume of water in cubic meter also is added to the unit of price. Result of testing the accuracy sensor water flow reached 98,8 % while sensor photodiode had scale measurement water turbidity reacehed 0 - 173 NTU.\n\nOther format:\n\nKeywords\nMonitoring System; Microcontroller ATMega328; Water flow sensor; Water turbidity; Photodiode\n\nArticle Metrics:\n\nArticle Info\nSection: Articles\nLanguage: ID\nFull Text:\nStatistics: 724 971", "rvoir. The output of this system contains information on water discharge, volume of water in cubic meter also is added to the unit of price. Result of testing the accuracy sensor water flow reached 98,8 % while sensor photodiode had scale measurement water turbidity reacehed 0 - 173 NTU.\n\nOther format:\n\nKeywords\nMonitoring System; Microcontroller ATMega328; Water flow sensor; Water turbidity; Photodiode\n\nArticle Metrics:\n\nArticle Info\nSection: Articles\nLanguage: ID\nFull Text:\nStatistics: 724 971", "rvoir. The output of this system contains information on water discharge, volume of water in cubic meter also is added to the unit of price. Result of testing the accuracy sensor water flow reached 98,8 % while sensor photodiode had scale measurement water turbidity reacehed 0 - 173 NTU.\n\nOther format:\n\nKeywords\nMonitoring System; Microcontroller ATMega328; Water flow sensor; Water turbidity; Photodiode\n\nArticle Metrics:\n\nArticle Info\nSection: Articles\nLanguage: ID\nFull Text:\nStatistics: 724 971", "rvoir. The output of this system contains information on water discharge, volume of water in cubic meter also is added to the unit of price. Result of testing the accuracy sensor water flow reached 98,8 % while sensor photodiode had scale measurement water turbidity reacehed 0 - 173 NTU.\n\nOther format:\n\nKeywords\nMonitoring System; Microcontroller ATMega328; Water flow sensor; Water turbidity; Photodiode\n\nArticle Metrics:\n\nArticle Info\nSection: Articles\nLanguage: ID\nFull Text:\nStatistics: 724 971", "rvoir. The output of this system contains information on water discharge, volume of water in cubic meter also is added to the unit of price. Result of testing the accuracy sensor water flow reached 98,8 % while sensor photodiode had scale measurement water turbidity reacehed 0 - 173 NTU.\n\nOther format:\n\nKeywords\nMonitoring System; Microcontroller ATMega328; Water flow sensor; Water turbidity; Photodiode\n\nArticle Metrics:\n\nArticle Info\nSection: Articles\nLanguage: ID\nFull Text:\nStatistics: 724 971", "rvoir. The output of this system contains information on water discharge, volume of water in cubic meter also is added to the unit of price. Result of testing the accuracy sensor water flow reached 98,8 % while sensor photodiode had scale measurement water turbidity reacehed 0 - 173 NTU.\n\nOther format:\n\nKeywords\nMonitoring System; Microcontroller ATMega328; Water flow sensor; Water turbidity; Photodiode\n\nArticle Metrics:\n\nArticle Info\nSection: Articles\nLanguage: ID\nFull Text:\nStatistics: 724 971", "rvoir. The output of this system contains information on water discharge, volume of water in cubic meter also is added to the unit of price. Result of testing the accuracy sensor water flow reached 98,8 % while sensor photodiode had scale measurement water turbidity reacehed 0 - 173 NTU.\n\nOther format:\n\nKeywords\nMonitoring System; Microcontroller ATMega328; Water flow sensor; Water turbidity; Photodiode\n\nArticle Metrics:\n\nArticle Info\nSection: Articles\nLanguage: ID\nFull Text:\nStatistics: 724 971", "rvoir. The output of this system contains information on water discharge, volume of water in cubic meter also is added to the unit of price. Result of testing the accuracy sensor water flow reached 98,8 % while sensor photodiode had scale measurement water turbidity reacehed 0 - 173 NTU.\n\nOther format:\n\nKeywords\nMonitoring System; Microcontroller ATMega328; Water flow sensor; Water turbidity; Photodiode\n\nArticle Metrics:\n\nArticle Info\nSection: Articles\nLanguage: ID\nFull Text:\nStatistics: 724 971", "rvoir. The output of this system contains information on water discharge, volume of water in cubic meter also is added to the unit of price. Result of testing the accuracy sensor water flow reached 98,8 % while sensor photodiode had scale measurement water turbidity reacehed 0 - 173 NTU.