human
Question: What are the clearance requirements for a fire hydrant?
Context: Fire2419 pages 26-26: The clearance requirements for a fire hydrant are as follows: the center-line of the fire hydrant outlet should be between 750 mm and 1200 mm above the ground, floor, or platform. The valve outlet should face away from the wall behind it, if any, and should be horizontal or sloping no more than 35° below the horizontal. A clearance of 1000 mm should be provided directly in front of the fire hydrant outlet for the connection and laying of hose. There should be a clearance of at least 100 mm around the valve handwheel when the hydrant valve is fully open. Score: 10 Fire2419 pages 20-20: The clearance requirements for a fire hydrant are specified in C3.2.2.2(e) of AS 2419.1-2005. According to the standard, a 10 meter clearance distance is required from the building to provide access to the fire hydrant under radiant heat from the fire and to give a degree of protection in the event of structural collapse. 9 Fire2419 pages 74-75: The text does not provide any information about the clearance requirements for a fire hydrant. Valid keys: Fire2419 pages 26-26, Fire2419 pages 20-20, Fire2419 pages 74-75
gpt
--- Reasoning ---
1. Is the question multiple-choice question?
No
2. Is it implied multiple-choice question?
No
3. If two experts were independently asked the question, will the final answer be exactly the same?
Yes

--- Answer ---
grounded