\n\nOther format:\n\nKeywords\nMonitoring System; Microcontroller ATMega328; Water flow sensor; Water turbidity; Photodiode\n\nArticle Metrics:\n\nArticle Info\nSection: Articles\nLanguage: ID\nFull Text:\nStatistics: 724 971", "rvoir. The output of this system contains information on water discharge, volume of water in cubic meter also is added to the unit of price. Result of testing the accuracy sensor water flow reached 98,8 % while sensor photodiode had scale measurement water turbidity reacehed 0 - 173 NTU.\n\nOther format:\n\nKeywords\nMonitoring System; Microcontroller ATMega328; Water flow sensor; Water turbidity; Photodiode\n\nArticle Metrics:\n\nArticle Info\nSection: Articles\nLanguage: ID\nFull Text:\nStatistics: 724 971", "rvoir. The output of this system contains information on water discharge, volume of water in cubic meter also is added to the unit of price. Result of testing the accuracy sensor water flow reached 98,8 % while sensor photodiode had scale measurement water turbidity reacehed 0 - 173 NTU.\n\nOther format:\n\nKeywords\nMonitoring System; Microcontroller ATMega328; Water flow sensor; Water turbidity; Photodiode\n\nArticle Metrics:\n\nArticle Info\nSection: Articles\nLanguage: ID\nFull Text:\nStatistics: 724 971", "rvoir. The output of this system contains information on water discharge, volume of water in cubic meter also is added to the unit of price. Result of testing the accuracy sensor water flow reached 98,8 % while sensor photodiode had scale measurement water turbidity reacehed 0 - 173 NTU.\n\nOther format:\n\nKeywords\nMonitoring System; Microcontroller ATMega328; Water flow sensor; Water turbidity; Photodiode\n\nArticle Metrics:\n\nArticle Info\nSection: Articles\nLanguage: ID\nFull Text:\nStatistics: 724 971", "rvoir. The output of this system contains information on water discharge, volume of water in cubic meter also is added to the unit of price. Result of testing the accuracy sensor water flow reached 98,8 % while sensor photodiode had scale measurement water turbidity reacehed 0 - 173 NTU.\n\nOther format:\n\nKeywords\nMonitoring System; Microcontroller ATMega328; Water flow sensor; Water turbidity; Photodiode\n\nArticle Metrics:\n\nArticle Info\nSection: Articles\nLanguage: ID\nFull Text:\nStatistics: 724 971", "rvoir. The output of this system contains information on water discharge, volume of water in cubic meter also is added to the unit of price. Result of testing the accuracy sensor water flow reached 98,8 % while sensor photodiode had scale measurement water turbidity reacehed 0 - 173 NTU.\n\nOther format:\n\nKeywords\nMonitoring System; Microcontroller ATMega328; Water flow sensor; Water turbidity; Photodiode\n\nArticle Metrics:\n\nArticle Info\nSection: Articles\nLanguage: ID\nFull Text:\nStatistics: 724 971", "rvoir. The output of this system contains information on water discharge, volume of water in cubic meter also is added to the unit of price. Result of testing the accuracy sensor water flow reached 98,8 % while sensor photodiode had scale measurement water turbidity reacehed 0 - 173 NTU.\n\nOther format:\n\nKeywords\nMonitoring System; Microcontroller ATMega328; Water flow sensor; Water turbidity; Photodiode\n\nArticle Metrics:\n\nArticle Info\nSection: Articles\nLanguage: ID\nFull Text:\nStatistics: 724 971", "rvoir. The output of this system contains information on water discharge, volume of water in cubic meter also is added to the unit of price. Result of testing the accuracy sensor water flow reached 98,8 % while sensor photodiode had scale measurement water turbidity reacehed 0 - 173 NTU.\n\nOther format:\n\nKeywords\nMonitoring System; Microcontroller ATMega328; Water flow sensor; Water turbidity; Photodiode\n\nArticle Metrics:\n\nArticle Info\nSection: Articles\nLanguage: ID\nFull Text:\nStatistics: 724 971"]}